This report is the exclusive property of this inspection company and the client(s) listed in the report title. Use of this report by any unauthorized persons is prohibited.
Sycamore Inspection Services, LLC
220 W Pacemont Rd
Columbus OH 43202-1014
Inspector: Joel Grimes
Inspector's phone: (614) 257-8020
Sample Property Inspection Report
||Sample Report 1
||100 Sample Report
||Monday, July 23, 2018
This report published on Wednesday, August 1, 2018 9:46:49 AM EDT
Report number: 0723201801
Time started: 1:00pm
Time finished: 4:00pm
Present during inspection: Client, Realtor
Client present for discussion at end of inspection: Yes
Weather conditions during inspection: Dry (no rain)
Temperature during inspection: Warm
Recent weather: Rain
Overnight temperature: Warm
Buildings inspected: One house
Age of main building: 1977
Source for main building age: Municipal records or property listing
Front of building faces: West
Main entrance faces: West
Structures built prior to the mid 1980s may contain lead and/or asbestos. Lead is commonly found in paint and in some plumbing components. The EPA does not recognize newer coats of paint as encapsulating older coats of lead-based paint. Asbestos is commonly found in various building materials such as insulation, siding, and/or floor and ceiling tiles. Laws were passed in 1978 to prohibit usage of lead and asbestos, but stocks of materials containing these substances remained in use for a number of years thereafter. Both lead and asbestos are known health hazards. Evaluating for the presence of lead and/or asbestos is beyond the scope of this inspection. Any mention of these materials in this report is made as a courtesy only, and meant to refer the client to a specialist. Consult with specialists as necessary, such as industrial hygienists, professional labs and/or abatement specialists for this type of evaluation. For information on lead, asbestos and other hazardous materials in homes, visit:http://www.reporthost.com/?EPAhttp://www.reporthost.com/?CPSChttp://www.reporthost.com/?CDC
Microbial growths were found at one or more locations in the attic and/or the basement. It is beyond the scope of this inspection to identify what substance or organism this staining is. However such staining is normally caused by excessively moist conditions, which in turn can be caused by plumbing or building envelope leaks and/or substandard ventilation. These conducive conditions should be corrected before making any attempts to remove or correct the staining. Normally affected materials such as drywall are removed, enclosed affected spaces are allowed to dry thoroughly, a mildewcide may be applied, and only then is drywall reinstalled. For evaluation and possible mitigation, consult with a qualified industrial hygienist or mold/moisture mitigation specialist. For more information, visit:http://www.reporthost.com/?MOLDCDChttp://www.reporthost.com/?MOLDEPA
Photo 2-1 2nd floor attic sheathing
Photo 2-5 basement vent
Limitations: Unless specifically included in the inspection, the following items and any related equipment, controls, electric systems and/or plumbing systems are excluded from this inspection: detached buildings or structures; fences and gates; retaining walls; underground drainage systems, catch basins or concealed sump pumps; swimming pools and related safety equipment, spas, hot tubs or saunas; whether deck, balcony and/or stair membranes are watertight; trees, landscaping, properties of soil, soil stability, erosion and erosion control; ponds, water features, irrigation or yard sprinkler systems; sport courts, playground, recreation or leisure equipment; areas below the exterior structures with less than 3 feet of vertical clearance; invisible fencing; sea walls, docks and boathouses; retractable awnings. Any comments made regarding these items are as a courtesy only.
Site profile: Minor slope
Driveway material: Asphalt
Sidewalk material: Poured in place concrete
Deck, patio, porch cover material and type: Covered (Refer to Roof section)
Exterior stair material: Concrete
Concrete patios were undermined in one or more areas, where soil has eroded out from beneath. Recommend that a qualified person repair as necessary to prevent further erosion and undermining.
The asphalt driveway surface was worn and is prone to developing cracks from water penetration. Recommend that a qualified person reseal the driveway. For more information, visit:http://www.reporthost.com/?RAD
Exterior and Foundation
Limitations: The inspector performs a visual inspection of accessible components or systems at the exterior. Items excluded from this inspection include below-grade foundation walls and footings; foundations, exterior surfaces or components obscured by vegetation, stored items or debris; wall structures obscured by coverings such as siding or trim. Some items such as siding, trim, soffits, vents and windows are often high off the ground, and may be viewed using binoculars from the ground or from a ladder. This may limit a full evaluation. Regarding foundations, some amount of cracking is normal in concrete slabs and foundation walls due to shrinkage and drying. Note that the inspector does not determine the adequacy of seismic reinforcement.
Wall inspection method: Viewed from ground
Apparent wall structure: Wood frame
Wall covering: Stucco, Vinyl, Solid brick (not veneer)
Apparent foundation type: Unfinished basement
Some sections of siding and/or trim were deteriorated and/or substandard. Recommend that a qualified person repair, replace or install siding or trim as necessary.
Photo 5-2 Vinyl siding with no overlap on pieces.
The masonry (brick or stone) veneer had loose bricks. Where cracks or openings are exposed, water may enter the wall structure causing mold, fungal growth and structural damage. This is a conducive condition for wood-destroying organisms. Recommend that a qualified contractor repair as necessary. For example, by repointing mortar or replacing broken or missing masonry.
The Garage door was installed with no "drip cap" or "Z" flashings installed above it. Better building practices call for such flashings, which greatly reduce the chance of leaks above windows and doors. Without this flashing, caulk and paint must be maintained or water can enter the wall structure and cause rot and possible structural damage. Depending on the exposure (e.g. roof overhang, height of exterior wall, direction of prevailing rain) this may or may not be an issue. The client should monitor these areas in the future and maintain caulk and paint as necessary. Consult with a qualified contractor about installing flashings where needed, and per standard building practices. Note that when trim or siding is removed to install flashing, damaged wood may be found and additional repairs may be needed.
Cracks, deterioration and/or damage were found in one or more areas of the exterior stucco finish. In damp climates, moisture may enter cracks or damaged areas and further deteriorate the stucco. Also the wall behind the stucco may become damaged from moisture. Note that areas behind the stucco are inaccessible and excluded from this inspection. Recommend that a qualified contractor repair or replace stucco as necessary.
Vegetation such as trees, shrubs and/or vines was in contact with or close to the building exterior. Vegetation can serve as a pathway for wood-destroying insects and can retain moisture against the exterior after it rains. This is a conducive condition for wood-destroying organisms. Recommend pruning, moving or removing vegetation as necessary to maintain at least 6 inches of space between it and the building exterior. A 1-foot clearance is better.
Caulk was missing in some areas. For example, at siding-trim junctions. Recommend that a qualified person renew or install caulk as necessary. Where gaps are wider than 1/4 inch, an appropriate material other than caulk should be used. For more information, visit:http://www.reporthost.com/?CAULK
Some foundation walls below the house were obscured by wall paneling. The inspector was unable to evaluate these areas. They are excluded from this inspection.
Limitations: Structural components such as joists and beams, and other components such as piping, wiring and/or ducting that are obscured by under-floor insulation are excluded from this inspection. The inspector does not determine if support posts, columns, beams, joists, studs, trusses, etc. are of adequate size, spanning or spacing.
The inspector does not guarantee or warrant that water will not accumulate in the crawl spaces in the future. Complete access to all crawl space areas during all seasons and during prolonged periods of all types of weather conditions (e.g. heavy rain, melting snow) would be needed to do so.
The inspector attempts to locate all crawl space access points and areas. Access points may be obscured or otherwise hidden by furnishings or stored items. In such cases, the client should ask the property owner where all access points are that are not described in this inspection, and have those areas inspected. Note that crawl space areas should be checked at least annually for water intrusion, plumbing leaks and pest activity.
Crawl space inspection method: Traversed
Pier or support post material: Concrete block
Vapor barrier present: None visible
Evidence of prior water intrusion or accumulation was found in one or more sections of the crawl space. For example, sediment stains on the vapor barrier or foundation, and/or efflorescence on the foundation. Accumulated water is a conducive condition for wood-destroying organisms and should not be present in the crawl space. Recommend that the client review any disclosure statements available and ask the property owner about past accumulation of water in the crawl space. The crawl space should be monitored in the future for accumulated water, especially after heavy and/or prolonged periods of rain. If water is found to accumulate, then recommend that a qualified contractor who specializes in drainage issues evaluate and repair as necessary. Typical repairs for preventing water from accumulating in crawl spaces include:
- Repairing, installing or improving rain run-off systems (gutters, downspouts and extensions or drain lines)
- Improving perimeter grading
- Repairing, installing or improving underground footing and/or curtain drains
Ideally, water should not enter crawl spaces, but if water must be controlled after it enters the crawl space, then typical repairs include installing trenches, gravity drains and/or sump pump(s) in the crawl space.
No vapor barrier was installed in the crawl space. This is a conducive condition for wood-destroying organisms due to the likelihood of water evaporating from the soil below up into the structure. A 6 mil black plastic sheet should be placed over all exposed soil with seams overlapped to 24 inches, and not in contact with any wood structural components. The sheeting should be held in place with bricks or stones, not wood. Recommend that a qualified contractor install a vapor barrier per standard building practices.
Limitations: Structural components such as joists and beams, and other components such as piping, wiring and/or ducting that are obscured by under-floor insulation are also excluded from this inspection. Note that the inspector does not determine if support posts, columns, beams, joists, studs, trusses, etc. are of adequate size, spanning or spacing.
The inspector does not guarantee or warrant that water will not accumulate in the basement in the future. Access to the basement during all seasons and during prolonged periods of all types of weather conditions (e.g. heavy rain, melting snow) would be needed to do so. The inspector does not determine the adequacy of basement floor or stairwell drains, or determine if such drains are clear or clogged.
Note that all basement areas should be checked periodically for water intrusion, plumbing leaks and pest activity.
Pier or support post material: Bearing wall, Concrete block
Floor structure above: Solid wood joists
Stains and elevated levels of moisture were found in one or more wall areas. The stains appear to be due to an active basement wall leak. Recommend that a qualified contractor evaluate and repair as necessary.
Photo 14-1 SW corner of basement
Sealant or water-proofing coating was found on basement walls and/or floors. This may indicate that water has infiltrated or accumulated in the basement previously. Monitor the basement for excessive moisture conditions in the future, and review any disclosure statements related to accumulated moisture in the basement. Note that the inspector does not guarantee or warrant that water will not accumulate in the basement in the future.
Some basement walls and ceilings below the house were obscured by wall paneling and drywall. The inspector was unable to evaluate these areas. They are excluded from this inspection.
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; solar roofing components. Any comments made regarding these items are made as a courtesy only. Note that the inspector does not provide an estimate of remaining life on the roof surface material, nor guarantee that leaks have not occurred in the roof surface, skylights or roof penetrations in the past. Regarding roof leaks, only active leaks, visible evidence of possible sources of leaks, and evidence of past leaks observed during the inspection are reported on as part of this inspection. The inspector does not guarantee or warrant that leaks will not occur in the future. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high wind and rain, melting snow) would be needed to do so. Occupants should monitor the condition of roofing materials in the future. For older roofs, recommend that a professional inspect the roof surface, flashings, appurtenances, etc. annually and maintain/repair as might be required. If needed, the roofer should enter attic space(s). Regarding the roof drainage system, unless the inspection was conducted during and after prolonged periods of heavy rain, the inspector was unable to determine if gutters, downspouts and extensions perform adequately or are leak-free.
Roof inspection method: Partially traversed
Roof surface material: Asphalt or fiberglass composition shingles
Roof type: Gable
Apparent number of layers of roof surface material: One
Gutter and downspout material: Metal
Gutter and downspout installation: Full
Fungal rot or significant water damage was found at one or more roof areas at fascia boards. Recommend that a qualified contractor repair as necessary. For example, by replacing all rotten wood, priming and painting new wood and installing flashing.
Photo 17-1 Above Garage Door
Photo 17-2 Facia board above garage door
Attic and Roof Structure
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; areas and components obscured by insulation. Any comments made regarding these items are made as a courtesy only. The inspector does not determine the adequacy of the attic ventilation system. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high/low temperatures, high/low humidity, high wind and rain, melting snow) would be needed to do so. The inspector is not a licensed engineer and does not determine the adequacy of roof structure components such as trusses, rafters or ceiling beams, or their spacing or sizing.
Attic inspection method: Viewed from hatch(es)
Location of attic access point #A: Bedroom closet
Location of attic access point #B: Garage
Attic access points that were opened and viewed, traversed or partially traversed: A, B
Roof structure type: Rafters
Ceiling structure: Ceiling joists
Ceiling insulation material: Mineral wool loose fill
Approximate attic insulation R value (may vary in areas): R-21
Roof ventilation type: Box vents (roof jacks)
One or more sections of the roof structure appeared to have substandard ventilation, soffit or lower vents were missing. This can result in high attic and roof surface temperatures, reduce the life of the roof covering materials, and/or increase cooling costs. High levels of moisture are also likely to accumulate in the roof structure or attic, and can be a conducive condition for wood-destroying organisms. Standard building practices require one free square foot of ventilation for every 150 square feet of attic space, and that vents be evenly distributed between the lowest points of the roof structure and the highest points to promote air circulation. Often this means that both soffit vents and ridge or gable end vents are installed. Recommend that a qualified contractor evaluate and repair per standard building practices.
Roof Sheathing was damaged. This may significantly weaken the roof structure. Recommend that a qualified contractor repair as necessary.
One or more exhaust fan ducts in the attic were not attached to a vent hood or cap. As a result, conditioned air will enter the attic when the fan is operated. Ducts terminating near an attic vent but without a dedicated vent hood or cap will likely blow conditioned air back into the attic. This can result in excessive moisture in the attic. Recommend that a qualified contractor repair per standard building practices, so exhaust fan ducts are permanently fastened to vent hoods or caps.
What appeared to be past water stains were visible on the roof structure at one or more locations in the attic. However, no elevated levels of moisture were found at these stains during the inspection. The stains may have been caused by a past leak. Recommend asking the property owner about past leaks. Monitor these areas in the future, especially after heavy rains to determine if active leaks exist. If leaks are found, recommend that a qualified contractor evaluate and repair as necessary.
Photo 21-1 Lower Roof
Garage or Carport
Limitations: The inspector cannot reasonably determine the integrity of all elements of limited fire resistance at residential construction or verify firewall ratings at multi unit construction. Requirements for ventilation in garages vary between municipalities.
Type of door between garage and house: Wood
Exterior door material: Wood
Type of garage vehicle door: Sectional
Number of vehicle doors: 1
Mechanical auto-reverse operable (reverses when meeting reasonable resistance during closing): Yes
One or more holes were found in the attached garage walls or ceilings. Current standard building practices call for wooden-framed ceilings and walls that divide the house and garage to provide limited fire-resistance rating to prevent the spread of fire from the garage to the house. Recommend that a qualified person repair per standard building practices. For example, by patching openings or holes, firestopping holes or gaps with fire-resistant caulking, and/or installing fire-resistant wall covering (e.g. Type X drywall). For more information, visit:http://www.reporthost.com/?AGFR
Limitations: The following items are not included in this inspection: generator systems, transfer switches, surge suppressors, inaccessible or concealed wiring; underground utilities and systems; low-voltage lighting or lighting on timers or sensors. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of grounding or bonding, if this system has an adequate capacity for the client's specific or anticipated needs, or if this system has any reserve capacity for additions or expansion. The inspector does not operate circuit breakers as part of the inspection, and does not install or change light bulbs. The inspector does not evaluate every wall switch or receptacle, but instead tests a representative number of them per various standards of practice. When furnishings, stored items or child-protective caps are present some receptacles are usually inaccessible and are not tested; these are excluded from this inspection. Receptacles that are not of standard 110 volt configuration, including 240-volt dryer receptacles, are not tested and are excluded. The functionality of, power source for and placement of smoke and carbon monoxide alarms is not determined as part of this inspection. Upon taking occupancy, proper operating and placement of smoke and carbon monoxide alarms should be verified and batteries should be changed. These devices have a limited lifespan and should be replaced every 10 years. The inspector attempts to locate and evaluate all main and sub-panels. However, panels are often concealed. If panels are found after the inspection, a qualified electrician should evaluate and repair if necessary. The inspector attempts to determine the overall electrical service size, but such estimates are not guaranteed because the overall capacity may be diminished by lesser-rated components in the system. Any repairs recommended should be made by a licensed electrician.
Primary service type: Underground
Number of service conductors: 3
Service voltage (volts): 120-240
Estimated service amperage: 200
Service entrance conductor material: Stranded aluminum
System ground: Copper
Location of main service panel #A: Basement
Location of main disconnect: Breaker at top of main service panel
Branch circuit wiring type: non-metallic sheathed
Ground fault circuit interrupter (GFCI) protection present: Yes
Arc fault circuit interrupter (AFCI) protection present: Yes
Smoke alarms installed: Yes, but not tested
One or more circuit breakers in panel(s) #A were "double tapped," where two or more wires were installed in the breaker's lug. Most breakers are designed for only one wire to be connected. This is a safety hazard since the lug bolt can tighten securely against one wire but leave other(s) loose. Arcing, sparks and fires can result. Recommend that a qualified electrician repair as necessary. For more information, visit:http://www.reporthost.com/?DBLTAP
Plumbing / Fuel Systems
Limitations: The following items are not included in this inspection: private/shared wells and related equipment; private sewage disposal systems; hot tubs or spas; main, side and lateral sewer lines; gray water systems; pressure boosting systems; trap primers; incinerating or composting toilets; fire suppression systems; water softeners, conditioners or filtering systems; plumbing components concealed within the foundation or building structure, or in inaccessible areas such as below tubs; underground utilities and systems; overflow drains for tubs and sinks; backflow prevention devices. Any comments made regarding these items are as a courtesy only. Note that the inspector does not operate water supply or shut-off valves due to the possibility of valves leaking or breaking when operated. The inspector does not test for lead in the water supply, the water pipes or solder, does not determine if plumbing and fuel lines are adequately sized, and does not determine the existence or condition of underground or above-ground fuel tanks.
Water service: Public
Location of main water shut-off: Basement
Supply pipe material: Copper
Drain pipe material: Plastic
Waste pipe material: Plastic
Location(s) of plumbing clean-outs: Basement
Vent pipe material: Plastic
Sump pump installed: Yes
Limitations: Evaluation of and determining the adequacy or completeness of the following items are not included in this inspection: water recirculation pumps; solar water heating systems; Energy Smart or energy saver controls; catch pan drains. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on water heaters, does not determine if water heaters are appropriately sized, or perform any evaluations that require a pilot light to be lit or a shut-off valve to be operated.
Energy source: Electricity
Estimated age: 2017
Capacity (in gallons): 50
Temperature-pressure relief valve installed: Yes
Serial number: Q331731898
Location of water heater: Basement
Hot water temperature tested: Yes
Water temperature (degrees Fahrenheit): 106
Heating, Ventilation and Air Condition (HVAC)
Limitations: The following items are not included in this inspection: humidifiers, dehumidifiers, electronic air filters; solar, coal or wood-fired heat systems; thermostat or temperature control accuracy and timed functions; heating components concealed within the building structure or in inaccessible areas; underground utilities and systems; safety devices and controls (due to automatic operation). Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on heating or cooling system components, does not determine if heating or cooling systems are appropriately sized, does not test coolant pressure, or perform any evaluations that require a pilot light to be lit, a shut-off valve to be operated, a circuit breaker to be turned "on" or a serviceman's or oil emergency switch to be operated. It is beyond the scope of this inspection to determine if furnace heat exchangers are intact and free of leaks. Condensation pans and drain lines may clog or leak at any time and should be monitored while in operation in the future. Where buildings contain furnishings or stored items, the inspector may not be able to verify that a heat source is present in all "liveable" rooms (e.g. bedrooms, kitchens and living/dining rooms).
General heating system type(s): Forced air, Furnace
General heating distribution type(s): Ducts and registers
Last service date of primary heat source: 6/11/10
Source for last service date of primary heat source: Label
Forced air heating system fuel type: Electric
Estimated age of forced air furnace: 2010
Forced air heating system manufacturer: Carrier
Forced air furnace serial number: 1710A85706
Location of forced air furnace: Basement
Location of heat pump or air conditioning unit: east
Type: Split system
Estimated age of heat pump or air conditioning unit: 2010
Manufacturer of cooling system and/or heat pump: Carrier
Heat pump or air conditioner serial number: 2010E25827
The last service date of the forced air heating/cooling system appeared to be more than 1 year ago, or the inspector was unable to determine the last service date. Ask the property owner when it was last serviced. If unable to determine the last service date, or if this system was serviced more than 1 year ago, recommend that a qualified HVAC contractor service this system and make repairs if necessary. Because this system has a compressor and refrigerant system, this servicing should be performed annually in the future. Any needed repairs noted in this report should be brought to the attention of the contractor when it's serviced.
The air handler's primary condensate drain line was leaking. Condensate drain water may accumulate, leak and cause water damage to surrounding areas. Recommend that a qualified HVAC contractor repair as necessary.
Fireplaces, Stoves, Chimneys and Flues
Limitations: The following items are not included in this inspection: coal stoves, gas logs, chimney flues (except where visible). Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of drafting or sizing in fireplace and stove flues, and also does not determine if prefabricated or zero-clearance fireplaces are installed in accordance with the manufacturer's specifications. The inspector does not perform any evaluations that require a pilot light to be lit, and does not light fires. The inspector provides a basic visual examination of a chimney and any associated wood burning device. The National Fire Protection Association has stated that an in-depth Level 2 chimney inspection should be part of every sale or transfer of property with a wood-burning device. Such an inspection may reveal defects that are not apparent to the home inspector who is a generalist.
Wood-burning fireplace type: Masonry
Wood-burning chimney type: Masonry
The brick chimney was severely deteriorated. For example, loose or missing mortar, cracked, broken, loose or spalled bricks. Loose bricks can pose a safety hazard, and deteriorated masonry can allow water to infiltrate the chimney structure and cause further damage. Recommend that a qualified contractor repair as necessary.
One or more ash clean-out doors were corroded. Recommend that a qualified person repair or replace as necessary.
Limitations: The following items are not included in this inspection: household appliances such as stoves, ovens, cook tops, ranges, warming ovens, griddles, broilers, dishwashers, trash compactors, refrigerators, freezers, ice makers, hot water dispensers and water filters; appliance timers, clocks, cook functions, self and/or continuous cleaning operations, thermostat or temperature control accuracy, and lights. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of the remaining life of appliances, and does not determine the adequacy of operation of appliances. The inspector does not note appliance manufacturers, models or serial numbers and does not determine if appliances are subject to recalls. Areas and components behind and obscured by appliances are inaccessible and excluded from this inspection.
Permanently installed kitchen appliances present during inspection: Range, Oven, Dishwasher, Refrigerator, Under-sink food disposal, Microwave oven
Type of ventilation: Hood or built into microwave over range or cooktop
2 cooktop burner(s) were inoperable. Recommend that a qualified person repair as necessary.
Bathrooms, Laundry and Sinks
Limitations: The following items are not included in this inspection: overflow drains for tubs and sinks; heated towel racks, saunas, steam generators, clothes washers, clothes dryers. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of washing machine drain lines, washing machine catch pan drain lines, or clothes dryer exhaust ducts. The inspector does not operate water supply or shut-off valves for sinks, toilets, bidets, clothes washers, etc. due to the possibility of valves leaking or breaking when operated. The inspector does not determine if shower pans or tub and shower enclosures are water tight, or determine the completeness or operability of any gas piping to laundry appliances.
Location #A: Full bath, second floor
Location #B: Master bath, second floor
Location #C: Half bath, first floor
Bathroom and laundry ventilation type: Windows, Spot exhaust fans, with individual ducts
The bathroom with a shower or bathtub at location(s) #B didn't have an exhaust fan installed. Moisture can accumulate and result in mold, bacteria or fungal growth. Even if the bathroom has a window that opens, it may not provide adequate ventilation, especially during cold weather when windows are closed or when wind blows air into the bathroom. Recommend that a qualified contractor install exhaust fans per standard building practices where missing in bathrooms with showers or bathtubs.
Tile, caulk and/or grout in the shower enclosure at location(s) #B were deteriorated (e.g. loose or cracked tiles, missing grout) or substandard. Water may leak through gaps and damage the wall or floor structure as a result. Recommend that a qualified contractor repair as necessary. Note that the condition of the structure behind and below the shower enclosure is unknown due to it being concealed.
The sink drain stopper mechanism at location(s) #A and C was inoperable. Recommend that a qualified person repair or replace as necessary.
Interior, Doors and Windows
Limitations: The following items are not included in this inspection: security, intercom and sound systems; communications wiring; central vacuum systems; elevators and stair lifts; cosmetic deficiencies such as nail-pops, scuff marks, dents, dings, blemishes or issues due to normal wear and tear in wall, floor and ceiling surfaces and coverings, or in equipment; deficiencies relating to interior decorating; low voltage and gas lighting systems. Any comments made regarding these items are as a courtesy only. Note that the inspector does not evaluate any areas or items which require moving stored items, furnishings, debris, equipment, floor coverings, insulation or similar materials. The inspector does not test for asbestos, lead, radon, mold, hazardous waste, urea formaldehyde urethane, or any other toxic substance. Some items such as window, drawer, cabinet door or closet door operability are tested on a sampled basis. The client should be aware that paint may obscure wall and ceiling defects, floor coverings may obscure floor defects, and furnishings may obscure wall, floor and floor covering defects. If furnishings were present during the inspection, recommend a full evaluation of walls, floors and ceilings that were previously obscured when possible. Carpeting and flooring, when installed over concrete slabs, may conceal moisture. If dampness wicks through a slab and is hidden by floor coverings that moisture can result in unhygienic conditions, odors or problems that will only be discovered when/if the flooring is removed. Determining the cause and/or source of odors is not within the scope of this inspection.
Exterior door material: Metal
Type(s) of windows: Metal, Multi-pane, Double-hung
Wall type or covering: Drywall
Ceiling type or covering: Drywall
One or more interior doors were sticking in the door jamb and were difficult to operate. Recommend that a qualified person repair as necessary. For example, by trimming doors.
Minor cracks, nail pops and/or blemishes were found in walls and/or ceilings in one or more areas. Cracks and nail pops are common, are often caused by lumber shrinkage or minor settlement, and can be more or less noticeable depending on changes in humidity. They did not appear to be a structural concern, but the client may wish to repair these for aesthetic reasons. For recurring cracks, consider using an elastic crack covering product:http://www.reporthost.com/?ECC
Please let me know if you have any questions about your report or the property. Good luck with your future purchase.