326 Nelson St SW Unit 504 Atlanta GA 30313-1352 404-836-0224 Jud@inspectitllc.Com Www.Inspectitllc.Com
Inspector: Jud Rowell
Property Inspection Report
40 Hillsborough Ct Sharpsburg GA 30277-3028
Saturday, December 21, 2019
This report published on Sunday, December 22, 2019 10:35:43 AM EST
This report is the exclusive property of Inspectit LLC and the client(s) listed in the report title. Use of this report by any unauthorized persons is prohibited.
How to Read this Report
This report is organized by the property's functional areas. Within each functional area, descriptive information is listed first and is shown in bold type. Items of concern follow descriptive information.
Concerns are shown and sorted according to these types:
Poses a safety hazard
Correction likely involves a significant expense
Recommend repairing or replacing
Recommend repair and/or maintenance
Recommend ongoing maintenance
Recommend evaluation by a specialist
Item or component is in serviceable condition
For your information
Click here for a glossary of building construction terms.Contact your inspector If there are terms that you do not understand, or visit the glossary of construction terms at https://www.reporthost.com/glossary.asp
Client present for discussion at end of inspection: No
Weather conditions during inspection: Rain
Temperature during inspection: Cold
Inspection fee: 245.00
Payment method: Invoiced
Type of building: Single family
Buildings inspected: One house
Age of main building: Mmm
Front of building faces: East
Main entrance faces: East
1) Microbial growths were found at one or more locations in the garage. It is beyond the scope of this inspection to identify what substance or organism this staining is. However such staining is normally caused by excessively moist conditions, which in turn can be caused by plumbing or building envelope leaks and/or substandard ventilation. These conducive conditions should be corrected before making any attempts to remove or correct the staining. Normally affected materials such as drywall are removed, enclosed affected spaces are allowed to dry thoroughly, a mildewcide may be applied, and only then is drywall reinstalled. For evaluation and possible mitigation, consult with a qualified industrial hygienist or mold/moisture mitigation specialist. For more information, visit: http://www.reporthost.com/?MOLDCDC http://www.reporthost.com/?MOLDEPA
Limitations: Unless specifically included in the inspection, the following items and any related equipment, controls, electric systems and/or plumbing systems are excluded from this inspection: detached buildings or structures; fences and gates; retaining walls; underground drainage systems, catch basins or concealed sump pumps; swimming pools and related safety equipment, spas, hot tubs or saunas; whether deck, balcony and/or stair membranes are watertight; trees, landscaping, properties of soil, soil stability, erosion and erosion control; ponds, water features, irrigation or yard sprinkler systems; sport courts, playground, recreation or leisure equipment; areas below the exterior structures with less than 3 feet of vertical clearance; invisible fencing; sea walls, docks and boathouses; retractable awnings. Any comments made regarding these items are as a courtesy only.
Site profile: Minor slope
Condition of driveway: Appeared serviceable
Driveway material: Poured in place concrete
Condition of sidewalks and/or patios: Appeared serviceable
Sidewalk material: Poured in place concrete
Condition of decks, porches and/or balconies: Appeared serviceable
Condition of stairs, handrails and guardrails: Appeared serviceable
Exterior stair material: Wood
2) Handrails at one or more flights of stairs were loose. This is a safety hazard. Recommend that a qualified person repair as necessary.
3) Wooden deck or porch surfaces and/or railings were overdue for normal maintenance. Recommend that a qualified person clean and preserve as necessary. Where decks have been coated with a finish such as opaque stains or paint, it may be too difficult to strip the finish and apply anything but paint or opaque stain. Where transparent stain or penetrating oil has been applied in the past, recommend that a penetrating oil be used. For more information, visit: http://www.reporthost.com/?PENOIL http://www.reporthost.com/?DKMAIN
Limitations: The inspector performs a visual inspection of accessible components or systems at the exterior. Items excluded from this inspection include below-grade foundation walls and footings; foundations, exterior surfaces or components obscured by vegetation, stored items or debris; wall structures obscured by coverings such as siding or trim. Some items such as siding, trim, soffits, vents and windows are often high off the ground, and may be viewed using binoculars from the ground or from a ladder. This may limit a full evaluation. Regarding foundations, some amount of cracking is normal in concrete slabs and foundation walls due to shrinkage and drying. Note that the inspector does not determine the adequacy of seismic reinforcement.
Wall inspection method: Viewed from ground
Condition of wall exterior covering: Appeared serviceable
Apparent wall structure: Wood frame
Wall covering: Vinyl, Brick veneer
Condition of foundation and footings: Appeared serviceable
Apparent foundation type: Unfinished basement
Foundation/stem wall material: Poured in place concrete
Footing material (under foundation stem wall): Poured in place concrete
4) Some sections of siding and/or trim were loose. Recommend that a qualified person repair, replace or install siding or trim as necessary.
5) Vegetation such as trees, shrubs and/or vines was in contact with or close to the building exterior. Vegetation can serve as a pathway for wood-destroying insects and can retain moisture against the exterior after it rains. This is a conducive condition for wood-destroying organisms. Recommend pruning, moving or removing vegetation as necessary to maintain at least 6 inches of space between it and the building exterior. A 1-foot clearance is better.
6) Trees were in contact with or were close to the building at one or more locations. Damage to the building can occur, especially during high winds, or may have already occurred (see other comments in this report). Recommend that a qualified tree service contractor or certified arborist remove trees as necessary to prevent damage to the building exterior.
Limitations: Structural components such as joists and beams, and other components such as piping, wiring and/or ducting that are obscured by under-floor insulation are also excluded from this inspection. Note that the inspector does not determine if support posts, columns, beams, joists, studs, trusses, etc. are of adequate size, spanning or spacing.
The inspector does not guarantee or warrant that water will not accumulate in the basement in the future. Access to the basement during all seasons and during prolonged periods of all types of weather conditions (e.g. heavy rain, melting snow) would be needed to do so. The inspector does not determine the adequacy of basement floor or stairwell drains, or determine if such drains are clear or clogged.
Note that all basement areas should be checked periodically for water intrusion, plumbing leaks and pest activity.
Condition of exterior entry doors: Appeared serviceable
Exterior door material: Metal
Condition of floor substructure above: Appeared serviceable
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; solar roofing components. Any comments made regarding these items are made as a courtesy only. Note that the inspector does not provide an estimate of remaining life on the roof surface material, nor guarantee that leaks have not occurred in the roof surface, skylights or roof penetrations in the past. Regarding roof leaks, only active leaks, visible evidence of possible sources of leaks, and evidence of past leaks observed during the inspection are reported on as part of this inspection. The inspector does not guarantee or warrant that leaks will not occur in the future. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high wind and rain, melting snow) would be needed to do so. Regarding the roof drainage system, unless the inspection was conducted during and after prolonged periods of heavy rain, the inspector was unable to determine if gutters, downspouts and extensions performed adequately or were leak-free.
Roof inspection method: Viewed with inspection pole.
Condition of roof surface material: Appeared serviceable
Roof surface material: Asphalt or fiberglass composition shingles
Roof type: Gable
Apparent number of layers of roof surface material: One
Condition of exposed flashings: Appeared serviceable
Condition of gutters, downspouts and extensions: Appeared serviceable
7) Extensions such as splash blocks or drain pipes for one or more downspouts were substandard and/or damaged. Water can accumulate around the building foundation or inside crawl spaces or basements as a result. Recommend that a qualified person install, replace or repair extensions as necessary so rainwater drains away from the structure.
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; areas and components obscured by insulation. Any comments made regarding these items are made as a courtesy only. The inspector does not determine the adequacy of the attic ventilation system. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high/low temperatures, high/low humidity, high wind and rain, melting snow) would be needed to do so. The inspector is not a licensed engineer and does not determine the adequacy of roof structure components such as trusses, rafters or ceiling beams, or their spacing or sizing.
Attic inspection method: Traversed
Condition of roof structure: Appeared serviceable
Roof structure type: Rafters
Ceiling structure: Ceiling joists
Condition of insulation in attic (ceiling, skylight chase, etc.): Appeared serviceable
Ceiling insulation material: Fiberglass loose fill
Condition of roof ventilation: Appeared serviceable
Roof ventilation type: Ridge vent(s)
9) Rodent traps were found in the attic. Recommend monitoring and if rodents are found recommend a pest control professional repair as necessary.
Limitations: The following items are not included in this inspection: generator systems, transfer switches, surge suppressors, inaccessible or concealed wiring; underground utilities and systems; low-voltage lighting or lighting on timers or sensors. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of grounding or bonding, if this system has an adequate capacity for the client's specific or anticipated needs, or if this system has any reserve capacity for additions or expansion. The inspector does not operate circuit breakers as part of the inspection, and does not install or change light bulbs. The inspector does not evaluate every wall switch or receptacle, but instead tests a representative number of them per various standards of practice. When furnishings, stored items or child-protective caps are present some receptacles are usually inaccessible and are not tested; these are excluded from this inspection. Receptacles that are not of standard 110 volt configuration, including 240-volt dryer receptacles, are not tested and are excluded. The functionality of, power source for and placement of smoke and carbon monoxide alarms is not determined as part of this inspection. Upon taking occupancy, proper operating and placement of smoke and carbon monoxide alarms should be verified and batteries should be changed. These devices have a limited lifespan and should be replaced every 10 years. The inspector attempts to locate and evaluate all main and sub-panels. However, panels are often concealed. If panels are found after the inspection, a qualified electrician should evaluate and repair if necessary. The inspector attempts to determine the overall electrical service size, but such estimates are not guaranteed because the overall capacity may be diminished by lesser-rated components in the system. Any repairs recommended should be made by a licensed electrician.
Electric service condition: Appeared serviceable
Primary service type: Underground
Number of service conductors: 3
Service voltage (volts): 120-240
Estimated service amperage: 200
Primary service overload protection type: Circuit breakers
Main disconnect rating (amps): 200
Condition of main service panel: Appeared serviceable
Location of main service panel #A: Building exterior
Location of main disconnect: At main disconnect panel outside
Carbon monoxide alarms installed: No, recommend install
11) One or more wall switches were substandard. The light switch popped when turned on and off.. Recommend that a qualified electrician replace worn switches as necessary.
12) One or more cover plates for switches, receptacles (outlets) or junction boxes were missing or broken. These plates are intended to contain fire and prevent electric shock from occurring due to exposed wires. Recommend that a qualified person install cover plates where necessary.
13) Batteries in all the smoke alarms should be replaced after taking occupancy, and annually in the future. "Chirping" noises emitted from smoke alarms typically indicate that batteries need replacing. For more information, visit: http://www.reporthost.com/?SMKALRM
14) One or more globes or covers for light fixtures were missing or damaged. Recommend replacing as necessary to avoid exposed bulbs. With closet lighting or where flammable stored objects are near light fixtures, missing or broken covers can be a fire hazard.
15) One or more circuit breakers in panel(s) #A were in the tripped position. Consult with the property owner to determine why breakers were tripped or off, and that a qualified electrician evaluate and repair if necessary. Note that the inspector does not operate circuit breakers.
16) One or more light fixtures were inoperable (didn't turn on when nearby switches were operated). Recommend further evaluation by replacing bulbs and/or consulting with the property owner. If replacing bulbs doesn't work and/or no other switch(es) can be found, then recommend that a qualified electrician evaluate and repair or replace light fixtures as necessary.
Limitations: The following items are not included in this inspection: private/shared wells and related equipment; private sewage disposal systems; hot tubs or spas; main, side and lateral sewer lines; gray water systems; pressure boosting systems; trap primers; incinerating or composting toilets; fire suppression systems; water softeners, conditioners or filtering systems; plumbing components concealed within the foundation or building structure, or in inaccessible areas such as below tubs; underground utilities and systems; overflow drains for tubs and sinks; backflow prevention devices. Any comments made regarding these items are as a courtesy only. Note that the inspector does not operate water supply or shut-off valves due to the possibility of valves leaking or breaking when operated. The inspector does not test for lead in the water supply, the water pipes or solder, does not determine if plumbing and fuel lines are adequately sized, and does not determine the existence or condition of underground or above-ground fuel tanks.
Condition of service and main line: Appeared serviceable
Water pressure (psi): 55
Location of main water shut-off: Basement
Condition of supply lines: Appeared serviceable
Supply pipe material: CPVC plastic
Condition of drain pipes: Appeared serviceable
Drain pipe material: Plastic
Condition of waste lines: Appeared serviceable
Waste pipe material: Plastic
Vent pipe condition: Appeared serviceable
Vent pipe material: Plastic
Type of irrigation system supply source: Public
Location of main fuel shut-off valve: At gas meter
Limitations: Evaluation of and determining the adequacy or completeness of the following items are not included in this inspection: water recirculation pumps; solar water heating systems; Energy Smart or energy saver controls; catch pan drains. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on water heaters, does not determine if water heaters are appropriately sized, or perform any evaluations that require a pilot light to be lit or a shut-off valve to be operated.
Condition of water heater: Appeared serviceable
Energy source: Natural gas
Capacity (in gallons): 50
Location of water heater: Basement
Hot water temperature tested: Yes
Water temperature (degrees Fahrenheit): 110
Condition of burners: Appeared serviceable
Condition of venting system: Appeared serviceable
17) The estimated useful life for most water heaters is 8-12 years. This water heater appeared to be beyond this age and/or its useful lifespan and may need replacing at any time. Recommend budgeting for a replacement in the near future, or considering replacement now before any leaks occur. The client should be aware that significant flooding can occur if the water heater fails. If not replaced now, consider having a qualified person install a catch pan and drain or a water alarm to help prevent damage if water does leak.
Limitations: The following items are not included in this inspection: humidifiers, dehumidifiers, electronic air filters; solar, coal or wood-fired heat systems; thermostat or temperature control accuracy and timed functions; heating components concealed within the building structure or in inaccessible areas; underground utilities and systems; safety devices and controls (due to automatic operation). Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on heating or cooling system components, does not determine if heating or cooling systems are appropriately sized, does not test coolant pressure, or perform any evaluations that require a pilot light to be lit, a shut-off valve to be operated, a circuit breaker to be turned "on" or a serviceman's or oil emergency switch to be operated. It is beyond the scope of this inspection to determine if furnace heat exchangers are intact and free of leaks. Condensation pans and drain lines may clog or leak at any time and should be monitored while in operation in the future. Where buildings contain furnishings or stored items, the inspector may not be able to verify that a heat source is present in all "liveable" rooms (e.g. bedrooms, kitchens and living/dining rooms).
General heating system type(s): Forced air, Furnace
General heating distribution type(s): Ducts and registers
Condition of forced air heating/(cooling) system: Appeared serviceable
Forced air heating system fuel type: Natural gas
Location of forced air furnace: Basement, Attic
Condition of furnace filters: Appeared serviceable
Condition of forced air ducts and registers: Appeared serviceable
Condition of cooling system and/or heat pump: Appeared serviceable
Cooling system and/or heat pump fuel type: Electric
Type: Split system
Condition of controls: Appeared serviceable
18) The estimated useful life for most heat pumps and air conditioning condensing units is 10-15 years. This unit appeared to be beyond this age and/or its useful lifespan and may need replacing or significant repairs at any time. Recommend budgeting for a replacement in the near future.
Air conditioner year of manufacture: 2003
Recommend asking owner for current service records for review. If there are no current service records recommend a service be performed by a qualified professional.
19) The estimated useful life for most forced air furnaces is 15-20 years. This furnace appeared to be near this age and/or its useful lifespan and may need replacing or significant repairs at any time. Recommend budgeting for a replacement in the near future.
Furnace year of manufacture: 2002
Recommend asking owner for current service records for review. If there are no current service records recommend a service be performed by a qualified professional.
20) One or more ceiling fans appeared to be inoperable, or the inspector was unable to find normal controls with which to operate the fan(s). Recommend asking the property owner about their operation, and if necessary, that a qualified electrician evaluate and repair.
Limitations: The following items are not included in this inspection: coal stoves, gas logs, chimney flues (except where visible). Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of drafting or sizing in fireplace and stove flues, and also does not determine if prefabricated or zero-clearance fireplaces are installed in accordance with the manufacturer's specifications. The inspector does not perform any evaluations that require a pilot light to be lit, and does not light fires. The inspector provides a basic visual examination of a chimney and any associated wood burning device. The National Fire Protection Association has stated that an in-depth Level 2 chimney inspection should be part of every sale or transfer of property with a wood-burning device. Such an inspection may reveal defects that are not apparent to the home inspector who is a generalist.
Condition of gas-fired fireplaces or stoves: Appeared serviceable
Gas fireplace or stove type: Metal pre-fab fireplace
23) Recommend that the client review all available documentation for gas-fired fireplaces and stoves. Depending on how they are operated (for routine heating versus ambiance), such appliances may need servicing annually or every few years. Consult with the property owner and/or a qualified specialist to determine if service is needed now.
Limitations: The following items are not included in this inspection: household appliances such as stoves, ovens, cook tops, ranges, warming ovens, griddles, broilers, dishwashers, trash compactors, refrigerators, freezers, ice makers, hot water dispensers and water filters; appliance timers, clocks, cook functions, self and/or continuous cleaning operations, thermostat or temperature control accuracy, and lights. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of the remaining life of appliances, and does not determine the adequacy of operation of appliances. The inspector does not note appliance manufacturers, models or serial numbers and does not determine if appliances are subject to recalls. Areas and components behind and obscured by appliances are inaccessible and excluded from this inspection.
Condition of counters: Appeared serviceable
Condition of sinks and related plumbing: Appeared serviceable
Condition of under-sink food disposal: Appeared serviceable
Condition of dishwasher: Appeared serviceable
Condition of range, cooktop or oven: Appeared serviceable
Range, cooktop or oven type: Natural gas
Type of ventilation: Hood or built into microwave over range or cooktop
Condition of refrigerator: N/A (none installed)
Condition of built-in microwave oven: Appeared serviceable
24) The sink faucet was loose. Recommend that a qualified person repair as necessary.
Condition of sinks and related plumbing: Appeared serviceable
Condition of toilets: Appeared serviceable
Condition of bathtubs and related plumbing: Appeared serviceable
Condition of shower(s) and related plumbing: Appeared serviceable
Condition of ventilation systems: Appeared serviceable
Bathroom and laundry ventilation type: Spot exhaust fans
Gas supply for laundry equipment present: Yes
240 volt receptacle for laundry equipment present: Yes
25) The toilet at location(s) #B and C didn't flush or had a weak flush. Recommend that a qualified plumber evaluate and repair or replace the toilet as necessary.
26) The exhaust fan at location(s) #C was inoperable. Moisture may accumulate and result in mold, bacteria or fungal growth. Recommend that a qualified person clean, repair or replace fans as necessary.
27) Gaps, no caulk, or substandard caulking were found between countertops and backsplashes at location(s) #C. Water can penetrate these areas and cause damage. Recommend that a qualified person repair as necessary. For example, by installing or replacing caulk.
28) Gaps, no caulk, or substandard caulking were found between the shower enclosure and the walls at location(s) #B. Water can penetrate these areas and cause damage. Recommend that a qualified person re-caulk or install caulking as necessary.
Limitations: The following items are not included in this inspection: security, intercom and sound systems; communications wiring; central vacuum systems; elevators and stair lifts; cosmetic deficiencies such as nail-pops, scuff marks, dents, dings, blemishes or issues due to normal wear and tear in wall, floor and ceiling surfaces and coverings, or in equipment; deficiencies relating to interior decorating; low voltage and gas lighting systems. Any comments made regarding these items are as a courtesy only. Note that the inspector does not evaluate any areas or items which require moving stored items, furnishings, debris, equipment, floor coverings, insulation or similar materials. The inspector does not test for asbestos, lead, radon, mold, hazardous waste, urea formaldehyde urethane, or any other toxic substance. Some items such as window, drawer, cabinet door or closet door operability are tested on a sampled basis. The client should be aware that paint may obscure wall and ceiling defects, floor coverings may obscure floor defects, and furnishings may obscure wall, floor and floor covering defects. If furnishings were present during the inspection, recommend a full evaluation of walls, floors and ceilings that were previously obscured when possible. Determining the cause and/or source of odors is not within the scope of this inspection.
Condition of windows and skylights: Required repair, replacement and/or evaluation (see comments below)
Type(s) of windows: Vinyl
Condition of walls and ceilings: Appeared serviceable
Wall type or covering: Drywall
Ceiling type or covering: Drywall
Condition of flooring: Appeared serviceable
Flooring type or covering: Carpet, Wood or wood products, Tile
Condition of stairs, handrails and guardrails: Appeared serviceable
29) Condensation or staining was visible between multi-pane glass in one or more windows. This usually indicates that the seal between the panes of glass has failed or that the desiccant material that absorbs moisture is saturated. As a result, the view through the window may be obscured, the window's R-value will be reduced, and accumulated condensation may leak into the wall structure below. Recommend that a qualified contractor evaluate and repair windows as necessary. Usually, this means replacing the glass in window frames.
Be aware that evidence of failed seals or desiccant may be more or less visible depending on the temperature, humidity, sunlight, etc. Windows or glass-paneled doors other than those that the inspector identified may also have failed seals and need glass replaced. It is beyond the scope of this inspection to identify every window with failed seals or desiccant.
30) Squeaking or creaking noises occur when walking on one or more sections of flooring. This is usually caused by substandard construction practices where the sub-floor decking is not adequately fastened to the framing below. For example, not enough glue was used and/or nails were used rather than screws. In most cases, this is only an annoyance rather than a structural problem. Various solutions such as Squeeeeek No More and Counter Snap fasteners exist to correct this. Repairs to eliminate the squeaks or creaks may be more or less difficult depending on the floor covering and the access to the underside of the sub-floor. Recommend that a qualified contractor evaluate and repair as necessary. For more information, visit: http://www.reporthost.com/?SQUEAK
31) One or more window screens were damaged or deteriorated. These window(s) may not provide ventilation during months when insects are active. Recommend replacing window screens as necessary.
32) Some interior door hardware (locksets) were damaged. Recommend that a qualified person repair or replace as necessary.
33) Windows in the the master bedroom were damaged. Recommend a qualified professional evaluate and repair as necessary.
34) One or more exterior doors appeared to come off track. Recommend a qualified professional evaluate and repair as necessary.
Limitations: This report only includes findings from accessible and visible areas on the day of the inspection. In addition to the inaccessible areas documented in this report, examples of other inaccessible areas include: sub areas less than 18 inches in height; attic areas less than 5 feet in height, areas blocked by ducts, pipes or insulation; areas where locks or permanently attached covers prevent access; areas where insulation would be damaged if traversed; areas obscured by vegetation. All inaccessible areas are subject to infestation or damage from wood-destroying organisms. The inspector does not move furnishings, stored items, debris, floor or wall coverings, insulation, or other materials as part of the inspection, nor perform destructive testing. Wood-destroying organisms may infest, re-infest or become active at any time. No warranty is provided as part of this inspection.
Visible evidence of active wood-destroying insects: No
Visible evidence of active wood decay fungi: No
Visible evidence of past wood-destroying insects: No
Visible evidence of past wood decay fungi: No
Visible evidence of damage by wood-destroying insects: No
Visible evidence of damage by wood decay fungi: No
Visible evidence of conditions conducive to wood-destroying organisms: No