This report is the exclusive property of this inspection company and the client(s) listed in the report title. Use of this report by any unauthorized persons is prohibited.
Handy Home Medic
25 Brendel Ave
Hamburg NY 14075-5109
Inspector: Joshua Collins
Neil Caldiero Home Inspection Report
Inspector: Joshua Collins
||285 Prospect Ave
East Aurora, NY
||Tuesday, October 25, 2016
This report published on Wednesday, October 26, 2016 8:17:51 AM EDT
Limitations: Unless specifically included in the inspection, the following items and any related equipment, controls, electric systems and/or plumbing systems are excluded from this inspection: detached buildings or structures; fences and gates; retaining walls; underground drainage systems, catch basins or concealed sump pumps; swimming pools and related safety equipment, spas, hot tubs or saunas; whether deck, balcony and/or stair membranes are watertight; trees, landscaping, properties of soil, soil stability, erosion and erosion control; ponds, water features, irrigation or yard sprinkler systems; sport courts, playground, recreation or leisure equipment; areas below the exterior structures with less than 3 feet of vertical clearance; invisible fencing; sea walls, docks and boathouses; retractable awnings. Any comments made regarding these items are as a courtesy only.
Site profile: Level
The condition of the drain(s) is unknown. It's beyond the scope of a home inspection to determine if these drains flow adequately during prolonged periods of heavy rain. Recommend consulting with the property owners about this if possible, and monitoring drains in the future. If water is found to accumulate, then recommend that a qualified contractor evaluate and repair as necessary. For example, by cleaning, repairing or installing drains.
Exterior and Foundation
Limitations: The inspector performs a visual inspection of accessible components or systems at the exterior. Items excluded from this inspection include below-grade foundation walls and footings; foundations, exterior surfaces or components obscured by vegetation, stored items or debris; wall structures obscured by coverings such as siding or trim. Some items such as siding, trim, soffits, vents and windows are often high off the ground, and may be viewed using binoculars from the ground or from a ladder. This may limit a full evaluation. Regarding foundations, some amount of cracking is normal in concrete slabs and foundation walls due to shrinkage and drying. Note that the inspector does not determine the adequacy of seismic reinforcement.
Wall inspection method: Viewed from ground
Condition of wall exterior covering: Appeared serviceable
Condition of wall exterior covering: Appeared serviceable, Required repairs, replacement and/or evaluation (see comments below)
Apparent wall structure: Stone lower/ wood main structure
Wall covering: Vinyl
Condition of foundation and footings: Required evaluation (see comments below), Interior in crawl space eval footings
Apparent foundation type: Crawl space, Unfinished basement
Foundation/stem wall material: Stone
The masonry (brick or stone) was deteriorated or damaged in some areas. Where cracks or openings are exposed, water can enter the wall structure causing mold, fungal growth and structural damage. This is a conducive condition for wood-destroying organisms. Recommend that a qualified contractor repair as necessary. For example, by repointing mortar or replacing broken or missing masonry.
One or more exhaust duct end caps were missing. Their purpose is to prevent unconditioned air from entering the building, and keep out birds, rodents and bugs. Blocked ducts can cause fan motors and/or clothes dryers to overheat and can pose a fire hazard. Recommend that a qualified person repair or replace caps as necessary.
Caulking around windows is dried out and should be repaired by re-caulking so that water cannot penetrate behind aluminium and rot the wood.
Caulk was deteriorated in some areas. For example, around windows and/or at siding butt joints. Recommend that a qualified person renew or install caulk as necessary. Where gaps are wider than 1/4 inch, an appropriate material other than caulk should be used. For more information, visit:http://www.reporthost.com/?CAULK
Limitations: Structural components such as joists and beams, and other components such as piping, wiring and/or ducting that are obscured by under-floor insulation are excluded from this inspection. The inspector does not determine if support posts, columns, beams, joists, studs, trusses, etc. are of adequate size, spanning or spacing.
The inspector does not guarantee or warrant that water will not accumulate in the crawl spaces in the future. Complete access to all crawl space areas during all seasons and during prolonged periods of all types of weather conditions (e.g. heavy rain, melting snow) would be needed to do so.
The inspector attempts to locate all crawl space access points and areas. Access points may be obscured or otherwise hidden by furnishings or stored items. In such cases, the client should ask the property owner where all access points are that are not described in this inspection, and have those areas inspected. Note that crawl space areas should be checked at least annually for water intrusion, plumbing leaks and pest activity.
Crawl space inspection method: Viewed from hatch(es)
Condition of floor substructure above: Appeared serviceable
Pier or support post material: Wood
Condition of vapor barrier: Required repairs, replacement and/or evaluation (see comments below)
Vapor barrier present: Partial, Just Plastic thrown on ground in small area
Condition of crawl space ventilation: Not determined (inaccessible or obscured)
No vapor barrier was installed in the crawl space. This is a conducive condition for wood-destroying organisms due to the likelihood of water evaporating from the soil below up into the structure. A 6 mil black plastic sheet should be placed over all exposed soil with seams overlapped to 24 inches, and not in contact with any wood structural components. The sheeting should be held in place with bricks or stones, not wood. Recommend that a qualified contractor install a vapor barrier per standard building practices.
No under-floor insulation was installed in the crawl space. Recommend that a qualified person install insulation for better energy efficiency and per standard building practices. Typically this is R-19 rated fiberglass batt with the attached facing installed against the warm (floor) side.
One or more support posts appear to have been added since the original construction based on the inspector's observations. Such posts may have been added to reduce bounce or sag in floors above. Consult with the property owner about this, or have a qualified contractor evaluate and make repairs if necessary.
Added support posts and no Vapor Barrier/ installed incorrect.
Limitations: Structural components such as joists and beams, and other components such as piping, wiring and/or ducting that are obscured by under-floor insulation are also excluded from this inspection. Note that the inspector does not determine if support posts, columns, beams, joists, studs, trusses, etc. are of adequate size, spanning or spacing.
The inspector does not guarantee or warrant that water will not accumulate in the basement in the future. Access to the basement during all seasons and during prolonged periods of all types of weather conditions (e.g. heavy rain, melting snow) would be needed to do so. The inspector does not determine the adequacy of basement floor or stairwell drains, or determine if such drains are clear or clogged.
Note that all basement areas should be checked periodically for water intrusion, plumbing leaks and pest activity.
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; solar roofing components. Any comments made regarding these items are made as a courtesy only. Note that the inspector does not provide an estimate of remaining life on the roof surface material, nor guarantee that leaks have not occurred in the roof surface, skylights or roof penetrations in the past. Regarding roof leaks, only active leaks, visible evidence of possible sources of leaks, and evidence of past leaks observed during the inspection are reported on as part of this inspection. The inspector does not guarantee or warrant that leaks will not occur in the future. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high wind and rain, melting snow) would be needed to do so. Occupants should monitor the condition of roofing materials in the future. For older roofs, recommend that a professional inspect the roof surface, flashings, appurtenances, etc. annually and maintain/repair as might be required. If needed, the roofer should enter attic space(s). Regarding the roof drainage system, unless the inspection was conducted during and after prolonged periods of heavy rain, the inspector was unable to determine if gutters, downspouts and extensions perform adequately or are leak-free.
Roof inspection method: Viewed from ground
Condition of roof surface material: Required repair, replacement and/or evaluation (see comments below), Near, at or beyond service life, Area's of roof appear to be at the end of life.
Roof surface material: Asphalt or fiberglass composition shingles
Roof type: Gable
Condition of gutters, downspouts and extensions: Appeared serviceable
One or more gutters and/or downspouts were damaged. Rainwater can come in contact with the building exterior or accumulate around the building foundation as a result. This is a conducive condition for wood-destroying organisms. Recommend that a qualified person repair as necessary.
Should be six feet from foundation
Should be six feet from foundation
The coating on the flat or low-slope roof surface was deteriorated. Such coatings are designed to protect against ultraviolet light and moisture, help prevent leaks and cracks, lower-roof surface temperatures, and maintain waterproofing properties. Recommend that a qualified person apply a new roof coating now and as necessary in the future. Typically this is done every four to five years.
The roof structure below the shingles or shakes was "skip sheathed," where boards (typically 1x4 inches or 1x6 inches) with wide gaps between them were installed below the shingles, instead of plywood or oriented strand board (OSB) sheathing. Skip sheathing is commonly done with wood shake or shingle surfaces. The client should be aware that if a new composition shingle roof is installed, all existing layers of roofing materials will need to be removed, and continuous sheeting such as plywood or OSB will need to be installed before installing the shingles. This is a significant additional expense.
Cedar Shake not plywood or OSB
Limitations: The following items are not included in this inspection: generator systems, transfer switches, surge suppressors, inaccessible or concealed wiring; underground utilities and systems; low-voltage lighting or lighting on timers or sensors. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of grounding or bonding, if this system has an adequate capacity for the client's specific or anticipated needs, or if this system has any reserve capacity for additions or expansion. The inspector does not operate circuit breakers as part of the inspection, and does not install or change light bulbs. The inspector does not evaluate every wall switch or receptacle, but instead tests a representative number of them per various standards of practice. When furnishings, stored items or child-protective caps are present some receptacles are usually inaccessible and are not tested; these are excluded from this inspection. Receptacles that are not of standard 110 volt configuration, including 240-volt dryer receptacles, are not tested and are excluded. The functionality of, power source for and placement of smoke and carbon monoxide alarms is not determined as part of this inspection. Upon taking occupancy, proper operating and placement of smoke and carbon monoxide alarms should be verified and batteries should be changed. These devices have a limited lifespan and should be replaced every 10 years. The inspector attempts to locate and evaluate all main and sub-panels. However, panels are often concealed. If panels are found after the inspection, a qualified electrician should evaluate and repair if necessary. The inspector attempts to determine the overall electrical service size, but such estimates are not guaranteed because the overall capacity may be diminished by lesser-rated components in the system. Any repairs recommended should be made by a licensed electrician.
Electric service condition: Required repair, replacement and/or evaluation (see comments below)
Primary service type: Overhead
Number of service conductors: 3
Service voltage (volts): 120-240
Primary service overload protection type: Circuit breakers
Service entrance conductor material: Stranded copper
Condition of main service panel: Appeared serviceable
Location of main service panel #A: Basement
Location of main disconnect: Breaker at top of main service panel
Main service line has serious sheathing missing and metal is exposed where the sheathing is missing. Have a company evaluate the service line.
One or more electric receptacles at the exterior had no visible ground fault circuit interrupter (GFCI) protection, or the inspector was unable to determine if GFCI protection was present. If not GFCI-protected, receptacles in wet areas pose a shock hazard. Recommend that a qualified electrician evaluate and install GFCI protection if necessary and per standard building practices. General guidelines for GFCI-protected receptacles include the following locations:
- Outdoors (since 1973)
- Bathrooms (since 1975)
- Garages (since 1978)
- Kitchens (since 1987)
- Crawl spaces and unfinished basements (since 1990)
- Wet bar sinks (since 1993)
- Laundry and utility sinks (since 2005)
For more information, visit:http://www.reporthost.com/?GFCI
Exterior outlet needs GFCI rated for exterior.
One or more receptacles were worn. Worn receptacles can work intermittently or when the plug is wiggled. They can overheat or arc and spark due to loose connections. This is a potential fire hazard. Recommend that a qualified electrician replace such receptacles as necessary.
One or more electric receptacles had reverse-polarity wiring, where the hot and neutral wires were reversed. This is a shock hazard. Recommend that a qualified electrician repair as necessary. For more information, visit:http://www.reporthost.com/?RPR
No permanently installed smoke alarms were found. This is a potential safety hazard. A qualified electrician should install smoke alarms per standard building practices (e.g. in hallways leading to bedrooms, in each bedroom, on each floor and in attached garages). For more information, visit:http://www.reporthost.com/?SMKALRM
No permanently installed carbon monoxide alarms were found. This is a potential safety hazard. Some states and/or municipalities require CO alarms to be installed for new construction and/or for homes being sold. Recommend installing approved CO alarms outside of each separate sleeping area in the immediate vicinity of the bedrooms on each level and in accordance with the manufacturer's recommendations. For more information, visit:http://www.reporthost.com/?COALRM
Branch circuit wiring installed in buildings built prior to the mid 1980s is typically rated for a maximum temperature of only 60 degrees Celsius. This includes non-metallic sheathed (Romex) wiring, and both BX and AC metal-clad flexible wiring. Knob and tube wiring, typically installed in homes built prior to 1950, may be rated for even lower maximum temperatures. Newer electric fixtures including lighting and fans typically require wiring rated for 90 degrees Celsius. Connecting newer fixtures to older, 60-degree-rated wiring is a potential fire hazard. Repairs for such conditions may involve replacing the last few feet of wiring to newer fixtures with new 90-degree-rated wire, and installing a junction box to join the old and new wiring.
It is beyond the scope of this inspection to determine if such incompatible components are installed, or to determine the extent to which they're installed. Based on the age of this building, the client should be aware of this safety hazard, both for existing fixtures and when planning to upgrade with newer fixtures. Consult with a qualified electrician for repairs as necessary.
2-slot receptacles rather than 3-slot, grounded receptacles were installed in one or more areas. These do not have an equipment ground and are considered unsafe by today's standards. Appliances that require a ground should not be used with 2-slot receptacles. Examples of such appliances include computers and related hardware, refrigerators, freezers, portable air conditioners, clothes washers, aquarium pumps, and electrically operated gardening tools. The client should be aware of this limitation when planning use for various rooms, such as an office. Upgrading to grounded receptacles typically requires installing new wiring from the main service panel or sub-panel to the receptacle(s), in addition to replacing the receptacle(s). Consult with a qualified electrician about upgrading to 3-wire, grounded circuits.
The legend for circuit breakers or fuses in panel(s) # was missing, incomplete, illegible or confusing. This is a potential shock or fire hazard in the event of an emergency when power needs to be turned off. Recommend correcting the legend so it's accurate, complete and legible. Evaluation by a qualified electrician may be necessary.
The electric service to this property appeared to be rated at substantially less than 200 amps and may be inadequate. Depending on the client's needs, recommend consulting with a qualified electrician about upgrading to a 200 amp service. Note that the electric service's rating is based on the lowest rating for the meter base, the service conductors, the main service panel and the main disconnect switch. One or more of these components may need replacing to upgrade.
Coming from the HVAC there appears to be a wire that goes into the breaker box and is a double tap where the white neutral and black hot are both being used as HOT.
Limitations: Evaluation of and determining the adequacy or completeness of the following items are not included in this inspection: water recirculation pumps; solar water heating systems; Energy Smart or energy saver controls; catch pan drains. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on water heaters, does not determine if water heaters are appropriately sized, or perform any evaluations that require a pilot light to be lit or a shut-off valve to be operated.
Past manufactured life span of six years
Heating, Ventilation and Air Condition (HVAC)
Limitations: The following items are not included in this inspection: humidifiers, dehumidifiers, electronic air filters; solar, coal or wood-fired heat systems; thermostat or temperature control accuracy and timed functions; heating components concealed within the building structure or in inaccessible areas; underground utilities and systems; safety devices and controls (due to automatic operation). Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on heating or cooling system components, does not determine if heating or cooling systems are appropriately sized, does not test coolant pressure, or perform any evaluations that require a pilot light to be lit, a shut-off valve to be operated, a circuit breaker to be turned "on" or a serviceman's or oil emergency switch to be operated. It is beyond the scope of this inspection to determine if furnace heat exchangers are intact and free of leaks. Condensation pans and drain lines may clog or leak at any time and should be monitored while in operation in the future. Where buildings contain furnishings or stored items, the inspector may not be able to verify that a heat source is present in all "liveable" rooms (e.g. bedrooms, kitchens and living/dining rooms).
In basement HVAC duct work is seperating.
HVAC conduit separation
Limitations: The following items are not included in this inspection: household appliances such as stoves, ovens, cook tops, ranges, warming ovens, griddles, broilers, dishwashers, trash compactors, refrigerators, freezers, ice makers, hot water dispensers and water filters; appliance timers, clocks, cook functions, self and/or continuous cleaning operations, thermostat or temperature control accuracy, and lights. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of the remaining life of appliances, and does not determine the adequacy of operation of appliances. The inspector does not note appliance manufacturers, models or serial numbers and does not determine if appliances are subject to recalls. Areas and components behind and obscured by appliances are inaccessible and excluded from this inspection.
Kitchen sink hot water stays on and must be shut off under sink. This could cause higher water bills and energy cost if left on.
Bathrooms, Laundry and Sinks
Limitations: The following items are not included in this inspection: overflow drains for tubs and sinks; heated towel racks, saunas, steam generators, clothes washers, clothes dryers. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of washing machine drain lines, washing machine catch pan drain lines, or clothes dryer exhaust ducts. The inspector does not operate water supply or shut-off valves for sinks, toilets, bidets, clothes washers, etc. due to the possibility of valves leaking or breaking when operated. The inspector does not determine if shower pans or tub and shower enclosures are water tight, or determine the completeness or operability of any gas piping to laundry appliances.
Upstairs shower regulator pushes back into the wall when used.
Push inside of wall and not properly secured.
The first floor laundry has on open PVC pipe that may let sewer gases in when the washing machine discharges, there is a trap installed under the sink.
Interior, Doors and Windows
Limitations: The following items are not included in this inspection: security, intercom and sound systems; communications wiring; central vacuum systems; elevators and stair lifts; cosmetic deficiencies such as nail-pops, scuff marks, dents, dings, blemishes or issues due to normal wear and tear in wall, floor and ceiling surfaces and coverings, or in equipment; deficiencies relating to interior decorating; low voltage and gas lighting systems. Any comments made regarding these items are as a courtesy only. Note that the inspector does not evaluate any areas or items which require moving stored items, furnishings, debris, equipment, floor coverings, insulation or similar materials. The inspector does not test for asbestos, lead, radon, mold, hazardous waste, urea formaldehyde urethane, or any other toxic substance. Some items such as window, drawer, cabinet door or closet door operability are tested on a sampled basis. The client should be aware that paint may obscure wall and ceiling defects, floor coverings may obscure floor defects, and furnishings may obscure wall, floor and floor covering defects. If furnishings were present during the inspection, recommend a full evaluation of walls, floors and ceilings that were previously obscured when possible. Determining the cause and/or source of odors is not within the scope of this inspection.
The interior door leading into the center upstairs bedroom is warped and does not latch and close properly.
Limitations: The following items are not included in this inspection: private/shared wells and related equipment; private sewage disposal systems; hot tubs or spas; main, side and lateral sewer lines; gray water systems; pressure boosting systems; trap primers; incinerating or composting toilets; fire suppression systems; water softeners, conditioners or filtering systems; plumbing components concealed within the foundation or building structure, or in inaccessible areas such as below tubs; underground utilities and systems; overflow drains for tubs and sinks; backflow prevention devices. Any comments made regarding these items are as a courtesy only. Note that the inspector does not operate water supply or shut-off valves due to the possibility of valves leaking or breaking when operated. The inspector does not test for lead in the water supply, the water pipes or solder, does not determine if plumbing and fuel lines are adequately sized, and does not determine the existence or condition of underground or above-ground fuel tanks.
Water service: Public
Location of main water shut-off: Basement
Condition of drain pipes: Appeared serviceable
Condition of waste lines: Appeared serviceable
Waste pipe material: Plastic, Cast iron
Exterior of House
Plug being used for external power source.
Rear of house no storm door.
Painted over rotted wood
Picture of HVAC
Picture of down stairs shower
Picture of breaker box, cover was not installed
Your default report footer here...