This report is the exclusive property of Sigman Home Inspection LLC and the client(s) listed in the report title. Use of this report by any unauthorized persons is prohibited.
Property Inspection Report
||Monday, June 01, 2015
This report published on Tuesday, August 11, 2015 8:05:19 PM PDT
How to Read this Report
This report is organized by the property's functional areas. Within each functional area, descriptive information is listed first and is shown in bold type. Items of concern follow descriptive information.
Concerns are shown and sorted according to these types:
|Safety||Poses a safety hazard|
|Repair/Replace||Recommend repairing or replacing|
|Repair/Maintain||Recommend repair and/or maintenance|
|Minor Defect||Correction likely involves only a minor expense|
|Maintain||Recommend ongoing maintenance|
|Evaluate||Recommend evaluation by a specialist|
|Comment||For your information|
Click here for a glossary of building construction terms.Contact your inspector If there are terms that you do not understand, or visit the glossary of construction terms at http://www.reporthost.com/glossary.asp
Report number: 150601
Time started: 1pm
Time finished: 4pm
Present during inspection: Client
Client present for discussion at end of inspection: Yes
Inspector: Derek Sigman
Weather conditions during inspection: Dry (no rain), Sunny
Temperature during inspection: Warm
Ground condition: Dry
Recent weather: Dry (no rain), Sunny
Overnight temperature: Warm
Inspection fee: $400
Payment method: Check
Type of building: Single family
Buildings inspected: One house
Number of residential units inspected: 1
Age of main building: 2007
Source for main building age: Municipal records or property listing
Front of building faces: South
Main entrance faces: South
Limitations: Unless specifically included in the inspection, the following items and any related equipment, controls, electric systems and/or plumbing systems are excluded from this inspection: detached buildings or structures; fences and gates; retaining walls; underground drainage systems, catch basins or concealed sump pumps; swimming pools and related safety equipment, spas, hot tubs or saunas; whether deck, balcony and/or stair membranes are watertight; trees, landscaping, properties of soil, soil stability, erosion and erosion control; ponds, water features, irrigation or yard sprinkler systems; sport courts, playground, recreation or leisure equipment; areas below the exterior structures with less than 3 feet of vertical clearance; invisible fencing; sea walls, docks and boathouses; retractable awnings. Any comments made regarding these items are as a courtesy only.
Condition of fences and gates: Required repairs, replacement and/or evaluation (see comments below)
Fence and gate material: Wood
Site profile: Level
Condition of driveway: Appeared serviceable
Driveway material: Poured in place concrete
Condition of sidewalks and/or patios: Appeared serviceable
Sidewalk material: Poured in place concrete
Condition of deck, patio and/or porch covers: Appeared serviceable
Condition of stairs, handrails and guardrails: Required repairs, replacement and/or evaluation (see comments below)
Exterior stair material: Wood
One or more gates were damaged or deteriorated and need repair.
Gate on right of house was deteriorated - requires reinforcing and protective coating of paint or wood finish.
Significant erosion was found in one or more areas. Recommend having a qualified person evaluate and make repairs as necessary to repair erosion, and to prevent erosion in the future.
Patio at back of house - ground is eroded underneath.
Minor deterioration (e.g. cracks, holes, settlement, heaving) was found in sidewalks or patios, but no trip hazards were found. The client may wish to have repairs made for cosmetic reasons.
Settlement has occurred at the patio leading to the front entrance. It appears there was a gap that had been patched with grout.
Exterior and Foundation
Limitations: The inspector performs a visual inspection of accessible components or systems at the exterior. Items excluded from this inspection include below-grade foundation walls and footings; foundations, exterior surfaces or components obscured by vegetation, stored items or debris; wall structures obscured by coverings such as siding or trim. Some items such as siding, trim, soffits, vents and windows are often high off the ground, and may be viewed using binoculars from the ground or from a ladder. This may limit a full evaluation. Regarding foundations, some amount of cracking is normal in concrete slabs and foundation walls due to shrinkage and drying. Note that the inspector does not determine the adequacy of seismic reinforcement.
Wall inspection method: Viewed from ground, from a ladder
Condition of wall exterior covering: Appeared serviceable
Apparent wall structure: Wood frame
Wall covering: Cement fiber
Condition of foundation and footings: Appeared serviceable
Apparent foundation type: Crawl space
Foundation/stem wall material: Poured in place concrete
Footing material (under foundation stem wall): Poured in place concrete
Flashing at one or more locations was loose. Leaks can occur as a result. Recommend that a qualified person repair, replace or install flashing as necessary, and per standard building practices.
One piece of seam flashing on the left side of the house was loose and falling out from behind the seam.
The paint or stain finish in some areas was failing (e.g. peeling, faded, worn, thinning). Siding and trim with a failing finish can be damaged by moisture. Recommend that a qualified contractor prep (e.g. clean, scrape, sand, prime, caulk) and repaint or restain the building exterior where necessary and per standard building practices. Any repairs needed to the siding or trim should be made prior to this.
*The wood trim around all windows at the front of the house and garage door trim. Also some areas under soffits. Paint is deteriorated. Recommend painting and caulking.
One or more shutters were loose.
2 shutters at front of house
Limitations: Structural components such as joists and beams, and other components such as piping, wiring and/or ducting that are obscured by under-floor insulation are excluded from this inspection. The inspector does not determine if support posts, columns, beams, joists, studs, trusses, etc. are of adequate size, spanning or spacing.
The inspector does not guarantee or warrant that water will not accumulate in the crawl spaces in the future. Complete access to all crawl space areas during all seasons and during prolonged periods of all types of weather conditions (e.g. heavy rain, melting snow) would be needed to do so.
The inspector attempts to locate all crawl space access points and areas. Access points may be obscured or otherwise hidden by furnishings or stored items. In such cases, the client should ask the property owner where all access points are that are not described in this inspection, and have those areas inspected. Note that crawl space areas should be checked at least annually for water intrusion, plumbing leaks and pest activity.
Crawl space inspection method: Traversed
Location of crawl space access point #A: 1st flor closet
Crawl space access points that were opened and viewed, traversed or partially traversed: A
Condition of floor substructure above: Appeared serviceable
Pier or support post material: Wood
Beam material: Solid wood
Floor structure above: Solid wood joists
Condition of insulation underneath floor above: Appeared serviceable
Insulation material underneath floor above: Fiberglass roll or batt
Condition of vapor barrier: Appeared serviceable
Vapor barrier present: Yes
Condition of crawl space ventilation: Appeared serviceable
Ventilation type: Unconditioned space, with vents
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; solar roofing components. Any comments made regarding these items are made as a courtesy only. Note that the inspector does not provide an estimate of remaining life on the roof surface material, nor guarantee that leaks have not occurred in the roof surface, skylights or roof penetrations in the past. Regarding roof leaks, only active leaks, visible evidence of possible sources of leaks, and evidence of past leaks observed during the inspection are reported on as part of this inspection. The inspector does not guarantee or warrant that leaks will not occur in the future. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high wind and rain, melting snow) would be needed to do so. Occupants should monitor the condition of roofing materials in the future. For older roofs, recommend that a professional inspect the roof surface, flashings, appurtenances, etc. annually and maintain/repair as might be required. If needed, the roofer should enter attic space(s). Regarding the roof drainage system, unless the inspection was conducted during and after prolonged periods of heavy rain, the inspector was unable to determine if gutters, downspouts and extensions perform adequately or are leak-free.
Age of roof surface(s): 2007
Roof inspection method: Partially traversed, Viewed from eaves on ladder, Viewed from ground
Condition of roof surface material: Appeared serviceable
Roof surface material: Asphalt or fiberglass composition shingles
Roof type: Hipped
Apparent number of layers of roof surface material: One
Condition of exposed flashings: Required repair, replacement and/or evaluation (see comments below)
Condition of gutters, downspouts and extensions: Appeared serviceable
Gutter and downspout material: Metal
Gutter and downspout installation: Full
Significant amounts of debris have accumulated in one or more gutters or downspouts. Gutters can overflow and cause water to come in contact with the building exterior, or water can accumulate around the foundation. This is a conducive condition for wood-destroying organisms. Recommend cleaning gutters and downspouts now and as necessary in the future.
Mostly isolated to front of house near the tree.
Moss was growing on the roof. As a result, shingles can lift or be damaged. Leaks can result and/or the roof surface can fail prematurely. Efforts should be made to kill the moss during its growing season (wet months). Typically, zinc or phosphate-based chemicals are used for this and must be applied periodically. For information on various moss treatment products and their pros and cons, visit:http://www.reporthost.com/?MOSS
*Moss growth is minimal but preventative measures may be taken to minimize the growth since the local climate is conducive to moss growth.
Attic and Roof Structure
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; areas and components obscured by insulation. Any comments made regarding these items are made as a courtesy only. The inspector does not determine the adequacy of the attic ventilation system. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high/low temperatures, high/low humidity, high wind and rain, melting snow) would be needed to do so. The inspector is not a licensed engineer and does not determine the adequacy of roof structure components such as trusses, rafters or ceiling beams, or their spacing or sizing.
Attic inspection method: Viewed from hatch(es)
Location of attic access point #A: Master bedroom closet, second floor
Attic access points that were opened and viewed, traversed or partially traversed: A
Condition of roof structure: Appeared serviceable
Roof structure type: Trusses
Ceiling structure: Ceiling joists
Condition of insulation in attic (ceiling, skylight chase, etc.): Appeared serviceable
Ceiling insulation material: Fiberglass loose fill
Approximate attic insulation R value (may vary in areas): R-38
Vapor retarder: None
Condition of roof ventilation: Appeared serviceable
Roof ventilation type: Open soffit vents
All attic areas and roof structures more than 12 feet from attic access point(s) #A were inaccessible due to possible damage to insulation if traversed and/or lack of permanent walkways. These areas were not evaluated and are excluded from the inspection.
Garage or Carport
Limitations: The inspector does not determine the adequacy of firewall ratings. Requirements for ventilation in garages vary between municipalities.
Condition of door between garage and house: Appeared serviceable
Condition of garage vehicle door(s): Appeared serviceable
Type of garage vehicle door: Sectional
Number of vehicle doors: 1
Condition of automatic opener(s): Appeared serviceable
Condition of garage floor: Appeared serviceable
Condition of garage interior: Appeared serviceable
The step(s) installed below the door between the garage and the house were loose and/or deteriorated. This is a fall or trip hazard. A qualified person should repair as necessary.
One of the bottom tread boards was split.
Minor cracks were found in the concrete slab floor. These are common and appeared to be only a cosmetic issue.
Limitations: The following items are not included in this inspection: generator systems, transfer switches, surge suppressors, inaccessible or concealed wiring; underground utilities and systems; low-voltage lighting or lighting on timers or sensors. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of grounding or bonding, if this system has an adequate capacity for the client's specific or anticipated needs, or if this system has any reserve capacity for additions or expansion. The inspector does not operate circuit breakers as part of the inspection, and does not install or change light bulbs. The inspector does not evaluate every wall switch or receptacle, but instead tests a representative number of them per various standards of practice. When furnishings, stored items or child-protective caps are present some receptacles are usually inaccessible and are not tested; these are excluded from this inspection. Receptacles that are not of standard 110 volt configuration, including 240-volt dryer receptacles, are not tested and are excluded. The functionality of, power source for and placement of smoke and carbon monoxide alarms is not determined as part of this inspection. Upon taking occupancy, proper operating and placement of smoke and carbon monoxide alarms should be verified and batteries should be changed. These devices have a limited lifespan and should be replaced every 10 years. The inspector attempts to locate and evaluate all main and sub-panels. However, panels are often concealed. If panels are found after the inspection, a qualified electrician should evaluate and repair if necessary. The inspector attempts to determine the overall electrical service size, but such estimates are not guaranteed because the overall capacity may be diminished by lesser-rated components in the system. Any repairs recommended should be made by a licensed electrician.
Electric service condition: Appeared serviceable
Primary service type: Underground
Number of service conductors: 3
Service voltage (volts): 120-240
Estimated service amperage: 200
Primary service overload protection type: Circuit breakers
Service entrance conductor material: Stranded aluminum
Main disconnect rating (amps): 200
System ground: Ground rod(s) in soil
Condition of main service panel: Appeared serviceable
Location of main service panel #A: Garage
Location of main disconnect: Breaker at bottom of main service panel
Circuit breakers that were in the "off" position: Dryer
Condition of branch circuit wiring: Serviceable
Branch circuit wiring type: Non-metallic sheathed
Ground fault circuit interrupter (GFCI) protection present: Yes
Arc fault circuit interrupter (AFCI) protection present: Yes
Smoke alarms installed: Yes, but not tested
Carbon monoxide alarms installed: Yes, but not tested
Smoke alarm power source(s): Hard wired
One or more light fixtures installed outside were missing components. This is a potential shock and/or fire hazard. Recommend that a qualified electrician repair as necessary.
Front porch light missing cover
Plumbing / Fuel Systems
Limitations: The following items are not included in this inspection: private/shared wells and related equipment; private sewage disposal systems; hot tubs or spas; main, side and lateral sewer lines; gray water systems; pressure boosting systems; trap primers; incinerating or composting toilets; fire suppression systems; water softeners, conditioners or filtering systems; plumbing components concealed within the foundation or building structure, or in inaccessible areas such as below tubs; underground utilities and systems; overflow drains for tubs and sinks; backflow prevention devices. Any comments made regarding these items are as a courtesy only. Note that the inspector does not operate water supply or shut-off valves due to the possibility of valves leaking or breaking when operated. The inspector does not test for lead in the water supply, the water pipes or solder, does not determine if plumbing and fuel lines are adequately sized, and does not determine the existence or condition of underground or above-ground fuel tanks.
Condition of service and main line: Appeared serviceable
Water service: Public
Location of main water meter: By street, Front yard
Location of main water shut-off: Garage
Condition of supply lines: Appeared serviceable
Supply pipe material: PEX plastic
Condition of drain pipes: Appeared serviceable
Drain pipe material: Plastic
Condition of waste lines: Appeared serviceable
Waste pipe material: Plastic
Location(s) of plumbing clean-outs: Crawl space, Building exterior
Vent pipe condition: Appeared serviceable
Vent pipe material: Plastic
Condition of fuel system: Appeared serviceable
Location of main fuel shut-off valve: At gas meter
Flexible CSST gas line found in crawlspace. Could not verify that the lines were direct bonded. Direct bonding of CSST gas lines is required by the manufacturer and 2009 and later editions of the National Fuel Gas Code, the International Fuel Gas Code and the Uniform Plumbing Code.
Potential fire hazard during electrical storms.
More information can be found at http://www.csstsafety.com/index.html
Exterior gas line for bbq grill in back of house had surface corrosion. Recommend cleaning and painting with a protective coating.
Limitations: Evaluation of and determining the adequacy or completeness of the following items are not included in this inspection: water recirculation pumps; solar water heating systems; Energy Smart or energy saver controls; catch pan drains. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on water heaters, does not determine if water heaters are appropriately sized, or perform any evaluations that require a pilot light to be lit or a shut-off valve to be operated.
Condition of water heater: Appeared serviceable
Energy source: Natural gas
Estimated age: 2007
Capacity (in gallons): 75
Temperature-pressure relief valve installed: Yes
Manufacturer: A.O. Smith
Model number: FCG 75 300 300
Serial number: K07J072453
Location of water heater: Garage
Condition of burners: Appeared serviceable
Condition of combustion air supply: Appeared serviceable
The estimated useful life for most water heaters is 8-12 years. This water heater appeared to be near this age and/or its useful lifespan and may need replacing at any time. Recommend budgeting for a replacement in the near future, or considering replacement now before any leaks occur. The client should be aware that significant flooding can occur if the water heater fails. If not replaced now, consider having a qualified person install a catch pan and drain or a water alarm to help prevent damage if water does leak.
Water heater is 8 years old.
Heating, Ventilation and Air Condition (HVAC)
Limitations: The following items are not included in this inspection: humidifiers, dehumidifiers, electronic air filters; solar, coal or wood-fired heat systems; thermostat or temperature control accuracy and timed functions; heating components concealed within the building structure or in inaccessible areas; underground utilities and systems; safety devices and controls (due to automatic operation). Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on heating or cooling system components, does not determine if heating or cooling systems are appropriately sized, does not test coolant pressure, or perform any evaluations that require a pilot light to be lit, a shut-off valve to be operated, a circuit breaker to be turned "on" or a serviceman's or oil emergency switch to be operated. It is beyond the scope of this inspection to determine if furnace heat exchangers are intact and free of leaks. Condensation pans and drain lines may clog or leak at any time and should be monitored while in operation in the future. Where buildings contain furnishings or stored items, the inspector may not be able to verify that a heat source is present in all "liveable" rooms (e.g. bedrooms, kitchens and living/dining rooms).
General heating system type(s): Forced air, Furnace
General heating distribution type(s): Ducts and registers
Condition of forced air heating/(cooling) system: Appeared serviceable
Forced air heating system fuel type: Natural gas
Estimated age of forced air furnace: 2007
Forced air heating system manufacturer: Coleman
Forced air furnace model #: GM8S100C20DH11B
Forced air furnace serial number: W0K6938424
Location of forced air furnace: Garage
Forced air system capacity in BTUs or kilowatts: 100
Condition of furnace filters: Required replacement
Location for forced air filter(s): Behind return air grill(s)
Condition of forced air ducts and registers: Appeared serviceable
Condition of burners: Appeared serviceable
Condition of combustion air supply: Appeared serviceable
Type of combustion air supply: Vented door
Condition of cooling system and/or heat pump: Appeared serviceable
Cooling system and/or heat pump fuel type: Electric
Location: Back of house
Type: Split system
Estimated age: 2015
Approximate tonnage: 3
Condition of cooling system and/or heat pump: Rheem
Heat pump or air conditioner model number: RA1336AJ1NB
Heat pump or air conditioner serial number: W181506747
Condition of controls: Appeared serviceable
The air handler's primary condensate drain line was routed so it drains close the foundation. Significant amounts of water can be produced by this system and can cause water infiltration. In extreme cases the wet soil may not adequately support the foundation. Recommend repairing as necessary so condensate water drains well away from the foundation. For example, by installing a splash block.
Fireplaces, Stoves, Chimneys and Flues
Limitations: The following items are not included in this inspection: coal stoves, gas logs, chimney flues (except where visible). Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of drafting or sizing in fireplace and stove flues, and also does not determine if prefabricated or zero-clearance fireplaces are installed in accordance with the manufacturer's specifications. The inspector does not perform any evaluations that require a pilot light to be lit, and does not light fires. The inspector provides a basic visual examination of a chimney and any associated wood burning device. The National Fire Protection Association has stated that an in-depth Level 2 chimney inspection should be part of every sale or transfer of property with a wood-burning device. Such an inspection may reveal defects that are not apparent to the home inspector who is a generalist.
Condition of gas-fired fireplaces or stoves: Appeared serviceable
Gas fireplace or stove type: Metal pre-fab fireplace
Fan or blower installed in gas-fired fireplace or stove: No
Condition of chimneys and flues: Appeared serviceable
Gas-fired flue type: Direct vent
Limitations: The following items are not included in this inspection: household appliances such as stoves, ovens, cook tops, ranges, warming ovens, griddles, broilers, dishwashers, trash compactors, refrigerators, freezers, ice makers, hot water dispensers and water filters; appliance timers, clocks, cook functions, self and/or continuous cleaning operations, thermostat or temperature control accuracy, and lights. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of the remaining life of appliances, and does not determine the adequacy of operation of appliances. The inspector does not note appliance manufacturers, models or serial numbers and does not determine if appliances are subject to recalls. Areas and components behind and obscured by appliances are inaccessible and excluded from this inspection.
Permanently installed kitchen appliances present during inspection: Range, Oven, Dishwasher, Microwave oven
Condition of counters: Appeared serviceable
Condition of cabinets: Appeared serviceable
Condition of sinks and related plumbing: Appeared serviceable
Condition of under-sink food disposal: Required repair, replacement and/or evaluation (see comments below)
Condition of dishwasher: Appeared serviceable
Condition of range, cooktop or oven: Appeared serviceable
Range, cooktop or oven type: Natural gas
Type of ventilation: Hood or built into microwave over range or cooktop
Condition of refrigerator: N/A (none installed)
Condition of built-in microwave oven: Appeared serviceable
The under-sink food disposal was noisy or vibrated excessively. Recommend that a qualified contractor repair or replace as necessary.
Food disposal had some pieces of plastic in it - otherwise operated normally. Remove all debris from food disposal.
Trim above shelving in pantry area was not installed properly. Not attached to top of cabinets.
Bathrooms, Laundry and Sinks
Limitations: The following items are not included in this inspection: overflow drains for tubs and sinks; heated towel racks, saunas, steam generators, clothes washers, clothes dryers. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of washing machine drain lines, washing machine catch pan drain lines, or clothes dryer exhaust ducts. The inspector does not operate water supply or shut-off valves for sinks, toilets, bidets, clothes washers, etc. due to the possibility of valves leaking or breaking when operated. The inspector does not determine if shower pans or tub and shower enclosures are water tight, or determine the completeness or operability of any gas piping to laundry appliances.
Location #A: Half bath, first floor
Location #B: Full bath, Master bath, second floor
Location #C: Full bath, second floor
Location #D: Laundry room/area, second floor
Condition of counters: Appeared serviceable
Condition of cabinets: Appeared serviceable
Condition of flooring: Appeared serviceable
Condition of sinks and related plumbing: Appeared serviceable
Condition of toilets: Appeared serviceable
Condition of bathtubs and related plumbing: Required repair, replacement and/or evaluation (see comments below)
Condition of shower(s) and related plumbing: Required repair, replacement and/or evaluation (see comments below)
Condition of ventilation systems: Required repair, replacement and/or evaluation (see comments below)
Bathroom and laundry ventilation type: Spot exhaust fans
Gas supply for laundry equipment present: No
240 volt receptacle for laundry equipment present: Yes
The clothes dryer exhaust duct appeared to need cleaning. Significant amounts of lint build-up were visible and may reduce air flow. This is a fire hazard. Recommend that a qualified person clean this duct now and as necessary in the future. Some chimney sweeps or heating/cooling duct cleaners perform this service. For more information, visit:http://www.reporthost.com/?DRYER
The shower head at location(s) #B was missing. Recommend that a qualified person repair as necessary.
2nd floor master bath
The cover to the exhaust fan at location(s) #D was loose. Recommend that a qualified person repair or replace covers as necessary.
The sink at location(s) #C drained slowly. Recommend clearing drain and/or having a qualified plumber repair if necessary.
Recommend cleaning all sink P-traps as normal maintenance. Sink at 2nd floor bath on left drained slow.
The exhaust fan or fan cover at location(s) #A, B, C and D needed cleaning. Dirty or clogged fans can result in moisture accumulation and subsequent mold, bacteria or fungal growth. Recommend cleaning fan covers or fans now and as necessary in the future.
Interior, Doors and Windows
Limitations: The following items are not included in this inspection: security, intercom and sound systems; communications wiring; central vacuum systems; elevators and stair lifts; cosmetic deficiencies such as nail-pops, scuff marks, dents, dings, blemishes or issues due to normal wear and tear in wall, floor and ceiling surfaces and coverings, or in equipment; deficiencies relating to interior decorating; low voltage and gas lighting systems. Any comments made regarding these items are as a courtesy only. Note that the inspector does not evaluate any areas or items which require moving stored items, furnishings, debris, equipment, floor coverings, insulation or similar materials. The inspector does not test for asbestos, lead, radon, mold, hazardous waste, urea formaldehyde urethane, or any other toxic substance. Some items such as window, drawer, cabinet door or closet door operability are tested on a sampled basis. The client should be aware that paint may obscure wall and ceiling defects, floor coverings may obscure floor defects, and furnishings may obscure wall, floor and floor covering defects. If furnishings were present during the inspection, recommend a full evaluation of walls, floors and ceilings that were previously obscured when possible. Determining the cause and/or source of odors is not within the scope of this inspection.
Condition of exterior entry doors: Appeared serviceable
Condition of interior doors: Appeared serviceable
Condition of windows and skylights: Appeared serviceable
Type(s) of windows: Vinyl
Condition of walls and ceilings: Appeared serviceable
Wall type or covering: Drywall
Ceiling type or covering: Drywall
Condition of flooring: Appeared serviceable
Condition of stairs, handrails and guardrails: Appeared serviceable
One or more window screens were damaged or deteriorated. These window(s) may not provide ventilation during months when insects are active. Recommend replacing window screens as necessary.
One window screen removed from 2nd floor window bedroom front of house.
One window screen coming out - back of house.
Minor cracks, nail pops and/or blemishes were found in walls and/or ceilings in one or more areas. Cracks and nail pops are common, are often caused by lumber shrinkage or minor settlement, and can be more or less noticeable depending on changes in humidity. They did not appear to be a structural concern, but the client may wish to repair these for aesthetic reasons. For recurring cracks, consider using an elastic crack covering product:http://www.reporthost.com/?ECC
Nail pops were mostly in 2nd floor master bathroom above mirror and some in first floor dining room ceiling.
Wood Destroying Organism Findings
Limitations: This report only includes findings from accessible and visible areas on the day of the inspection. In addition to the inaccessible areas documented in this report, examples of other inaccessible areas include: sub areas less than 18 inches in height; attic areas less than 5 feet in height, areas blocked by ducts, pipes or insulation; areas where locks or permanently attached covers prevent access; areas where insulation would be damaged if traversed; areas obscured by vegetation. All inaccessible areas are subject to infestation or damage from wood-destroying organisms. The inspector does not move furnishings, stored items, debris, floor or wall coverings, insulation, or other materials as part of the inspection, nor perform destructive testing. Wood-destroying organisms may infest, re-infest or become active at any time. No warranty is provided as part of this inspection.
Visible evidence of active wood-destroying insects: No
Visible evidence of active wood decay fungi: No
Visible evidence of past wood-destroying insects: No
Visible evidence of past wood decay fungi: No
Visible evidence of damage by wood-destroying insects: No
Visible evidence of damage by wood decay fungi: No
Visible evidence of conditions conducive to wood-destroying organisms: Yes, *Noted throughout report.
©2015 Sigman Home Inspection LLC