This report is the exclusive property of Specquest LLC and the client(s) listed in the report title. Use of this report by any unauthorized persons is prohibited.This report has been produced in accordance with our signed contract (pre-inspection agreement) and is subject to the terms and conditions agreed upon therein. All printed comments and the opinions expressed herein are those of Specquest LLC.
Specquest LLCWebsite: http://www.specquestpro.com
Inspector's email: firstname.lastname@example.org
Phone: (720) 775-5245
Property Inspection Report
||John & Mary Homeowner
||123 Home Dr
Anywhere CA 95835
||Friday, July 01, 2016
This report published on Wednesday, October 12, 2016 4:31:32 PM PDT
How to Read this Report
This report is organized by the property's functional areas. Within each functional area, descriptive information is listed first and is shown in bold type. Items of concern follow descriptive information.
Concerns are shown and sorted according to these types:
|Safety||Poses a safety hazard|
|Repair/Replace||Recommend repairing or replacing|
|Repair/Maintain||Recommend repair and/or maintenance|
|Minor Defect||Correction likely involves only a minor expense|
|Maintain||Recommend ongoing maintenance|
|Evaluate||Recommend evaluation by a specialist|
|Monitor||Recommend monitoring in the future|
|Comment||For your information|
Click here for a glossary of building construction terms.Contact your inspector If there are terms that you do not understand, or visit the glossary of construction terms at http://www.reporthost.com/glossary.asp
Report number: 104
Time started: 9:50 AM
Time finished: 11:55 AM
Present during inspection: Client, Realtor
Client present for discussion at end of inspection: Yes
Weather conditions during inspection: Dry (no rain), Sunny
Temperature during inspection: Warm, 80 Degrees
Ground condition: Dry
Recent weather: Dry (no rain), Sunny
Overnight temperature: Warm
Inspection fee: 350
Payment method: Credit card
Type of building: Single family
Buildings inspected: One house
Age of main building: 11
Source for main building age: Realtor
Front of building faces: East
Limitations: Unless specifically included in the inspection, the following items and any related equipment, controls, electric systems and/or plumbing systems are excluded from this inspection: detached buildings or structures; fences and gates; retaining walls; underground drainage systems, catch basins or concealed sump pumps; swimming pools and related safety equipment, spas, hot tubs or saunas; whether deck, balcony and/or stair membranes are watertight; trees, landscaping, properties of soil, soil stability, erosion and erosion control; ponds, water features, irrigation or yard sprinkler systems; sport courts, playground, recreation or leisure equipment; areas below the exterior structures with less than 3 feet of vertical clearance; invisible fencing. Any comments made regarding these items are as a courtesy only.
Condition of fences and gates: Appeared serviceable, Required repairs, replacement and/or evaluation; Missing fence picket in back (lying in front of fence)
Fence and gate material: Wood
Site profile: Minor slope
Condition of driveway: Appeared serviceable
Driveway material: Poured in place concrete
Condition of sidewalks and/or patios: Appeared serviceable
Sidewalk material: Poured in place concrete
Condition of deck, patio and/or porch covers: Appeared serviceable
Deck, patio, porch cover material and type: Open
2) Safety, Repair/Maintain
Settlement, heaving and/or deterioration resulting in trip hazards were found in the sidewalks towards main electrical disconnect. For safety reasons, recommend that a qualified contractor repair as necessary to eliminate trip hazards.
Exterior and Foundation
Limitations: The inspector performs a visual inspection of accessible components or systems at the exterior. Items excluded from this inspection include below-grade foundation walls and footings; foundations, exterior surfaces or components obscured by vegetation, stored items or debris; wall structures obscured by coverings such as siding or trim. Some items such as siding, trim, soffits, vents and windows are often high off the ground, and may be viewed using binoculars from the ground or from a ladder. This may limit a full evaluation. Regarding foundations, some amount of cracking is normal in concrete slabs and foundation walls due to shrinkage and drying. Note that the inspector does not determine the adequacy of seismic reinforcement.
Wall inspection method: Viewed from ground
Condition of wall exterior covering: Appeared serviceable
Apparent wall structure: Wood frame
Wall covering: Stucco
Condition of foundation and footings: Appeared serviceable, largely not visible
Apparent foundation type: Concrete slab on grade
Anchor bolts or hold downs for seismic reinforcement: None visible
One or more holes or gaps were found in siding or trim. Vermin, insects or water may enter the structure. Recommend that a qualified person repair as necessary.
Stucco Crack 2
Cracks, deterioration and/or damage were found in one or more areas of the exterior stucco finish. In damp climates, moisture may enter cracks or damaged areas and further deteriorate the stucco. Also the wall behind the stucco may become damaged from moisture. Note that areas behind the stucco are inaccessible and excluded from this inspection. Recommend that a qualified contractor repair or replace stucco as necessary.
Stucco Crack 3
Stucco Crack 4
Stucco Crack 5
Trees were in contact with or were close to the building at one or more locations. Damage to the building may occur, especially during high winds, or may have already occurred (see other comments in this report). Recommend that a qualified tree service contractor or certified arborist remove trees as necessary to prevent damage to the building exterior.
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access. Any comments made regarding these items are made as a courtesy only. Note that the inspector does not provide an estimate of remaining life on the roof surface material, nor guarantee that leaks have not occurred in the roof surface, skylights or roof penetrations in the past. Regarding roof leaks, only active leaks, visible evidence of possible sources of leaks, and evidence of past leaks observed during the inspection are reported on as part of this inspection. The inspector does not guarantee or warrant that leaks will not occur in the future. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high wind and rain) would be needed to do so. Occupants should monitor the condition of roofing materials in the future. For older roofs, recommend that a professional inspect the roof surface, flashings, appurtenances, etc. annually and maintain/repair as might be required. If needed, the roofer should enter attic space(s). Regarding the roof drainage system, unless the inspection was conducted during and after prolonged periods of heavy rain, the inspector was unable to determine if gutters, downspouts and extensions perform adequately or are leak-free.
Age of roof surface(s): 11
Roof inspection method: Viewed from eaves on ladder, Viewed from ground
Condition of roof surface material: Appeared serviceable
Roof surface material: Clay tile
Roof type: Hipped
Condition of exposed flashings: Appeared serviceable
Condition of gutters, downspouts and extensions: Appeared serviceable
Gutter and downspout material: Metal
Gutter and downspout installation: Full
Stains were found on one or more gutters that indicate past leaks have occurred. However, the inspector was unable to verify that the gutters do or don't leak because of lack of recent rainfall. Monitor the gutters in the future while it's raining to determine if gutters leak. If they do, then recommend that a qualified person repair as necessary to prevent water from coming in contact with the building or accumulating around the building foundation.
7) Comment -
Normally the inspector attempts to traverse roof surfaces during the inspection. However, due to roof configuration (very high and fragile materials), the inspector was unable to traverse the roof and wasn't able to fully evaluate the entire roof surface.
Attic and Roof Structure
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; areas and components obscured by insulation. Any comments made regarding these items are made as a courtesy only. The inspector does not determine the adequacy of the attic ventilation system. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high/low temperatures, high/low humidity, high wind and rain) would be needed to do so. The inspector is not a licensed engineer and does not determine the adequacy of roof structure components such as trusses, rafters or ceiling beams, or their spacing or sizing.
Attic inspection method: Partially traversed
Location of attic access point #A: Hallway, Second floor
Attic access points that were opened and viewed, traversed or partially traversed: A
Condition of roof structure: Appeared serviceable
Roof structure type: Trusses
Ceiling structure: Trusses
Condition of insulation in attic (ceiling, skylight chase, etc.): Appeared serviceable
Ceiling insulation material: Fiberglass loose fill
Approximate attic insulation R value (may vary in areas): R-38
Vapor retarder: None visible, but may exist
Condition of roof ventilation: Appeared serviceable
Roof ventilation type: Open soffit vents
8) Repair/Maintain -
Attic access hatches had no weatherstripping. Weatherstripping should be installed around hatches or doors as necessary to prevent heated interior air from entering the attic.
Garage or Carport
Limitations: The inspector does not determine the adequacy of firewall ratings. Requirements for ventilation in garages vary between municipalities.
Condition of door between garage and house: Appeared serviceable
Type of door between garage and house: Solid core, Metal
Condition of exterior entry doors: Appeared serviceable
Exterior door material: Metal
Condition of garage vehicle door(s): Appeared serviceable
Type of garage vehicle door: Sectional
Number of vehicle doors: 1
Condition of automatic opener(s): Appeared serviceable
Mechanical auto-reverse operable (reverses when meeting reasonable resistance during closing): Yes
Condition of garage floor: Appeared serviceable
Condition of garage interior: Appeared serviceable
Garage ventilation: Exists, Adequate
9) Safety, Repair/Replace -
Substandard shelving was installed above center of garage. This is a potential safety hazard due to the risk of collapse, especially if heavy items are stored on the shelves. Recommend that a qualified person remove shelving, or repair or modify as necessary.
10) Safety, Repair/Maintain -
One or more garage vehicle doors had an automatic opener installed, and the manual lock mechanism on the door hadn't been permanently disabled. The automatic opener can be damaged, or injury can occur if the automatic door opener is operated with the manual lock engaged. A qualified person should disable or remove the lock mechanism per standard building practices.
11) Safety, Comment
Hookups for a clothes washer and/or dryer were installed in the garage. The client should be aware that any source of spark or flame, including motors and circuitry in laundry equipment, are a potential source for spark (or flame with a gas-fired clothes dryer). Such equipment should be elevated at least 18 inches off the floor because vapors from gasoline or other flammable fluids that are heavier than air may be present. Dryer duct vents into garage. Suggest qualified contractor evaluate and correct as necessary.
Garage Dryer Vent Duct
Limitations: The following items are not included in this inspection: generator systems, transfer switches, surge suppressors, inaccessible or concealed wiring; underground utilities and systems; low-voltage lighting or lighting on timers or sensors. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of grounding or bonding, if this system has an adequate capacity for the client's specific or anticipated needs, or if this system has any reserve capacity for additions or expansion. The inspector does not operate circuit breakers as part of the inspection, and does not install or change light bulbs. The inspector does not evaluate every wall switch or receptacle, but instead tests a representative number of them per various standards of practice. When furnishings, stored items or child-protective caps are present some receptacles are usually inaccessible and are not tested; these are excluded from this inspection. Receptacles that are not of standard 110 volt configuration, including 240-volt dryer receptacles, are not tested and are excluded. The functionality of, power source for and placement of smoke and carbon monoxide alarms is not determined as part of this inspection. Upon taking occupancy, proper operating and placement of smoke and carbon monoxide alarms should be verified and batteries should be changed. These devices have a limited lifespan and should be replaced every 10 years. The inspector attempts to locate and evaluate all main and sub-panels. However, panels are often concealed. If panels are found after the inspection, a qualified electrician should evaluate and repair if necessary. The inspector attempts to determine the overall electrical service size, but such estimates are not guaranteed because the overall capacity may be diminished by lesser-rated components in the system. Any repairs recommended should be made by a licensed electrician.
Electric service condition: Appeared serviceable
Primary service type: Underground
Service voltage (volts): Not determined (components inaccessible or obscured), Locked
Estimated service amperage: Not determined (components inaccessible or obscured), Locked
Service entrance conductor material: Not determined (components inaccessible or obscured), Locked
Main disconnect rating (amps): Not determined, Locked
System ground: Not determined, not readily apparent, Locked
Condition of main service panel: Not determined (inaccessible or obscured, or panel not opened), Not able to inspect - Had pad lock and there was no key available
Location of main service panel #A: Building exterior
Location of main disconnect: Not determined (inaccessible or obscured, or not readily apparent), Not able to access - Locked
Condition of branch circuit wiring: Outlets inspected were functional
Solid strand aluminum branch circuit wiring present: Not determined (inaccessible or obscured, or panels not opened)
Ground fault circuit interrupter (GFCI) protection present: Yes
Arc fault circuit interrupter (AFCI) protection present: Not determined, Not visible - Panel locked
Smoke alarms installed: Yes, but not tested
Carbon monoxide alarms installed: No, recommend install
Smoke alarm power source(s): Battery
12) Safety, Repair/Maintain
Based on the age of this structure and the appearance of existing smoke alarms, the alarms may have been installed more than 10 years ago. According to National Fire Protection Association
, aging smoke alarms don't operate as efficiently and often are the source for nuisance alarms. Older smoke alarms are estimated to have a 30% probability of failure within the first 10 years. Newer smoke alarms do better, but should be replaced after 10 years. Unless you know that the smoke alarms are new, replacing them when moving into a new residence is also recommended by NFPA.
13) Safety, Repair/Maintain -
No permanently installed carbon monoxide alarms were found. This is a potential safety hazard. Recommend installing approved CO alarms outside of each separate sleeping area in the immediate vicinity of the bedrooms on each level and in accordance with the manufacturer's recommendations.
14) Evaluate, Comment
The inspector was unable to open and evaluate panel #A because panel was locked. This panel is excluded from this inspection. Recommend that lock be removed so panel can be opened and fully evaluation.
Main Electrical Locked
Plumbing / Fuel Systems
Limitations: The following items are not included in this inspection: private/shared wells and related equipment; private sewage disposal systems; hot tubs or spas; main, side and lateral sewer lines; gray water systems; pressure boosting systems; trap primers; incinerating or composting toilets; fire suppression systems; water softeners, conditioners or filtering systems; plumbing components concealed within the foundation or building structure, or in inaccessible areas such as below tubs; underground utilities and systems; overflow drains for tubs and sinks; backflow prevention devices. Any comments made regarding these items are as a courtesy only. Note that the inspector does not operate water supply or shut-off valves due to the possibility of valves leaking or breaking when operated. The inspector does not test for lead in the water supply, the water pipes or solder, does not determine if plumbing and fuel lines are adequately sized, and does not determine the existence or condition of underground or above-ground fuel tanks.
Condition of service and main line: Appeared serviceable
Water service: Public
Location of main water meter: By street, Front yard
Location of main water shut-off: Building exterior
Service pipe material: Copper
Condition of supply lines: Appeared serviceable
Supply pipe material: Copper
Condition of drain pipes: Appeared serviceable
Drain pipe material: Plastic
Condition of waste lines: Appeared serviceable
Waste pipe material: Plastic
Location(s) of plumbing clean-outs: Laundry room, Building exterior, Driveway
Vent pipe condition: Not determined (inaccessible, obscured, or water service off), Could not traverse roof
Vent pipe material: Not determined (inaccessible or obscured), No access, Concealed
Condition of fuel system: Appeared serviceable
Location of main fuel shut-off valve: At gas meter, At building exterior
15) Safety, Minor Defect
One or more hose bibs were missing backflow prevention devices. These devices reduce the likelihood of gray water entering the potable water supply. Recommend installing backflow prevention devices on all hose bibs where missing. They are available at most home improvement stores and are easily installed.
Limitations: Evaluation of and determining the adequacy or completeness of the following items are not included in this inspection: water recirculation pumps; solar water heating systems; Energy Smart or energy saver controls; catch pan drains. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on water heaters, does not determine if water heaters are appropriately sized, or perform any evaluations that require a pilot light to be lit or a shut-off valve to be operated.
Condition of water heater: Appeared serviceable, Near service life
Energy source: Natural gas
Estimated age: 10
Capacity (in gallons): 50
Temperature-pressure relief valve installed: Yes
Manufacturer: A.O. Smith
Model number: GVR 50 100
Serial number: A06J009895
Location of water heater: Garage
Hot water temperature tested: No
Condition of burners: Appeared serviceable
Condition of venting system: Appeared serviceable
Condition of combustion air supply: Appeared serviceable
16) Safety, Repair/Replace -
The temperature-pressure relief valve drain line was longer than 15 feet. This is a potential safety hazard due to the risk of explosion from restricted flow. A qualified plumber should repair per standard building practices.
17) Repair/Maintain -
Rumbling or gurgling noises were heard from the water heater. This can be caused by air in the tank, or by pockets of hot water in sediment. Recommend that a qualified person flush the tank. If necessary a qualified plumber should evaluate and repair or replace the water heater.
Heating, Ventilation and Air Condition (HVAC)
Limitations: The following items are not included in this inspection: humidifiers, dehumidifiers, electronic air filters; solar, coal or wood-fired heat systems; thermostat or temperature control accuracy and timed functions; heating components concealed within the building structure or in inaccessible areas; underground utilities and systems; safety devices and controls (due to automatic operation). Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on heating or cooling system components, does not determine if heating or cooling systems are appropriately sized, does not test coolant pressure, or perform any evaluations that require a pilot light to be lit, a shut-off valve to be operated, a circuit breaker to be turned "on" or a serviceman's or oil emergency switch to be operated. It is beyond the scope of this inspection to determine if furnace heat exchangers are intact and free of leaks. Condensation pans and drain lines may clog or leak at any time and should be monitored while in operation in the future. Where buildings contain furnishings or stored items, the inspector may not be able to verify that a heat source is present in all "liveable" rooms (e.g. bedrooms, kitchens and living/dining rooms).
General heating system type(s): Forced air, Furnace
General heating distribution type(s): Ducts and registers
Last service date of primary heat source: Unknown
Condition of forced air heating/(cooling) system: Appeared serviceable
Forced air heating system fuel type: Natural gas
Forced air heating system & cooling system manufacturer: Carrier
Forced air furnace model #: 58STX090-16
Forced air furnace serial number: 3405A31197
Location of forced air furnace: Attic
Forced air system capacity in BTUs or kilowatts: 68,000
Condition of furnace filters: Appeared serviceable
Condition of forced air ducts and registers: Appeared serviceable
Condition of cooling system: Appeared serviceable
Cooling system type: Electric
Location of air conditioning unit: Building exterior, west
Estimated age air conditioning unit: 11
Approximate tonnage: 3.5
Condition of cooling system: Appeared serviceable
Air conditioner model number: 38BRC042340
Air conditioner serial number: 3405E44284
Condition of controls: Appeared serviceable
18) Safety, Repair/Maintain, Evaluate -
The last service date of the gas forced air furnace appeared to be more than 1 year ago, or the inspector was unable to determine the last service date. Ask the property owner when it was last serviced. If unable to determine the last service date, or if this system was serviced more than 1 year ago, recommend that a qualified HVAC contractor inspect, clean, and service this system, and make repairs if necessary. For safety reasons, and because this system is fueled by gas, this servicing should be performed annually in the future. Any needed repairs noted in this report should be brought to the attention of the HVAC contractor when it's serviced.
Fireplaces, Stoves, Chimneys and Flues
Limitations: The following items are not included in this inspection: coal stoves, gas logs, chimney flues (except where visible). Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of drafting or sizing in fireplace and stove flues, and also does not determine if prefabricated or zero-clearance fireplaces are installed in accordance with the manufacturer's specifications. The inspector does not perform any evaluations that require a pilot light to be lit, and does not light fires. The inspector provides a basic visual examination of a chimney and any associated wood burning device. The National Fire Protection Association has stated that an in-depth Level 2 chimney inspection should be part of every sale or transfer of property with a wood-burning device. Such an inspection may reveal defects that are not apparent to the home inspector who is a generalist.
Condition of gas-fired fireplaces: Appeared serviceable
Gas fireplace type: Metal pre-fab fireplace
Fan or blower installed in gas-fired fireplace: No
19) Safety, Maintain, Evaluate -
Recommend that the client review all available documentation for gas-fired fireplaces and stoves. Depending on how they are operated (for routine heating versus ambiance), such appliances may need servicing annually or every few years. Consult with the property owner and/or a qualified specialist to determine if service is needed now. Any needed repairs noted in this report should be brought to the attention of the specialist when it's serviced.
The gas fireplace was not fully evaluated because the pilot light was off. The inspector only operates normal controls (e.g. on/off switch or thermostat) and does not light pilot lights or operate gas shut-off valves. Recommend that the client review all documentation for such gas appliances and familiarize themselves with the lighting procedure. If necessary, a qualified specialist should assist in lighting such appliances, and make any needed repairs.
Limitations: The following items are not included in this inspection: household appliances such as stoves, ovens, warming ovens, griddles, broilers, trash compactors, refrigerators, freezers, ice makers, hot water dispensers and water filters; appliance timers, clocks, cook functions, self and/or continuous cleaning operations, thermostat or temperature control accuracy, and lights. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of the remaining life of appliances, and does not determine the adequacy of operation of appliances. The inspector does not note appliance manufacturers, models or serial numbers and does not determine if appliances are subject to recalls. Areas and components behind and obscured by appliances are inaccessible and excluded from this inspection.
Permanently installed kitchen appliances present during inspection: Oven, Cooktop, Dishwasher, Refrigerator, Under-sink food disposal, Microwave oven
Condition of counters: Appeared serviceable
Condition of cabinets: Appeared serviceable
Condition of sinks and related plumbing: Appeared serviceable
Condition of under-sink food disposal: Required repair, replacement and/or evaluation
Condition of dishwasher: Beyond service life
Condition of range, cooktop or oven: Appeared serviceable, Near service life
Range, cooktop or oven type: Natural gas
Type of ventilation: Hood or built into microwave over range or cooktop
Condition of refrigerator: Near, at or beyond service life. It didn't appear to cool but was turned on with temperature on "colder" setting. Checked at the beginning and end of inspection (2 hours) and no change. Infra-red
Condition of built-in microwave oven: Appeared serviceable, Near, at or beyond service life, Rust showing inside
21) Repair/Replace, Evaluate
The dishwasher was leaking. Recommend that a qualified specialist evaluate and repair or replace as necessary.
Dishwasher Hole 1
Dishwasher Hole 2
The sink faucet was dripping in the "off" condition. Recommend that a qualified person repair as necessary.
Dripping Kitchen Sink
23) Repair/Maintain -
The dishwasher wasn't securely attached to the counter or cabinets. Fasteners were loose. Recommend that a qualified person install fasteners per standard building practices.
24) Repair/Maintain -
The dishwasher door springs malfunctioned. The door should not fall open quickly, and it should stop securely in a horizontal position. Recommend that a qualified person repair as necessary.
25) Comment -
The estimated useful life for most kitchen appliances is 10-15 years. One or more appliances (dishwasher, refrigerator, range, cooktop and/or microwave) appeared to be near, at or beyond their service life. Even if operable, recommend budgeting for replacements in the near future.
26) Comment -
Refrigerator shelving was loose.
The microwave oven didn't have a built-in turntable. Rust near light. At or near end of service life.
Bathrooms, Laundry and Sinks
Limitations: The following items are not included in this inspection: overflow drains for tubs and sinks; heated towel racks, saunas, steam generators, clothes washers, clothes dryers. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of washing machine drain lines, washing machine catch pan drain lines, or clothes dryer exhaust ducts. The inspector does not operate water supply or shut-off valves for sinks, toilets, bidets, clothes washers, etc. due to the possibility of valves leaking or breaking when operated. The inspector does not determine if shower pans or tub and shower enclosures are water tight, or determine the completeness or operability of any gas piping to laundry appliances.
Location #A: Full bath, Master bath, second floor
Location #B: Full bath, second floor
Location #C: Full bath, first floor
Condition of counters: Appeared serviceable
Condition of cabinets: Appeared serviceable, Required repair, replacement and/or evaluation (see comments below)
Condition of flooring: Appeared serviceable
Condition of sinks and related plumbing: Appeared serviceable
Condition of toilets: Appeared serviceable
Condition of bathtubs and related plumbing: Appeared serviceable (see comment below)
Condition of shower(s) and related plumbing: Appeared serviceable
Condition of ventilation systems: Appeared serviceable
Bathroom and laundry ventilation type: Central exhaust fan, with wye ducts
Gas supply for laundry equipment present: Yes
240 volt receptacle for laundry equipment present: Yes
28) Safety, Repair/Replace, Evaluate
The inspector was unable to verify that the glass used in one or more enclosure walls by the shower at location #A was approved safety glass. Glazing that is not approved safety glass located in areas subject to human impact is a potential safety hazard. Standard building practices require that approved safety glass be used in enclosures for bathtubs, showers, spas, saunas and steam rooms, and in windows where the bottom edge of the window is less than 60 inches above the drain inlet or standing surface. Wire-reinforced glass is not acceptable. Recommend that a qualified contractor evaluate further to determine if glazing is approved safety glass, and replace glass if necessary, and per standard building practices.
No Evidence of Tempered Glass
No Tempered Glass Picture 2
One or more cabinets, drawers and/or cabinet doors at location(s) #A and B were damaged, deteriorated or missing. Recommend that a qualified person repair or replace as necessary.
30) Repair/Maintain -
Cabinet door handles or drawer pulls were missing at location(s) #A, B and C. Where operation is difficult, recommend installing handles and/or pulls.
Gaps, no caulk, or substandard caulking were found between the bathtub and the floor at location #B. Water may penetrate these areas and cause damage. Recommend that a qualified person re-caulk or install caulking as necessary.
The shower at location #C drained slowly. Recommend clearing drain and/or that a qualified plumber repair if necessary.
Interior, Doors and Windows
Limitations: The following items are not included in this inspection: security, intercom and sound systems; communications wiring; central vacuum systems; elevators and stair lifts; cosmetic deficiencies such as nail-pops, scuff marks, dents, dings, blemishes or issues due to normal wear and tear in wall, floor and ceiling surfaces and coverings, or in equipment; deficiencies relating to interior decorating; low voltage and gas lighting systems. Any comments made regarding these items are as a courtesy only. Note that the inspector does not evaluate any areas or items which require moving stored items, furnishings, debris, equipment, floor coverings, insulation or similar materials. The inspector does not test for asbestos, lead, radon, mold, hazardous waste, urea formaldehyde urethane, or any other toxic substance. Some items such as window, drawer, cabinet door or closet door operability are tested on a sampled basis. The client should be aware that paint may obscure wall and ceiling defects, floor coverings may obscure floor defects, and furnishings may obscure wall, floor and floor covering defects. If furnishings were present during the inspection, recommend a full evaluation of walls, floors and ceilings that were previously obscured when possible. Determining the cause and/or source of odors is not within the scope of this inspection.
Condition of exterior entry doors: Appeared serviceable
Exterior door material: Fiberglass or vinyl
Condition of interior doors: Appeared serviceable
Condition of windows and skylights: Appeared serviceable
Type(s) of windows: Vinyl, Multi-pane, Sliding, Fixed
Condition of walls and ceilings: Appeared serviceable (see comments below)
Wall type or covering: Drywall
Ceiling type or covering: Drywall
Condition of flooring: Appeared serviceable
Condition of concrete slab floor(s): Appeared serviceable
Flooring type or covering: Carpet, Vinyl, linoleum or marmoleum, Laminate, Tile
Condition of stairs, handrails and guardrails: Appeared serviceable
33) Repair/Replace, Evaluate
This structure appears to have settled, or was leaning based on the presence of cracks in walls, ceilings or junctions between them, or door frames not being square. Although drywall cracking is fairly common in newer construction, recommend that a qualified contractor evaluate further.
Drywall Crack 1
Drywall Crack 3
Ceiling Drywall Crack 2
Some interior door hardware (locksets) were inoperable. Recommend that a qualified person repair or replace as necessary.
Master bathroom was not working. Bathroom #B (upstairs) does not have a lock as required per current building standards.
Faulty Bathroom Door Lock
No Bathroom Door Lock
35) Repair/Replace -
Carpeting in one or more areas was damaged or deteriorated. Recommend that a qualified contractor replace as necessary.
Lock mechanisms on one or more windows were inoperable. This can pose a security risk. Recommend that a qualified person repair as necessary.
Above kitchen sink.
Kitchen Window Lock Faluty
37) Minor Defect
Minor cracks, nail pops and/or blemishes were found in walls and/or ceilings in one or more areas. Cracks and nail pops are common, are often caused by lumber shrinkage or minor settlement, and can be more or less noticeable depending on changes in humidity. They did not appear to be a structural concern, but the client may wish to repair these for aesthetic reasons.
Drywall Crack 4
Drywall Nail Pops
Drywall Crack Stairwell
38) Comment -
Concrete slab floors were obscured by carpeting and/or flooring and couldn't be fully evaluated.
Like us on Facebook https://www.facebook.com/specquest/
Review us on Yelp https://www.yelp.com/biz/specquest-dixon
We love referrals!!
Thank-you for your business!