This report published on Monday, November 11, 2019 9:45:33 PM CST
This report is the exclusive property of this inspection company and the client(s) listed in the report title. Use of this report by any unauthorized persons is prohibited.
How to Read this Report
This report is organized by the property's functional areas. Within each functional area, descriptive information is listed first and is shown in bold type. Items of concern follow descriptive information.
Concerns are shown and sorted according to these types:
Poses a safety hazard
Correction likely involves a significant expense
Suggest repairing or replacing
Suggest repair and/or maintenance
Correction likely involves only a minor expense
Recommend ongoing maintenance
Recommend evaluation by a specialist
Recommend monitoring in the future
Item or component is in serviceable condition
For your information
Click here for a glossary of building construction terms.Contact your inspector If there are terms that you do not understand, or visit the glossary of construction terms at https://www.reporthost.com/glossary.asp
Limitations: Unless specifically included in the inspection, the following items and any related equipment, controls, electric systems and/or plumbing systems are excluded from this inspection: detached buildings or structures; fences and gates; retaining walls; underground drainage systems, catch basins or concealed sump pumps; swimming pools and related safety equipment, spas, hot tubs or saunas; whether deck, balcony and/or stair membranes are watertight; trees, landscaping, properties of soil, soil stability, erosion and erosion control; ponds, water features, irrigation or yard sprinkler systems; sport courts, playground, recreation or leisure equipment; areas below the exterior structures with less than 3 feet of vertical clearance; invisible fencing; sea walls, docks and boathouses; retractable awnings. Any comments made regarding these items are as a courtesy only.
Site profile: Level
Condition of driveway: Appeared serviceable
Driveway material: Gravel
Condition of sidewalks and/or patios: Appeared serviceable
Sidewalk material: Stones
Condition of deck, patio and/or porch covers: Appeared serviceable
Deck, patio, porch cover material and type: Covered (Refer to Roof section)
Condition of decks, porches and/or balconies: Appeared serviceable
Condition of stairs, handrails and guardrails: Appeared serviceable
Exterior stair material: Masonry
2) Vegetation was overgrown around equipment for one or more utilities such as gas or electric meters. Vegetation should be pruned or removed as necessary to allow unobstructed access.
3) Sewer clean out in front yard the screw in plug is damaged. Rear patio has a drain suggest watching that it does not get clogged Flag stone rear patio is uneven with some trip hazards Front steps has some missing mortar from between the brick Crack in front porch slap. May want to fill for appearance. Exposed PVC sewer pipe on the side of the home use caution not to damage.
Limitations: The inspector performs a visual inspection of accessible components or systems at the exterior. Items excluded from this inspection include below-grade foundation walls and footings; foundations, exterior surfaces or components obscured by vegetation, stored items or debris; wall structures obscured by coverings such as siding or trim. Some items such as siding, trim, soffits, vents and windows are often high off the ground, and may be viewed using binoculars from the ground or from a ladder. This may limit a full evaluation. Regarding foundations, some amount of cracking is normal in concrete slabs and foundation walls due to shrinkage and drying. Note that the inspector does not determine the adequacy of seismic reinforcement.
Wall inspection method: Viewed from ground
Condition of wall exterior covering: Appeared serviceable
Apparent wall structure: Wood frame
Wall covering: Wood fiber
Condition of foundation and footings: Appeared serviceable
Apparent foundation type: Crawl space
Footing material (under foundation stem wall): Poured in place concrete
4) Some sections of siding and/or trim were deteriorated and/or split. Recommend that a qualified person repair, replace or install siding or trim as necessary.
5) Soil was in contact with or less than 6 inches from siding or trim. Regardless of what material is used for siding, it should not be in contact with the soil. If made of wood, siding or trim will eventually rot. For other materials, ground or surface water can infiltrate siding or trim and cause damage to the wall structure. Wood-destroying insects are likely to infest and damage the wall structure. This is a conducive condition for wood-destroying organisms. Recommend grading or removing soil as necessary to maintain a 6-inch clearance. Note that damage from fungal rot and/or insects may be found when soil is removed, and repairs may be necessary.
6) Fence(s) were attached to or in contact with the building exterior. Such attachments can serve as a pathway for wood-destroying insects and can retain moisture against the exterior after it rains. This is a conducive condition for wood-destroying organisms. Recommend that a qualified person repair as necessary so there is at least a 2-inch gap between fences and building exteriors.
7) Vegetation such as trees, shrubs and/or vines was in contact with or close to the building exterior. Vegetation can serve as a pathway for wood-destroying insects and can retain moisture against the exterior after it rains. This is a conducive condition for wood-destroying organisms. Recommend pruning, moving or removing vegetation as necessary to maintain at least 6 inches of space between it and the building exterior. A 1-foot clearance is better.
8) The paint or stain finish in some areas was failing (e.g. peeling, faded, worn, thinning). Siding and trim with a failing finish can be damaged by moisture. Recommend that a qualified contractor prep (e.g. clean, scrape, sand, prime, caulk) and repaint or restain the building exterior where necessary and per standard building practices. Any repairs needed to the siding or trim should be made prior to this.
9) Caulk was missing and/or deteriorated in some areas. For example, around windows, around doors, at siding butt joints and/or at siding-trim junctions. Recommend that a qualified person renew or install caulk as necessary. Where gaps are wider than 1/4 inch, an appropriate material other than caulk should be used. For more information, visit: http://www.reporthost.com/?CAULK
10) Various areas of missing paint, loose and rotted wood on the exterior of the upper porch exterior.
11) Most of the windows of the home have been screwed shut and will not open.
Limitations: Structural components such as joists and beams, and other components such as piping, wiring and/or ducting that are obscured by under-floor insulation are excluded from this inspection. The inspector does not determine if support posts, columns, beams, joists, studs, trusses, etc. are of adequate size, spanning or spacing.
The inspector does not guarantee or warrant that water will not accumulate in the crawl spaces in the future. Complete access to all crawl space areas during all seasons and during prolonged periods of all types of weather conditions (e.g. heavy rain, melting snow) would be needed to do so.
The inspector attempts to locate all crawl space access points and areas. Access points may be obscured or otherwise hidden by furnishings or stored items. In such cases, the client should ask the property owner where all access points are that are not described in this inspection, and have those areas inspected. Note that crawl space areas should be checked at least annually for water intrusion, plumbing leaks and pest activity.
Crawl space inspection method: Traversed
Condition of floor substructure above: Appeared serviceable, Not determined (inaccessible or obscured)
Pier or support post material: Concrete
Beam material: Solid wood
Floor structure above: Solid wood joists
Condition of insulation underneath floor above: Appeared serviceable
Insulation material underneath floor above: Spray Foam
Condition of vapor barrier: Appeared serviceable
Condition of crawl space ventilation: Appeared serviceable
12) Views of under the home.
13) The dryer vent pipe exhaust under the home. The pipe is a long run for air to be pushed although 35 feet is the maximum length but deduct 5 feet per 90 degree bned. Suggest re-routing to shorten the run if needed.
14) PVC pipe is connected to older cast iron pipe. These neoprene fitting work well but do not last forever. Under the home is damp. There are signs where water has flowed under the home and it appeared to enter where the entrance panel is. There were many very small toads under the home. This indicates that water has possible held under the water long enough for toads to hatch.
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; solar roofing components. Any comments made regarding these items are made as a courtesy only. Note that the inspector does not provide an estimate of remaining life on the roof surface material, nor guarantee that leaks have not occurred in the roof surface, skylights or roof penetrations in the past. Regarding roof leaks, only active leaks, visible evidence of possible sources of leaks, and evidence of past leaks observed during the inspection are reported on as part of this inspection. The inspector does not guarantee or warrant that leaks will not occur in the future. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high wind and rain, melting snow) would be needed to do so. Regarding the roof drainage system, unless the inspection was conducted during and after prolonged periods of heavy rain, the inspector was unable to determine if gutters, downspouts and extensions performed adequately or were leak-free.
Roof inspection method: Traversed
Condition of roof surface material: Appeared serviceable
Roof surface material: Asphalt or fiberglass composition shingles
Roof type: Gable
Apparent number of layers of roof surface material: One
Condition of exposed flashings: Appeared serviceable
Condition of gutters, downspouts and extensions: Appeared serviceable
15) Some composition shingles were cracked. Leaks can occur as a result. This is a conducive condition for wood-destroying organisms. Recommend that a qualified contractor repair as necessary. For example, by replacing shingles.
16) Nail heads were exposed at one or more shingles. More than just a few exposed nail heads may indicate a substandard roof installation. Recommend applying an approved sealant over exposed nail heads now and as necessary in the future to prevent leaks.
17) There is evidence that the roof has had areas of repair
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; areas and components obscured by insulation. Any comments made regarding these items are made as a courtesy only. The inspector does not determine the adequacy of the attic ventilation system. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high/low temperatures, high/low humidity, high wind and rain, melting snow) would be needed to do so. The inspector is not a licensed engineer and does not determine the adequacy of roof structure components such as trusses, rafters or ceiling beams, or their spacing or sizing.
Attic inspection method: Traversed
Condition of roof structure: Appeared serviceable
Roof structure type: Rafters
Ceiling structure: Ceiling joists
Condition of insulation in attic (ceiling, skylight chase, etc.): Required repair, replacement and/or evaluation (see comments below)
Ceiling insulation material: Fiberglass roll or batt
Approximate attic insulation R value (may vary in areas): R-19
Vapor retarder: None
Condition of roof ventilation: Required repair, replacement and/or evaluation (see comments below)
19) One or more sections of the roof structure appeared to have substandard ventilation, soffit vents were missing and/or ridge vents were missing. This can result in high attic and roof surface temperatures, reduce the life of the roof covering materials, and/or increase cooling costs. High levels of moisture are also likely to accumulate in the roof structure or attic, and can be a conducive condition for wood-destroying organisms. Standard building practices require one free square foot of ventilation for every 150 square feet of attic space, and that vents be evenly distributed between the lowest points of the roof structure and the highest points to promote air circulation. Often this means that both soffit vents and ridge or gable end vents are installed. Recommend that a qualified contractor evaluate and repair per standard building practices.
20) One or more attic access hatches or doors were not insulated, or had substandard insulation. Recommend installing insulation as necessary and per current standards at hatches or doors for better energy efficiency. For more information, visit: http://www.reporthost.com/?ATTACC
21) The ceiling insulation in one or more areas of the attic was missing. Heating and cooling costs may be higher due to reduced energy efficiency. Recommend that a qualified person repair, replace or install insulation as necessary and per standard building practices (typically R-38).
22) One electrical junction box in the attic for the power vent fan is missing a cover.
Limitations: The inspector does not determine the adequacy of firewall ratings. Requirements for ventilation in garages vary between municipalities.
Type: Detached, Garage
Condition of garage vehicle door(s): Appeared serviceable
Type of garage vehicle door: Sectional
Number of vehicle doors: 1
Condition of automatic opener(s): Appeared serviceable
Mechanical auto-reverse operable (reverses when meeting reasonable resistance during closing): Yes
Condition of garage floor: Appeared serviceable
Garage ventilation: Exists
23) One or more garage vehicle doors were damaged or deteriorated. Recommend that a qualified contractor repair or replace door(s) as necessary.
24) The rear garage is in functional condition. Vinyl on two sides and corrugated metal roofing on the west and north sides. Some damage to the vinyl, window on the east end has a broken glass. The roof has some minor leaks and one that has been repaired. The east rear corner of the roof appears to have a leak giving the color of the soffit material. Power supply mast roof jack is leaking.
25) The electrical supply mast roof jack or gasket is deteriorated and allowing rain water to enter. The east end of the roof has some tree damage to the ridge cap and edge.
Limitations: The following items are not included in this inspection: generator systems, transfer switches, surge suppressors, inaccessible or concealed wiring; underground utilities and systems; low-voltage lighting or lighting on timers or sensors. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of grounding or bonding, if this system has an adequate capacity for the client's specific or anticipated needs, or if this system has any reserve capacity for additions or expansion. The inspector does not operate circuit breakers as part of the inspection, and does not install or change light bulbs. The inspector does not evaluate every wall switch or receptacle, but instead tests a representative number of them per various standards of practice. When furnishings, stored items or child-protective caps are present some receptacles are usually inaccessible and are not tested; these are excluded from this inspection. Receptacles that are not of standard 110 volt configuration, including 240-volt dryer receptacles, are not tested and are excluded. The functionality of, power source for and placement of smoke and carbon monoxide alarms is not determined as part of this inspection. Upon taking occupancy, proper operating and placement of smoke and carbon monoxide alarms should be verified and batteries should be changed. These devices have a limited lifespan and should be replaced every 10 years. The inspector attempts to locate and evaluate all main and sub-panels. However, panels are often concealed. If panels are found after the inspection, a qualified electrician should evaluate and repair if necessary. The inspector attempts to determine the overall electrical service size, but such estimates are not guaranteed because the overall capacity may be diminished by lesser-rated components in the system. Any repairs recommended should be made by a licensed electrician.
Electric service condition: Appeared serviceable
Primary service type: Overhead
Service voltage (volts): 120-240
Estimated service amperage: 200
Primary service overload protection type: Circuit breakers
Service entrance conductor material: Stranded copper
Main disconnect rating (amps): 200
System ground: Ground rod(s) in soil
Condition of main service panel: Appeared serviceable
Condition of sub-panel(s): Appeared serviceable
Location of main service panel #A: Building exterior
Location of main service panel #B: Living room
Location of sub-panel #C: Garage
Location of main disconnect: Breaker at top of main service panel
Arc fault circuit interrupter (AFCI) protection present: No
Smoke alarms installed: Yes, but not tested
Carbon monoxide alarms installed: Yes, but not tested
26) One or more electric receptacles (outlets) at the garage and/or exterior had no visible ground fault circuit interrupter (GFCI) protection, or the inspector was unable to determine if GFCI protection was present. If not GFCI-protected, receptacles in wet areas pose a shock hazard. Recommend that a qualified electrician evaluate and install GFCI protection if necessary and per standard building practices. General guidelines for GFCI-protected receptacles include the following locations:
Outdoors (since 1973)
Bathrooms (since 1975)
Garages (since 1978)
Kitchens (since 1987)
Crawl spaces and unfinished basements (since 1990)
27) One or more electric receptacles (outlets) were incorrectly wired with an open neutral. Recommend that a qualified electrician repair as necessary.
More than on outlet in the upstairs rooms.
28) One or more cover plates for switches, receptacles (outlets) or junction boxes were missing or broken. These plates are intended to contain fire and prevent electric shock from occurring due to exposed wires. Recommend that a qualified person install cover plates where necessary. One found in the attic only
29) Based on the age of this structure and the appearance of existing smoke alarms, the alarms may have been installed more than 10 years ago. According to National Fire Protection Association, aging smoke alarms don't operate as efficiently and often are the source for nuisance alarms. Older smoke alarms are estimated to have a 30% probability of failure within the first 10 years. Newer smoke alarms do better, but should be replaced after 10 years. Unless you know that the smoke alarms are new, replacing them when moving into a new residence is also recommended by NFPA. For more information, visit: http://www.reporthost.com/?SMKALRMLS
30) Few receptacles (outlets) were installed in one or more areas by modern standards. This can result in "octopus" wiring with extension cords, which is a fire hazard. Consult with a qualified electrician about upgrading circuits with additional receptacles per standard building practices. Some rooms had very few receptacles which is common with a home of this age
31) 2- slot outlet was found in front room. It does not have power.
32) Bulbs in one or more light fixtures were missing or broken. These light fixtures couldn't be fully evaluated. If replacement bulbs are inoperable, then recommend that a qualified electrician evaluate and repair or replace light fixtures as necessary.
33) Sub panel for hot tub is assumed to not be energized. Views of the interior and exterior electrical service panels
34) One or more Electrical outlets in the home was not flush with the wall or had gaps around the edges. Some receptacles were not flush or were crooked.
35) Door bell did not work, camera door bells were in place.
Limitations: The following items are not included in this inspection: private/shared wells and related equipment; private sewage disposal systems; hot tubs or spas; main, side and lateral sewer lines; gray water systems; pressure boosting systems; trap primers; incinerating or composting toilets; fire suppression systems; water softeners, conditioners or filtering systems; plumbing components concealed within the foundation or building structure, or in inaccessible areas such as below tubs; underground utilities and systems; overflow drains for tubs and sinks; backflow prevention devices. Any comments made regarding these items are as a courtesy only. Note that the inspector does not operate water supply or shut-off valves due to the possibility of valves leaking or breaking when operated. The inspector does not test for lead in the water supply, the water pipes or solder, does not determine if plumbing and fuel lines are adequately sized, and does not determine the existence or condition of underground or above-ground fuel tanks.
Condition of service and main line: Appeared serviceable
Water service: Public
Location of main water shut-off: Crawl space, Main shut off was found at the meter only
Condition of supply lines: Appeared serviceable
Supply pipe material: Copper, Galvanized steel
Condition of drain pipes: Appeared serviceable
Drain pipe material: Plastic, Galvanized steel
Condition of waste lines: Appeared serviceable
Waste pipe material: Plastic, Cast iron
Vent pipe condition: Appeared serviceable
Vent pipe material: Plastic, Galvanized steel
Sump pump installed: None visible
Sewage ejector pump installed: None visible
Condition of fuel system: Appeared serviceable
Location of main fuel shut-off valve: At gas meter
36) What appeared to be the main water shut-off valve was located in the crawl space. This is an inconvenient location at best, and may prevent the water from being turned off in a timely manner in the event of a plumbing emergency. Consider having a qualified plumber relocate the shut-off valve to a more convenient location, such as in a closet or a cabinet under a sink.
37) Views of cast iron pipe under the home and connections to PVC pipe
Limitations: Evaluation of and determining the adequacy or completeness of the following items are not included in this inspection: water recirculation pumps; solar water heating systems; Energy Smart or energy saver controls; catch pan drains. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on water heaters, does not determine if water heaters are appropriately sized, or perform any evaluations that require a pilot light to be lit or a shut-off valve to be operated.
Limitations: The following items are not included in this inspection: humidifiers, dehumidifiers, electronic air filters; solar, coal or wood-fired heat systems; thermostat or temperature control accuracy and timed functions; heating components concealed within the building structure or in inaccessible areas; underground utilities and systems; safety devices and controls (due to automatic operation). Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on heating or cooling system components, does not determine if heating or cooling systems are appropriately sized, does not test coolant pressure, or perform any evaluations that require a pilot light to be lit, a shut-off valve to be operated, a circuit breaker to be turned "on" or a serviceman's or oil emergency switch to be operated. It is beyond the scope of this inspection to determine if furnace heat exchangers are intact and free of leaks. Condensation pans and drain lines may clog or leak at any time and should be monitored while in operation in the future. Where buildings contain furnishings or stored items, the inspector may not be able to verify that a heat source is present in all "liveable" rooms (e.g. bedrooms, kitchens and living/dining rooms).
General heating system type(s): Forced air, Furnace
Year of Manufacture: 2006/2005
Capacity in Tons or Kilowatts: 4 ton 2 ton
General heating distribution type(s): Ducts and registers
Condition of forced air heating/(cooling) system: Appeared serviceable
Forced air heating system fuel type: Electric
Condition of furnace filters: Appeared serviceable
Condition of forced air ducts and registers: Appeared serviceable
Type: Split system
39) The estimated useful life for most heat pumps and air conditioning condensing units is 10-15 years. This unit appeared to be near this age and/or its useful lifespan and may need replacing or significant repairs at any time. Recommend budgeting for a replacement in the near future.
40) Smaller upstairs HVAC unit has an air leak on the under side where the plenum connects to the unit.
41) Insulation on the heat pump or air conditioning condensing unit's refrigerant lines was deteriorated or missing in some areas. This may result in reduced efficiency and increased energy costs. Recommend that a qualified person replace or install insulation as necessary.
42) The electrical supply does not have a bushing to hold the wire where it enters the HVAC unit. Smaller unit for upstairs.
43) The inside HVAC unit is not equipped with water sensor to detect excess water in the drain system or under the unit. This sensor will shut off the HVAC unit if the drain clogs and detects the excess water.
Down stairs unit only
44) Exterior HVAC units were built in 2006 3 and 2 ton units
45) Views of the HVAC units. Both are in the attic side by side. The larger unit for downstairs does not have an emergency shut off in the drain system. Both units drain out the same pipe to the ground outside. Condensation drips from the drain lines onto the attic floor.
Limitations: The following items are not included in this inspection: coal stoves, gas logs, chimney flues (except where visible). Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of drafting or sizing in fireplace and stove flues, and also does not determine if prefabricated or zero-clearance fireplaces are installed in accordance with the manufacturer's specifications. The inspector does not perform any evaluations that require a pilot light to be lit, and does not light fires. The inspector provides a basic visual examination of a chimney and any associated wood burning device. The National Fire Protection Association has stated that an in-depth Level 2 chimney inspection should be part of every sale or transfer of property with a wood-burning device. Such an inspection may reveal defects that are not apparent to the home inspector who is a generalist.
Condition of wood-burning fireplaces, stoves: Appeared serviceable
Condition of gas-fired fireplaces or stoves: Appeared serviceable
Gas fireplace or stove type: Freestanding stove
46) Wood burning masonry fireplace has been closed off and the chimney in no longer in place. Gas fireplace is vent less so be sure the carbon monoxide detector is in working condition. The hearth is a little uneven with a crack in the front.
47) The gas fireplace or stove was not fully evaluated because the pilot light was off. The inspector only operates normal controls (e.g. on/off switch or thermostat) and does not light pilot lights or operate gas shut-off valves. Recommend that the client review all documentation for such gas appliances and familiarize themselves with the lighting procedure. If necessary, a qualified specialist should assist in lighting such appliances, and make any needed repairs.
48) Normal controls such as an on/off switch, thermostat or remote control were not found for one or more gas fireplaces or stoves, or the controls had no effect on the appliance(s). As a result, the inspector was unable to make a full evaluation. Consult with the property owner, review all documentation for such gas appliances, and become familiar with the lighting procedure. If necessary, a qualified specialist should assist in lighting such appliances, and make any needed repairs.
Limitations: The following items are not included in this inspection: household appliances such as stoves, ovens, cook tops, ranges, warming ovens, griddles, broilers, dishwashers, trash compactors, refrigerators, freezers, ice makers, hot water dispensers and water filters; appliance timers, clocks, cook functions, self and/or continuous cleaning operations, thermostat or temperature control accuracy, and lights. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of the remaining life of appliances, and does not determine the adequacy of operation of appliances. The inspector does not note appliance manufacturers, models or serial numbers and does not determine if appliances are subject to recalls. Areas and components behind and obscured by appliances are inaccessible and excluded from this inspection.
Condition of counters: Appeared serviceable
Condition of cabinets: Appeared serviceable
Condition of sinks and related plumbing: Appeared serviceable
Condition of under-sink food disposal: Appeared serviceable
Condition of dishwasher: Appeared serviceable
Condition of range, cooktop or oven: Appeared serviceable
Range, cooktop or oven type: Natural gas
Type of ventilation: Hood or built into microwave over range or cooktop
Condition of refrigerator: Appeared serviceable
Condition of built-in microwave oven: Appeared serviceable
49) The range could tip forward. An anti-tip bracket may not be installed. This is a potential safety hazard since the range can tip forward when weight is applied to the open door, such as when a small child climbs on it or if heavy objects are dropped on it. Anti-tip brackets have been sold with all free-standing ranges since 1985. Recommend installing an anti-tip bracket to eliminate this safety hazard. For more information, visit: http://www.reporthost.com/?ATB
50) An exhaust hood was installed over the cook top or range, but the fan recirculated the exhaust air back into the kitchen. This may be due to no duct being installed, baffles at the front of the hood not being installed, or a problem with the duct. This can be a nuisance for odor and grease accumulation. Where a gas-fired range or cook top is installed, carbon monoxide and excessive levels of moisture can accumulate in living spaces. Recommend that a qualified contractor evaluate and repair as necessary so exhaust air is ducted outdoors.
51) Upstairs kitchen counter leans to the left. Small freezer has excess ice built up
Limitations: The following items are not included in this inspection: overflow drains for tubs and sinks; heated towel racks, saunas, steam generators, clothes washers, clothes dryers. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of washing machine drain lines, washing machine catch pan drain lines, or clothes dryer exhaust ducts. The inspector does not operate water supply or shut-off valves for sinks, toilets, bidets, clothes washers, etc. due to the possibility of valves leaking or breaking when operated. The inspector does not determine if shower pans or tub and shower enclosures are water tight, or determine the completeness or operability of any gas piping to laundry appliances.
Location #A: Full bath, first floor
Location #B: Half bath, first floor
Location #C: Full bath, second floor
Condition of counters: Appeared serviceable
Condition of cabinets: Appeared serviceable
Condition of flooring: Appeared serviceable
Condition of sinks and related plumbing: Appeared serviceable
Bathroom Sink Stoppers: Not operational, C
Condition of toilets: Appeared serviceable
Condition of bathtubs and related plumbing: Appeared serviceable
Condition of shower(s) and related plumbing: Appeared serviceable
Condition of ventilation systems: Missing
Gas supply for laundry equipment present: No, Not determined
240 volt receptacle for laundry equipment present: Yes
53) The clothes dryer was equipped with a vinyl or mylar, accordion-type, flexible exhaust duct. The U.S. Consumer Product Safety Commission considers these types of ducts to be unsafe, and a fire hazard. They can trap lint and are susceptible to kinks or crushing, which can greatly reduce the air flow and cause overheating. Recommend that such ducts be replaced with a rigid or corrugated semi-rigid metal duct, and by a qualified contractor if necessary. For more information, visit: http://www.reporthost.com/?DRYER
54) The toilet at location(s) #A, B and C was loose where it attached to the floor. Leaks can occur. Flooring, the sub-floor or areas below may get damaged. Sewer gases can enter living spaces. Recommend that a qualified contractor remove the toilet(s) for further evaluation and repair if necessary. A new wax ring should be installed and toilet(s) should be securely anchored to the floor to prevent movement and leaking.
55) The clothes dryer exhaust duct terminated in the crawl space. Clothes dryers produce large amounts of moisture which should not enter structure interiors. Moisture may accumulate and result in mold, bacteria or fungal growth. Recommend that a qualified person install, repair or replace the duct as necessary so it terminates outdoors, and per standard building practices. For more information, visit: http://www.reporthost.com/?DRYER
56) The sink at location(s) #C drained slowly. Recommend clearing drain and/or having a qualified plumber repair if necessary.
57) The bathtub drain stopper mechanism at location(s) #C was missing. Recommend that a qualified person repair or replace as necessary.
58) Tile and/or grout in the shower enclosure at location(s) #A were deteriorated (e.g. loose or cracked tiles, missing grout) or substandard. Water can damage the wall structure as a result. Recommend that a qualified contractor repair as necessary.
59) Downstairs bathroom sink stopper mechanism does not operate Upstairs sink drains slowly and the wall next to it has water damage
Limitations: The following items are not included in this inspection: security, intercom and sound systems; communications wiring; central vacuum systems; elevators and stair lifts; cosmetic deficiencies such as nail-pops, scuff marks, dents, dings, blemishes or issues due to normal wear and tear in wall, floor and ceiling surfaces and coverings, or in equipment; deficiencies relating to interior decorating; low voltage and gas lighting systems. Any comments made regarding these items are as a courtesy only. Note that the inspector does not evaluate any areas or items which require moving stored items, furnishings, debris, equipment, floor coverings, insulation or similar materials. The inspector does not test for asbestos, lead, radon, mold, hazardous waste, urea formaldehyde urethane, or any other toxic substance. Some items such as window, drawer, cabinet door or closet door operability are tested on a sampled basis. The client should be aware that paint may obscure wall and ceiling defects, floor coverings may obscure floor defects, and furnishings may obscure wall, floor and floor covering defects. If furnishings were present during the inspection, recommend a full evaluation of walls, floors and ceilings that were previously obscured when possible. Determining the cause and/or source of odors is not within the scope of this inspection.
Condition of exterior entry doors: Appeared serviceable
Exterior door material: Wood, Metal, Glass panel
Condition of interior doors: Required repair, replacement and/or evaluation (see comments below)
Condition of windows and skylights: Required repair, replacement and/or evaluation (see comments below)
Type(s) of windows: Wood, Single-pane, Single-hung
Condition of walls and ceilings: Appeared serviceable
Wall type or covering: Drywall
Ceiling type or covering: Drywall
Condition of flooring: Appeared serviceable
Flooring type or covering: Wood or wood products
Condition of stairs, handrails and guardrails: Appeared serviceable
60) One or more handrails had no "returns" installed, where ends of handrails turn and connect to adjacent walls so objects or clothing will not catch on the open ends. This is a safety hazard. Recommend that a qualified person install returns per standard building practices.
61) Floors in one or more areas were not level. This can be caused by foundation settlement or movement of the foundation, posts and/or beams. Significant repairs may be needed to make floors level. Recommend that a qualified contractor and/or engineer evaluate further. Repairs should be performed by a qualified contractor.
62) One or more interior doors were Loose, sagging or ill fitting. Recommend that a qualified person replace or repair doors as necessary.
63) One or more windows that were designed to open and close were stuck shut, difficult to open and close and/or screwed shut. Recommend that a qualified person repair windows as necessary so they open and close easily. One window in the home would open. Front and rear windows were screwed shut. One upstairs window would open.
64) More than one window pane was cracked or chipped.
65) There is evidence that the ceiling in one or more rooms have has repairs conducted
66) Upstairs kitchen floor has a damaged tile
67) Stains were found in one or more ceiling areas. However, no elevated levels of moisture were found. The stain(s) may be due to past roof and/or plumbing leaks.Consult with the property owner and monitor the stained area(s) in the future, especially after heavy or prolonged rain. If elevated moisture is found in the future, then recommend that a qualified contractor evaluate and repair as necessary.
68) One or more exterior doors had minor damage and/or deterioration. Although serviceable, the client may wish to repair or replace such doors for appearances' sake. Front door
69) Screens were missing from many windows. These windows may not provide ventilation during months when insects are active.
Limitations: This report only includes findings from accessible and visible areas on the day of the inspection. In addition to the inaccessible areas documented in this report, examples of other inaccessible areas include: sub areas less than 18 inches in height; attic areas less than 5 feet in height, areas blocked by ducts, pipes or insulation; areas where locks or permanently attached covers prevent access; areas where insulation would be damaged if traversed; areas obscured by vegetation. All inaccessible areas are subject to infestation or damage from wood-destroying organisms. The inspector does not move furnishings, stored items, debris, floor or wall coverings, insulation, or other materials as part of the inspection, nor perform destructive testing. Wood-destroying organisms may infest, re-infest or become active at any time. No warranty is provided as part of this inspection.
70) This inspection is not an official termite inspection. Although as a courtesy the inspector does look for any signs of termites. It is recommended that a licensed termite inspection company complete an inspection on the property.
Thank you for choosing IN-N-OUT Home Inspection Services. We hope that we have assisted you in making an informed decision. If you have any further questions please feel free to contact us. Paul Craig 228-806-9916