This report published on Monday, February 18, 2019 8:59:38 PM CST
This report is the exclusive property of this inspection company and the client(s) listed in the report title. Use of this report by any unauthorized persons is prohibited.
How to Read this Report
This report is organized by the property's functional areas. Within each functional area, descriptive information is listed first and is shown in bold type. Items of concern follow descriptive information.
Concerns are shown and sorted according to these types:
Poses a safety hazard
Correction likely involves a significant expense
Recommend repairing or replacing
Recommend repair and/or maintenance
Correction likely involves only a minor expense
Recommend ongoing maintenance
Recommend evaluation by a specialist
Recommend monitoring in the future
Item or component is in serviceable condition
For your information
Click here for a glossary of building construction terms.Contact your inspector If there are terms that you do not understand, or visit the glossary of construction terms at https://www.reporthost.com/glossary.asp
Limitations: Unless specifically included in the inspection, the following items and any related equipment, controls, electric systems and/or plumbing systems are excluded from this inspection: detached buildings or structures; fences and gates; retaining walls; underground drainage systems, catch basins or concealed sump pumps; swimming pools and related safety equipment, spas, hot tubs or saunas; whether deck, balcony and/or stair membranes are watertight; trees, landscaping, properties of soil, soil stability, erosion and erosion control; ponds, water features, irrigation or yard sprinkler systems; sport courts, playground, recreation or leisure equipment; areas below the exterior structures with less than 3 feet of vertical clearance; invisible fencing; sea walls, docks and boathouses; retractable awnings. Any comments made regarding these items are as a courtesy only.
Site profile: Minor slope
Condition of driveway: Appeared serviceable
Driveway material: Poured in place concrete
Condition of sidewalks and/or patios: Appeared serviceable
Sidewalk material: Poured in place concrete
Condition of decks, porches and/or balconies: Required repairs, replacement and/or evaluation (see comments below)
Deck, porch and/or balcony material: Wood
Condition of stairs, handrails and guardrails: Required repairs, replacement and/or evaluation (see comments below)
Exterior stair material: Wood
1) Treads for stairs at one or more locations were less than 10 inches deep and pose a fall or trip hazard. Stair treads should be at least 10 inches deep. At a minimum, be aware of this hazard, especially when guests who are not familiar with the stairs are present. Recommend that a qualified contractor repair per standard building practices.
2) One or more decking boards were loose and/or broken In some cases this may pose a trip hazard or the board could break completely through possibly causing serious injury. Recommend that a qualified person repair as necessary.
3) Guardrails at one or more locations with drop-offs higher than 30 inches were wobbly and/or damaged, and pose a fall hazard. Recommend that a qualified person repair guardrails as necessary.
Although guardrails are not required for a deck less than 30", both guardrails were missing fasteners which made then very unstable. guardrails need to be refastened with proper fasteners secure them properly
4) One or more decking boards were loose and/or Broken. In some cases this may pose a trip hazard. Recommend that a qualified person repair as necessary.
5) Minor deterioration (e.g. cracks, holes, settlement, heaving) was found in the driveway, but no trip hazards were found. The client may wish to have repairs made for cosmetic reasons.
Limitations: The inspector performs a visual inspection of accessible components or systems at the exterior. Items excluded from this inspection include below-grade foundation walls and footings; foundations, exterior surfaces or components obscured by vegetation, stored items or debris; wall structures obscured by coverings such as siding or trim. Some items such as siding, trim, soffits, vents and windows are often high off the ground, and may be viewed using binoculars from the ground or from a ladder. This may limit a full evaluation. Regarding foundations, some amount of cracking is normal in concrete slabs and foundation walls due to shrinkage and drying. Note that the inspector does not determine the adequacy of seismic reinforcement.
Wall inspection method: Viewed from ground
Condition of wall exterior covering: Appeared serviceable
Apparent wall structure: Wood frame
Wall covering: Brick veneer
Condition of foundation and footings: Appeared serviceable
Apparent foundation type: Concrete slab on grade
Foundation/stem wall material: Poured in place concrete
Footing material (under foundation stem wall): Not determined (inaccessible or obscured)
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; solar roofing components. Any comments made regarding these items are made as a courtesy only. Note that the inspector does not provide an estimate of remaining life on the roof surface material, nor guarantee that leaks have not occurred in the roof surface, skylights or roof penetrations in the past. Regarding roof leaks, only active leaks, visible evidence of possible sources of leaks, and evidence of past leaks observed during the inspection are reported on as part of this inspection. The inspector does not guarantee or warrant that leaks will not occur in the future. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high wind and rain, melting snow) would be needed to do so. Occupants should monitor the condition of roofing materials in the future. For older roofs, recommend that a professional inspect the roof surface, flashings, appurtenances, etc. annually and maintain/repair as might be required. If needed, the roofer should enter attic space(s). Regarding the roof drainage system, unless the inspection was conducted during and after prolonged periods of heavy rain, the inspector was unable to determine if gutters, downspouts and extensions perform adequately or are leak-free.
Roof inspection method: Traversed
Condition of roof surface material: Appeared serviceable
Roof surface material: Asphalt or fiberglass composition shingles
Roof type: Gable
Apparent number of layers of roof surface material: One
Condition of exposed flashings: Appeared serviceable
6) One or more rubber or neoprene pipe flashings were split or cracked. Leaks can occur as a result. This is a conducive condition for wood-destroying organisms. Recommend that a qualified contractor replace flashings where necessary.
7) Nail heads were exposed at one or more shingles. More than just a few exposed nail heads may indicate a substandard roof installation. Recommend applying an approved sealant over exposed nail heads now and as necessary in the future to prevent leaks.
8) All vent flashings and Attic turbine vents had exposed nailheads on the surface of the roof. this can lead to water penetration into the roof materials and water damage. Recommend sealing the exposed nail heads and maintain.
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; areas and components obscured by insulation. Any comments made regarding these items are made as a courtesy only. The inspector does not determine the adequacy of the attic ventilation system. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high/low temperatures, high/low humidity, high wind and rain, melting snow) would be needed to do so. The inspector is not a licensed engineer and does not determine the adequacy of roof structure components such as trusses, rafters or ceiling beams, or their spacing or sizing.
Attic inspection method: Viewed from hatch(es)
Condition of roof structure: Appeared serviceable
Roof structure type: Trusses
Ceiling structure: Trusses
Condition of insulation in attic (ceiling, skylight chase, etc.): Required repair, replacement and/or evaluation (see comments below)
Ceiling insulation material: Fiberglass loose fill
Vapor retarder: Not determined (inaccessible or obscured)
Condition of roof ventilation: Appeared serviceable
Roof ventilation type: Gable end vents, Mechanical vents with turbine
9) The ceiling insulation installed in the attic was substandard and appeared to have an R rating that's significantly less than current standards (R-38). Heating and cooling costs will likely be higher due to poor energy efficiency. Recommend that a qualified contractor install insulation for better energy efficiency and per standard building practices.
10) One or more attic access hatches or doors were not insulated, or had substandard insulation. Weatherstripping was also missing or substandard. Recommend installing weatherstripping and insulation per current standards at hatches or doors for better energy efficiency. For more information, visit: http://www.reporthost.com/?ATTACC
11) The ceiling insulation in one or more areas of the attic was substandard. Heating and cooling costs may be higher due to reduced energy efficiency. Recommend that a qualified person repair, replace or install insulation as necessary and per standard building practices (typically R-38).
12) Due to the style of roof construction and location of havc unit. the attic was unaccessable except for minor visual inspection from the access panel. which was a pull down staircase located in the converted garage. No apparent issues were noted other than the insulation was obviously substandard do to the fact it just came to the top of the ceiling joists which would only be about 5-1/2". Recommend further evaluation of insulation by licensed contractor to bring insulation value to recommended level.
Limitations: The following items are not included in this inspection: generator systems, transfer switches, surge suppressors, inaccessible or concealed wiring; underground utilities and systems; low-voltage lighting or lighting on timers or sensors. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of grounding or bonding, if this system has an adequate capacity for the client's specific or anticipated needs, or if this system has any reserve capacity for additions or expansion. The inspector does not operate circuit breakers as part of the inspection, and does not install or change light bulbs. The inspector does not evaluate every wall switch or receptacle, but instead tests a representative number of them per various standards of practice. When furnishings, stored items or child-protective caps are present some receptacles are usually inaccessible and are not tested; these are excluded from this inspection. Receptacles that are not of standard 110 volt configuration, including 240-volt dryer receptacles, are not tested and are excluded. The functionality of, power source for and placement of smoke and carbon monoxide alarms is not determined as part of this inspection. Upon taking occupancy, proper operating and placement of smoke and carbon monoxide alarms should be verified and batteries should be changed. These devices have a limited lifespan and should be replaced every 10 years. The inspector attempts to locate and evaluate all main and sub-panels. However, panels are often concealed. If panels are found after the inspection, a qualified electrician should evaluate and repair if necessary. The inspector attempts to determine the overall electrical service size, but such estimates are not guaranteed because the overall capacity may be diminished by lesser-rated components in the system. Any repairs recommended should be made by a licensed electrician.
Electric service condition: Appeared serviceable
Primary service type: Underground
Number of service conductors: Not determined (components inaccessible or obscured)
Service voltage (volts): 120-240
Estimated service amperage: Not determined (components inaccessible or obscured)
Primary service overload protection type: Circuit breakers
Main disconnect rating (amps): Not applicable, no single main disconnect
System ground: Not determined, not readily apparent
Condition of main service panel: Not determined (inaccessible or obscured, or panel not opened)
Location of main service panel #A: Converted garage closet
Location of main disconnect: No single main disconnect, use all breakers in main service panel
Smoke alarms installed:
Carbon monoxide alarms installed: No, recommend install
14) One or more ground fault circuit interrupter (GFCI) devices protecting receptacles at the full bath wouldn't trip when tested. This is a potential shock hazard. Recommend that a qualified electrician evaluate and repair as necessary.
GFCI receptacle in the full bath did not trip when tested with the GFCI tester and also showed a open neutral.
15) One or more electric receptacles at the exterior had no visible ground fault circuit interrupter (GFCI) protection. If not GFCI-protected, receptacles in wet areas pose a shock hazard. Recommend that a qualified electrician evaluate and install GFCI protection if necessary and per standard building practices. General guidelines for GFCI-protected receptacles include the following locations:
Outdoors (since 1973)
Bathrooms (since 1975)
Garages (since 1978)
Kitchens (since 1987)
Crawl spaces and unfinished basements (since 1990)
16) One or more electric receptacles at the bedroom(s), kitchen, family room, dining room, living room and/or laundry area had no visible arc fault circuit interrupter (AFCI) protection, or the inspector was unable to determine if AFCI protection was present. This is a potential safety hazard. Recommend that a qualified electrician evaluate and install AFCI protection if necessary and per standard building practices. General guidelines for AFCI-protected receptacles include the following locations:
Bedrooms (since 1999)
Kitchens, laundry areas, family rooms, dining rooms, living rooms, parlors, libraries, dens and recreation rooms, sunrooms, closets and hallways (since 2014)
17) Panel(s) # had inadequate working space. This is a safety hazard when opening or working in panels. Electric panels should have the following clearances:
An open area 30 inches wide by 3 feet deep in front of the panel
6 feet 6 inches of headroom in front of the panel
The wall below the panel is clear to the floor
The center of the grip of the operating handle of the switch or circuit breaker not more than 6 feet 7 inches above the floor or working platform
Recommend that a qualified contractor repair or make modifications per standard building practices. If panels must be opened for repairs, then a qualified electrician should perform repairs.
18) One or more electric receptacles were incorrectly wired with an open neutral. All receptacles in the East half of the house showed an open neutral and all of the receptacles in the west half of the house showed correct wiring.Recommend that a qualified electrician evaluated repair as necessary.
19) No permanently installed carbon monoxide alarms were found. This is a potential safety hazard. Some states and/or municipalities require CO alarms to be installed for new construction and/or for homes being sold. Recommend installing approved CO alarms outside of each separate sleeping area in the immediate vicinity of the bedrooms on each level and in accordance with the manufacturer's recommendations. For more information, visit: http://www.reporthost.com/?COALRM
20) Branch circuit wiring installed in buildings built prior to the mid 1980s is typically rated for a maximum temperature of only 60 degrees Celsius. This includes non-metallic sheathed (Romex) wiring, and both BX and AC metal-clad flexible wiring. Knob and tube wiring, typically installed in homes built prior to 1950, may be rated for even lower maximum temperatures. Newer electric fixtures including lighting and fans typically require wiring rated for 90 degrees Celsius. Connecting newer fixtures to older, 60-degree-rated wiring is a potential fire hazard. Repairs for such conditions may involve replacing the last few feet of wiring to newer fixtures with new 90-degree-rated wire, and installing a junction box to join the old and new wiring.
It is beyond the scope of this inspection to determine if such incompatible components are installed, or to determine the extent to which they're installed. Based on the age of this building, the client should be aware of this safety hazard, both for existing fixtures and when planning to upgrade with newer fixtures. Consult with a qualified electrician for repairs as necessary.
21) The inspector was unable to open and evaluate panel(s) #A because items were blocking access. The condition of these panel(s) is unknown and they are excluded from this inspection. Repairs may be needed. Recommend that a qualified person correct conditions, or that a qualified contractor make repairs if necessary so panels can be opened, and that a qualified person fully evaluate panel(s).
22) The legend for circuit breakers or fuses in panel(s) #A was missing, incomplete, illegible or confusing. This is a potential shock or fire hazard in the event of an emergency when power needs to be turned off. Recommend correcting the legend so it's accurate, complete and legible. Evaluation by a qualified electrician may be necessary.
Limitations: The following items are not included in this inspection: private/shared wells and related equipment; private sewage disposal systems; hot tubs or spas; main, side and lateral sewer lines; gray water systems; pressure boosting systems; trap primers; incinerating or composting toilets; fire suppression systems; water softeners, conditioners or filtering systems; plumbing components concealed within the foundation or building structure, or in inaccessible areas such as below tubs; underground utilities and systems; overflow drains for tubs and sinks; backflow prevention devices. Any comments made regarding these items are as a courtesy only. Note that the inspector does not operate water supply or shut-off valves due to the possibility of valves leaking or breaking when operated. The inspector does not test for lead in the water supply, the water pipes or solder, does not determine if plumbing and fuel lines are adequately sized, and does not determine the existence or condition of underground or above-ground fuel tanks.
Condition of service and main line: Appeared serviceable
Water service: Public
Location of main water shut-off: Not determined (obscured, inaccessible or none found)
Condition of supply lines: Appeared serviceable
Supply pipe material: Not determined (inaccessible or obscured)
Condition of drain pipes: Appeared serviceable
Drain pipe material: Plastic
Condition of waste lines: Appeared serviceable
Waste pipe material: Plastic
Vent pipe condition: Appeared serviceable
Vent pipe material: Plastic
Sump pump installed: No
Sewage ejector pump installed: No
Condition of fuel system: Appeared serviceable
Location of main fuel shut-off valve: At gas meter
23) The drain for the wash machine was not tested and was disclosed by seller that it may be collapsed and inoperable. further evaluation from a licensed plumber needs to be done to determine the condition of this drain.
24) The inspector did not determine the location of the main water shut-off valve, or verify that a readily accessible shut-off valve in the building exists. Recommend consulting with the property owner to determine if a main shut-off valve exists, locating it yourself, or that a qualified plumber find it if necessary. If no readily accessible main shut-off valve is found in the building, then recommend that a qualified plumber install one so the water supply can be quickly turned off in the event of an emergency, such as when a supply pipe bursts.
Limitations: Evaluation of and determining the adequacy or completeness of the following items are not included in this inspection: water recirculation pumps; solar water heating systems; Energy Smart or energy saver controls; catch pan drains. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on water heaters, does not determine if water heaters are appropriately sized, or perform any evaluations that require a pilot light to be lit or a shut-off valve to be operated.
Condition of water heater: Appeared serviceable
Energy source: Natural gas
Capacity (in gallons): 40
Temperature-pressure relief valve installed: Yes
Location of water heater: Converted Garage
Hot water temperature tested: Yes
Water temperature (degrees Fahrenheit): 115
Condition of burners: Appeared serviceable
Condition of venting system: Appeared serviceable
25) The water heater did not have earthquake straps installed. This is a potential safety hazard in the event of an earthquake due to the risk of the water heater tipping over, gas lines breaking if it's gas-fired, or electric wiring being damaged if powered by electricity. Leaks may also occur in water-supply pipes or fittings. Recommend that a qualified person install earthquake straps per standard building practices.
26) The TPR drain line was routed into the washing machine drain that was disclosed did not drain properly and was possibly collapsed. If the TPR valve began to leak or opened because of a malfunction, this would caused severe water damage inside of the residence.
Limitations: The following items are not included in this inspection: humidifiers, dehumidifiers, electronic air filters; solar, coal or wood-fired heat systems; thermostat or temperature control accuracy and timed functions; heating components concealed within the building structure or in inaccessible areas; underground utilities and systems; safety devices and controls (due to automatic operation). Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on heating or cooling system components, does not determine if heating or cooling systems are appropriately sized, does not test coolant pressure, or perform any evaluations that require a pilot light to be lit, a shut-off valve to be operated, a circuit breaker to be turned "on" or a serviceman's or oil emergency switch to be operated. It is beyond the scope of this inspection to determine if furnace heat exchangers are intact and free of leaks. Condensation pans and drain lines may clog or leak at any time and should be monitored while in operation in the future. Where buildings contain furnishings or stored items, the inspector may not be able to verify that a heat source is present in all "liveable" rooms (e.g. bedrooms, kitchens and living/dining rooms).
General heating system type(s): Forced air
General heating distribution type(s): Ducts and registers
Last service date of primary heat source: Undetermined
Source for last service date of primary heat source: None
Condition of forced air heating/(cooling) system: Appeared serviceable
Forced air heating system fuel type: Natural gas
Estimated age of forced air furnace: Not Determined
Location of forced air furnace: Converted Garage
Condition of furnace filters: Required replacement
Condition of forced air ducts and registers: Appeared serviceable
Type of combustion air supply: Intake duct
Condition of venting system: Appeared serviceable
Condition of cooling system and/or heat pump: Not determined
Cooling system and/or heat pump fuel type: Electric
Location of heat pump or air conditioning unit: west
Type: Split system
Condition of controls: Appeared serviceable
27) The last service date of the forced air heating/cooling system appeared to be more than 1 year ago, or the inspector was unable to determine the last service date. Ask the property owner when it was last serviced. If unable to determine the last service date, or if this system was serviced more than 1 year ago, recommend that a qualified HVAC contractor service this system and make repairs if necessary. Because this system has a compressor and refrigerant system, this servicing should be performed annually in the future. Any needed repairs noted in this report should be brought to the attention of the contractor when it's serviced.
28) Recommend that home buyers replace or clean HVAC filters upon taking occupancy depending on the type of filters installed. Regardless of the type, recommend checking filters monthly in the future and replacing or cleaning them as necessary. How frequently they need replacing or cleaning depends on the type and quality of the filter, how the system is configured (e.g. always on vs. "Auto"), and on environmental factors (e.g. pets, smoking, frequency of house cleaning, number of occupants, the season).
29) The cooling fins at the air handler evaporator coils were dirty. Recommend that a qualified person clean fins as necessary.
30) The outdoor air temperature was below 65 degrees Fahrenheit during the inspection. Air conditioning systems can be damaged if operated during such low temperatures. Because of this, the inspector was unable to operate and fully evaluate the cooling system.
31) A whole house fan was installed. These fans provide cooling for interior spaces by blowing hot interior air up into the attic and out through attic vents, and by drawing cooler air in from the outside through open windows. They are intented to operate only when the outside temperature is cooler than inside. Multiple windows should be opened to equal or exceed 3 times the area of the fan opening. If air conditioning is installed it should not be operated while the whole house fan is operated. These fans do not dehumidify. They may be noisy during operation.
In some cases, additional attic venting is required for whole house fans to allow blown air to exit the attic. Attic vents should be kept clear at all times. Inadequate attic venting may result in attic air blowing through ceiling penetrations such as lights, or down through wall framing. It's beyond the scope of a home inspection to determine if attic venting is adequate. If concernced, review the fan's documentation and/or consult with a qualified contractor.
Be aware of safety issues related to whole house fans. Injury can occur if people come in contact with fan blades or belts. Louvers should always be open and the area above the fan should be unobstructed during operation, otherwise the fan may overheat and pose a fire hazard. Items should never be stored on top of the fan. Negative interior air pressure can cause gas-fired appliances such as water heaters and clothes dryers to backdraft, or cause flame rollout or pilot lights to blow out. Carbon monoxide and/or fire hazards may result. Children should never be allowed to operate whole house fans.
Whole house fans should be shut down during cooler months when not needed. This includes installing an insulated cover over the fan and turning power off to the the fan.
The client should be aware that some routine maintenance is required for whole house fans such as lubrication, and tightening or replacing belts cleaning. Consult with a heating and cooling specialist on this. Note also that motors and other components have a limited lifespan.
Limitations: The following items are not included in this inspection: household appliances such as stoves, ovens, cook tops, ranges, warming ovens, griddles, broilers, dishwashers, trash compactors, refrigerators, freezers, ice makers, hot water dispensers and water filters; appliance timers, clocks, cook functions, self and/or continuous cleaning operations, thermostat or temperature control accuracy, and lights. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of the remaining life of appliances, and does not determine the adequacy of operation of appliances. The inspector does not note appliance manufacturers, models or serial numbers and does not determine if appliances are subject to recalls. Areas and components behind and obscured by appliances are inaccessible and excluded from this inspection.
Condition of counters: Appeared serviceable
Condition of cabinets: Appeared serviceable
Condition of sinks and related plumbing: Appeared serviceable
Condition of under-sink food disposal: N/A (none installed)
Condition of dishwasher: Appeared serviceable
Condition of ranges, cooktops and/or ovens: Appeared serviceable
Range, cooktop, oven type: Natural gas
Type of ventilation: ducted to exterior
Condition of refrigerator: Appeared serviceable
Condition of built-in microwave oven: N/A (none installed)
32) The range could tip forward. An anti-tip bracket may not be installed. This is a potential safety hazard since the range can tip forward when weight is applied to the open door, such as when a small child climbs on it or if heavy objects are dropped on it. Anti-tip brackets have been sold with all free-standing ranges since 1985. Recommend installing an anti-tip bracket to eliminate this safety hazard. For more information, visit: http://www.reporthost.com/?ATB
33) The electrical connection for the dishwasher was plugged into a standard outlet. This needs to be upgraded to a GFCI outlet to prevent possible shock hazzards
Limitations: The following items are not included in this inspection: overflow drains for tubs and sinks; heated towel racks, saunas, steam generators, clothes washers, clothes dryers. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of washing machine drain lines, washing machine catch pan drain lines, or clothes dryer exhaust ducts. The inspector does not operate water supply or shut-off valves for sinks, toilets, bidets, clothes washers, etc. due to the possibility of valves leaking or breaking when operated. The inspector does not determine if shower pans or tub and shower enclosures are water tight, or determine the completeness or operability of any gas piping to laundry appliances.
Location #A: Full bath
Condition of counters: Appeared serviceable
Condition of cabinets: Appeared serviceable
Condition of flooring: Appeared serviceable
Condition of sinks and related plumbing: Appeared serviceable
Condition of toilets: Appeared serviceable
Condition of bathtubs and related plumbing: Appeared serviceable
Condition of shower(s) and related plumbing: Appeared serviceable
Bathroom and laundry ventilation type: Windows
Gas supply for laundry equipment present: Yes
240 volt receptacle for laundry equipment present: Yes
34) The bathroom with a shower or bathtub at location(s) #A didn't have an exhaust fan installed. Moisture can accumulate and result in mold, bacteria or fungal growth. Even if the bathroom has a window that opens, it may not provide adequate ventilation, especially during cold weather when windows are closed or when wind blows air into the bathroom. Recommend that a qualified contractor install exhaust fans per standard building practices where missing in bathrooms with showers or bathtubs.
35) The sink at location(s) #A drained slowly. Recommend clearing drain and/or having a qualified plumber repair if necessary.
36) Gaps, no caulk, or substandard caulking were found between the bathtub and the walls at location(s) #. Water may penetrate these areas and cause damage. Recommend that a qualified person re-caulk or install caulking as necessary.
Limitations: The following items are not included in this inspection: security, intercom and sound systems; communications wiring; central vacuum systems; elevators and stair lifts; cosmetic deficiencies such as nail-pops, scuff marks, dents, dings, blemishes or issues due to normal wear and tear in wall, floor and ceiling surfaces and coverings, or in equipment; deficiencies relating to interior decorating; low voltage and gas lighting systems. Any comments made regarding these items are as a courtesy only. Note that the inspector does not evaluate any areas or items which require moving stored items, furnishings, debris, equipment, floor coverings, insulation or similar materials. The inspector does not test for asbestos, lead, radon, mold, hazardous waste, urea formaldehyde urethane, or any other toxic substance. Some items such as window, drawer, cabinet door or closet door operability are tested on a sampled basis. The client should be aware that paint may obscure wall and ceiling defects, floor coverings may obscure floor defects, and furnishings may obscure wall, floor and floor covering defects. If furnishings were present during the inspection, recommend a full evaluation of walls, floors and ceilings that were previously obscured when possible. Carpeting and flooring, when installed over concrete slabs, may conceal moisture. If dampness wicks through a slab and is hidden by floor coverings that moisture can result in unhygienic conditions, odors or problems that will only be discovered when/if the flooring is removed. Determining the cause and/or source of odors is not within the scope of this inspection.
Condition of exterior entry doors: Required repair, replacement and/or evaluation (see comments below)
Exterior door material: Metal
Condition of interior doors: Appeared serviceable
Condition of windows and skylights: Appeared serviceable
Type(s) of windows: Vinyl, Metal
Wall type or covering: Drywall
Ceiling type or covering: Drywall
Condition of flooring: Appeared serviceable
Condition of concrete slab floor(s): Appeared serviceable
Flooring type or covering: Carpet, Tile
37) One or more window screens were damaged or deteriorated. These window(s) may not provide ventilation during months when insects are active. Recommend replacing window screens as necessary.
38) Carpeting in one or more areas was damaged or deteriorated. Recommend that a qualified contractor replace as necessary.
39) Lock mechanisms on one or more windows were inoperable. This can pose a security risk. Recommend that a qualified person repair as necessary.
Limitations: This report only includes findings from accessible and visible areas on the day of the inspection. In addition to the inaccessible areas documented in this report, examples of other inaccessible areas include: sub areas less than 18 inches in height; attic areas less than 5 feet in height, areas blocked by ducts, pipes or insulation; areas where locks or permanently attached covers prevent access; areas where insulation would be damaged if traversed; areas obscured by vegetation. All inaccessible areas are subject to infestation or damage from wood-destroying organisms. The inspector does not move furnishings, stored items, debris, floor or wall coverings, insulation, or other materials as part of the inspection, nor perform destructive testing. Wood-destroying organisms may infest, re-infest or become active at any time. No warranty is provided as part of this inspection.
Visible evidence of active wood-destroying insects: No
Visible evidence of active wood decay fungi: No
Visible evidence of past wood decay fungi: No
Visible evidence of damage by wood-destroying insects: No
Visible evidence of damage by wood decay fungi: No
Visible evidence of conditions conducive to wood-destroying organisms: No
Client present for discussion at end of inspection: Yes
Weather conditions during inspection: Dry (no rain), Overcast
Temperature during inspection: Cool
Type of building: Single family
Buildings inspected: One house
Number of residential units inspected: 1
Age of main building: 56
Source for main building age: Property owner
Front of building faces: East
Main entrance faces: East
40) Structures built prior to the mid 1980s may contain lead and/or asbestos. Lead is commonly found in paint and in some plumbing components. The EPA does not recognize newer coats of paint as encapsulating older coats of lead-based paint. Asbestos is commonly found in various building materials such as insulation, siding, and/or floor and ceiling tiles. Laws were passed in 1978 to prohibit usage of lead and asbestos, but stocks of materials containing these substances remained in use for a number of years thereafter. Both lead and asbestos are known health hazards. Evaluating for the presence of lead and/or asbestos is beyond the scope of this inspection. Any mention of these materials in this report is made as a courtesy only, and meant to refer the client to a specialist. Consult with specialists as necessary, such as industrial hygienists, professional labs and/or abatement specialists for this type of evaluation. For information on lead, asbestos and other hazardous materials in homes, visit: http://www.reporthost.com/?EPA http://www.reporthost.com/?CPSC http://www.reporthost.com/?CDC
41) Some areas and items at this property were obscured by furniture. This often includes but is not limited to walls, floors, windows, inside and under cabinets, under sinks, on counter tops, in closets, behind window coverings, under rugs or carpets, and under or behind furniture. Areas around the exterior, under the structure, in the garage and in the attic may also be obscured by stored items. The inspector in general does not move personal belongings, furnishings, carpets or appliances. When furnishings, stored items or debris are present, all areas or items that are obscured, concealed or not readily accessible are excluded from the inspection. The client should be aware that when furnishings, stored items or debris are eventually moved, damage or problems that were not noted during the inspection may be found.