This report is the exclusive property of this inspection company and the client(s) listed in the report title. Use of this report by any unauthorized persons is prohibited.
Safe House Home Inspectors, LLCWebsite: http://www.safehouseinspector.com
Phone: (440) 497-0806
Inspector: Matt Ardo
Property Inspection Report
||270 east 327th
||Sunday, February 18, 2018
This report published on Monday, February 19, 2018 6:57:46 PM EST
How to Read this Report
This report is organized by the property's functional areas. Within each functional area, descriptive information is listed first and is shown in bold type. Items of concern follow descriptive information.
Concerns are shown and sorted according to these types:
|Safety||Poses a safety hazard|
|Major Defect||Correction likely involves a significant expense|
|Repair/Replace||Recommend repairing or replacing|
|Repair/Maintain||Recommend repair and/or maintenance|
|Minor Defect||Correction likely involves only a minor expense|
|Maintain||Recommend ongoing maintenance|
|Evaluate||Recommend evaluation by a specialist|
|Monitor||Recommend monitoring in the future|
|Comment||For your information|
Click here for a glossary of building construction terms.Contact your inspector If there are terms that you do not understand, or visit the glossary of construction terms at https://www.reporthost.com/glossary.asp
Present during inspection: Client
Weather conditions during inspection: Heavy snow, Windy
Temperature during inspection: Cold
Inspection fee: 350
Payment method: Credit card, Invoiced
Type of building: Single family
Buildings inspected: One house, One detached garage
Number of residential units inspected: 2
Age of main building: 1952
Source for main building age: Municipal records or property listing
Front of building faces: East
Main entrance faces: East
1) Safety, Comment
Structures built prior to the mid 1980s may contain lead and/or asbestos. Lead is commonly found in paint and in some plumbing components. The EPA does not recognize newer coats of paint as encapsulating older coats of lead-based paint. Asbestos is commonly found in various building materials such as insulation, siding, and/or floor and ceiling tiles. Laws were passed in 1978 to prohibit usage of lead and asbestos, but stocks of materials containing these substances remained in use for a number of years thereafter. Both lead and asbestos are known health hazards. Evaluating for the presence of lead and/or asbestos is beyond the scope of this inspection. Any mention of these materials in this report is made as a courtesy only, and meant to refer the client to a specialist. Consult with specialists as necessary, such as industrial hygienists, professional labs and/or abatement specialists for this type of evaluation. For information on lead, asbestos and other hazardous materials in homes, visit:http://www.reporthost.com/?EPAhttp://www.reporthost.com/?CPSChttp://www.reporthost.com/?CDC
Limitations: Unless specifically included in the inspection, the following items and any related equipment, controls, electric systems and/or plumbing systems are excluded from this inspection: detached buildings or structures; fences and gates; retaining walls; underground drainage systems, catch basins or concealed sump pumps; swimming pools and related safety equipment, spas, hot tubs or saunas; whether deck, balcony and/or stair membranes are watertight; trees, landscaping, properties of soil, soil stability, erosion and erosion control; ponds, water features, irrigation or yard sprinkler systems; sport courts, playground, recreation or leisure equipment; areas below the exterior structures with less than 3 feet of vertical clearance; invisible fencing; sea walls, docks and boathouses; retractable awnings. Any comments made regarding these items are as a courtesy only.
Site profile: Moderate slope
Condition of driveway: Appeared serviceable
Driveway material: Poured in place concrete
Condition of sidewalks and/or patios: Appeared serviceable
Sidewalk material: Poured in place concrete
Condition of decks, porches and/or balconies: Appeared serviceable
Deck, porch and/or balcony material: Plastic fiber
Condition of stairs, handrails and guardrails: Appeared serviceable
Exterior stair material: Plastic fiber
2) Safety, Repair/Replace -
Risers for stairs at one or more locations were higher than 7 3/4 inches and posed a fall or trip hazard. Risers should be 7 3/4 inches or shorter. At a minimum, be aware of this hazard, especially when guests who are not familiar with the stairs are present. Recommend that a qualified contractor repair per standard building practices.
3) Safety, Repair/Replace -
Handrails at one or more flights of stairs were missing. This is a potential fall hazard. Handrails should be installed at stairs with four or more risers or where stairs are greater than 30 inches high. Recommend that a qualified contractor install handrails where missing and per standard building practices.
4) Safety, Repair/Replace
Handrails at one or more flights of stairs were not graspable and posed a fall hazard. Handrails should be 1 1/4 - 2 inches in diameter if round, or 2 5/8 inches or less in width if flat. Recommend that a qualified person install graspable handrails or modify existing handrails per standard building practices.
5) Repair/Maintain, Monitor -
Significant amounts of standing water or evidence of past accumulated water were found at one or more locations in the yard or landscaped areas, and no drain was visible. If evidence of past water was found (e.g. silt accumulation or staining), monitor these areas in the future during periods of heavy rain. If standing water exists, recommend that a qualified person repair as necessary. For example, installing one or more drains, or grading soil.
6) Repair/Maintain -
The driveway sloped down towards the garage or house. A drain was installed to prevent water from reaching the garage or house, but it was substandard. Water may accumulate around or inside the garage or house, or under the house as a result. Recommend that a qualified person clear and/or repair drain(s) as necessary.
Exterior and Foundation
Limitations: The inspector performs a visual inspection of accessible components or systems at the exterior. Items excluded from this inspection include below-grade foundation walls and footings; foundations, exterior surfaces or components obscured by vegetation, stored items or debris; wall structures obscured by coverings such as siding or trim. Some items such as siding, trim, soffits, vents and windows are often high off the ground, and may be viewed using binoculars from the ground or from a ladder. This may limit a full evaluation. Regarding foundations, some amount of cracking is normal in concrete slabs and foundation walls due to shrinkage and drying. Note that the inspector does not determine the adequacy of seismic reinforcement.
Condition of foundation and footings: Appeared serviceable
Apparent foundation type: Finished basement
One or more holes or gaps were found in siding or trim. Vermin, insects or water may enter the structure. Recommend that a qualified person repair as necessary.
8) Repair/Maintain -
One or more minor cracks (1/8 inch or less) were found in the foundation. These didn't appear to be a structural concern, but recommend sealing them to prevent water infiltration and monitor them in the future. Numerous products exist to seal such cracks including hydraulic cement, non-shrinking grout, resilient caulks and epoxy sealants.
Limitations: Structural components such as joists and beams, and other components such as piping, wiring and/or ducting that are obscured by under-floor insulation are excluded from this inspection. The inspector does not determine if support posts, columns, beams, joists, studs, trusses, etc. are of adequate size, spanning or spacing.
The inspector does not guarantee or warrant that water will not accumulate in the crawl spaces in the future. Complete access to all crawl space areas during all seasons and during prolonged periods of all types of weather conditions (e.g. heavy rain, melting snow) would be needed to do so.
The inspector attempts to locate all crawl space access points and areas. Access points may be obscured or otherwise hidden by furnishings or stored items. In such cases, the client should ask the property owner where all access points are that are not described in this inspection, and have those areas inspected. Note that crawl space areas should be checked at least annually for water intrusion, plumbing leaks and pest activity.
Limitations: Structural components such as joists and beams, and other components such as piping, wiring and/or ducting that are obscured by under-floor insulation are also excluded from this inspection. Note that the inspector does not determine if support posts, columns, beams, joists, studs, trusses, etc. are of adequate size, spanning or spacing.
The inspector does not guarantee or warrant that water will not accumulate in the basement in the future. Access to the basement during all seasons and during prolonged periods of all types of weather conditions (e.g. heavy rain, melting snow) would be needed to do so. The inspector does not determine the adequacy of basement floor or stairwell drains, or determine if such drains are clear or clogged.
Note that all basement areas should be checked periodically for water intrusion, plumbing leaks and pest activity.
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; solar roofing components. Any comments made regarding these items are made as a courtesy only. Note that the inspector does not provide an estimate of remaining life on the roof surface material, nor guarantee that leaks have not occurred in the roof surface, skylights or roof penetrations in the past. Regarding roof leaks, only active leaks, visible evidence of possible sources of leaks, and evidence of past leaks observed during the inspection are reported on as part of this inspection. The inspector does not guarantee or warrant that leaks will not occur in the future. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high wind and rain, melting snow) would be needed to do so. Occupants should monitor the condition of roofing materials in the future. For older roofs, recommend that a professional inspect the roof surface, flashings, appurtenances, etc. annually and maintain/repair as might be required. If needed, the roofer should enter attic space(s). Regarding the roof drainage system, unless the inspection was conducted during and after prolonged periods of heavy rain, the inspector was unable to determine if gutters, downspouts and extensions perform adequately or are leak-free.
Roof inspection method: Traversed
Condition of roof surface material: Required repair, replacement and/or evaluation (see comments below)
Roof surface material: Asphalt or fiberglass composition shingles
Roof type: Gable
Apparent number of layers of roof surface material: Multiple
9) Repair/Replace, Evaluate
Flashings at the base of one or more chimneys were damaged. Leaks can occur as a result. This is a conducive condition for wood-destroying organisms. Recommend that a qualified contractor evaluate and repair as necessary.
Moss was growing on the roof. As a result, shingles can lift or be damaged. Leaks can result and/or the roof surface can fail prematurely. Efforts should be made to kill the moss during its growing season (wet months). Typically, zinc or phosphate-based chemicals are used for this and must be applied periodically. For information on various moss treatment products and their pros and cons, visit:http://www.reporthost.com/?MOSS
11) Comment -
This asphalt or fiberglass composition roof surface appeared to have two or more layers of shingles. Additional layers of composition shingles typically last only 80% of their rated life, and the shingle manufacturer's warranty may be voided. The client should be aware that all layers of roofing will need to be removed when this roof surface needs replacing.
Attic and Roof Structure
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; areas and components obscured by insulation. Any comments made regarding these items are made as a courtesy only. The inspector does not determine the adequacy of the attic ventilation system. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high/low temperatures, high/low humidity, high wind and rain, melting snow) would be needed to do so. The inspector is not a licensed engineer and does not determine the adequacy of roof structure components such as trusses, rafters or ceiling beams, or their spacing or sizing.
Attic inspection method: Traversed
Condition of insulation in attic (ceiling, skylight chase, etc.): Appeared serviceable
Ceiling insulation material: Fiberglass roll or batt
Approximate attic insulation R value (may vary in areas): R-13, Recommend more insulation.
Vapor retarder: None
Condition of roof ventilation: Appeared serviceable
Roof ventilation type: Ridge vent(s), Gable end vents, Open soffit vents
12) Repair/Replace -
The ceiling insulation installed in the attic was substandard and appeared to have an R rating that's significantly less than current standards (R-38). Heating and cooling costs will likely be higher due to poor energy efficiency. Recommend that a qualified contractor install insulation for better energy efficiency and per standard building practices.
13) Repair/Replace -
One or more exhaust ducts (e.g. bathroom fan, clothes dryer) in the attic were not insulated. This can result in moisture forming inside the duct or "sweating" on the outside of the duct depending on the surrounding air temperature and the exhaust air temperature. Recommend that a qualified person install insulation on exhaust ducts per standard building practices (typically R-4 rating), or replace uninsulated ducts with insulated ducts.
One or more attic access hatches or doors were not insulated, or had substandard insulation. Recommend installing insulation as necessary and per current standards at hatches or doors for better energy efficiency. For more information, visit:http://www.reporthost.com/?ATTACC
One or more attic access hatches or doors were not insulated, or had substandard insulation. Weatherstripping was also missing or substandard. Recommend installing weatherstripping and insulation per current standards at hatches or doors for better energy efficiency. For more information, visit:http://www.reporthost.com/?ATTACC
16) Repair/Maintain -
One or more attic or roof vent screens were missing, deteriorated or substandard. Recommend that a qualified person replace or repair screens as necessary to prevent birds or vermin from entering the attic.
Garage or Carport
Limitations: The inspector cannot reasonably determine the integrity of all elements of limited fire resistance at residential construction or verify firewall ratings at multi unit construction. Requirements for ventilation in garages vary between municipalities.
Limitations: The following items are not included in this inspection: generator systems, transfer switches, surge suppressors, inaccessible or concealed wiring; underground utilities and systems; low-voltage lighting or lighting on timers or sensors. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of grounding or bonding, if this system has an adequate capacity for the client's specific or anticipated needs, or if this system has any reserve capacity for additions or expansion. The inspector does not operate circuit breakers as part of the inspection, and does not install or change light bulbs. The inspector does not evaluate every wall switch or receptacle, but instead tests a representative number of them per various standards of practice. When furnishings, stored items or child-protective caps are present some receptacles are usually inaccessible and are not tested; these are excluded from this inspection. Receptacles that are not of standard 110 volt configuration, including 240-volt dryer receptacles, are not tested and are excluded. The functionality of, power source for and placement of smoke and carbon monoxide alarms is not determined as part of this inspection. Upon taking occupancy, proper operating and placement of smoke and carbon monoxide alarms should be verified and batteries should be changed. These devices have a limited lifespan and should be replaced every 10 years. The inspector attempts to locate and evaluate all main and sub-panels. However, panels are often concealed. If panels are found after the inspection, a qualified electrician should evaluate and repair if necessary. The inspector attempts to determine the overall electrical service size, but such estimates are not guaranteed because the overall capacity may be diminished by lesser-rated components in the system. Any repairs recommended should be made by a licensed electrician.
Electric service condition: Appeared serviceable
Primary service type: Overhead
Number of service conductors: 2
Service voltage (volts): 120-240
Estimated service amperage: 100
Primary service overload protection type: Circuit breakers
Main disconnect rating (amps): 100
System ground: Ground rod(s) in soil, Cold water supply pipes
Condition of main service panel: Appeared serviceable
Condition of sub-panel(s): Appeared serviceable
Location of main service panel #A: Basement
Location of main disconnect: Breaker at top of main service panel
Condition of branch circuit wiring: Serviceable
Branch circuit wiring type: non-metallic sheathed, knob and tube
Solid strand aluminum branch circuit wiring present: None visible
Ground fault circuit interrupter (GFCI) protection present: Yes
Smoke alarms installed: Yes, but not tested
Carbon monoxide alarms installed: Yes, but not tested
17) Safety, Repair/Maintain
One or more cover plates for switches, receptacles or junction boxes were missing or broken. These plates are intended to contain fire and prevent electric shock from occurring due to exposed wires. Recommend that a qualified person install cover plates where necessary.
18) Safety, Repair/Maintain
Based on the age of this structure and the appearance of existing smoke alarms, the alarms may have been installed more than 10 years ago. According to National Fire Protection Association
, aging smoke alarms don't operate as efficiently and often are the source for nuisance alarms. Older smoke alarms are estimated to have a 30% probability of failure within the first 10 years. Newer smoke alarms do better, but should be replaced after 10 years. Unless you know that the smoke alarms are new, replacing them when moving into a new residence is also recommended by NFPA. For more information, visit:http://www.reporthost.com/?SMKALRMLS
19) Safety, Evaluate -
Branch circuit wiring installed in buildings built prior to the mid 1980s is typically rated for a maximum temperature of only 60 degrees Celsius. This includes non-metallic sheathed (Romex) wiring, and both BX and AC metal-clad flexible wiring. Knob and tube wiring, typically installed in homes built prior to 1950, may be rated for even lower maximum temperatures. Newer electric fixtures including lighting and fans typically require wiring rated for 90 degrees Celsius. Connecting newer fixtures to older, 60-degree-rated wiring is a potential fire hazard. Repairs for such conditions may involve replacing the last few feet of wiring to newer fixtures with new 90-degree-rated wire, and installing a junction box to join the old and new wiring.
It is beyond the scope of this inspection to determine if such incompatible components are installed, or to determine the extent to which they're installed. Based on the age of this building, the client should be aware of this safety hazard, both for existing fixtures and when planning to upgrade with newer fixtures. Consult with a qualified electrician for repairs as necessary.
20) Safety, Evaluate -
Few receptacles were installed in one or more areas by modern standards. This can result in "octopus" wiring with extension cords, which is a fire hazard. Consult with a qualified electrician about upgrading circuits with additional receptacles per standard building practices.
21) Safety, Evaluate -
Few receptacles were installed in one or more areas by modern standards. This can result in "octopus" wiring with extension cords, which is a fire hazard. Also, 2-slot receptacles rather than 3-slot, grounded receptacles were installed in one or more areas. These do not have an equipment ground and are considered to be unsafe by today's standards. Appliances that require a ground should not be used with 2-slot receptacles. Examples of such appliances include computers and related hardware, refrigerators, freezers, portable air conditioners, clothes washers, aquarium pumps, and electrically operated gardening tools. The client should be aware of this limitation when planning use for various rooms, such as an office. Upgrading to grounded receptacles typically requires installing new wiring from the main service panel or sub-panel to the receptacle(s), in addition to replacing the receptacle(s). Consult with a qualified electrician about upgrading circuits with additional receptacles and 3-wire, grounded receptacles per standard building practices.
22) Repair/Maintain, Evaluate -
The legend for circuit breakers or fuses in panel(s) #A was missing, incomplete, illegible or confusing. This is a potential shock or fire hazard in the event of an emergency when power needs to be turned off. Recommend correcting the legend so it's accurate, complete and legible. Evaluation by a qualified electrician may be necessary.
Plumbing / Fuel Systems
Limitations: The following items are not included in this inspection: private/shared wells and related equipment; private sewage disposal systems; hot tubs or spas; main, side and lateral sewer lines; gray water systems; pressure boosting systems; trap primers; incinerating or composting toilets; fire suppression systems; water softeners, conditioners or filtering systems; plumbing components concealed within the foundation or building structure, or in inaccessible areas such as below tubs; underground utilities and systems; overflow drains for tubs and sinks; backflow prevention devices. Any comments made regarding these items are as a courtesy only. Note that the inspector does not operate water supply or shut-off valves due to the possibility of valves leaking or breaking when operated. The inspector does not test for lead in the water supply, the water pipes or solder, does not determine if plumbing and fuel lines are adequately sized, and does not determine the existence or condition of underground or above-ground fuel tanks.
Condition of service and main line: Appeared serviceable
Water service: Public
Location of main water shut-off: Basement
Condition of supply lines: Appeared serviceable
Supply pipe material: PEX plastic
Condition of drain pipes: Appeared serviceable
Drain pipe material: Galvanized steel
Condition of waste lines: Appeared serviceable
Waste pipe material: Cast iron
Vent pipe condition: Appeared serviceable
Vent pipe material: Cast iron
Sump pump installed: Yes
Condition of sump pump: Appeared serviceable
Condition of fuel system: Appeared serviceable
Location of main fuel shut-off valve: At gas meter
23) Safety, Comment
Copper water supply pipes were installed. Copper pipes installed prior to the late 1980s may be joined with solder that contains lead, which is a known health hazard especially for children. Laws were passed in 1985 prohibiting the use of lead in solder, but prior to that solder normally contained approximately 50% lead. The client should be aware of this, especially if children will be using this water supply system. Note that the inspector does not test for toxic materials such as lead. The client should consider having a qualified lab test for lead, and if necessary take steps to reduce or remove lead from the water supply. Various solutions include:
- Flush water taps or faucets. Do not drink water that has been sitting in the plumbing lines for more than 6 hours
- Install appropriate filters at points of use
- Use only cold water for cooking and drinking, as hot water dissolves lead more quickly than cold water
- Use bottled or distilled water
- Treat well water to make it less corrosive
- Have a qualified plumber replace supply pipes and/or plumbing components as necessary
For more information visit:http://www.reporthost.com/?LEADDWhttp://www.reporthost.com/?LEAD
This home was winterized. Typically this means the following:
- The water supply has been turned off at the meter or main shut-off valve
- The water supply to fixtures such as sinks, toilets, tubs and showers have been turned off at local shut-off valves
- Sink drain traps and toilet bowls have been filled with anti-freeze
- The water and power or fuel supplies to the water heater have been turned off
"De-winterizing" a home is not part of a home inspection. The inspector does not operate shut-off valves, meter valves, circuit breakers, or light pilot lights. This significantly limits the ability of the inspector to evaluate various systems and components such as plumbing fixtures, supply/drain/waste/vent lines and the water heater. They are excluded from this inspection. Recommend when the home has been completely de-winterized that a qualified person fully evaluate them.
25) Comment -
A sump pump was installed in the basement. These are specialty systems and only a limited evaluation was performed as part of this inspection. The inspector does not determine the adequacy of sump pumps and their associated drainage systems. The presence of a sump pump may indicate that water routinely accumulates below or inside the structure. Recommend asking the property owner how often the sump pump operates and for how long at different times of the year. The client should be aware that the service life of most sump pumps is 5-7 years, and that the pump may need replacing soon depending on its age and how often it operates.
26) Comment -
The gas meter was in contact with or too close to the soil below and is likely to rust as a result. Gas meters should be located 10 inches or more above the soil below. Soil should be graded or removed as necessary.
Limitations: Evaluation of and determining the adequacy or completeness of the following items are not included in this inspection: water recirculation pumps; solar water heating systems; Energy Smart or energy saver controls; catch pan drains. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on water heaters, does not determine if water heaters are appropriately sized, or perform any evaluations that require a pilot light to be lit or a shut-off valve to be operated.
Heating, Ventilation and Air Condition (HVAC)
Limitations: The following items are not included in this inspection: humidifiers, dehumidifiers, electronic air filters; solar, coal or wood-fired heat systems; thermostat or temperature control accuracy and timed functions; heating components concealed within the building structure or in inaccessible areas; underground utilities and systems; safety devices and controls (due to automatic operation). Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on heating or cooling system components, does not determine if heating or cooling systems are appropriately sized, does not test coolant pressure, or perform any evaluations that require a pilot light to be lit, a shut-off valve to be operated, a circuit breaker to be turned "on" or a serviceman's or oil emergency switch to be operated. It is beyond the scope of this inspection to determine if furnace heat exchangers are intact and free of leaks. Condensation pans and drain lines may clog or leak at any time and should be monitored while in operation in the future. Where buildings contain furnishings or stored items, the inspector may not be able to verify that a heat source is present in all "liveable" rooms (e.g. bedrooms, kitchens and living/dining rooms).
General heating system type(s): Forced air, Furnace
General heating distribution type(s): Ducts and registers
Last service date of primary heat source: 12/21/99
Source for last service date of primary heat source: Label
Condition of forced air heating/(cooling) system: Appeared serviceable
Forced air heating system fuel type: Natural gas
Location of forced air furnace: Basement
Forced air system capacity in BTUs or kilowatts: 80000
Condition of furnace filters: Required replacement
Location for forced air filter(s): At base of air handler
Condition of forced air ducts and registers: Appeared serviceable
Condition of cooling system and/or heat pump: Appeared serviceable
Cooling system and/or heat pump fuel type: Electric
Location of heat pump or air conditioning unit: east
Type: Packaged unit
Condition of controls: Appeared serviceable
27) Safety, Evaluate -
Because of the age and/or condition of the forced air furnace, recommend that a qualified HVAC contractor inspect the heat exchanger and perform a carbon monoxide test when it's serviced. Note that these tests are beyond the scope of a standard home inspection.
28) Major Defect, Comment -
The estimated useful life for most forced air furnaces is 15-20 years. This furnace appeared to be near and/or 12 this age and/or its useful lifespan and may need replacing or significant repairs at any time. Recommend budgeting for a replacement in the near future.
One or more sections of flex duct used for heating or cooling were sagging or had substandard support. Energy efficiency can be reduced due to restricted flow. Manufacturers typically recommend that flex duct be supported with the following guidelines:
- Ducts should not sag more than 1/2 inch every foot between supports
- Support straps should be spaced no farther apart than 5 feet
- Support straps should be soft, webbed nylon and at least 1 1/2 inches wide
Recommend that a qualified person repair per the manufacturer's specifications.
Fireplaces, Stoves, Chimneys and Flues
Limitations: The following items are not included in this inspection: coal stoves, gas logs, chimney flues (except where visible). Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of drafting or sizing in fireplace and stove flues, and also does not determine if prefabricated or zero-clearance fireplaces are installed in accordance with the manufacturer's specifications. The inspector does not perform any evaluations that require a pilot light to be lit, and does not light fires. The inspector provides a basic visual examination of a chimney and any associated wood burning device. The National Fire Protection Association has stated that an in-depth Level 2 chimney inspection should be part of every sale or transfer of property with a wood-burning device. Such an inspection may reveal defects that are not apparent to the home inspector who is a generalist.
Condition of gas-fired fireplaces or stoves: Appeared serviceable
Gas fireplace or stove type: Metal pre-fab fireplace
Condition of chimneys and flues: Appeared serviceable, Not determined
Gas-fired flue type: Not determined (obscured or inaccessible)
One or more masonry chimney crowns were missing. Crowns are meant to keep water off of the chimney structure and prevent damage from freeze-thaw cycles. Chimney crowns are commonly constructed by mounding concrete or mortar on the top chimney surface, however this is substandard. A properly constructed chimney crown should:
- Be constructed using either precast concrete slabs, cast-in-place steel reinforced concrete, solid stone, or metal
- Be sloped down from the flue a minimum of 3 inches of fall per foot of run
- Extend a minimum of 2 1/2 inches beyond the face of the chimney on all sides
- Not directly contact the flue liner (if installed), with the gap filled with flexible caulk
- Have flashing installed between the bottom of the crown and the top of the brick chimney
Recommend that a qualified contractor repair or replace crowns as necessary, and per standard building practices.
31) Repair/Maintain -
Mortar at the brick chimney was deteriorated (e.g. loose, missing, cracked). As a result, water is likely to infiltrate the chimney structure and cause further damage. Recommend that a qualified contractor repair as necessary. For example, by repointing the mortar.
32) Evaluate -
The gas fireplace or stove was not fully evaluated because the pilot light was off or a lighting procedure was required. The inspector only operates normal controls (e.g. on/off switch or thermostat) and does not light pilot lights or operate gas shut-off valves. Recommend that the client review all documentation for such gas appliances and familiarize themselves with the lighting procedure. If necessary, a qualified specialist should assist in lighting such appliances, and make any needed repairs.
Limitations: The following items are not included in this inspection: household appliances such as stoves, ovens, cook tops, ranges, warming ovens, griddles, broilers, dishwashers, trash compactors, refrigerators, freezers, ice makers, hot water dispensers and water filters; appliance timers, clocks, cook functions, self and/or continuous cleaning operations, thermostat or temperature control accuracy, and lights. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of the remaining life of appliances, and does not determine the adequacy of operation of appliances. The inspector does not note appliance manufacturers, models or serial numbers and does not determine if appliances are subject to recalls. Areas and components behind and obscured by appliances are inaccessible and excluded from this inspection.
Condition of counters: Appeared serviceable
Condition of cabinets: Appeared serviceable
Condition of sinks and related plumbing: Required repair, replacement and/or evaluation (see comments below)
Condition of under-sink food disposal: Appeared serviceable
Condition of dishwasher: Appeared serviceable
33) Comment -
The sink had minor wear, blemishes or deterioration.
Bathrooms, Laundry and Sinks
Limitations: The following items are not included in this inspection: overflow drains for tubs and sinks; heated towel racks, saunas, steam generators, clothes washers, clothes dryers. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of washing machine drain lines, washing machine catch pan drain lines, or clothes dryer exhaust ducts. The inspector does not operate water supply or shut-off valves for sinks, toilets, bidets, clothes washers, etc. due to the possibility of valves leaking or breaking when operated. The inspector does not determine if shower pans or tub and shower enclosures are water tight, or determine the completeness or operability of any gas piping to laundry appliances.
Interior, Doors and Windows
Limitations: The following items are not included in this inspection: security, intercom and sound systems; communications wiring; central vacuum systems; elevators and stair lifts; cosmetic deficiencies such as nail-pops, scuff marks, dents, dings, blemishes or issues due to normal wear and tear in wall, floor and ceiling surfaces and coverings, or in equipment; deficiencies relating to interior decorating; low voltage and gas lighting systems. Any comments made regarding these items are as a courtesy only. Note that the inspector does not evaluate any areas or items which require moving stored items, furnishings, debris, equipment, floor coverings, insulation or similar materials. The inspector does not test for asbestos, lead, radon, mold, hazardous waste, urea formaldehyde urethane, or any other toxic substance. Some items such as window, drawer, cabinet door or closet door operability are tested on a sampled basis. The client should be aware that paint may obscure wall and ceiling defects, floor coverings may obscure floor defects, and furnishings may obscure wall, floor and floor covering defects. If furnishings were present during the inspection, recommend a full evaluation of walls, floors and ceilings that were previously obscured when possible. Carpeting and flooring, when installed over concrete slabs, may conceal moisture. If dampness wicks through a slab and is hidden by floor coverings that moisture can result in unhygienic conditions, odors or problems that will only be discovered when/if the flooring is removed. Determining the cause and/or source of odors is not within the scope of this inspection.
Condition of exterior entry doors: Appeared serviceable
Exterior door material: Wood
Condition of walls and ceilings: Appeared serviceable
Wall type or covering: Plaster
Ceiling type or covering: Plaster
Condition of flooring: Appeared serviceable
Flooring type or covering: Carpet, Vinyl, linoleum or marmoleum, Wood or wood products
Condition of stairs, handrails and guardrails: Appeared serviceable
34) Repair/Replace -
Vinyl floor tiles were installed in one or more "wet" areas (e.g. kitchen, mud room, bathroom, laundry room). Spilled water can penetrate seams and damage the sub-floor. Recommend that a qualified contractor install continuous waterproof flooring in wet areas as necessary.
35) Minor Defect
Minor cracks, nail pops and/or blemishes were found in walls and/or ceilings in one or more areas. Cracks and nail pops are common, are often caused by lumber shrinkage or minor settlement, and can be more or less noticeable depending on changes in humidity. They did not appear to be a structural concern, but the client may wish to repair these for aesthetic reasons. For recurring cracks, consider using an elastic crack covering product:http://www.reporthost.com/?ECC
Cracks in rear bedroom wall
36) Maintain -
Carpeting in one or more areas was significantly stained or soiled. Recommend having carpeting professionally cleaned as necessary.
37) Comment -
One or more exterior doors had minor damage and/or deterioration. Although serviceable, the client may wish to repair or replace such doors for appearances' sake.
38) Comment -
One or more hinged exterior doors had no deadbolt lock installed and relied solely on the entry lockset for security. Recommend installing locksets on exterior doors where missing for added security.
Wood Destroying Organism Findings
Limitations: This report only includes findings from accessible and visible areas on the day of the inspection. In addition to the inaccessible areas documented in this report, examples of other inaccessible areas include: sub areas less than 18 inches in height; attic areas less than 5 feet in height, areas blocked by ducts, pipes or insulation; areas where locks or permanently attached covers prevent access; areas where insulation would be damaged if traversed; areas obscured by vegetation. All inaccessible areas are subject to infestation or damage from wood-destroying organisms. The inspector does not move furnishings, stored items, debris, floor or wall coverings, insulation, or other materials as part of the inspection, nor perform destructive testing. Wood-destroying organisms may infest, re-infest or become active at any time. No warranty is provided as part of this inspection.
Your default report footer here...