This report is the exclusive property of this inspection company and the client(s) listed in the report title. Use of this report by any unauthorized persons is prohibited.
Neighborhood Home Inspections, LLC
13414 188th Ave E
Bonney Lake WA 98391-9618
Inspector: John Dupras
Property Inspection Report
||Sunday, December 06, 2015
This report published on Thursday, September 01, 2016 8:33:45 AM PDT
Report number: 1115004
Time started: 12:15 pm
Time finished: 3:00 pm
Present during inspection: Client, Realtor
Client present for discussion at end of inspection: Yes
Inspector: John Dupras
Weather conditions during inspection: Dry (no rain), Sunny
Temperature during inspection: Cold
Ground condition: Damp
Recent weather: Dry (no rain), Sunny
Overnight temperature: Freezing
Type of building: Single family, Mobile home
Buildings inspected: One house
Age of main building: 24
Source for main building age: Client, Municipal records or property listing
Front of building faces: West
Main entrance faces: West
Additions and modifications: Front porch added.
Source for additions and modifications: Visual inspection
This manufactured home has been altered, and unless the required permit(s) from the Washington State Department of Labor and Industries have been obtained, the home may not be able to be offered for rent, lease or sale. Examples of alterations that require a permit include, but are not limited to:
- Heat pump/air conditioning installations
- Wood/pellet/gas stove or furnace installations
- Changing from electric to gas appliances
- Electrical or plumbing changes
- Structural changes or additions (decks, roof extensions, etc.)
- Removal of the Labor and Industries tag attached to the building exterior
The client should attempt to verify that the appropriate permits have been obtained for all alterations requiring permits. For more information, visit:http://www.reporthost.com/?MFGPERMIT
Some areas and items at this property were obscured by furniture and/or stored items. This often includes but is not limited to walls, floors, windows, inside and under cabinets, under sinks, on counter tops, in closets, behind window coverings, under rugs or carpets, and under or behind furniture. Areas around the exterior, under the structure, in the garage and in the attic may also be obscured by stored items. The inspector in general does not move personal belongings, furnishings, carpets or appliances. When furnishings, stored items or debris are present, all areas or items that are obscured, concealed or not readily accessible are excluded from the inspection. The client should be aware that when furnishings, stored items or debris are eventually moved, damage or problems that were not noted during the inspection may be found.
Limitations: Unless specifically included in the inspection, the following items and any related equipment, controls, electric systems and/or plumbing systems are excluded from this inspection: detached buildings or structures; fences and gates; retaining walls; underground drainage systems, catch basins or concealed sump pumps; swimming pools and related safety equipment, spas, hot tubs or saunas; whether deck, balcony and/or stair membranes are watertight; trees, landscaping, properties of soil, soil stability, erosion and erosion control; ponds, water features, irrigation or yard sprinkler systems; sport courts, playground, recreation or leisure equipment; areas below the exterior structures with less than 3 feet of vertical clearance; invisible fencing; sea walls, docks and boathouses; retractable awnings. Any comments made regarding these items are as a courtesy only.
Site profile: Level, Minor slope
Condition of driveway: Appeared serviceable
Driveway material: Gravel
Condition of sidewalks and/or patios: Appeared serviceable
Condition of deck, patio and/or porch covers: Appeared serviceable
Deck, patio, porch cover material and type: Covered (Refer to Roof section)
Condition of decks, porches and/or balconies: Appeared serviceable
Deck, porch and/or balcony material: Wood, concrete
Condition of stairs, handrails and guardrails: Appeared serviceable
Exterior stair material: Wood
Soil was in contact with or too close to wooden deck, porch or balcony substructure components. This is a conducive condition for wood-destroying organisms. Clearances to soil should be as follows:
- 12 inches below beams
- 18 inches below joists
- 6 inches below support post bases and other wood components
Pressure treated wood is typically rated for 25 year contact with soil, but the cut ends hidden below grade may not have been treated and can rot quickly. Support posts should be elevated above grade on concrete piers or footings, and be separated from the concrete by metal brackets or an impermeable membrane such as shingle scraps. For other components, soil should be graded and/or removed to maintain these clearances if possible. Otherwise, replacing non-treated wood with treated wood, or installing borate-based products such as Impel rods may help to prevent infestation and damage. For more information, visit:http://www.reporthost.com/?IMPEL
Wooden deck or porch surfaces were overdue for normal maintenance. Recommend that a qualified person clean and preserve as necessary. Where decks have been coated with a finish such as opaque stains or paint, it may be too difficult to strip the finish and apply anything but paint or opaque stain. Where transparent stain or penetrating oil has been applied in the past, recommend that a penetrating oil be used. For more information, visit:http://www.reporthost.com/?PENOILhttp://www.reporthost.com/?DKMAIN
Vegetation was overgrown around equipment for one or more utilities such as gas or electric meters. Vegetation should be pruned or removed as necessary to allow unobstructed access.
No outbuildings or detached structures were evaluated. They are excluded from this inspection.
Some areas of the driveway were obscured by Vegitation and couldn't be fully evaluated.
Minor deterioration (e.g. cracks, holes, settlement, heaving) was found in the driveway, but no trip hazards were found. The client may wish to have repairs made for cosmetic reasons.
Minor deterioration (e.g. cracks, holes, settlement, heaving) was found in sidewalks or patios, but no trip hazards were found. The client may wish to have repairs made for cosmetic reasons.
All areas of the porch substructure were inaccessible due to limited space below. These areas couldn't be evaluated and are excluded from the inspection.
Exterior and Foundation
Limitations: The inspector performs a visual inspection of accessible components or systems at the exterior. Items excluded from this inspection include below-grade foundation walls and footings; foundations, exterior surfaces or components obscured by vegetation, stored items or debris; wall structures obscured by coverings such as siding or trim. Some items such as siding, trim, soffits, vents and windows are often high off the ground, and may be viewed using binoculars from the ground or from a ladder. This may limit a full evaluation. Regarding foundations, some amount of cracking is normal in concrete slabs and foundation walls due to shrinkage and drying. Note that the inspector does not determine the adequacy of seismic reinforcement.
Wall inspection method: Viewed from ground
Condition of wall exterior covering: Appeared serviceable
Apparent wall structure: Wood frame
Wall covering: Wood, Wood fiber
Condition of foundation and footings: Appeared serviceable
Apparent foundation type: Crawl space
Foundation/stem wall material: Not applicable, slab, manufactured or mobile home
Footing material (under foundation stem wall): Poured in place concrete
Tie downs for seismic reinforcement installed: Yes (but not evaluated, the inspector is not a licensed engineer)
One or more exhaust duct end caps were missing. Their purpose is to prevent unconditioned air from entering the building, and keep out birds, rodents and bugs. Blocked ducts can cause fan motors and/or clothes dryers to overheat and can pose a fire hazard. Recommend that a qualified person repair or replace caps as necessary.
Soil was in contact with or less than 6 inches from siding, trim or structural wood. This is a conducive condition for wood-destroying organisms. Recommend grading or removing soil as necessary to maintain a 6-inch clearance. If not possible, then recommend replacing untreated wood with pressure-treated wood. Installation of borate-based products such as Impel rods can also reduce the likelihood of rot or infestation if soil cannot be removed. Note that damage from fungal rot and/or insects may be found when soil is removed, and repairs may be necessary.
Some nail heads at the composition wood siding were protruding from the wood, or had been nailed in so as to break the surface of the siding, and caulk was missing. Most manufacturers of composition wood siding specify that nail heads should be flush with the surface, and that the surface of the siding should not be broken. If broken, then caulk should be applied to the nail heads to prevent water penetration and subsequent deterioration of the siding. Recommend that a qualified person repair per the siding manufacturer's specifications.
Some exterior wall sections were obscured by vegetation and couldn't be fully evaluated. They are excluded from this inspection.
No poured-in-place concrete footings were visible below the piers supporting this manufactured home. Settlement can occur as a result. Consult with a qualified contractor to determine options for installing footings per standard building practices. There may have been footings under the vapor barrier but unable to verify.
Anchors or tie-downs that hold the manufactured home down were observed in the crawl space. The inspector does note their presence, but does not count these anchors or determine if they comply with any past or present codes. The primary purpose of anchors is to hold the home down in the event of flooding, high wind or seismic activity.
Limitations: Structural components such as joists and beams, and other components such as piping, wiring and/or ducting that are obscured by under-floor insulation are excluded from this inspection. The inspector does not determine if support posts, columns, beams, joists, studs, trusses, etc. are of adequate size, spanning or spacing.
The inspector does not guarantee or warrant that water will not accumulate in the crawl spaces in the future. Complete access to all crawl space areas during all seasons and during prolonged periods of all types of weather conditions (e.g. heavy rain, melting snow) would be needed to do so.
The inspector attempts to locate all crawl space access points and areas. Access points may be obscured or otherwise hidden by furnishings or stored items. In such cases, the client should ask the property owner where all access points are that are not described in this inspection, and have those areas inspected. Note that crawl space areas should be checked at least annually for water intrusion, plumbing leaks and pest activity.
Crawl space inspection method: Traversed
Location of crawl space access point #A: Building exterior
Crawl space access points that were opened and viewed, traversed or partially traversed: A
Condition of floor substructure above: Not determined (inaccessible or obscured)
Pier or support post material: Concrete block
Beam material: Steel
Floor structure above: Not determined (inaccessible or obscured)
Condition of insulation underneath floor above: Appeared serviceable
Condition of vapor barrier: Appeared serviceable
Vapor barrier present: Yes
Condition of crawl space ventilation: Appeared serviceable
Ventilation type: with vents
As in most manufactured homes, a "bottom board" was attached to the underside of the floor structure. Its purpose is to protect and hold the under-floor insulation in place. It also helps prevent insects and vermin from nesting in the sub-floor, and helps prevent plumbing lines from freezing. It is permanently installed and obscures the floor structure and all wiring and plumbing within. The inspector makes no attempt to move or remove it for evaluation purposes. All areas and components obscured by the bottom board are excluded from this inspection.
The steel tongue, axle and/or wheels used to tow this manufactured home to this site have been removed from the steel under-carriage, but were left in place in the crawl space below the house. They block access to some areas and limit the inspector's ability to evaluate the crawl space. Note that Housing and Urban Development (HUD) standards require these be removed when a manufactured home is installed. For more information visit:http://www.reporthost.com/?MFGTNG
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; solar roofing components. Any comments made regarding these items are made as a courtesy only. Note that the inspector does not provide an estimate of remaining life on the roof surface material, nor guarantee that leaks have not occurred in the roof surface, skylights or roof penetrations in the past. Regarding roof leaks, only active leaks, visible evidence of possible sources of leaks, and evidence of past leaks observed during the inspection are reported on as part of this inspection. The inspector does not guarantee or warrant that leaks will not occur in the future. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high wind and rain, melting snow) would be needed to do so. Occupants should monitor the condition of roofing materials in the future. For older roofs, recommend that a professional inspect the roof surface, flashings, appurtenances, etc. annually and maintain/repair as might be required. If needed, the roofer should enter attic space(s). Regarding the roof drainage system, unless the inspection was conducted during and after prolonged periods of heavy rain, the inspector was unable to determine if gutters, downspouts and extensions perform adequately or are leak-free.
Age of roof surface(s): 3-5 years
Roof inspection method: Traversed
Condition of roof surface material: Appeared serviceable
Roof surface material: Asphalt or fiberglass composition shingles
Roof type: Gable
Apparent number of layers of roof surface material: One
Condition of exposed flashings: Appeared serviceable
Condition of gutters, downspouts and extensions: Appeared serviceable, Limited evaluation due to little or no rainfall during and prior to the inspection
Gutter and downspout material: Metal
Gutter and downspout installation: Full
Nail heads were exposed at one or more shingles. More than just a few exposed nail heads may indicate a substandard roof installation. Recommend applying an approved sealant over exposed nail heads now and as necessary in the future to prevent leaks.
Some roof surfaces were obscured by vegetation and couldn't be evaluated. These areas are excluded from this inspection.
Attic and Roof Structure
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; areas and components obscured by insulation. Any comments made regarding these items are made as a courtesy only. The inspector does not determine the adequacy of the attic ventilation system. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high/low temperatures, high/low humidity, high wind and rain, melting snow) would be needed to do so. The inspector is not a licensed engineer and does not determine the adequacy of roof structure components such as trusses, rafters or ceiling beams, or their spacing or sizing.
Attic inspection method: Not inspected because no access was found
Roof ventilation type: Ridge vent(s), Open soffit vents
Attic spaces less than 30 inches in height may exist in this building, but had no visible access points. This is acceptable per standard building practices. However, these spaces were not inspected and are excluded from this inspection.
Limitations: The following items are not included in this inspection: generator systems, transfer switches, surge suppressors, inaccessible or concealed wiring; underground utilities and systems; low-voltage lighting or lighting on timers or sensors. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of grounding or bonding, if this system has an adequate capacity for the client's specific or anticipated needs, or if this system has any reserve capacity for additions or expansion. The inspector does not operate circuit breakers as part of the inspection, and does not install or change light bulbs. The inspector does not evaluate every wall switch or receptacle, but instead tests a representative number of them per various standards of practice. When furnishings, stored items or child-protective caps are present some receptacles are usually inaccessible and are not tested; these are excluded from this inspection. Receptacles that are not of standard 110 volt configuration, including 240-volt dryer receptacles, are not tested and are excluded. The functionality of, power source for and placement of smoke and carbon monoxide alarms is not determined as part of this inspection. Upon taking occupancy, proper operating and placement of smoke and carbon monoxide alarms should be verified and batteries should be changed. These devices have a limited lifespan and should be replaced every 10 years. The inspector attempts to locate and evaluate all main and sub-panels. However, panels are often concealed. If panels are found after the inspection, a qualified electrician should evaluate and repair if necessary. The inspector attempts to determine the overall electrical service size, but such estimates are not guaranteed because the overall capacity may be diminished by lesser-rated components in the system. Any repairs recommended should be made by a licensed electrician.
Electric service condition: Appeared serviceable
Primary service type: Underground
Number of service conductors: 3
Service voltage (volts): 120-240
Estimated service amperage: 200
Primary service overload protection type: Circuit breakers
Service entrance conductor material: Stranded copper
Main disconnect rating (amps): 200
System ground: Not determined, not readily apparent
Condition of main service panel: Appeared serviceable
Condition of sub-panel(s): Appeared serviceable
Location of main service panel #A: Utility room
Location of sub-panel #C: Building exterior
Location of main disconnect: Breaker at top of main service panel
Condition of branch circuit wiring: Serviceable
Branch circuit wiring type: Non-metallic sheathed, Copper
Solid strand aluminum branch circuit wiring present: None visible
Ground fault circuit interrupter (GFCI) protection present: No
Arc fault circuit interrupter (AFCI) protection present: No
Smoke alarms installed: Yes, but not tested
Carbon monoxide alarms installed: Yes, but not tested
Smoke alarm power source(s): Hard wired
One or more electric receptacles at the kitchen had no visible ground fault circuit interrupter (GFCI) protection, or the inspector was unable to determine if GFCI protection was present. If not GFCI-protected, receptacles in wet areas pose a shock hazard. Recommend that a qualified electrician evaluate and install GFCI protection if necessary and per standard building practices. General guidelines for GFCI-protected receptacles include the following locations:
- Outdoors (since 1973)
- Bathrooms (since 1975)
- Garages (since 1978)
- Kitchens (since 1987)
- Crawl spaces and unfinished basements (since 1990)
- Wet bar sinks (since 1993)
- Laundry and utility sinks (since 2005)
For more information, visit:http://www.reporthost.com/?GFCI
Based on the age of this structure and the appearance of existing smoke alarms, the alarms may have been installed more than 10 years ago. According to National Fire Protection Association
, aging smoke alarms don't operate as efficiently and often are the source for nuisance alarms. Older smoke alarms are estimated to have a 30% probability of failure within the first 10 years. Newer smoke alarms do better, but should be replaced after 10 years. Unless you know that the smoke alarms are new, replacing them when moving into a new residence is also recommended by NFPA. For more information, visit:http://www.reporthost.com/?SMKALRMLS
Carbon monoxide alarms were missing from one or more sleeping areas. This is a potential safety hazard. Some states and/or municipalities require CO alarms to be installed in the vicinity of each sleeping area, on each level and in accordance with the manufacturer's recommendations. Recommend installing additional carbon monoxide alarms per these standards. For more information, visit:http://www.reporthost.com/?COALRM
One or more "plug-in" type carbon monoxide alarms were found. Because such CO alarms can be easily removed, recommend that the client verify that CO alarms haven't been removed upon taking occupancy. If removed, then recommend installing new CO alarms outside of each separate sleeping area in the immediate vicinity of the bedrooms on each level and in accordance with the manufacturer's recommendations. Note that some states and/or municipalities require CO alarms to be installed for new construction and/or for homes being sold. For more information, visit:http://www.reporthost.com/?COALRM
One or more screws that attach the cover or dead front to panel(s) #C were missing or not installed. Recommend installing screws where missing so the cover or dead front is secure. Only screws with blunt tips approved for this purpose should be installed, so wiring inside the panel is not damaged. Because energized wires may be located directly behind screw holes, the client should consider having a qualified electrician replace missing screws.
One or more light fixtures (exterior and master closet), were inoperable (didn't turn on when nearby switches were operated). Recommend further evaluation by replacing bulbs and/or consulting with the property owner. If replacing bulbs doesn't work and/or no other switch(es) can be found, then recommend that a qualified electrician evaluate and repair or replace light fixtures as necessary.
Bulbs in one or more light fixtures were missing or broken. These light fixtures couldn't be fully evaluated. If replacement bulbs are inoperable, then recommend that a qualified electrician evaluate and repair or replace light fixtures as necessary.
No doorbell was installed at the main entrance. The client wish to have one installed for convenience sake.
Plumbing / Fuel Systems
Limitations: The following items are not included in this inspection: private/shared wells and related equipment; private sewage disposal systems; hot tubs or spas; main, side and lateral sewer lines; gray water systems; pressure boosting systems; trap primers; incinerating or composting toilets; fire suppression systems; water softeners, conditioners or filtering systems; plumbing components concealed within the foundation or building structure, or in inaccessible areas such as below tubs; underground utilities and systems; overflow drains for tubs and sinks; backflow prevention devices. Any comments made regarding these items are as a courtesy only. Note that the inspector does not operate water supply or shut-off valves due to the possibility of valves leaking or breaking when operated. The inspector does not test for lead in the water supply, the water pipes or solder, does not determine if plumbing and fuel lines are adequately sized, and does not determine the existence or condition of underground or above-ground fuel tanks.
Condition of service and main line: Appeared serviceable
Water service: Public
Location of main water meter: Not determined (obscured, inaccessible or none found)
Location of main water shut-off: Crawl space
Service pipe material: Plastic
Condition of supply lines: Appeared serviceable
Supply pipe material: Not determined (inaccessible or obscured)
Condition of drain pipes: Appeared serviceable
Drain pipe material: Plastic
Condition of waste lines: Appeared serviceable
Waste pipe material: Plastic
Location(s) of plumbing clean-outs: Crawl space
Vent pipe condition: Appeared serviceable
Vent pipe material: Plastic
Sump pump installed: None visible
Based on visible components or information provided to the inspector, this property appeared to have a private sewage disposal (septic) system. These are specialty systems and are excluded from this inspection. Comments in this report related to this system are made as a courtesy only and are not meant to be a substitute for a full evaluation by a qualified specialist. Generally, septic tanks should be pumped and inspected every 3 years. Depending on the type of system and municipal regulations, inspection and maintenance may be required more frequently, often annually. Recommend the following:
- Consult with the property owner about this system's maintenance and repair history
- Review any documentation available for this system
- Review inspection and maintenance requirements for this system
- That a qualified specialist evaluate, perform maintenance and make repairs if necessary
For more information, visit:http://www.reporthost.com/?SEPTIC
The inspector did not determine the location of the water meter. Recommend consulting with the property owner to determine the meter location, that you locate it yourself, or consult with the local water municipality if necessary. It is especially important to find the meter if no main shut-off valve is found because the meter may be the only way to turn off the water supply in the event of an emergency, such as when a supply pipe bursts.
What appeared to be the main water shut-off valve was located in the crawl space. This is an inconvenient location at best, and may prevent the water from being turned off in a timely manner in the event of a plumbing emergency. Consider having a qualified plumber relocate the shut-off valve to a more convenient location, such as in a closet or a cabinet under a sink.
Limitations: Evaluation of and determining the adequacy or completeness of the following items are not included in this inspection: water recirculation pumps; solar water heating systems; Energy Smart or energy saver controls; catch pan drains. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on water heaters, does not determine if water heaters are appropriately sized, or perform any evaluations that require a pilot light to be lit or a shut-off valve to be operated.
Condition of water heater: Appeared serviceable
Energy source: Electricity
Capacity (in gallons): 50
Temperature-pressure relief valve installed: Yes
Model number: 82V52-2
Serial number: 0710R17557
Location of water heater: Utility room
Hot water temperature tested: Yes
Water temperature (degrees Fahrenheit): 112
Heating, Ventilation and Air Condition (HVAC)
Limitations: The following items are not included in this inspection: humidifiers, dehumidifiers, electronic air filters; solar, coal or wood-fired heat systems; thermostat or temperature control accuracy and timed functions; heating components concealed within the building structure or in inaccessible areas; underground utilities and systems; safety devices and controls (due to automatic operation). Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on heating or cooling system components, does not determine if heating or cooling systems are appropriately sized, does not test coolant pressure, or perform any evaluations that require a pilot light to be lit, a shut-off valve to be operated, a circuit breaker to be turned "on" or a serviceman's or oil emergency switch to be operated. It is beyond the scope of this inspection to determine if furnace heat exchangers are intact and free of leaks. Condensation pans and drain lines may clog or leak at any time and should be monitored while in operation in the future. Where buildings contain furnishings or stored items, the inspector may not be able to verify that a heat source is present in all "liveable" rooms (e.g. bedrooms, kitchens and living/dining rooms).
General heating system type(s): Heat pump
General heating distribution type(s): Ducts and registers
Last service date of primary heat source: 3-21-2011
Source for last service date of primary heat source: Label
Location of forced air furnace: Utility room
Location for forced air filter(s): At top of air handler
Condition of forced air ducts and registers: Appeared serviceable
Condition of cooling system and/or heat pump: Appeared serviceable
Cooling system and/or heat pump fuel type: Electric
Type: Split system
Estimated age: 4 years
Approximate tonnage: 5
Condition of cooling system and/or heat pump: York
Condition of controls: Appeared serviceable
24 hour automatic ventilation system present: None visible
The last service date of the forced air heating/cooling system appeared to be more than 1 year ago, or the inspector was unable to determine the last service date. Ask the property owner when it was last serviced. If unable to determine the last service date, or if this system was serviced more than 1 year ago, recommend that a qualified HVAC contractor service this system and make repairs if necessary. Because this system has a compressor and refrigerant system, this servicing should be performed annually in the future. Any needed repairs noted in this report should be brought to the attention of the contractor when it's serviced.
The air handler's primary condensate drain line was routed so it drains close the foundation. Significant amounts of water can be produced by this system and can cause water infiltration. In extreme cases the wet soil may not adequately support the foundation. Recommend repairing as necessary so condensate water drains well away from the foundation. For example, by installing a splash block.
The outdoor air temperature was below 65 degrees Fahrenheit during the inspection. Air conditioning systems can be damaged if operated during such low temperatures. Because of this, the inspector was unable to operate and fully evaluate the cooling system.
Fireplaces, Stoves, Chimneys and Flues
Limitations: The following items are not included in this inspection: coal stoves, gas logs, chimney flues (except where visible). Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of drafting or sizing in fireplace and stove flues, and also does not determine if prefabricated or zero-clearance fireplaces are installed in accordance with the manufacturer's specifications. The inspector does not perform any evaluations that require a pilot light to be lit, and does not light fires. The inspector provides a basic visual examination of a chimney and any associated wood burning device. The National Fire Protection Association has stated that an in-depth Level 2 chimney inspection should be part of every sale or transfer of property with a wood-burning device. Such an inspection may reveal defects that are not apparent to the home inspector who is a generalist.
Condition of wood-burning fireplaces, stoves: Not determined (inaccessible or obscured)
Wood-burning stove type: Freestanding
Fan or blower installed in wood-burning fireplace or stove: No
Condition of chimneys and flues: Appeared serviceable
Wood-burning chimney type: Metal
The single-wall metal stove pipe appears to pass through a combustible surface, or through a concealed space. Single-wall stove pipe should only be used as a connector to a chimney that is approved for installation through combustible spaces. This is a fire hazard. Recommend that a qualified contractor investigate and repair per standard building practices.
The wood stove appeared to be too close to combustibles. General guidelines require clearances of at least 48 inches between most wood stoves and surrounding combustible surfaces, or at least 38 inches when approved shielding is present. Many wood stoves have reduced minimum clearances, but it is beyond the scope of this inspection for the inspector to determine such manufacturer-specific information. Recommend reviewing documentation, or that a qualified specialist evaluate, to determine if the wood stove is installed per the manufacturer's specifications. Any repairs or modifications needed should be made by a qualified contractor.
Significant amounts of ash or fire materials were present in one or more fireplace or wood stove fireboxes. As a result, the inspector was unable to fully view or evaluate the firebox(es) and/or components inside (e.g. firebrick, metal liner, log lighter). These components are excluded from this inspection.
Limitations: The following items are not included in this inspection: household appliances such as stoves, ovens, cook tops, ranges, warming ovens, griddles, broilers, dishwashers, trash compactors, refrigerators, freezers, ice makers, hot water dispensers and water filters; appliance timers, clocks, cook functions, self and/or continuous cleaning operations, thermostat or temperature control accuracy, and lights. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of the remaining life of appliances, and does not determine the adequacy of operation of appliances. The inspector does not note appliance manufacturers, models or serial numbers and does not determine if appliances are subject to recalls. Areas and components behind and obscured by appliances are inaccessible and excluded from this inspection.
Permanently installed kitchen appliances present during inspection: Range, Oven, Dishwasher, Refrigerator
Condition of counters: Appeared serviceable
Condition of cabinets: Appeared serviceable
Condition of sinks and related plumbing: Appeared serviceable
Condition of dishwasher: Appeared serviceable
Condition of range, cooktop or oven: Appeared serviceable
Range, cooktop or oven type: Electric
Type of ventilation: Hood or built into microwave over range or cooktop
Condition of refrigerator: Appeared serviceable
The range could tip forward. An anti-tip bracket may not be installed. This is a potential safety hazard since the range can tip forward when weight is applied to the open door, such as when a small child climbs on it or if heavy objects are dropped on it. Anti-tip brackets have been sold with all free-standing ranges since 1985. Recommend installing an anti-tip bracket to eliminate this safety hazard. For more information, visit:http://www.reporthost.com/?ATB
The cooktop exhaust fan was inoperable. Recommend that a qualified person repair or replace as necessary.
The light in the exhaust hood was inoperable. Recommend replacing light bulb(s) or that repairs be made by a qualified person if necessary.
Improper wire connections
The areas below sink(s) were obscured by stored items or dishes and couldn't be fully evaluated.
Bathrooms, Laundry and Sinks
Limitations: The following items are not included in this inspection: overflow drains for tubs and sinks; heated towel racks, saunas, steam generators, clothes washers, clothes dryers. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of washing machine drain lines, washing machine catch pan drain lines, or clothes dryer exhaust ducts. The inspector does not operate water supply or shut-off valves for sinks, toilets, bidets, clothes washers, etc. due to the possibility of valves leaking or breaking when operated. The inspector does not determine if shower pans or tub and shower enclosures are water tight, or determine the completeness or operability of any gas piping to laundry appliances.
Location #A: Full bath, Master bath, first floor, south
Location #B: Full bath, first floor, east
Condition of counters: Appeared serviceable
Condition of cabinets: Appeared serviceable
Condition of flooring: Appeared serviceable
Condition of sinks and related plumbing: Appeared serviceable
Condition of toilets: Appeared serviceable
Condition of bathtubs and related plumbing: Appeared serviceable
Condition of shower(s) and related plumbing: Appeared serviceable
Condition of ventilation systems: Appeared serviceable
Bathroom and laundry ventilation type: Spot exhaust fans
Gas supply for laundry equipment present: No
240 volt receptacle for laundry equipment present: Yes
The laundry room didn't have an exhaust fan installed. Moisture can accumulate and result in mold, bacteria or fungal growth. Recommend that a qualified contractor install an exhaust fan per standard building practices.
Caulk around the base of the toilet at location(s) #A was missing, substandard and/or deteriorated. Modern standards require caulk to be installed around the entire toilet base where it meets the floor for sanitary reasons. Without it, soiled water can soak into flooring and sub-floor materials if the toilet overflows. Condensation from the toilet can also soak into the flooring. Recommend that a qualified person caulk around toilet bases per standard building practices.
Gaps, no caulk, or substandard caulking were found between the bathtub and the walls at location(s) #A. Water may penetrate these areas and cause damage. Recommend that a qualified person re-caulk or install caulking as necessary.
The bathtub drain stopper mechanism at location(s) #A was missing. Recommend that a qualified person repair or replace as necessary.
The bathtub at location(s) #B drained slowly. Recommend clearing drain and/or that a qualified plumber repair if necessary.
Interior, Doors and Windows
Limitations: The following items are not included in this inspection: security, intercom and sound systems; communications wiring; central vacuum systems; elevators and stair lifts; cosmetic deficiencies such as nail-pops, scuff marks, dents, dings, blemishes or issues due to normal wear and tear in wall, floor and ceiling surfaces and coverings, or in equipment; deficiencies relating to interior decorating; low voltage and gas lighting systems. Any comments made regarding these items are as a courtesy only. Note that the inspector does not evaluate any areas or items which require moving stored items, furnishings, debris, equipment, floor coverings, insulation or similar materials. The inspector does not test for asbestos, lead, radon, mold, hazardous waste, urea formaldehyde urethane, or any other toxic substance. Some items such as window, drawer, cabinet door or closet door operability are tested on a sampled basis. The client should be aware that paint may obscure wall and ceiling defects, floor coverings may obscure floor defects, and furnishings may obscure wall, floor and floor covering defects. If furnishings were present during the inspection, recommend a full evaluation of walls, floors and ceilings that were previously obscured when possible. Determining the cause and/or source of odors is not within the scope of this inspection.
Condition of exterior entry doors: Appeared serviceable
Exterior door material: Wood
Condition of interior doors: Appeared serviceable, Required repair, replacement and/or evaluation (see comments below)
Condition of windows and skylights: Appeared serviceable, Required repair, replacement and/or evaluation (see comments below)
Type(s) of windows: Metal, Multi-pane, Single-hung, Fixed
Condition of walls and ceilings: Appeared serviceable
Wall type or covering: Drywall or plaster
Ceiling type or covering: Drywall or plaster
Condition of flooring: Appeared serviceable
Flooring type or covering: Carpet, Vinyl, linoleum or marmoleum, Laminate
One or more exterior entrance doors were of hollow-core construction rather than solid core. This may represent a security hazard since these doors are easily broken. Recommend that a qualified contractor replace hollow-core, exterior entrance doors with solid core doors.
One or more interior doors were damaged. Recommend that a qualified person replace or repair doors as necessary.
One or more windows that were designed to open and close were difficult to open and close. Recommend that a qualified person repair windows as necessary so they open and close easily.
Weatherstripping around one or more exterior doors was damaged. Water may enter the building, or energy efficiency may be reduced. Recommend that a qualified person repair or replace weatherstripping as necessary.
Utility room exterior door
One or more exterior doors had minor damage and/or deterioration. Although serviceable, the client may wish to repair or replace such doors for appearances' sake.
No window screens were installed. Windows may not provide ventilation during months when insects are active.
Your default report footer here...