WI State Certification #: 2598-106 InterNACHI Member # NACHI13032117
Property Inspection Report
1234 Any Street Rhinelander, WI 54501
Monday, March 11, 2013
This report published on Friday, October 12, 2018 5:16:52 PM CDT
This report is the exclusive property of this inspection company and the client(s) listed in the report title. Use of this report by any unauthorized persons is prohibited.
How to Read this Report
This report is organized by the property's functional areas. Within each functional area, descriptive information is listed first and is shown in bold type. Items of concern follow descriptive information.
Concerns are shown and sorted according to these types:
Poses a safety hazard
Recommend repairing or replacing
Recommend repair and/or maintenance
Correction likely involves only a minor expense
Recommend ongoing maintenance
Recommend evaluation by a specialist
Recommend monitoring in the future
For your information
Click here for a glossary of building construction terms.Contact your inspector If there are terms that you do not understand, or visit the glossary of construction terms at https://www.reporthost.com/glossary.asp
Client present for discussion at end of inspection: No
Weather conditions during inspection: Dry (no rain)Cloudy
Temperature during inspection: Cold
Inspection fee: $295
Payment method: Invoiced
Type of building: Single family
Buildings inspected: One house attached garage
Number of residential units inspected: 1
Age of main building: 2004
Source for main building age: Realtor
Front of building faces: Southwest
Main entrance faces: Southwest
Occupied: Yes, Furniture or stored items were present
1) Some areas and items at this property were obscured by furnishings, stored items or debris. This often includes but is not limited to walls, floors, windows, inside and under cabinets, under sinks, on counter tops, in closets, behind window coverings, under rugs or carpets, and under or behind furniture. Areas around the exterior, under the structure, in the garage and in the attic may also be obscured by stored items. The inspector in general does not move personal belongings, furnishings, carpets or appliances. When furnishings, stored items or debris are present, all areas or items that are obscured, concealed or not readily accessible are excluded from the inspection. The client should be aware that when furnishings, stored items or debris are eventually moved, damage or problems that were not noted during the inspection may be found.
Limitations: Unless specifically included in the inspection, the following items and any related equipment, controls, electric systems and/or plumbing systems are excluded from this inspection: detached buildings or structures; fences and gates; retaining walls; underground drainage systems, catch basins or concealed sump pumps; swimming pools and related safety equipment, spas, hot tubs or saunas; whether deck, balcony and/or stair membranes are watertight; trees, landscaping, properties of soil, soil stability, erosion and erosion control; ponds, water features, irrigation or yard sprinkler systems; sport courts, playground, recreation or leisure equipment; areas below the exterior structures with less than 3 feet of vertical clearance; invisible fencing; sea walls, docks and boathouses; retractable awnings. Any comments made regarding these items are as a courtesy only.
Site profile: Level, Minor slope, Moderate slope
Condition of driveway: Covered with snow
Driveway material: Gravel
Condition of deck, patio and/or porch covers: Appeared serviceable
Deck, patio, porch cover material and type: Open, Covered (Refer to Roof section)
Condition of decks, porches and/or balconies: Appeared serviceable
Condition of stairs, handrails and guardrails: Appeared serviceable, Required repairs, replacement and/or evaluation (see comments below)Section of guardrail missing
2) Guardrails at one or more locations with drop-offs higher than 30 inches were missing. This poses a fall hazard. Guardrails should be installed where walking surfaces are more than 30 inches above the surrounding grade or surfaces below. Recommend installIng guardrails where missing and per standard building practices.
3) Guardrails at one or more locations with drop-offs higher than 30 inches had gaps that were too large. This poses a safety hazard for children (e.g. falling, getting stuck in railing). Guardrails should not have gaps or voids that allow passage of a sphere equal to or greater than 4 inches in diameter, or 6 inches in diameter at triangular spaces between stair edges and guardrails. Recommend repair or replace guardrails per standard building practices.
Limitations: The inspector performs a visual inspection of accessible components or systems at the exterior. Items excluded from this inspection include below-grade foundation walls and footings; foundations, exterior surfaces or components obscured by vegetation, stored items or debris; wall structures obscured by coverings such as siding or trim. Some items such as siding, trim, soffits, vents and windows are often high off the ground, and may be viewed using binoculars from the ground or from a ladder. This may limit a full evaluation. Regarding foundations, some amount of cracking is normal in concrete slabs and foundation walls due to shrinkage and drying. Note that the inspector does not determine the adequacy of seismic reinforcement.
Condition of wall exterior covering: Appeared serviceable
Apparent wall structure: Wood frame
Wall covering: Vinyl
Condition of foundation and footings: Appeared serviceable
Apparent foundation type: Daylight basement
Foundation/stem wall material: Poured in place concrete, Concrete block
Footing material (under foundation stem wall): Not determined (inaccessible or obscured)
Limitations: Structural components such as joists and beams, and other components such as piping, wiring and/or ducting that are obscured by under-floor insulation are also excluded from this inspection. Note that the inspector does not determine if support posts, columns, beams, joists, studs, trusses, etc. are of adequate size, spanning or spacing.
The inspector does not guarantee or warrant that water will not accumulate in the basement in the future. Access to the basement during all seasons and during prolonged periods of all types of weather conditions (e.g. heavy rain, melting snow) would be needed to do so. The inspector does not determine the adequacy of basement floor or stairwell drains, or determine if such drains are clear or clogged.
Note that all basement areas should be checked periodically for water intrusion, plumbing leaks and pest activity.
Condition of exterior entry doors: Appeared serviceable
Exterior door material: Sliding glass
Condition of floor substructure above crawl space: Appeared serviceable
Pier or support post material: Steel
Beam material: Steel
Floor structure: Wood trusses
Condition of insulation underneath floor above: Appeared serviceable - a few sill boxes are not Insulated
Insulation material underneath floor above: Fiberglass roll or batt
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; solar roofing components. Any comments made regarding these items are made as a courtesy only. Note that the inspector does not provide an estimate of remaining life on the roof surface material, nor guarantee that leaks have not occurred in the roof surface, skylights or roof penetrations in the past. Regarding roof leaks, only active leaks, visible evidence of possible sources of leaks, and evidence of past leaks observed during the inspection are reported on as part of this inspection. The inspector does not guarantee or warrant that leaks will not occur in the future. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high wind and rain, melting snow) would be needed to do so. Regarding the roof drainage system, unless the inspection was conducted during and after prolonged periods of heavy rain, the inspector was unable to determine if gutters, downspouts and extensions performed adequately or were leak-free.
Roof inspection method: Viewed from ground - Mostly covered with snow
Condition of roof surface material: Appeared serviceable - what's visible Iooks good
Roof surface material: Asphalt or fiberglass composition shingles
Roof type: Gable
Condition of exposed flashings: no visible Flashings to report on
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; areas and components obscured by insulation. Any comments made regarding these items are made as a courtesy only. The inspector does not determine the adequacy of the attic ventilation system. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high/low temperatures, high/low humidity, high wind and rain, melting snow) would be needed to do so. The inspector is not a licensed engineer and does not determine the adequacy of roof structure components such as trusses, rafters or ceiling beams, or their spacing or sizing.
Attic inspection method: Viewed from hatch(es), small access in garage on fire wall - access in master bedroom closet not accessible due to shelves
Condition of roof structure: Appeared serviceable
Roof structure type: Trusses
Ceiling structure: Trusses
Condition of insulation in attic (ceiling, skylight chase, etc.): Appeared serviceable
Ceiling insulation material: Fiberglass loose fill, Cellulose loose fill
Approximate attic insulation R value (may vary in areas): R-30 to R-38 estimate
Vapor retarder: Installed
Condition of roof ventilation: Appeared serviceable
Limitations: The inspector does not determine the adequacy of firewall ratings. Requirements for ventilation in garages vary between municipalities.
Condition of door between garage and house: Appeared serviceable
Type of door between garage and house: Metal, With visible fire-resistance rating
Condition of garage vehicle door(s): Appeared serviceable
Type of garage vehicle door: Sectional
Number of vehicle doors: 1
Condition of automatic opener(s): Appeared serviceable
Mechanical auto-reverse operable (reverses when meeting reasonable resistance during closing): Yes
Condition of garage floor: Appeared serviceable
Condition of garage interior: Appeared serviceable
Garage ventilation: Exists, Adequate
7) One or more gaps, holes, or seams were found in the attached garage walls. Current standard building practices call for wooden-framed ceilings and walls that divide the house and garage to provide limited fire-resistance rating to prevent the spread of fire from the garage to the house. Recommend that a qualified person repair per standard building practices. For example, by patching openings or holes, firestopping holes or gaps with fire-resistant caulking, and/or installing fire-resistant wall covering (e.g. Type X drywall). For more information, visit: http://www.reporthost.com/?AGFR
Joints on drywall firewall should be taped/mudded with at least one coat to help prevent fire spreading
Limitations: The following items are not included in this inspection: generator systems, transfer switches, surge suppressors, inaccessible or concealed wiring; underground utilities and systems; low-voltage lighting or lighting on timers or sensors. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of grounding or bonding, if this system has an adequate capacity for the client's specific or anticipated needs, or if this system has any reserve capacity for additions or expansion. The inspector does not operate circuit breakers as part of the inspection, and does not install or change light bulbs. The inspector does not evaluate every wall switch or receptacle, but instead tests a representative number of them per various standards of practice. When furnishings, stored items or child-protective caps are present some receptacles are usually inaccessible and are not tested; these are excluded from this inspection. Receptacles that are not of standard 110 volt configuration, including 240-volt dryer receptacles, are not tested and are excluded. The functionality of, power source for and placement of smoke and carbon monoxide alarms is not determined as part of this inspection. Upon taking occupancy, proper operating and placement of smoke and carbon monoxide alarms should be verified and batteries should be changed. These devices have a limited lifespan and should be replaced every 10 years. The inspector attempts to locate and evaluate all main and sub-panels. However, panels are often concealed. If panels are found after the inspection, a qualified electrician should evaluate and repair if necessary. The inspector attempts to determine the overall electrical service size, but such estimates are not guaranteed because the overall capacity may be diminished by lesser-rated components in the system.
Electric service condition: Appeared serviceable
Primary service type: Underground
Number of service conductors: 3
Service voltage (volts): 120-240
Estimated service amperage: 200
Primary service overload protection type: Circuit breakers
Service entrance conductor material: Stranded copper
Main disconnect rating (amps): 200
System ground: Not determined, not readily apparent
Condition of main service panel: Appeared serviceable
Smoke alarms installed: Yes - tested and inter-connected
Carbon monoxide alarms installed: No, recommend install
8) One or more circuit breakers in panel(s) #A were "double tapped," where two or more wires were installed in the breaker's lug. Most breakers are designed for only one wire to be connected. This is a safety hazard since the lug bolt can tighten securely against one wire but leave other(s) loose. Arcing, sparks and fires can result. Recommend that a qualified electrician repair as necessary. For more information, visit: http://www.reporthost.com/?DBLTAP
9) Neutral wires were doubled or bundled together under the same lug on the neutral bus bar in panel(s) #B. This is a potential safety hazard in the event that one of the circuits needs to be isolated during servicing. For one neutral to be disconnected, other neutrals from energized circuits sharing the same lug will be loosened. Power surges may result on the energized circuits and result in damage or fire. Also, multiple wires under the same lug may not be secure, resulting in loose wires, arcing, sparks and fire. Recommend that a qualified electrician repair per standard building practices. For more information, visit: http://www.reporthost.com/?DTNB
10) Non-metallic sheathed wiring was loose, unsupported, or inadequately supported at one or more locations. Such wiring should be trimmed to length if necessary and attached to runners or to solid backing with fasteners at intervals of 4 1/2 feet or less. Fasteners should be installed within 12 inches of all enclosures. Recommend that a qualified electrician repair per standard building practices.
11) One or more electric receptacles (outlets) had reverse-polarity wiring, where the hot and neutral wires were reversed. This is a shock hazard. Recommend that a qualified electrician repair as necessary. For more information, visit: http://www.reporthost.com/?RPR
outlet on island in kitchen
12) One or more cover plates for switches, receptacles (outlets) or junction boxes were missing or broken. These plates are intended to contain fire and prevent electric shock from occurring due to exposed wires. Recommend install cover plates where necessary. In the basement 2 or more outlets and several junction boxes
13) extra breakers and debri in bottom of main panel - recommend removing
Limitations: The following items are not included in this inspection: private/shared wells and related equipment; private sewage disposal systems; hot tubs or spas; main, side and lateral sewer lines; gray water systems; pressure boosting systems; trap primers; incinerating or composting toilets; fire suppression systems; water softeners, conditioners or filtering systems; plumbing components concealed within the foundation or building structure, or in inaccessible areas such as below tubs; underground utilities and systems; overflow drains for tubs and sinks; backflow prevention devices. Any comments made regarding these items are as a courtesy only. Note that the inspector does not operate water supply or shut-off valves due to the possibility of valves leaking or breaking when operated. The inspector does not test for lead in the water supply, the water pipes or solder, does not determine if plumbing and fuel lines are adequately sized, and does not determine the existence or condition of underground or above-ground fuel tanks.
Condition of service and main line: Appeared serviceable
Water service: Private well
Water pressure (psi): 55 psi
Location of main water shut-off: Basement
Condition of supply lines: Appeared serviceable
Supply pipe material: Copper
Condition of drain pipes: Appeared serviceable
Drain pipe material: Plastic
Condition of waste lines: Appeared serviceable
Waste pipe material: Plastic
Vent pipe condition: Appeared serviceable
Vent pipe material: Plastic
Sump pump installed: Yes
Condition of sump pump: Not determined (inaccessible or obscured)
Sewage ejector pump installed: Yes
Condition of sewage ejector pump: Not determined (inaccessible or obscured)
Condition of fuel system: Appeared serviceable
Visible fuel storage systems: None visible
Location of main fuel shut-off valve: At gas meter
14) Based on visible equipment or information provided to the inspector, the water supply to this property appeared to be from a private well. Private well water supplies are specialty systems and are excluded from this inspection. Comments in this report related to this system are made as a courtesy only and are not meant to be a substitute for a full evaluation by a qualified specialist. The inspector does not test private well water for contamination or pollutants, determine if the supply and/or flow are adequate, or provide an estimate for remaining life of well pumps, pressure tanks or equipment. Only visible and accessible components are evaluated. Recommend the following:
That a qualified well contractor fully evaluate the well, including a pump/flow test
That the well water be tested per the client's concerns (coliforms, pH, contaminants, etc.)
Research the well's history (how/when constructed, how/when maintained or repaired, past performance, past health issues)
Document the current well capacity and water quality for future reference
15) A water softener system was installed on the premises. These are specialty systems and are excluded from this inspection. Comments in this report related to this system are made as a courtesy only and are not meant to be a substitute for a full evaluation by a qualified specialist. Water softeners typically work by removing unwanted minerals (e.g. calcium, magnesium) from the water supply. They prevent build-up of scale inside water supply pipes, improve lathering while washing, and prevent spots on dishes. Recommend consulting with the property owner about this system to determine its condition, required maintenance, age, expected remaining life, etc. For more information, visit: http://www.reporthost.com/?WTRSFT http://www.reporthost.com/?HRDWTR
Limitations: Evaluation of and determining the adequacy or completeness of the following items are not included in this inspection: water recirculation pumps; solar water heating systems; Energy Smart or energy saver controls; catch pan drains. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on water heaters, does not determine if water heaters are appropriately sized, or perform any evaluations that require a pilot light to be lit or a shut-off valve to be operated.
Limitations: The following items are not included in this inspection: humidifiers, dehumidifiers, electronic air filters; solar, coal or wood-fired heat systems; thermostat or temperature control accuracy and timed functions; heating components concealed within the building structure or in inaccessible areas; underground utilities and systems; safety devices and controls (due to automatic operation). Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on heating or cooling system components, does not determine if heating or cooling systems are appropriately sized, does not test coolant pressure, or perform any evaluations that require a pilot light to be lit, a shut-off valve to be operated, a circuit breaker to be turned "on" or a serviceman's or oil emergency switch to be operated. It is beyond the scope of this inspection to determine if furnace heat exchangers are intact and free of leaks. Condensation pans and drain lines may clog or leak at any time and should be monitored while in operation in the future. Where buildings contain furnishings or stored items, the inspector may not be able to verify that a heat source is present in all "liveable" rooms (e.g. bedrooms, kitchens and living/dining rooms).
General heating system type(s): Forced air, Furnace
General heating distribution type(s): Ducts and registers
Condition of forced air heating/(cooling) system: Appeared serviceable
Forced air heating system fuel type: Natural gas
Location of forced air furnace: Basement
Forced air system capacity in BTUs or kilowatts: 110,000 BTU
Condition of furnace filters: Required replacement
Location for forced air filter(s): Side of furnace
Condition of forced air ducts and registers: Appeared serviceable
Condition of burners: Appeared serviceable
Condition of cooling system and/or heat pump: Appeared serviceable
Cooling system and/or heat pump fuel type: Electric
Location: in plenum
Type: Packaged unit
Condition of controls: Appeared serviceable
17) Note: mouse or rodent feces in furnace
18) The outdoor air temperature was below 65 degrees Fahrenheit during the inspection. Air conditioning systems can be damaged if operated during such low temperatures. Because of this, the inspector was unable to operate and fully evaluate the cooling system.
Limitations: The following items are not included in this inspection: coal stoves, gas logs, chimney flues (except where visible). Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of drafting or sizing in fireplace and stove flues, and also does not determine if prefabricated or zero-clearance fireplaces are installed in accordance with the manufacturer's specifications. The inspector does not perform any evaluations that require a pilot light to be lit, and does not light fires. The inspector provides a basic visual examination of a chimney and any associated wood burning device. The National Fire Protection Association has stated that an in-depth Level 2 chimney inspection should be part of every sale or transfer of property with a wood-burning device. Such an inspection may reveal defects that are not apparent to the home inspector who is a generalist.
Condition of gas-fired fireplaces or stoves: Appeared serviceable
Gas fireplace or stove type: Metal pre-fab fireplace
Condition of chimneys and flues: Appeared serviceable
Limitations: The following items are not included in this inspection: household appliances such as stoves, ovens, cook tops, ranges, warming ovens, griddles, broilers, dishwashers, trash compactors, refrigerators, freezers, ice makers, hot water dispensers and water filters; appliance timers, clocks, cook functions, self and/or continuous cleaning operations, thermostat or temperature control accuracy, and lights. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of the remaining life of appliances, and does not determine the adequacy of operation of appliances. The inspector does not note appliance manufacturers, models or serial numbers and does not determine if appliances are subject to recalls. Areas and components behind and obscured by appliances are inaccessible and excluded from this inspection.
Condition of counters: Appeared serviceable
Condition of cabinets: Appeared serviceable
Condition of sinks and related plumbing: Appeared serviceable, Required repair, replacement and/or evaluation (see comments below)
20) evidence of past leak on left drain in kitchen - is not leaking currently
Limitations: The following items are not included in this inspection: overflow drains for tubs and sinks; heated towel racks, saunas, steam generators, clothes washers, clothes dryers. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of washing machine drain lines, washing machine catch pan drain lines, or clothes dryer exhaust ducts. The inspector does not operate water supply or shut-off valves for sinks, toilets, bidets, clothes washers, etc. due to the possibility of valves leaking or breaking when operated. The inspector does not determine if shower pans or tub and shower enclosures are water tight, or determine the completeness or operability of any gas piping to laundry appliances.
Location #A: Half bath, first floor
Location #B: Full bath, Master bath, first floor
Location #C: Full bath, second floor
Condition of counters: Appeared serviceable
Condition of cabinets: Appeared serviceable
Condition of flooring: Appeared serviceable
Condition of sinks and related plumbing: Appeared serviceable
Condition of toilets: Appeared serviceable
Condition of bathtubs and related plumbing: Appeared serviceable
Condition of shower(s) and related plumbing: Appeared serviceable
Condition of ventilation systems: Appeared serviceable
Bathroom ventilation type: Central exhaust fan
Gas supply for laundry equipment present: No
240 volt receptacle for laundry equipment present: Yes - missing outlet cover
21) Gaps, no caulk, or substandard caulking were found between the shower enclosure and the floor, walls at location(s) #B, C. Water can penetrate these areas and cause damage. Recommend that a qualified person re-caulk or install caulking as necessary.
22) Water damage was found in shelving or cabinet components below one or more sinks at location(s) #C. Doesn't appear to be leaking currently
Limitations: The following items are not included in this inspection: security, intercom and sound systems; communications wiring; central vacuum systems; elevators and stair lifts; cosmetic deficiencies such as nail-pops, scuff marks, dents, dings, blemishes or issues due to normal wear and tear in wall, floor and ceiling surfaces and coverings, or in equipment; deficiencies relating to interior decorating; low voltage and gas lighting systems. Any comments made regarding these items are as a courtesy only. Note that the inspector does not evaluate any areas or items which require moving stored items, furnishings, debris, equipment, floor coverings, insulation or similar materials. The inspector does not test for asbestos, lead, radon, mold, hazardous waste, urea formaldehyde urethane, or any other toxic substance. Some items such as window, drawer, cabinet door or closet door operability are tested on a sampled basis. The client should be aware that paint may obscure wall and ceiling defects, floor coverings may obscure floor defects, and furnishings may obscure wall, floor and floor covering defects. If furnishings were present during the inspection, recommend a full evaluation of walls, floors and ceilings that were previously obscured when possible. Determining the cause and/or source of odors is not within the scope of this inspection.
Condition of exterior entry doors: Appeared serviceable
Exterior door material: Metal, Fiberglass or vinyl, Glass panel, Sliding glass
Condition of interior doors: Appeared serviceable
Condition of windows and skylights: Appeared serviceable, Required repair, replacement and/or evaluation (see comments below)Window on back of garage is broken
Type(s) of windows: Wood, Metal, Multi-pane, Casement
Condition of walls and ceilings: Appeared serviceable
Wall type or covering: Drywall, Wood
Ceiling type or covering: Drywall, Wood
Condition of flooring: Appeared serviceable
Flooring type or covering: Carpet, Vinyl, linoleum or marmoleum
23) Window on back of garage is broken - recommend replacing
24) Minor cracks, nail pops and/or blemishes were found in walls and/or ceilings in one or more areas. Cracks and nail pops are common, are often caused by lumber shrinkage or minor settlement, and can be more or less noticeable depending on changes in humidity. They did not appear to be a structural concern, but the client may wish to repair these for aesthetic reasons. For recurring cracks, consider using an elastic crack covering product: http://www.reporthost.com/?ECC
Thank you for trusting ProHome Inspection Services - Please feel free to call with any questions or concerns.