This report is the exclusive property of this A+ Handy Inspections and the client(s) listed in the report title. Use of this report by any unauthorized persons is prohibited.
A+ Handy Inspections, LLCWebsite: http://www.aplushandyinspections.com
Phone: (360) 303-7994 · (425) 466-1129
1522 Fairview St
Bellingham WA 98229-5211
Inspector: Doug Handy
Licensed Home Inspector #1973
Property Inspection Report
||2061 Aaron Dr
Lynden WA 98264-3946
||Monday, October 16, 2017
This report published on Monday, October 16, 2017 7:49:21 PM PDT
How to Read this Report
This report is organized by the property's functional areas. Within each functional area, descriptive information is listed first and is shown in bold type. Items of concern follow descriptive information.
Concerns are shown and sorted according to these types:
|Safety||Poses a safety hazard|
|Major Defect||Correction likely involves a significant expense|
|Repair/Replace||Recommend repairing or replacing|
|Repair/Maintain||Recommend repair and/or maintenance|
|Minor Defect||Correction likely involves only a minor expense|
|Maintain||Recommend ongoing maintenance|
|Evaluate||Recommend evaluation by a specialist|
|Monitor||Recommend monitoring in the future|
|Comment||For your information|
Click here for a glossary of building construction terms.Contact your inspector If there are terms that you do not understand, or visit the glossary of construction terms at http://www.reporthost.com/glossary.asp
Report number: DJH 0000014
Time started: 9:00 AM
Present during inspection: Client, Realtor, Jason Cacanaugh, Windermere Real Estate
Client present for discussion at end of inspection: Yes
Weather conditions during inspection: Dry (no rain)
Temperature during inspection: Cool
Payment method: Check
Type of building: Single family
Buildings inspected: One house
Number of residential units inspected: 1
Age of main building: 1989
Source for main building age: Municipal records or property listing
Front of building faces: East
Main entrance faces: East
1) Evaluate, Comment -
The natural gas service was not turned on during the inspection. The inspector operates only "normal" controls such as thermostats, stove burner knobs, and on/off switches, and does not operate gas shut-off valves or activate pilot lights. As a result, items such as but not limited to the gas supply system, gas-fired water heater, gas-fired forced air furnace, gas fireplace, stove and range weren't fully evaluated. The inspector was unable to test for gas leaks. Recommend that a qualified person make a full evaluation of the gas supply system and gas-fired appliances after the gas supply is turned back on. Any problems that are found after this evaluation should be repaired by a qualified contractor.
Site profile: Level
Condition of driveway: Appeared serviceable
Driveway material: Poured in place concrete
Condition of sidewalks and/or patios: Appeared serviceable
Sidewalk material: Poured in place concrete
Condition of deck, patio and/or porch covers: Appeared serviceable
Deck, patio, porch cover material and type: Covered (Refer to Roof section)
Condition of decks, porches and/or balconies: Appeared serviceable
Deck, porch and/or balcony material: Concrete
Condition of stairs, handrails and guardrails: Appeared serviceable
Exterior stair material: Concrete
3) Comment -
Minor deterioration (e.g. cracks, holes, settlement, heaving) was found in the driveway, but no trip hazards were found. No repairs required, just cosmetic cracks.
Exterior and Foundation
Limitations: The inspector performs a visual inspection of accessible components or systems at the exterior. Items excluded from this inspection include below-grade foundation walls and footings; foundations, exterior surfaces or components obscured by vegetation, stored items or debris; wall structures obscured by coverings such as siding or trim. Some items such as siding, trim, soffits, vents and windows are often high off the ground, and may be viewed using binoculars from the ground or from a ladder. This may limit a full evaluation. Regarding foundations, some amount of cracking is normal in concrete slabs and foundation walls due to shrinkage and drying. Note that the inspector does not determine the adequacy of seismic reinforcement.
Wall inspection method: Viewed from ground
Condition of wall exterior covering: Appeared serviceable
Apparent wall structure: Wood frame
Wall covering: Wood fiber, Cement fiber
Condition of foundation and footings: Appeared serviceable
Apparent foundation type: Unfinished basement, Finished basement
Foundation/stem wall material: Poured in place concrete
Footing material (under foundation stem wall): Poured in place concrete
Three planters were attached to the front of building exterior. This can result in high levels of moisture at the building exterior near planters. It is a conducive condition for wood-destroying organisms. Recommend removing planters, or repairing so there is a gap of at least 2 inches between planters and the building exterior for better airflow and to allow building exteriors to dry quickly.
A couple of minor holes or gaps were found in siding. Insects or water may enter the structure. Recommend that a qualified person fill of caulk as necessary.
Soil was in contact with or less than 6 inches from wood for window wells on the north side of house. This can be conducive condition for wood-destroying organisms. If not possible, then recommend replacing untreated wood with pressure-treated wood. Installation of borate-based products such as Impel rods can also reduce the likelihood of rot or infestation if soil cannot be removed. Note that damage from fungal rot and/or insects may be found when soil is removed, and repairs may be necessary. Also, recommend grading or removing soil as necessary to maintain a 6-inch clearance for siding on the north side.
Three windows are below grade, and the wells have started filling with dirt. Vent wells should be lower than the windows. To prevent debris or dirt to come in contact with window wraps. This is a conducive condition for wood-destroying organisms. Recommend removing excess soil. To prevent dirt from coming back in, lower the grade level, install a membrane and fill over with 2" of gravel.
8) Minor Defect
A couple of very small pieces of siding was damaged. Recommend touching up with paint and just monitor.
Caulk is starting to deteriorated in some areas. For example, at siding butt joints. Recommend that a qualified person monitor/renew or install caulk as necessary. Where gaps are wider than 1/4 inch, an appropriate material other than caulk should be used. For more information, visit:http://www.reporthost.com/?CAULK
Limitations: Structural components such as joists and beams, and other components such as piping, wiring and/or ducting that are obscured by under-floor insulation are also excluded from this inspection. Note that the inspector does not determine if support posts, columns, beams, joists, studs, trusses, etc. are of adequate size, spanning or spacing.
The inspector does not guarantee or warrant that water will not accumulate in the basement in the future. Access to the basement during all seasons and during prolonged periods of all types of weather conditions (e.g. heavy rain, melting snow) would be needed to do so. The inspector does not determine the adequacy of basement floor or stairwell drains, or determine if such drains are clear or clogged.
Note that all basement areas should be checked periodically for water intrusion, plumbing leaks and pest activity.
Condition of floor substructure above: Appeared serviceable
Pier or support post material: Wood
Beam material: Solid wood
Floor structure above: Solid wood joists
Limitations: Any comments made regarding these items are made as a courtesy only. Note that the inspector does not provide an estimate of remaining life on the roof surface material, nor guarantee that leaks have not occurred in the roof surface, skylights or roof penetrations in the past. Regarding roof leaks, only active leaks, visible evidence of possible sources of leaks, and evidence of past leaks observed during the inspection are reported on as part of this inspection. The inspector does not guarantee or warrant that leaks will not occur in the future. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high wind and rain, melting snow) would be needed to do so. Occupants should monitor the condition of roofing materials in the future. For older roofs, recommend that a professional inspect the roof surface, flashings, appurtenances, etc. annually and maintain/repair as might be required. If needed, the roofer should enter attic space(s). Regarding the roof drainage system, unless the inspection was conducted during and after prolonged periods of heavy rain, the inspector was unable to determine if gutters, downspouts and extensions perform adequately or are leak-free.
Roof inspection method: Traversed
Condition of roof surface material: Near, at or beyond service life
Roof surface material: Asphalt or fiberglass composition shingles
Roof type: Gable, Hipped
Apparent number of layers of roof surface material: One
Condition of exposed flashings: Required repair, replacement and/or evaluation (see comments below)
Condition of gutters, downspouts and extensions: Appeared serviceable
Moss was growing on the roof. As a result, shingles can lift or be damaged. Leaks can result and/or the roof surface can fail prematurely. Efforts should be made to kill the moss during its growing season (wet months). Typically, zinc or phosphate-based chemicals are used for this and must be applied periodically. For information on various moss treatment products and their pros and cons, visit:http://www.reporthost.com/?MOSS
Nail heads are exposed on a few shingles on the roof. More than just a few exposed nail heads may indicate a substandard roof installation. Recommend applying an approved sealant over exposed nail heads now and as necessary in the future to prevent leaks.
Attic and Roof Structure
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; areas and components obscured by insulation. Any comments made regarding these items are made as a courtesy only. The inspector does not determine the adequacy of the attic ventilation system. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high/low temperatures, high/low humidity, high wind and rain, melting snow) would be needed to do so. The inspector is not a licensed engineer and does not determine the adequacy of roof structure components such as trusses, rafters or ceiling beams, or their spacing or sizing.
Attic inspection method: Traversed
Condition of roof structure: Appeared serviceable
Roof structure type: Trusses
Ceiling structure: Trusses
Condition of insulation in attic (ceiling, skylight chase, etc.): Appeared serviceable
Ceiling insulation material: Fiberglass loose fill
Approximate attic insulation R value (may vary in areas): R-38
Condition of roof ventilation: Required repair, replacement and/or evaluation (see comments below)
Roof ventilation type: Box vents (roof jacks), Enclosed soffit vents
Garage or Carport
Limitations: The inspector does not determine the adequacy of firewall ratings. Requirements for ventilation in garages vary between municipalities.
Condition of door between garage and house: Appeared serviceable
Type of door between garage and house: Metal
Condition of garage vehicle door(s): Appeared serviceable
Type of garage vehicle door: Sectional
Number of vehicle doors: 2
Condition of automatic opener(s): Appeared serviceable, Required repair, replacement and/or evaluation (see comments below)
Mechanical auto-reverse operable (reverses when meeting reasonable resistance during closing): Yes
Condition of garage floor: Appeared serviceable
Condition of garage interior: Appeared serviceable
17) Safety, Repair/Replace
No photoelectric sensors were installed on the south garage vehicle door automatic opener. These have been required on all automatic door openers since 1993 and improve safety by triggering the door's auto-reverse feature without need for the door to come in contact with the object, person or animal that is preventing the door from closing. Recommend that a qualified contractor install photoelectric sensors where missing for improved safety. For more information on garage door safety issues, visit:http://www.reporthost.com/?GDPES
18) Evaluate -
The south automatic vehicle door opener is noisy and probably close to end of life. Recommend that a qualified contractor evaluate and repair or replace opener(s) as necessary.
The wall-mounted controls for both automatic garage vehicle door openers are just a few inches below the 5 feet off the floor guideline, or within reach of children. This is a safety hazard. Children should not be able to operate automatic garage vehicle door openers. A qualified person should relocate controls for door openers so they are at least 5 feet above floors and/or out of reach of children. For more information on garage door safety issues, visit:http://www.reporthost.com/?NRGD
20) Comment -
Minor cracks were found in the concrete slab floor. These are common and appeared to be only a cosmetic issue.
Limitations: The following items are not included in this inspection: underground utilities and systems; Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of grounding or bonding, if this system has an adequate capacity for the client's specific or anticipated needs, or if this system has any reserve capacity for additions or expansion. The inspector does not operate circuit breakers as part of the inspection, and does not install or change light bulbs. The inspector does not evaluate every wall switch or receptacle, but instead tests a representative number of them per various standards of practice. When furnishings, stored items or child-protective caps are present some receptacles are usually inaccessible and are not tested; these are excluded from this inspection. Receptacles that are not of standard 110 volt configuration, including 240-volt dryer receptacles, are not tested and are excluded. The functionality of, power source for and placement of smoke and carbon monoxide alarms is not determined as part of this inspection. Upon taking occupancy, proper operating and placement of smoke and carbon monoxide alarms should be verified and batteries should be changed. These devices have a limited lifespan and should be replaced every 10 years. The inspector attempts to locate and evaluate all main and sub-panels. However, panels are often concealed. If panels are found after the inspection, a qualified electrician should evaluate and repair if necessary. The inspector attempts to determine the overall electrical service size, but such estimates are not guaranteed because the overall capacity may be diminished by lesser-rated components in the system. Any repairs recommended should be made by a licensed electrician.
Electric service condition: Appeared serviceable
Primary service type: Underground
Number of service conductors: 3
Service voltage (volts): 120-240
Estimated service amperage: 200
Primary service overload protection type: Circuit breakers
Service entrance conductor material: Stranded aluminum
Main disconnect rating (amps): 200
System ground: Ground rod(s) in soil
Condition of main service panel: Appeared serviceable
Location of main service panel #A: Garage
Location of main disconnect: Breaker at top of main service panel
Condition of branch circuit wiring: Serviceable
Branch circuit wiring type: non-metallic sheathed
Solid strand aluminum branch circuit wiring present: None visible
Ground fault circuit interrupter (GFCI) protection present: Yes
Arc fault circuit interrupter (AFCI) protection present: No
Smoke alarms installed: Yes, but not tested
Carbon monoxide alarms installed: No, recommend install
22) Safety, Repair/Replace
Smoke alarms were missing from all bedrooms, down stairs hallways leading to bedrooms and/or in the attached garage. Smoke alarms should be installed as necessary so a functioning alarm exists in each hallway leading to bedrooms, in each bedroom, on each level and in any attached garage. For more information, visit:http://www.reporthost.com/?SMKALRM
23) Safety, Repair/Maintain
No permanently installed carbon monoxide alarms were found. This is a potential safety hazard. Some states and/or municipalities require CO alarms to be installed for new construction and/or for homes being sold. Recommend installing approved CO alarms outside of each separate sleeping area in the immediate vicinity of the bedrooms on each level and in accordance with the manufacturer's recommendations. For more information, visit:http://www.reporthost.com/?COALRM
In the recreation room, one light switch by door turns all the lights on. When turning light switch to bar on, makes those two lights blink, light switches appeared to be incorrectly wired. This may be a safety hazard. Recommend that a qualified electrician repair as necessary.
One cover plate for a junction boxes was missing in the garage. These plates are intended to contain fire and prevent electric shock from occurring due to exposed wires. Recommend that a qualified person install cover plates where necessary.
One electric receptacles in which they were installed were loose and/or not securely anchored in the downstairs bedroom. Wire conductors can be damaged due to repeated movement and/or tension on wires, or insulation can be damaged. This is a shock and fire hazard. Recommend that a qualified electrician repair as necessary.
28) Comment -
Bulbs in a couple of light fixtures were missing or broken/not working. These light fixtures couldn't be fully evaluated. If replacement bulbs are inoperable, then test for proper operation and repair as necessary.
Plumbing / Fuel Systems
Limitations: Any comments made regarding these items are as a courtesy only. Note that the inspector does not operate water supply or shut-off valves due to the possibility of valves leaking or breaking when operated. The inspector does not test for lead in the water supply, the water pipes or solder, does not determine if plumbing and fuel lines are adequately sized, and does not determine the existence or condition of underground or above-ground fuel tanks.
Condition of service and main line: Appeared serviceable
Water service: Public
Location of main water shut-off: Basement, In mechanical room
Condition of supply lines: Appeared serviceable
Supply pipe material: Copper, PEX plastic
Condition of drain pipes: Appeared serviceable
Drain pipe material: Plastic
Condition of waste lines: Appeared serviceable
Waste pipe material: Plastic
Vent pipe condition: Appeared serviceable
Vent pipe material: Plastic
Sump pump installed: None visible
Limitations: Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on water heaters, does not determine if water heaters are appropriately sized, or perform any evaluations that require a pilot light to be lit or a shut-off valve to be operated.
Condition of water heater: Appeared serviceable, Bradford White Coprp., Model #MI5039FBN, Serial #JK17185169
Energy source: Natural gas
Estimated age: Oct. 2012, 5 years old.
Capacity (in gallons): 50
Temperature-pressure relief valve installed: Yes
Location of water heater: Mechanical room
Hot water temperature tested: No, Gas was turned off.
Water temperature (degrees Fahrenheit): Unknown
Condition of burners: Appeared serviceable
Condition of venting system: Appeared serviceable
30) Safety, Repair/Maintain
No drain line was installed for the temperature-pressure relief valve. This is a potential safety hazard due to the risk of scalding if someone is standing next to the water heater when the valve opens. Recommend that a qualified plumber install a drain line per standard building practices.
The water heater's earthquake reinforcement was substandard. For example, struts were used rather than straps, substandard fasteners were used, or they may allow significant movement. This is a potential safety hazard in the event of an earthquake due to the risk of the water heater tipping over, gas lines leaking if gas-fired, or electric wiring being damaged if powered by electricity. Water leaks may also occur. Recommend that a qualified person repair or replace existing earthquake reinforcement per standard building practices.
32) Evaluate, Comment -
The water heater's gas supply was off. The water heater and hot water supply system (e.g. faucets, controls) were not fully evaluated because of this. Recommend that a full evaluation be made by a qualified person when conditions have been corrected so the water heater is operable. Note that per the standards of practice for various professional home inspection organizations, the inspector does not operate shut-off valves, pilot lights or over-current protection devices, or any controls other than "normal controls."
Heating, Ventilation and Air Condition (HVAC)
Limitations: The following items are not included in this inspection: thermostat or temperature control accuracy and timed functions; underground utilities and systems; safety devices and controls (due to automatic operation). Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on heating or cooling system components, does not determine if heating or cooling systems are appropriately sized, does not test coolant pressure, or perform any evaluations that require a pilot light to be lit, a shut-off valve to be operated, a circuit breaker to be turned "on" or a serviceman's or oil emergency switch to be operated. It is beyond the scope of this inspection to determine if furnace heat exchangers are intact and free of leaks. Condensation pans and drain lines may clog or leak at any time and should be monitored while in operation in the future. Where buildings contain furnishings or stored items, the inspector may not be able to verify that a heat source is present in all "liveable" rooms (e.g. bedrooms, kitchens and living/dining rooms).
General heating system type(s): Forced air, Furnace, Carrier model #58SXAG80-101GG, serial #100
General heating distribution type(s): Ducts and registers
Last service date of primary heat source: None noted since installtion in 1990.
Source for last service date of primary heat source: Label
Condition of forced air heating/(cooling) system: Not determined (inaccessible, obscured, or power, gas or oil service off)
Forced air heating system fuel type: Natural gas
Location of forced air furnace: Mechanical room, Basement
Condition of furnace filters: Required replacement
Location for forced air filter(s): At base of air handler
Condition of forced air ducts and registers: Appeared serviceable
Condition of burners: Not determined (inaccessible, obscured, or gas or oil service off)
Type of combustion air supply: Intake duct, Vent(s) to exterior
Condition of venting system: Appeared serviceable
Condition of controls: Appeared serviceable
Recommend that home buyers replace or clean HVAC filters upon taking occupancy depending on the type of filters installed. Regardless of the type, recommend checking filters monthly in the future and replacing or cleaning them as necessary. How frequently they need replacing or cleaning depends on the type and quality of the filter, how the system is configured (e.g. always on vs. "Auto"), and on environmental factors (e.g. pets, smoking, frequency of house cleaning, number of occupants, the season).
34) Evaluate, Comment
The furnace heating system was not fully evaluated because the gas supply was off. Recommend that a full evaluation be made by a qualified person when conditions have been corrected so the system is operable. Note that the inspector does not operate shut-off valves, pilot lights or circuit breakers, or any controls other than normal controls (thermostat). The estimated useful life for most forced air furnaces is 15-20 years. The age of the furnace is 01/1990. Be aware that this furnace may be near, at, or beyond its useful life and may need replacing or significant repairs at any time. Recommend doing a complete service on furnace to evaluate life expectancy after gas is turned on. Budgeting for a replacement if necessary.
Fireplaces, Stoves, Chimneys and Flues
Limitations: Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of drafting or sizing in fireplace and stove flues, and also does not determine if prefabricated or zero-clearance fireplaces are installed in accordance with the manufacturer's specifications. The inspector does not perform any evaluations that require a pilot light to be lit, and does not light fires. The inspector provides a basic visual examination of a chimney and any associated wood burning device. The National Fire Protection Association has stated that an in-depth Level 2 chimney inspection should be part of every sale or transfer of property with a wood-burning device. Such an inspection may reveal defects that are not apparent to the home inspector who is a generalist.
Condition of gas-fired fireplaces or stoves: Not determined (didn't respond to normal controls, gas off, etc.)
Gas fireplace or stove type: Metal pre-fab fireplace
Gas-fired flue type: Direct vent
The gas fireplaces or stoves did not respond to normal controls (e.g. on/off switch, thermostat, remote control) and were not fully evaluated as a result. The gas supply may have been turned off, or some other condition may have prevented operation. The inspector only operates normal controls and does not light pilot lights or operate gas shut-off valves. Consult with the property owner, review all documentation for such gas appliances, and become familiar with the lighting procedure. If necessary, a qualified specialist should assist in lighting such appliances, and make any needed repairs.
Limitations: The following items are not included in this inspection: household appliances such as stoves, ovens, cook tops, ranges, warming ovens, griddles, broilers, dishwashers, trash compactors, refrigerators, freezers, ice makers, hot water dispensers and water filters; appliance timers, clocks, cook functions, self and/or continuous cleaning operations, thermostat or temperature control accuracy, and lights. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of the remaining life of appliances, and does not determine the adequacy of operation of appliances. The inspector does not note appliance manufacturers, models or serial numbers and does not determine if appliances are subject to recalls. Areas and components behind and obscured by appliances are inaccessible and excluded from this inspection.
Condition of counters: Appeared serviceable
Condition of cabinets: Appeared serviceable
Condition of sinks and related plumbing: Appeared serviceable, Required repair, replacement and/or evaluation (see comments below)
Condition of under-sink food disposal: N/A (none installed)
Condition of dishwasher: Appeared serviceable
Condition of ranges, cooktops and/or ovens: Near, at or beyond service life. Modern Maid
Range, cooktop, oven type: Natural gas
Condition of refrigerator: N/A (none installed)
Condition of built-in microwave oven: N/A (none installed)
The kitchen sink drain pipe used an S-trap rather than a P-trap, or no P-trap was visible. Siphons and sudden flows of water in S-Traps can drain all the water out of the trap, leaving it dry. Sewer gases can then enter living areas. Recommend that a qualified plumber repair per standard building practices.
The cooktop exhaust fan was noisy or vibrated excessively. Recommend that a qualified person repair or replace as necessary.
Bathrooms, Laundry and Sinks
Limitations: The following items are not included in this inspection: overflow drains for tubs and sinks; heated towel racks, saunas, steam generators, clothes washers, clothes dryers. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of washing machine drain lines, washing machine catch pan drain lines, or clothes dryer exhaust ducts. The inspector does not operate water supply or shut-off valves for sinks, toilets, bidets, clothes washers, etc. due to the possibility of valves leaking or breaking when operated. The inspector does not determine if shower pans or tub and shower enclosures are water tight, or determine the completeness or operability of any gas piping to laundry appliances.
Location #A: Full bath, Master bath, first floor, west
Location #B: Full bath, first floor, east
Location #C: Laundry room/area, first floor, east
Condition of counters: Appeared serviceable
Condition of cabinets: Appeared serviceable
Condition of flooring: Appeared serviceable
Condition of sinks and related plumbing: Appeared serviceable
Condition of toilets: Appeared serviceable
Condition of bathtubs and related plumbing: Appeared serviceable
Condition of shower(s) and related plumbing: Appeared serviceable
Condition of ventilation systems: Appeared serviceable, Required repair, replacement and/or evaluation (see comments below)
Bathroom and laundry ventilation type: Spot exhaust fans
Gas supply for laundry equipment present: Yes
240 volt receptacle for laundry equipment present: No
The sink faucet for the common bathroom was missing the aerator adapter. Recommend that a qualified person repair/replace as necessary.
The sink at the common bathroom drained slowly. Recommend clearing drain and/or having a qualified plumber repair if necessary.
Caulk around the base of the toilet at the common bathroom was missing. Modern standards require caulk to be installed around the entire toilet base where it meets the floor for sanitary reasons. Without it, soiled water can soak into flooring and sub-floor materials if the toilet overflows. Condensation from the toilet can also soak into the flooring. Recommend that a qualified person caulk around toilet bases per standard building practices.
Caulk, or substandard caulking were found between the bathtub and the floor in the common bathroom. Water may penetrate these areas and cause damage. Recommend that a qualified person re-caulk or install caulking as necessary.
The exhaust fan in the master bathroom was weak or slow and missing the cover. Moisture may accumulate and result in mold, bacteria or fungal growth. Recommend that a qualified person clean, repair or replace fans as necessary.
Some very small stains were found in the shelving or cabinets below the sink in the master bathroom and laundry room. Plumbing leaks may have occurred in the past.
The sink in the laundry room was worn and blemished.
Interior, Doors and Windows
Limitations: The following items are not included in this inspection: security, intercom and sound systems; communications wiring; central vacuum systems; elevators and stair lifts; cosmetic deficiencies such as nail-pops, scuff marks, dents, dings, blemishes or issues due to normal wear and tear in wall, floor and ceiling surfaces and coverings, or in equipment; deficiencies relating to interior decorating; low voltage and gas lighting systems. Any comments made regarding these items are as a courtesy only. Note that the inspector does not evaluate any areas or items which require moving stored items, furnishings, debris, equipment, floor coverings, insulation or similar materials. The inspector does not test for asbestos, lead, radon, mold, hazardous waste, urea formaldehyde urethane, or any other toxic substance. Some items such as window, drawer, cabinet door or closet door operability are tested on a sampled basis. The client should be aware that paint may obscure wall and ceiling defects, floor coverings may obscure floor defects, and furnishings may obscure wall, floor and floor covering defects. If furnishings were present during the inspection, recommend a full evaluation of walls, floors and ceilings that were previously obscured when possible. Determining the cause and/or source of odors is not within the scope of this inspection.
Condition of exterior entry doors: Appeared serviceable
Exterior door material: Wood
Condition of interior doors: Appeared serviceable
Type(s) of windows: Vinyl, Multi-pane
Condition of walls and ceilings: Appeared serviceable
Wall type or covering: Drywall
Ceiling type or covering: Drywall
Condition of flooring: Appeared serviceable
Condition of concrete slab floor(s): Appeared serviceable
Flooring type or covering: Carpet, Vinyl, linoleum or marmoleum, Wood or wood products
Condition of stairs, handrails and guardrails: Required repairs, replacement and/or evaluation (see comments below)
45) Safety, Repair/Maintain
One bedroom and one unfinished room had windows that were too small. Unless a bedroom has an exterior entry door, at least one window requires adequate egress in the event of a fire or emergency to allow escape or to allow access by emergency personnel. Such windows should have a minimum open width of 20 inches and a minimum open height of 24 inches. Grade floor egress windows should have a net clear opening of 5 square feet and other egress windows should have a net clear opening of 5.7 square feet. Recommend that a qualified contractor repair or make modifications per standard building practices. For more information, visit:http://www.reporthost.com/?EGRESS
The master bathroom window screen is damaged or deteriorated. This window may not provide ventilation during months when insects are active. Recommend replacing window screens as necessary.
Handrails at the flight of stairs were too low (30 in) and pose a fall hazard. Handrails should be located at least 34 inches and at most 38 inches above the nose of each tread/riser. Recommend that a qualified person repair per standard building practices.
Squeaking or creaking noises occur when walking in the laundry room flooring and stairs. In most cases, this is only an annoyance rather than a structural problem. Various solutions such as Squeeeeek No More and Counter Snap fasteners
exist to correct this. Repairs to eliminate the squeaks or creaks may be more or less difficult depending on the floor covering and the access to the underside of the sub-floor. Recommend that a qualified contractor evaluate and repair as necessary. For more information, visit:http://www.reporthost.com/?SQUEAK
Two window wood sills have some previous water damage from open window and/or glass stains on them. One in master bathroom and other one is in the upstairs bedroom in NE corner of house. Recommend refinish wood window cell as necessary.
52) Minor Defect
Minor cracks, nail pops and/or blemishes were found in walls and/or ceilings in one or more areas. Cracks and nail pops are common, are often caused by lumber shrinkage or minor settlement, and can be more or less noticeable depending on changes in humidity. They did not appear to be a structural concern, but the client may wish to repair these for aesthetic reasons. For recurring cracks, consider using an elastic crack covering product:http://www.reporthost.com/?ECC
Thank you for choosing A+ Handy Inspections, LLC. Please contact me at any time with questions regarding your inspection report.