This report published on Thursday, June 20, 2019 12:38:03 PM EDT
This report is the exclusive property of this inspection company and the client(s) listed in the report title. Use of this report by any unauthorized persons is prohibited.
How to Read this Report
This report is organized by the property's functional areas. Within each functional area, descriptive information is listed first and is shown in bold type. Items of concern follow descriptive information.
Concerns are shown and sorted according to these types:
Poses a risk of injury or death
Correction likely involves a significant expense
Recommend repairing or replacing
Recommend repair and/or maintenance
Correction likely involves only a minor expense
Recommend ongoing maintenance
Recommend evaluation by a specialist
For your information
Click here for a glossary of building construction terms.Contact your inspector If there are terms that you do not understand, or visit the glossary of construction terms at https://www.reporthost.com/glossary.asp
Exterior door material: Solid core steel, Sliding glass
Water pressure (psi): 45
Exterior wall condition: Fair
1) Safety, Repair/Replace, Evaluate - One or more ground fault circuit interrupter (GFCI) receptacles didn't trip with the inspector's test instrument. Recommend having a qualified, licensed electrician evaluate and repair or replace receptacles or the wiring to the receptacles as necessary.
2) Safety, Repair/Replace - Screen missing from pool and screen door has no locks or safety device to keep doors closed. Recommend repair.
3) Major Defect, Repair/Replace - The pool pump was not working properly and has a large amount of air in the lines. There may be a leak or issue with the pump. Recommend having a pool company evaluate and repair as needed.
The solar heater for the pool was not in working condition and control panel damaged. Recommend repair.
4) Repair/Replace - The end cap on the clothes dryer exhaust duct is missing. One should be installed to prevent air from entering the house through the clothes dryer, save energy, and keep out birds, rodents and bugs. Birds' nests can block the opening and are flammable. Recommend installing a vent cap.
5) Repair/Replace - The drain on the pool deck is clogged and water fills up when it rains at the home and has no way to exit the deck. Recommend repair of deck drain.
6) Repair/Maintain, Maintain, Comment - The sprinkler system was NOT working properly during the inspection. The inspector does recommend that the system be repaired by licensed irrigation company. Cost estimate: $2000.00
7) Maintain, Comment - The inspector found step cracks in the exterior of the home walls during the inspection. These are common in many Florida homes, recommend filling the cracks with sealant and painting. They are no major concern.
8) Comment - Minor cracks were found in the sidewalk. These are only a cosmetic concern and no action is recommended.
Roof covering: Asphalt or fiberglass composition shingles
Estimated age of roof: 17 years
Roof ventilation: Adequate
Roof Condition: Recommend Roofing Contractor
9) Safety, Major Defect, Repair/Replace, Evaluate - The roof has leaks at several areas. There are missing shingles on the roof. There is a large leak causing mold in the home that needs fixed asap. Recommend roofing contractor for replacement of the roof.
Recommend mold remediation company for removal of active damage.
No persons should be staying in the home longer than 30 min without a mask or respirator. Due not recommend home to be occupied until leaks and mold is removed on the surface and inside walls. with proper testing after removal for mold spores in the air. Cost estimate: $15000.00
10) Safety, Repair/Replace - Lead flashing at one or more sewer vent pipes is damaged and need replaced. Recommend roofing contractor. Possible cause of roof leaks also.
11) Major Defect, Repair/Replace - The tiles at the from of the garage installed on the floor are broken and sharp edges that can cut feet and cause serious damage. It was improperly installed and needs entire tile in garage removed.
12) Repair/Replace - Walls in the garage are damaged at the bottom for a long period of leaking from around the water heater. Recommend repair.
Primary service overload protection type: Circuit breakers
Service amperage (amps): 150
Service voltage (volts): 120-240
Location of main service panel: Side of the home
Location of sub panels: Garage wall
Location of main disconnect: Top bank of breakers in main service panel (split bus)
Service conductor material: Copper
Main disconnect rating (amps): 150
Smoke detectors present: No
Electrical panel condition: Fair
Outlets and switches condition: Poor, Needs repair
17) Safety, Repair/Replace - No smoke detectors are visible. Recommend installing smoke detectors as necessary so a functioning one exists in each hallway leading to bedrooms, and in each bedroom. For more information on smoke detectors visit http://www.cpsc.gov/cpscpub/pubs/5077.html
18) Comment - The Electrical Panel was in fair Condition during the Inspection. The inspector did not find and concerns to report.
19) Safety, Major Defect, Comment - The estimated useful life for most water heaters is 8 to 12 years. This water heater appears to be 17 years old and leaking. The entire bottom is rusted out and this is a safety hazard and needs replaced asap. Cost estimate: $1000.00
20) Safety, Repair/Replace, Evaluate - Significant amounts of what appears to be mold is visible in one or more sections of supply and/or return air ducts. If it is mold, it can be a health hazard, espcially for those with allergies or respiratory problems. The Environmental Protection Agency (EPA) recommends considering having ducts professionally cleaned when "There is substantial visible mold growth inside hard surface (e.g., sheet metal) ducts or on other components of your heating and cooling system". The client may wish to have a qualified industrial hygenist or indoor air quality service provider evaluate the ducts and/or have a qualified service provider professionally clean the ducts. For more information on duct cleaning in relation to indoor air quality, visit: http://www.epa.gov/iaq/pubs/airduct.html
21) - The system has been stripped missing components in the outside unit. Appears sold for scrap. The entire system needs replaced. Recommend AC Company. Cost estimate: $10,000.00
25) Safety, Repair/Replace - Owners are removing all light fixtures and ceiling fans, Leaving exposed wiring that is a safety hazard.
26) Safety, Minor Defect - Cover plate(s) are missing from one or more electric receptacle boxes. They are intended to contain fire and prevent electric shock from exposed wires. This is a safety hazard and poses a risk of both fire and shock. Recommend installing cover plates over receptacle boxes where missing.
27) Major Defect, Repair/Replace - Hall bathroom shower missing all walls and facets. Recommend repair. Cost estimate: $2000.00
28) Repair/Replace - Screen(s) missing in one or more windows. Window(s) may not provide ventilation during months when insects are active. Recommend installing screens.
29) Repair/Replace - Fixtures such as door stops, towel bars and/or toilet paper holders are missing in one or more areas. Recommend having a qualified contractor install fixtures where missing.
30) Repair/Replace - The Kitchen Facet is leaking from the top of the handle and needs repaired or replaced.
31) Repair/Replace - Bathroom downstairs facets doesn't come on and needs repaired.
32) Repair/Replace - Stair covering was improperly installed and needs removed and replaced properly without loose boards and missing areas.
33) Repair/Maintain - Tiles loose and need repaired on bathroom downstairs.
34) Repair/Maintain - Closet doors damaged and need repaired.
35) Repair/Maintain - Ceiling damaged in the kitchen and needs properly patched.
36) Minor Defect - One or more sink stopper mechanisms are missing, inoperable or in disrepair. Recommend intalling or repairing sink stopper mechanisms as necessary.
1. INSPECTOR agrees to perform a visual inspection of the home/building and to provide CLIENT with a written inspection report identifying the defects that INSPECTOR both observed and deemed material. INSPECTOR may offer comments as a courtesy, but these comments will not comprise the bargained-for report. The report is only supplementary to the sellers disclosure. 2. Unless otherwise inconsistent with this Agreement or not possible, INSPECTOR agrees to perform the inspection in accordance to the current Standards of Practice of the National Association of Certified Home Inspectors posted at http://www.nachi.org/sop.htm. CLIENT understands that these standards contain certain limitations, exceptions, and exclusions. 3. The inspection and report are performed and prepared for the use of CLIENT, who gives INSPECTOR permission to discuss observations with real estate agents, owners, repairpersons, and other interested parties. INSPECTOR accepts no responsibility for use or misinterpretation by third parties. INSPECTORS inspection of the property and the accompanying report are in no way intended to be a guarantee or warranty, express or implied, regarding the future use, operability, habitability or suitability of the home/building or its components. Any and all warranties, express or implied, including warranties of merchantability and fitness for a particular purpose, are expressly excluded by this Agreement.
4. INSPECTOR assumes no liability for the cost of repair or replacement of unreported defects or deficiencies either current or arising in the future. CLIENT acknowledges that the liability of INSPECTOR, its agents, employees, for claims or damages, costs of defense or suit, attorneys fees and expenses and payments arising out of or related to the INSPECTORS negligence or breach of any obligation under this Agreement, including errors and omissions in the inspection or the report, shall be limited to liquidated damages in an amount equal to the fee paid to the INSPECTOR, and this liability shall be exclusive. CLIENT waives any claim for consequential, exemplary, special or incidental damages or for the loss of the use of the home/building even if the CLIENT has been advised of the possibility of such damages. The parties acknowledge that the liquidated damages are not intended as a penalty but are intended (i) to reflect the fact that actual damages may be difficult and impractical to ascertain; (ii) to allocate risk among the INSPECTOR and CLIENT; and (iii) to enable the INSPECTOR to perform the inspection at the stated fee.
5. INSPECTOR does not perform engineering, architectural, plumbing, or any other job function requiring an occupational license in the jurisdiction where the inspection is taking place, unless the inspector holds a valid occupational license, in which case he/she may inform the CLIENT that he/she is so licensed, and is therefore qualified to go beyond this basic home inspection, and for additional fee, perform additional inspections beyond those within the scope of the basic home inspection. Any agreement for such additional inspections shall be in a separate writing.
6. In the event of a claim against INSPECTOR, CLIENT agrees to supply INSPECTOR with the following: (1) Written notification of adverse conditions within 14 days of discovery, and (2) Access to the premises. Failure to comply with the above conditions will release INSPECTOR and its agents from any and all obligations or liability of any kind. 7. The parties agree that any litigation arising out of this Agreement shall be filed only in the Court having jurisdiction in the County in which the INSPECTOR has its principal place of business. In the event that CLIENT fails to prove any adverse claims against INSPECTOR in a court of law, CLIENT agrees to pay all legal costs, expenses and fees of INSPECTOR in defending said claims. 8. If any court declares any provision of this Agreement invalid or unenforceable, the remaining provisions will remain in effect. This Agreement represents the entire agreement between the parties. All prior communications are merged into this Agreement, and there are no terms or conditions other than those set forth herein. No statement or promise of INSPECTOR or its agents shall be binding unless reduced to writing and signed by INSPECTOR. No change or modification shall be enforceable against any party unless such change or modification is in writing and signed by the parties. This Agreement shall be binding upon and enforceable by the parties and their heirs, executors, administrators, successors and assignees. CLIENT shall have no cause of action against INSPECTOR after one year from the date of the inspection. 9. Payment of the fee to INSPECTOR (less any deposit noted above) is due upon completion of the on-site inspection. The CLIENT agrees to pay all legal and time expenses incurred in collecting due payments, including attorneys fees, if any. If CLIENT is a corporation, LLC, or similar entity, the person signing this Agreement on behalf of such entity does personally guaranty payment of the fee by the entity. CLIENT HAS CAREFULLY READ THE FOREGOING, AGREES TO IT, AND ACKNOWLEDGES RECEIPT OF A COPY OF THIS AGREEMENT. [sig]