This report published on Thursday, November 14, 2019 11:32:56 AM EST
This report is the exclusive property of this inspection company and the client(s) listed in the report title. Use of this report by any unauthorized persons is prohibited.
How to Read this Report
This report is organized by the property's functional areas. Within each functional area, descriptive information is listed first and is shown in bold type. Items of concern follow descriptive information.
Concerns are shown and sorted according to these types:
Poses a safety hazard
Correction likely involves a significant expense
Recommend repairing or replacing
Recommend repair and/or maintenance
Correction likely involves only a minor expense
Recommend ongoing maintenance
Recommend evaluation by a specialist
For your information
Click here for a glossary of building construction terms.Contact your inspector If there are terms that you do not understand, or visit the glossary of construction terms at https://www.reporthost.com/glossary.asp
Client present for discussion at end of inspection: Yes
Weather conditions during inspection: Dry (no rain)
Temperature during inspection: Cool
Inspection fee: $490.00
Payment method: Check
Type of building: Single family, Apartment
Buildings inspected: One house, One detached garage, One additional dwelling unit
Number of residential units inspected: 2
Age of main building: 100+years
Source for main building age: Realtor
Front of building faces: North
Main entrance faces: North
Occupied: Apartment occupied
1) Structures built prior to the mid 1980s may contain lead and/or asbestos. Lead is commonly found in paint and in some plumbing components. The EPA does not recognize newer coats of paint as encapsulating older coats of lead-based paint. Asbestos is commonly found in various building materials such as insulation, siding, and/or floor and ceiling tiles. Laws were passed in 1978 to prohibit usage of lead and asbestos, but stocks of materials containing these substances remained in use for a number of years thereafter. Both lead and asbestos are known health hazards. Evaluating for the presence of lead and/or asbestos is beyond the scope of this inspection. Any mention of these materials in this report is made as a courtesy only, and meant to refer the client to a specialist. Consult with specialists as necessary, such as industrial hygienists, professional labs and/or abatement specialists for this type of evaluation. For information on lead, asbestos and other hazardous materials in homes, visit: https://www.reporthost.com/?EPA https://www.reporthost.com/?CPSC https://www.reporthost.com/?CDC
2) Some areas and items at this property were obscured by furniture and/or stored items. This often includes but is not limited to walls, floors, windows, inside and under cabinets, under sinks, on counter tops, in closets, behind window coverings, under rugs or carpets, and under or behind furniture. Areas around the exterior, under the structure, in the garage and in the attic may also be obscured by stored items. The inspector in general does not move personal belongings, furnishings, carpets or appliances. When furnishings, stored items or debris are present, all areas or items that are obscured, concealed or not readily accessible are excluded from the inspection. The client should be aware that when furnishings, stored items or debris are eventually moved, damage or problems that were not noted during the inspection may be found.
Limitations: Unless specifically included in the inspection, the following items and any related equipment, controls, electric systems and/or plumbing systems are excluded from this inspection: detached buildings or structures; fences and gates; retaining walls; underground drainage systems, catch basins or concealed sump pumps; swimming pools and related safety equipment, spas, hot tubs or saunas; whether deck, balcony and/or stair membranes are watertight; trees, landscaping, properties of soil, soil stability, erosion and erosion control; ponds, water features, irrigation or yard sprinkler systems; sport courts, playground, recreation or leisure equipment; areas below the exterior structures with less than 3 feet of vertical clearance; invisible fencing; sea walls, docks and boathouses; retractable awnings. Any comments made regarding these items are as a courtesy only.
Site profile: Level
Condition of driveway: Appeared serviceable
Driveway material: Gravel
Condition of sidewalks and/or patios: Appeared serviceable
Sidewalk material: Paving stones
Condition of deck, patio and/or porch covers: Appeared serviceable
Deck, patio, porch cover material and type: Covered (Refer to Roof section)
Condition of decks, porches and/or balconies: Required repairs, replacement and/or evaluation (see comments below)
Deck, porch and/or balcony material: Wood
Condition of stairs, handrails and guardrails: Required repairs, replacement and/or evaluation (see comments below)
Exterior stair material: Wood
3) Handrails at one or more flights of stairs were loose. This is a safety hazard. Recommend that a qualified person repair as necessary.
On garage entry steps
4) Concern with covered deck structure attached to side of home. Client should be aware that wall and roof structure were constructed with substanandard building practices. Including improper attachment to house structure; missing support posts; buckling roof rafter. Client may wish to ask homeowner about permits for this structure.
Limitations: The inspector performs a visual inspection of accessible components or systems at the exterior. Items excluded from this inspection include below-grade foundation walls and footings; foundations, exterior surfaces or components obscured by vegetation, stored items or debris; wall structures obscured by coverings such as siding or trim. Some items such as siding, trim, soffits, vents and windows are often high off the ground, and may be viewed using binoculars from the ground or from a ladder. This may limit a full evaluation. Regarding foundations, some amount of cracking is normal in concrete slabs and foundation walls due to shrinkage and drying. Note that the inspector does not determine the adequacy of seismic reinforcement.
Wall inspection method: Viewed from ground
Condition of wall exterior covering: Required repairs, replacement and/or evaluation (see comments below)
Apparent wall structure: Wood frame
Wall covering: Wood, Vinyl
Condition of foundation and footings: Required repairs, replacement and/or evaluation (see comments below)
Apparent foundation type: Unfinished basement
Foundation/stem wall material: Stone
Footing material (under foundation stem wall): Not determined (inaccessible or obscured)
5) Many sections of siding and/or trim were substandard. Recommend that a qualified person repair, replace or install siding or trim as necessary.
In regard to missing/substandard flashing on window sills.
6) In regard to rear garage:
Soil was in contact with or less than 6 inches from siding, trim or structural wood. This is a conducive condition for wood-destroying organisms. Recommend grading or removing soil as necessary to maintain a 6-inch clearance. If not possible, then recommend replacing untreated wood with pressure-treated wood. Installation of borate-based products such as Impel rods can also reduce the likelihood of rot or infestation if soil cannot be removed. Note that damage from fungal rot and/or insects may be found when soil is removed, and repairs may be necessary.
7) One or more holes or gaps were found in siding or trim. Vermin, insects or water may enter the structure. Recommend that a qualified person repair as necessary.
8) Brick on foundation had some deterioration and missing mortar or mortar in disrepair. Recommend evaluation and repair by a qualified contractor.
One or more minor cracks (1/8 inch or less) were found in the foundation. These didn't appear to be a structural concern, but recommend sealing them to prevent water infiltration and monitor them in the future. Numerous products exist to seal such cracks including hydraulic cement, non-shrinking grout, resilient caulks and epoxy sealants.
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; solar roofing components. Any comments made regarding these items are made as a courtesy only. Note that the inspector does not provide an estimate of remaining life on the roof surface material, nor guarantee that leaks have not occurred in the roof surface, skylights or roof penetrations in the past. Regarding roof leaks, only active leaks, visible evidence of possible sources of leaks, and evidence of past leaks observed during the inspection are reported on as part of this inspection. The inspector does not guarantee or warrant that leaks will not occur in the future. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high wind and rain, melting snow) would be needed to do so. Occupants should monitor the condition of roofing materials in the future. For older roofs, recommend that a professional inspect the roof surface, flashings, appurtenances, etc. annually and maintain/repair as might be required. If needed, the roofer should enter attic space(s). Regarding the roof drainage system, unless the inspection was conducted during and after prolonged periods of heavy rain, the inspector was unable to determine if gutters, downspouts and extensions perform adequately or are leak-free.
Roof inspection method: Viewed from ground, Viewed from windows
Condition of roof surface material: Required repair, replacement and/or evaluation (see comments below), Inregard to rear garage structure
Roof surface material: Asphalt or fiberglass composition shingles, Metal panel
Roof type: Gable
Apparent number of layers of roof surface material: Multiple, On rear garage
Condition of exposed flashings: Required repair, replacement and/or evaluation (see comments below)
9) The roof surface appeared to be near the end of its service life and will likely need replacing in the near future even if repairs are made now. Recommend discussing replacement options with a qualified contractor, and budgeting for a replacement roof surface in the near future. The client may also wish to consider having a qualified contractor attempt to issue a "5 year roof certificate."
10) One or more roof flashings were lifting. Leaks can occur as a result. This is a conducive condition for wood-destroying organisms. Recommend that a qualified person repair as necessary.
11) In regard to rear garage structure:
Moss was growing on the roof. As a result, shingles can lift or be damaged. Leaks can result and/or the roof surface can fail prematurely. Efforts should be made to kill the moss during its growing season (wet months). Typically, zinc or phosphate-based chemicals are used for this and must be applied periodically. For information on various moss treatment products and their pros and cons, visit: https://www.reporthost.com/?MOSS
12) This asphalt or fiberglass composition roof surface appeared to have two or more layers of shingles. Additional layers of composition shingles typically last only 80% of their rated life, and the shingle manufacturer's warranty may be voided. The client should be aware that all layers of roofing will need to be removed when this roof surface needs replacing.
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; areas and components obscured by insulation. Any comments made regarding these items are made as a courtesy only. The inspector does not determine the adequacy of the attic ventilation system. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high/low temperatures, high/low humidity, high wind and rain, melting snow) would be needed to do so. The inspector is not a licensed engineer and does not determine the adequacy of roof structure components such as trusses, rafters or ceiling beams, or their spacing or sizing.
Attic inspection method: Viewed from hatch(es)
Condition of roof structure: Appeared serviceable
Roof structure type: Rafters
Ceiling structure: Not determined (inaccessible or obscured)
Condition of insulation in attic (ceiling, skylight chase, etc.): Appeared serviceable
Ceiling insulation material: Mineral wool loose fill
Approximate attic insulation R value (may vary in areas): Not determined (inaccessible or obscured)
Vapor retarder: Not determined (inaccessible or obscured)
Condition of roof ventilation: Required repair, replacement and/or evaluation (see comments below)
Roof ventilation type: Gable end vents
13) One or more sections of the roof structure appeared to have substandard ventilation, soffit or lower vents were missing. This can result in high attic and roof surface temperatures, reduce the life of the roof covering materials, and/or increase cooling costs. High levels of moisture are also likely to accumulate in the roof structure or attic, and can be a conducive condition for wood-destroying organisms. Standard building practices require one free square foot of ventilation for every 150 square feet of attic space, and that vents be evenly distributed between the lowest points of the roof structure and the highest points to promote air circulation. Often this means that both soffit vents and ridge or gable end vents are installed. Recommend that a qualified contractor evaluate and repair per standard building practices.
Limitations: The following items are not included in this inspection: generator systems, transfer switches, surge suppressors, inaccessible or concealed wiring; underground utilities and systems; low-voltage lighting or lighting on timers or sensors. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of grounding or bonding, if this system has an adequate capacity for the client's specific or anticipated needs, or if this system has any reserve capacity for additions or expansion. The inspector does not operate circuit breakers as part of the inspection, and does not install or change light bulbs. The inspector does not evaluate every wall switch or receptacle, but instead tests a representative number of them per various standards of practice. When furnishings, stored items or child-protective caps are present some receptacles are usually inaccessible and are not tested; these are excluded from this inspection. Receptacles that are not of standard 110 volt configuration, including 240-volt dryer receptacles, are not tested and are excluded. The functionality of, power source for and placement of smoke and carbon monoxide alarms is not determined as part of this inspection. Upon taking occupancy, proper operating and placement of smoke and carbon monoxide alarms should be verified and batteries should be changed. These devices have a limited lifespan and should be replaced every 10 years. The inspector attempts to locate and evaluate all main and sub-panels. However, panels are often concealed. If panels are found after the inspection, a qualified electrician should evaluate and repair if necessary. The inspector attempts to determine the overall electrical service size, but such estimates are not guaranteed because the overall capacity may be diminished by lesser-rated components in the system. Any repairs recommended should be made by a licensed electrician.
Electric service condition: Appeared serviceable
Primary service type: Overhead
Number of service conductors: 3
Service voltage (volts): 120-240
Estimated service amperage: 100
Primary service overload protection type: Circuit breakers
Service entrance conductor material: Stranded aluminum
Main disconnect rating (amps): 100
System ground: Not determined, not readily apparent
Condition of main service panel: Appeared serviceable
Condition of sub-panel(s): Required repair, replacement and/or evaluation (see comments below)
Location of main service panel #A: Basement
Location of main service panel #B: Garage
Location of sub-panel #C: Mechanical room, Garage/apt
Location of main disconnect: Breaker at top of main service panel
Condition of branch circuit wiring: Required repair, replacement and/or evaluation (see comments below)
Carbon monoxide alarms installed: Yes, but not tested
15) Substandard wiring was found at the garage. For example, loose wiring, exposed splices, missing or broken cover plates and/or loose boxes. This is a safety hazard. Recommend that a qualified electrician evaluate and repair as necessary and per standard building practices.
In regard to rear garage wiring
16) One or more ground fault circuit interrupter (GFCI) devices protecting receptacles at the full bath was inoperable . This is a potential shock hazard. Recommend that a qualified electrician evaluate and repair as necessary.
17) One or more electric receptacles at the exterior had no visible ground fault circuit interrupter (GFCI) protection, or the inspector was unable to determine if GFCI protection was present. If not GFCI-protected, receptacles in wet areas pose a shock hazard. Recommend that a qualified electrician evaluate and install GFCI protection if necessary and per standard building practices. General guidelines for GFCI-protected receptacles include the following locations:
Outdoors (since 1973)
Bathrooms (since 1975)
Garages (since 1978)
Kitchens (since 1987)
Crawl spaces and unfinished basements (since 1990)
18) Neutral and equipment ground wires were bonded (connected) at sub-panel(s) # C. This should only occur in the main service panel, not sub-panels, and is a shock hazard. Neutral wires should be attached to a "floating" neutral bar not bonded to the panel, and grounding wires should be attached to a separate grounding bar bonded to the sub-panel. Recommend that a qualified electrician repair per standard building practices. For more information, visit: https://www.reporthost.com/?SUBGRND
Panel cover was not attached. This is a safety hazard in regard to fire and shock hazard for occupants.
19) Bare wire ends, or wires with a substandard termination, were found at one or more locations. This is a potential shock hazard. Recommend that a qualified electrician repair as necessary. For example, by cutting wires to length and terminating with wire nuts in a permanently mounted, covered junction box.
20) In garage for exterior lights: Extension cords were being used as permanent wiring at one or more locations. They should only be used for portable equipment on a temporary basis. Using extension cords as permanent wiring is a potential fire and shock hazard, and indicates that wiring is inadequate and needs updating. Extension cords may be undersized. Connections may not be secure resulting in power fluctuations, damage to equipment, overheating and sparks that could start a fire. Recommend that a qualified electrician repair per standard building practices and eliminate extension cords for permanently installed equipment.
21) One or more conduits or conduit fittings installed outside were not rated for exterior use. This is a potential shock and fire hazard. Recommend that a qualified electrician repair per standard building practices.
22) One or more knockouts were missing from panel(s) #A. Holes in panels are a potential fire hazard if a malfunction ever occurs inside the panel. Rodents can also enter panels through holes. Recommend that a qualified person install knockout covers where missing and per standard building practices.
23) One or more cover plates for switches, receptacles or junction boxes were missing or broken. These plates are intended to contain fire and prevent electric shock from occurring due to exposed wires. Recommend that a qualified person install cover plates where necessary.
24) One or more receptacles had a prong from a plug broken off in a slot, or slot(s) were clogged with foreign objects. Recommend that a qualified electrician replace such receptacles as necessary.
25) Stairweay lights: One or more light fixtures were inoperable (didn't turn on when nearby switches were operated). Recommend further evaluation by replacing bulbs and/or consulting with the property owner. If replacing bulbs doesn't work and/or no other switch(es) can be found, then recommend that a qualified electrician evaluate and repair or replace light fixtures as necessary.
Limitations: The following items are not included in this inspection: private/shared wells and related equipment; private sewage disposal systems; hot tubs or spas; main, side and lateral sewer lines; gray water systems; pressure boosting systems; trap primers; incinerating or composting toilets; fire suppression systems; water softeners, conditioners or filtering systems; plumbing components concealed within the foundation or building structure, or in inaccessible areas such as below tubs; underground utilities and systems; overflow drains for tubs and sinks; backflow prevention devices. Any comments made regarding these items are as a courtesy only. Note that the inspector does not operate water supply or shut-off valves due to the possibility of valves leaking or breaking when operated. The inspector does not test for lead in the water supply, the water pipes or solder, does not determine if plumbing and fuel lines are adequately sized, and does not determine the existence or condition of underground or above-ground fuel tanks.
Condition of service and main line: Appeared serviceable
Limitations: Evaluation of and determining the adequacy or completeness of the following items are not included in this inspection: water recirculation pumps; solar water heating systems; Energy Smart or energy saver controls; catch pan drains. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on water heaters, does not determine if water heaters are appropriately sized, or perform any evaluations that require a pilot light to be lit or a shut-off valve to be operated.
Condition of water heater: Required repair, replacement and/or evaluation (see comments below), Near, at or beyond service life
Energy source: Electricity
Estimated age: 2 Tanks 10 years old
Capacity (in gallons): 30, 40
Temperature-pressure relief valve installed: Yes
Location of water heater: Mechanical room, Basement
Water temperature (degrees Fahrenheit): 110 in main house 130 in apt
26) No drain line was installed for the temperature-pressure relief valve. This is a potential safety hazard due to the risk of scalding if someone is standing next to the water heater when the valve opens. Recommend that a qualified plumber install a drain line per standard building practices.
27) The estimated useful life for most water heaters is 8-12 years. This water heater appeared to be at this age and/or its useful lifespan and may need replacing at any time. Recommend budgeting for a replacement in the near future, or considering replacement now before any leaks occur. The client should be aware that significant flooding can occur if the water heater fails. If not replaced now, consider having a qualified person install a catch pan and drain or a water alarm to help prevent damage if water does leak.
28) Recommend adding flood pan below apartment water heater, in case the water heater fails.
Limitations: The following items are not included in this inspection: humidifiers, dehumidifiers, electronic air filters; solar, coal or wood-fired heat systems; thermostat or temperature control accuracy and timed functions; heating components concealed within the building structure or in inaccessible areas; underground utilities and systems; safety devices and controls (due to automatic operation). Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on heating or cooling system components, does not determine if heating or cooling systems are appropriately sized, does not test coolant pressure, or perform any evaluations that require a pilot light to be lit, a shut-off valve to be operated, a circuit breaker to be turned "on" or a serviceman's or oil emergency switch to be operated. It is beyond the scope of this inspection to determine if furnace heat exchangers are intact and free of leaks. Condensation pans and drain lines may clog or leak at any time and should be monitored while in operation in the future. Where buildings contain furnishings or stored items, the inspector may not be able to verify that a heat source is present in all "liveable" rooms (e.g. bedrooms, kitchens and living/dining rooms).
General heating system type(s): Forced air, Furnace, Individual heater in Apartment/Garage had gas hesater
General heating distribution type(s): None, individual heaters
Last service date of primary heat source: unknown
Condition of forced air heating/(cooling) system: Appeared serviceable
Forced air heating system fuel type: Propane
Estimated age of forced air furnace: Rinnai heater age unknown
Condition of hydronic or steam heat system: Required repair, replacement and/or evaluation (see comments below), Recommend qulified contractor for servicing and cleaning
Type of hydronic or steam heat: Hydronic (hot water)
Hydronic or steam heat fuel type: Oil
Condition of burners: Appeared serviceable
Type of combustion air supply: No dedicated source visible, uses room air
Condition of venting system: Appeared serviceable
Condition of controls: Required repair, replacement and/or evaluation (see comments below)
29) One or more control knobs were substandard. Recommend replacing knobs as necessary.
Second floor control in need of replacement.
30) The digital display on the thermostat was dim or displayed readings in a substandard way. This may be caused by a low or dead battery. The batteries should be replaced. If this condition persists after replacing the batteries, then recommend that a qualified HVAC contractor evaluate and repair or replace as necessary.
Limitations: The following items are not included in this inspection: coal stoves, gas logs, chimney flues (except where visible). Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of drafting or sizing in fireplace and stove flues, and also does not determine if prefabricated or zero-clearance fireplaces are installed in accordance with the manufacturer's specifications. The inspector does not perform any evaluations that require a pilot light to be lit, and does not light fires. The inspector provides a basic visual examination of a chimney and any associated wood burning device. The National Fire Protection Association has stated that an in-depth Level 2 chimney inspection should be part of every sale or transfer of property with a wood-burning device. Such an inspection may reveal defects that are not apparent to the home inspector who is a generalist.
Condition of gas-fired fireplaces or stoves: Appeared serviceable
Gas fireplace or stove type: Freestanding stove, In garage
Condition of chimneys and flues: Appeared serviceable
Gas-fired flue type: Direct vent
Pellet Stove: Pellet stove appeared to be in serviceable condition/ Recommend flue inspection prior to first use
31) No spark screen or rain cap was installed at one or more chimney flue terminations. Spark screens reduce the chance of embers exiting the flue and causing fires. They also prevent wildlife (e.g. birds, rodents, raccoons) from entering flues. Rain caps prevent water from entering flues, mixing with combustion deposits and creating caustic chemicals which can corrode flues. They also prevent damage to masonry from freeze-thaw cycles and prevent metal components (e.g. dampers, metal firebox liners) from rusting. Recommend that a qualified person install rain caps with spark screens per standard building practices where missing.
32) Client should be aware that location of direct vents may be a safety hazard to children/tenants. Vent temperature are high when appliances are in use.
Limitations: The following items are not included in this inspection: household appliances such as stoves, ovens, cook tops, ranges, warming ovens, griddles, broilers, dishwashers, trash compactors, refrigerators, freezers, ice makers, hot water dispensers and water filters; appliance timers, clocks, cook functions, self and/or continuous cleaning operations, thermostat or temperature control accuracy, and lights. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of the remaining life of appliances, and does not determine the adequacy of operation of appliances. The inspector does not note appliance manufacturers, models or serial numbers and does not determine if appliances are subject to recalls. Areas and components behind and obscured by appliances are inaccessible and excluded from this inspection.
Condition of counters: Appeared serviceable
Condition of cabinets: Appeared serviceable
Condition of sinks and related plumbing: Appeared serviceable
Condition of dishwasher: Required repair, replacement and/or evaluation (see comments below)
Condition of range, cooktop or oven: Near, at or beyond service life
Range, cooktop or oven type: Electric
Condition of refrigerator: Appeared serviceable
33) The dishwasher was inoperable. Recommend that a qualified specialist evaluate and repair or replace as necessary.
In apartment unit
34) The cooktop exhaust fan was inoperable. Recommend that a qualified person repair or replace as necessary.
35) Kitchen in main house was incomplete: Wiring service supply was missing for dishwasher and stove. No appliances installed. Wiring for oven was in basement. Wiring for dishwasher was under cabinet.
Limitations: The following items are not included in this inspection: overflow drains for tubs and sinks; heated towel racks, saunas, steam generators, clothes washers, clothes dryers. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of washing machine drain lines, washing machine catch pan drain lines, or clothes dryer exhaust ducts. The inspector does not operate water supply or shut-off valves for sinks, toilets, bidets, clothes washers, etc. due to the possibility of valves leaking or breaking when operated. The inspector does not determine if shower pans or tub and shower enclosures are water tight, or determine the completeness or operability of any gas piping to laundry appliances.
Location #A: Full bath, second floor, Main House
Location #B: Full bath, first floor
Location #C: Full bath, second floor, Apartment Unit
Condition of counters: Appeared serviceable
Condition of cabinets: Appeared serviceable
Condition of flooring: Required repairs, replacement and/or evaluation (see comments below), Vinyl tile in bathroom
Condition of sinks and related plumbing: Required repair, replacement and/or evaluation (see comments below)
Condition of toilets: Appeared serviceable
Condition of bathtubs and related plumbing: Appeared serviceable
Condition of shower(s) and related plumbing: Appeared serviceable
Condition of ventilation systems: Required repair, replacement and/or evaluation (see comments below)
36) The bathroom with a shower or bathtub at location(s) #A didn't have an exhaust fan installed. Moisture can accumulate and result in mold, bacteria or fungal growth. Even if the bathroom has a window that opens, it may not provide adequate ventilation, especially during cold weather when windows are closed or when wind blows air into the bathroom. Recommend that a qualified contractor install exhaust fans per standard building practices where missing in bathrooms with showers or bathtubs.
37) One or more leaks were found at water shut-off valves for the sink at location(s) #A. A qualified plumber should repair as necessary.
Limitations: The following items are not included in this inspection: security, intercom and sound systems; communications wiring; central vacuum systems; elevators and stair lifts; cosmetic deficiencies such as nail-pops, scuff marks, dents, dings, blemishes or issues due to normal wear and tear in wall, floor and ceiling surfaces and coverings, or in equipment; deficiencies relating to interior decorating; low voltage and gas lighting systems. Any comments made regarding these items are as a courtesy only. Note that the inspector does not evaluate any areas or items which require moving stored items, furnishings, debris, equipment, floor coverings, insulation or similar materials. The inspector does not test for asbestos, lead, radon, mold, hazardous waste, urea formaldehyde urethane, or any other toxic substance. Some items such as window, drawer, cabinet door or closet door operability are tested on a sampled basis. The client should be aware that paint may obscure wall and ceiling defects, floor coverings may obscure floor defects, and furnishings may obscure wall, floor and floor covering defects. If furnishings were present during the inspection, recommend a full evaluation of walls, floors and ceilings that were previously obscured when possible. Determining the cause and/or source of odors is not within the scope of this inspection.
Condition of exterior entry doors: Appeared serviceable
Exterior door material: Wood, Metal
Condition of interior doors: Appeared serviceable
Condition of windows and skylights: Appeared serviceable
Type(s) of windows: Vinyl
Condition of walls and ceilings: Required repairs, replacement and/or evaluation (see comments below)
Wall type or covering: Drywall or plaster
Ceiling type or covering: Drywall or plaster
Condition of flooring: Appeared serviceable
Flooring type or covering: Wood or wood products, Laminate, Tile
Condition of stairs, handrails and guardrails: Appeared serviceable
38) Stains and elevated levels of moisture were found in one or more ceiling areas. The stains appear to be due to an active plumbing leak. Recommend that a qualified contractor evaluate and repair as necessary.
Active leak apparent in living room from second floor bathroom sink valve.
39) In second floor bathroom: Vinyl floor tiles were installed in one or more "wet" areas (e.g. kitchen, mud room, bathroom, laundry room). Spilled water can penetrate seams and damage the sub-floor. Recommend that a qualified contractor install continuous waterproof flooring in wet areas as necessary.
40) Minor cracks, nail pops and/or blemishes were found in walls and/or ceilings in one or more areas. Cracks and nail pops are common, are often caused by lumber shrinkage or minor settlement, and can be more or less noticeable depending on changes in humidity. They did not appear to be a structural concern, but the client may wish to repair these for aesthetic reasons. For recurring cracks, consider using an elastic crack covering product: https://www.reporthost.com/?ECC
Limitations: This report only includes findings from accessible and visible areas on the day of the inspection. In addition to the inaccessible areas documented in this report, examples of other inaccessible areas include: sub areas less than 18 inches in height; attic areas less than 5 feet in height, areas blocked by ducts, pipes or insulation; areas where locks or permanently attached covers prevent access; areas where insulation would be damaged if traversed; areas obscured by vegetation. All inaccessible areas are subject to infestation or damage from wood-destroying organisms. The inspector does not move furnishings, stored items, debris, floor or wall coverings, insulation, or other materials as part of the inspection, nor perform destructive testing. Wood-destroying organisms may infest, re-infest or become active at any time. No warranty is provided as part of this inspection.
Visible evidence of active wood-destroying insects: No
Visible evidence of active wood decay fungi: No
Visible evidence of past wood-destroying insects: No
Visible evidence of past wood decay fungi: No
Visible evidence of damage by wood-destroying insects: No
Visible evidence of damage by wood decay fungi: No
Visible evidence of conditions conducive to wood-destroying organisms: Yes, Garage siding in contact with soil and siding damage on main house/holes in siding
This report is the exclusive property of Millyard Home Inspection and the Client.