This report is the exclusive property of this inspection company and the client(s) listed in the report title. Use of this report by any unauthorized persons is prohibited.
Atlas Home Inspection
3829 Killdeer Dr
Antioch CA 94509-6429
Inspector: Ted Elsberry
Property Inspection Report
||1234 Pine Street
||Friday, January 06, 2017
This report published on Tuesday, July 18, 2017 8:27:06 AM PDT
Report number: 1111
Time started: 10:45am
Time finished: 12:45pm
Client present for discussion at end of inspection: No
Weather conditions during inspection: Rain
Temperature during inspection: Cool
Type of building: Single family
Buildings inspected: One house
Age of main building: 60 years
Source for main building age: Municipal records or property listing
Front of building faces: Southeast
Main entrance faces: Southeast
Structures built prior to the mid 1980s may contain lead and/or asbestos. Lead is commonly found in paint and in some plumbing components. The EPA does not recognize newer coats of paint as encapsulating older coats of lead-based paint. Asbestos is commonly found in various building materials such as insulation, siding, and/or floor and ceiling tiles. Laws were passed in 1978 to prohibit usage of lead and asbestos, but stocks of materials containing these substances remained in use for a number of years thereafter. Both lead and asbestos are known health hazards. Evaluating for the presence of lead and/or asbestos is beyond the scope of this inspection. Any mention of these materials in this report is made as a courtesy only, and meant to refer the client to a specialist. Consult with specialists as necessary, such as industrial hygienists, professional labs and/or abatement specialists for this type of evaluation. For information on lead, asbestos and other hazardous materials in homes, visit:http://www.reporthost.com/?EPAhttp://www.reporthost.com/?CPSChttp://www.reporthost.com/?CDC
Limitations: Unless specifically included in the inspection, the following items and any related equipment, controls, electric systems and/or plumbing systems are excluded from this inspection: detached buildings or structures; fences and gates; retaining walls; underground drainage systems, catch basins or concealed sump pumps; swimming pools and related safety equipment, spas, hot tubs or saunas; whether deck, balcony and/or stair membranes are watertight; trees, landscaping, properties of soil, soil stability, erosion and erosion control; ponds, water features, irrigation or yard sprinkler systems; sport courts, playground, recreation or leisure equipment; areas below the exterior structures with less than 3 feet of vertical clearance; invisible fencing; sea walls, docks and boathouses; retractable awnings. Any comments made regarding these items are as a courtesy only.
Site profile: Level, Minor slope
Condition of driveway: Appeared serviceable
Driveway material: Poured in place concrete
Condition of sidewalks and/or patios: Appeared serviceable
Sidewalk material: Poured in place concrete
Condition of deck, patio and/or porch covers: Appeared serviceable
Deck, patio, porch cover material and type: Covered (Refer to Roof section)
Exterior and Foundation
Limitations: The inspector performs a visual inspection of accessible components or systems at the exterior. Items excluded from this inspection include below-grade foundation walls and footings; foundations, exterior surfaces or components obscured by vegetation, stored items or debris; wall structures obscured by coverings such as siding or trim. Some items such as siding, trim, soffits, vents and windows are often high off the ground, and may be viewed using binoculars from the ground or from a ladder. This may limit a full evaluation. Regarding foundations, some amount of cracking is normal in concrete slabs and foundation walls due to shrinkage and drying. Note that the inspector does not determine the adequacy of seismic reinforcement.
Wall inspection method: Viewed from ground
Condition of wall exterior covering: Appeared serviceable
Apparent wall structure: Wood frame
Wall covering: Wood, Wood fiber, Stucco
Condition of foundation and footings: Appeared serviceable
Apparent foundation type: Crawl space, Post and pier, Concrete garage slab
Foundation/stem wall material: Poured in place concrete, Post and pier construction, no stem wall
Footing material (under foundation stem wall): Poured in place concrete
One or more precast concrete pier blocks were used to support posts or beams, and no poured-in-place concrete footing was visible below. Pier blocks resting directly on soil are prone to settlement. Recommend that a qualified contractor evaluate and repair as necessary and per standard building practices. For example, by pouring concrete footings below.
Trees were in contact with or were close to the building at one or more locations. Damage to the building can occur, especially during high winds, or may have already occurred (see other comments in this report). Recommend that a qualified tree service contractor or certified arborist remove trees as necessary to prevent damage to the building exterior.
Limitations: Structural components such as joists and beams, and other components such as piping, wiring and/or ducting that are obscured by under-floor insulation are excluded from this inspection. The inspector does not determine if support posts, columns, beams, joists, studs, trusses, etc. are of adequate size, spanning or spacing.
The inspector does not guarantee or warrant that water will not accumulate in the crawl spaces in the future. Complete access to all crawl space areas during all seasons and during prolonged periods of all types of weather conditions (e.g. heavy rain, melting snow) would be needed to do so.
The inspector attempts to locate all crawl space access points and areas. Access points may be obscured or otherwise hidden by furnishings or stored items. In such cases, the client should ask the property owner where all access points are that are not described in this inspection, and have those areas inspected. Note that crawl space areas should be checked at least annually for water intrusion, plumbing leaks and pest activity.
Crawl space inspection method: Partially traversed
Condition of floor substructure above: Appeared serviceable
Pier or support post material: Wood, Concrete block, Steel
Beam material: Solid wood
Floor structure above: Solid wood joists
Condition of insulation underneath floor above: Appeared serviceable
Insulation material underneath floor above: None visible
Condition of vapor barrier: Appeared serviceable
Vapor barrier present: Yes
Condition of crawl space ventilation: Appeared serviceable
Ventilation type: with vents
No under-floor insulation was installed in the crawl space. Recommend that a qualified person install insulation for better energy efficiency and per standard building practices. Typically this is R-19 rated fiberglass batt with the attached facing installed against the warm (floor) side.
One or more support posts appear to have been added since the original construction based on the inspector's observations. Such posts may have been added to reduce bounce or sag in floors above. Consult with the property owner about this, or that a qualified contractor evaluate and make permanent repairs per standard building practices if necessary.
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; solar roofing components. Any comments made regarding these items are made as a courtesy only. Note that the inspector does not provide an estimate of remaining life on the roof surface material, nor guarantee that leaks have not occurred in the roof surface, skylights or roof penetrations in the past. Regarding roof leaks, only active leaks, visible evidence of possible sources of leaks, and evidence of past leaks observed during the inspection are reported on as part of this inspection. The inspector does not guarantee or warrant that leaks will not occur in the future. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high wind and rain, melting snow) would be needed to do so. Occupants should monitor the condition of roofing materials in the future. For older roofs, recommend that a professional inspect the roof surface, flashings, appurtenances, etc. annually and maintain/repair as might be required. If needed, the roofer should enter attic space(s). Regarding the roof drainage system, unless the inspection was conducted during and after prolonged periods of heavy rain, the inspector was unable to determine if gutters, downspouts and extensions perform adequately or are leak-free.
Roof inspection method: Traversed
Condition of roof surface material: Appeared serviceable
Roof surface material: Asphalt or fiberglass composition shingles
Roof type: Gable
Apparent number of layers of roof surface material: One
Condition of exposed flashings: Appeared serviceable
Condition of gutters, downspouts and extensions: Required repair, replacement and/or evaluation (see comments below)
Extensions such as splash blocks or drain pipes for one or more downspouts were missing . Water can accumulate around the building foundation or inside crawl spaces or basements as a result. Recommend that a qualified person install, replace or repair extensions as necessary so rainwater drains away from the structure.
Significant amounts of debris have accumulated in one or more gutters or downspouts. Gutters can overflow and cause water to come in contact with the building exterior, or water can accumulate around the foundation. This is a conducive condition for wood-destroying organisms. Recommend cleaning gutters and downspouts now and as necessary in the future.
Attic and Roof Structure
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; areas and components obscured by insulation. Any comments made regarding these items are made as a courtesy only. The inspector does not determine the adequacy of the attic ventilation system. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high/low temperatures, high/low humidity, high wind and rain, melting snow) would be needed to do so. The inspector is not a licensed engineer and does not determine the adequacy of roof structure components such as trusses, rafters or ceiling beams, or their spacing or sizing.
Attic inspection method: Viewed from hatch(es), Not inspected because no access was found
Condition of roof structure: Appeared serviceable
Roof structure type: Rafters
Ceiling structure: Ceiling joists
Condition of insulation in attic (ceiling, skylight chase, etc.): Appeared serviceable
Ceiling insulation material: Fiberglass roll or batt
Approximate attic insulation R value (may vary in areas): R-25
Condition of roof ventilation: Appeared serviceable
Roof ventilation type: Open soffit vents
Attic spaces less than 30 inches in height may exist in this building, but had no visible access points. This is acceptable per standard building practices. However, these spaces were not inspected and are excluded from this inspection.
Garage or Carport
Limitations: The inspector does not determine the adequacy of firewall ratings. Requirements for ventilation in garages vary between municipalities.
Condition of door between garage and house: Appeared serviceable
Type of door between garage and house: Solid core
Condition of garage vehicle door(s): Appeared serviceable
Type of garage vehicle door: Sectional
Number of vehicle doors: 1
Condition of automatic opener(s): Required repair, replacement and/or evaluation (see comments below)
Mechanical auto-reverse operable (reverses when meeting reasonable resistance during closing): Yes, Suggest adjusting auto reverse for less resistance to engage
Condition of garage floor: Required repair, replacement and/or evaluation (see comments below)
Condition of garage interior: Appeared serviceable
Garage ventilation: None visible
No photoelectric sensors were installed for one or more garage vehicle doors' automatic opener. These have been required on all automatic door openers since 1993 and improve safety by triggering the door's auto-reverse feature without need for the door to come in contact with the object, person or animal that is preventing the door from closing. Recommend that a qualified contractor install photoelectric sensors where missing for improved safety. For more information on garage door safety issues, visit:http://www.reporthost.com/?GDPES
The Water Heater in the garage was installed so flames and/or sources of spark were less than 18 inches above the floor. This is a potential fire or explosion hazard. Such appliances should be installed so that open flames or sources of spark are located at least 18 inches above the floor. This minimizes the chance of explosion or fire from fuel vapors from vehicles or storage containers. A qualified person should repair per standard building practices. For example, by installing a platform if none exists or by repairing the existing platform if one does.
Minor cracks were found in the concrete slab floor. These are common and appeared to be only a cosmetic issue.
Limitations: The following items are not included in this inspection: generator systems, transfer switches, surge suppressors, inaccessible or concealed wiring; underground utilities and systems; low-voltage lighting or lighting on timers or sensors. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of grounding or bonding, if this system has an adequate capacity for the client's specific or anticipated needs, or if this system has any reserve capacity for additions or expansion. The inspector does not operate circuit breakers as part of the inspection, and does not install or change light bulbs. The inspector does not evaluate every wall switch or receptacle, but instead tests a representative number of them per various standards of practice. When furnishings, stored items or child-protective caps are present some receptacles are usually inaccessible and are not tested; these are excluded from this inspection. Receptacles that are not of standard 110 volt configuration, including 240-volt dryer receptacles, are not tested and are excluded. The functionality of, power source for and placement of smoke and carbon monoxide alarms is not determined as part of this inspection. Upon taking occupancy, proper operating and placement of smoke and carbon monoxide alarms should be verified and batteries should be changed. These devices have a limited lifespan and should be replaced every 10 years. The inspector attempts to locate and evaluate all main and sub-panels. However, panels are often concealed. If panels are found after the inspection, a qualified electrician should evaluate and repair if necessary. The inspector attempts to determine the overall electrical service size, but such estimates are not guaranteed because the overall capacity may be diminished by lesser-rated components in the system. Any repairs recommended should be made by a licensed electrician.
Electric service condition: Appeared serviceable
Primary service type: Overhead
Number of service conductors: 3
Service voltage (volts): 120-240
Estimated service amperage: 200
Primary service overload protection type: Circuit breakers
Service entrance conductor material: Stranded aluminum
Main disconnect rating (amps): 200
System ground: Ground rod(s) in soil
Condition of main service panel: Appeared serviceable
Location of main service panel #A: Garage
Location of main disconnect: At main disconnect panel outside
Condition of branch circuit wiring: Serviceable
Branch circuit wiring type: Non-metallic sheathed
Solid strand aluminum branch circuit wiring present: None visible
Ground fault circuit interrupter (GFCI) protection present: Yes, No
Arc fault circuit interrupter (AFCI) protection present: No
Smoke alarms installed: Yes, but not tested
Carbon monoxide alarms installed: Yes, but not tested
One or more ground fault circuit interrupter (GFCI) devices protecting receptacles at the 3/4 bath and/or full bath Was not present. This is a potential shock hazard. Recommend that a qualified electrician evaluate and repair as necessary.
Laundry Room Bath
One or more modern, 3-slot electric receptacles were found with an open ground. Three-slot receptacles should have a hot, a neutral and a ground wire connected. Homeowners often install new 3-slot receptacles on older, 2-wire circuits that only have hot and neutral wires. This is a shock hazard when appliances that require a ground are used with these receptacles. Examples of such appliances include computers and related hardware, refrigerators, freezers, portable air conditioners, clothes washers, aquarium pumps, and electrically operated gardening tools. Where the electric system was installed prior to when grounded circuits were required (1960s), it is permissible to replace 3-slot receptacles with 2-slot receptacles to prevent appliances that require a ground from being plugged in to an ungrounded circuit. However, the client should be aware of this limitation when planning use for various rooms, such as an office. For newer electric systems, circuits should be repaired so grounded, 3-wire cables provide power to 3-slot receptacles. Recommend that a qualified electrician repair per standard building practices.
Branch circuit wiring installed in buildings built prior to the mid 1980s is typically rated for a maximum temperature of only 60 degrees Celsius. This includes non-metallic sheathed (Romex) wiring, and both BX and AC metal-clad flexible wiring. Knob and tube wiring, typically installed in homes built prior to 1950, may be rated for even lower maximum temperatures. Newer electric fixtures including lighting and fans typically require wiring rated for 90 degrees Celsius. Connecting newer fixtures to older, 60-degree-rated wiring is a potential fire hazard. Repairs for such conditions may involve replacing the last few feet of wiring to newer fixtures with new 90-degree-rated wire, and installing a junction box to join the old and new wiring.
It is beyond the scope of this inspection to determine if such incompatible components are installed, or to determine the extent to which they're installed. Based on the age of this building, the client should be aware of this safety hazard, both for existing fixtures and when planning to upgrade with newer fixtures. Consult with a qualified electrician for repairs as necessary.
Plumbing / Fuel Systems
Limitations: The following items are not included in this inspection: private/shared wells and related equipment; private sewage disposal systems; hot tubs or spas; main, side and lateral sewer lines; gray water systems; pressure boosting systems; trap primers; incinerating or composting toilets; fire suppression systems; water softeners, conditioners or filtering systems; plumbing components concealed within the foundation or building structure, or in inaccessible areas such as below tubs; underground utilities and systems; overflow drains for tubs and sinks; backflow prevention devices. Any comments made regarding these items are as a courtesy only. Note that the inspector does not operate water supply or shut-off valves due to the possibility of valves leaking or breaking when operated. The inspector does not test for lead in the water supply, the water pipes or solder, does not determine if plumbing and fuel lines are adequately sized, and does not determine the existence or condition of underground or above-ground fuel tanks.
Condition of service and main line: Appeared serviceable
Water service: Public
Water pressure (psi): Adequate
Location of main water shut-off: Building exterior
Condition of supply lines: Appeared serviceable
Supply pipe material: Copper
Condition of drain pipes: Appeared serviceable
Drain pipe material: Plastic, Copper
Waste pipe material: Cast iron, Copper
Vent pipe condition: Appeared serviceable
Vent pipe material: Plastic, Cast iron
Condition of fuel system: Appeared serviceable
Location of main fuel shut-off valve: At gas meter
One or more uncoated brass flexible connectors were found in gas supply line(s). Some older brass connectors can separate from the tubing and cause a serious gas leak, explosion or fire. These connectors haven't been made since 1976. Moving appliances with such connectors, even slightly, whether to clean behind them or to inspect their gas connectors, can cause the connector to crack or break. Recommend that a qualified contractor replace uncoated brass flexible connectors. For more information, visit:http://www.reporthost.com/?FLEXCONN1
Upstairs Wall Heater
Copper water supply pipes were installed. Copper pipes installed prior to the late 1980s may be joined with solder that contains lead, which is a known health hazard especially for children. Laws were passed in 1985 prohibiting the use of lead in solder, but prior to that solder normally contained approximately 50% lead. The client should be aware of this, especially if children will be using this water supply system. Note that the inspector does not test for toxic materials such as lead. The client should consider having a qualified lab test for lead, and if necessary take steps to reduce or remove lead from the water supply. Various solutions include:
- Flush water taps or faucets. Do not drink water that has been sitting in the plumbing lines for more than 6 hours
- Install appropriate filters at points of use
- Use only cold water for cooking and drinking, as hot water dissolves lead more quickly than cold water
- Use bottled or distilled water
- Treat well water to make it less corrosive
- Have a qualified plumber replace supply pipes and/or plumbing components as necessary
For more information visit:http://www.reporthost.com/?LEADDWhttp://www.reporthost.com/?LEAD
Limitations: Evaluation of and determining the adequacy or completeness of the following items are not included in this inspection: water recirculation pumps; solar water heating systems; Energy Smart or energy saver controls; catch pan drains. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on water heaters, does not determine if water heaters are appropriately sized, or perform any evaluations that require a pilot light to be lit or a shut-off valve to be operated.
Condition of water heater: Appeared serviceable
Capacity (in gallons): 40
Location of water heater: Garage, Closet
Hot water temperature tested: Yes
Water temperature (degrees Fahrenheit): 130
Condition of burners: Appeared serviceable
Condition of venting system: Appeared serviceable
The hot water temperature was greater than 120 degrees Fahrenheit. This is a safety hazard due to the risk of scalding. The thermostat should be adjusted so the water temperature doesn't exceed 120 degrees. If the water heater is powered by electricity, a qualified person should perform the adjustment, since covers that expose energized equipment normally need to be removed. For more information on scalding dangers, visit:http://www.reporthost.com/?SCALD
The insulated jacket was missing and should be replaced.
The estimated useful life for most water heaters is 8-12 years. This water heater appeared to be at this age and/or its useful lifespan and may need replacing at any time. Recommend budgeting for a replacement in the near future, or considering replacement now before any leaks occur. The client should be aware that significant flooding can occur if the water heater fails. If not replaced now, consider having a qualified person install a catch pan and drain or a water alarm to help prevent damage if water does leak.
Mfgr date 12/2005
Heating, Ventilation and Air Condition (HVAC)
Limitations: The following items are not included in this inspection: humidifiers, dehumidifiers, electronic air filters; solar, coal or wood-fired heat systems; thermostat or temperature control accuracy and timed functions; heating components concealed within the building structure or in inaccessible areas; underground utilities and systems; safety devices and controls (due to automatic operation). Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on heating or cooling system components, does not determine if heating or cooling systems are appropriately sized, does not test coolant pressure, or perform any evaluations that require a pilot light to be lit, a shut-off valve to be operated, a circuit breaker to be turned "on" or a serviceman's or oil emergency switch to be operated. It is beyond the scope of this inspection to determine if furnace heat exchangers are intact and free of leaks. Condensation pans and drain lines may clog or leak at any time and should be monitored while in operation in the future. Where buildings contain furnishings or stored items, the inspector may not be able to verify that a heat source is present in all "liveable" rooms (e.g. bedrooms, kitchens and living/dining rooms).
General heating system type(s): Forced air, Furnace, Electric heaters
General heating distribution type(s): Ducts and registers
Condition of forced air heating/(cooling) system: Appeared serviceable
Forced air heating system fuel type: Natural gas
Estimated age of forced air furnace: 12 yrs
Location of forced air furnace: Closet
Forced air system capacity in BTUs or kilowatts:
Condition of furnace filters: Required washing or cleaning
Location for forced air filter(s): Behind return air grill(s)
Condition of forced air ducts and registers: Appeared serviceable
Condition of burners: Appeared serviceable
Type of combustion air supply: Vent(s) to exterior
Condition of venting system: Appeared serviceable
Condition of cooling system and/or heat pump: Appeared serviceable
Cooling system and/or heat pump fuel type: Natural gas
Location of heat pump or air conditioning unit: Building exterior
Condition of controls: Appeared serviceable
The outdoor air temperature was below 65 degrees Fahrenheit during the inspection. Air conditioning systems can be damaged if operated during such low temperatures. Because of this, the inspector was unable to operate and fully evaluate the cooling system.
Through-wall AC unit upstairs was unplugged and not inspected
Fireplaces, Stoves, Chimneys and Flues
Limitations: The following items are not included in this inspection: coal stoves, gas logs, chimney flues (except where visible). Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of drafting or sizing in fireplace and stove flues, and also does not determine if prefabricated or zero-clearance fireplaces are installed in accordance with the manufacturer's specifications. The inspector does not perform any evaluations that require a pilot light to be lit, and does not light fires. The inspector provides a basic visual examination of a chimney and any associated wood burning device. The National Fire Protection Association has stated that an in-depth Level 2 chimney inspection should be part of every sale or transfer of property with a wood-burning device. Such an inspection may reveal defects that are not apparent to the home inspector who is a generalist.
Condition of gas-fired fireplaces or stoves: Not determined (didn't respond to normal controls, gas off, etc.)
Gas fireplace or stove type: Metal pre-fab fireplace
Condition of chimneys and flues: Appeared serviceable
Gas-fired flue type: Masonry with metal liner
One or more gas fireplaces or stoves did not respond to normal controls (e.g. on/off switch, thermostat, remote control) and were not fully evaluated as a result. The pilot light or gas supply may have been turned off, or some other condition may have prevented operation. The inspector only operates normal controls and does not light pilot lights or operate gas shut-off valves. Consult with the property owner, review all documentation for such gas appliances, and become familiar with the lighting procedure. If necessary, a qualified specialist should assist in lighting such appliances, and make any needed repairs.
Limitations: The following items are not included in this inspection: household appliances such as stoves, ovens, cook tops, ranges, warming ovens, griddles, broilers, dishwashers, trash compactors, refrigerators, freezers, ice makers, hot water dispensers and water filters; appliance timers, clocks, cook functions, self and/or continuous cleaning operations, thermostat or temperature control accuracy, and lights. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of the remaining life of appliances, and does not determine the adequacy of operation of appliances. The inspector does not note appliance manufacturers, models or serial numbers and does not determine if appliances are subject to recalls. Areas and components behind and obscured by appliances are inaccessible and excluded from this inspection.
Condition of counters: Appeared serviceable
Condition of cabinets: Appeared serviceable
Condition of sinks and related plumbing: Appeared serviceable
Condition of under-sink food disposal: Appeared serviceable
Condition of dishwasher: Appeared serviceable
Condition of range, cooktop or oven: Appeared serviceable
Range, cooktop or oven type: Combination, Electronic ignition
Type of ventilation: Hood or built into microwave over range or cooktop
Condition of refrigerator: Appeared serviceable
Condition of built-in microwave oven: Appeared serviceable
The range could tip forward. An anti-tip bracket may not be installed. This is a potential safety hazard since the range can tip forward when weight is applied to the open door, such as when a small child climbs on it or if heavy objects are dropped on it. Anti-tip brackets have been sold with all free-standing ranges since 1985. Recommend installing an anti-tip bracket to eliminate this safety hazard. For more information, visit:http://www.reporthost.com/?ATB
Bathrooms, Laundry and Sinks
Limitations: The following items are not included in this inspection: overflow drains for tubs and sinks; heated towel racks, saunas, steam generators, clothes washers, clothes dryers. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of washing machine drain lines, washing machine catch pan drain lines, or clothes dryer exhaust ducts. The inspector does not operate water supply or shut-off valves for sinks, toilets, bidets, clothes washers, etc. due to the possibility of valves leaking or breaking when operated. The inspector does not determine if shower pans or tub and shower enclosures are water tight, or determine the completeness or operability of any gas piping to laundry appliances.
Location #A: 3/4 bath, Master bath
Location #B: Full bath, Hallway
Location #C: 3/4 bath, Laundry room/area
Condition of counters: Appeared serviceable
Condition of cabinets: Appeared serviceable
Condition of flooring: Appeared serviceable
Condition of sinks and related plumbing: Appeared serviceable
Condition of toilets: Appeared serviceable
Condition of shower(s) and related plumbing: Appeared serviceable
Condition of ventilation systems: Appeared serviceable
Bathroom and laundry ventilation type: Windows, Exhaust Fans
Gas supply for laundry equipment present: Yes
240 volt receptacle for laundry equipment present: Yes
The toilet at location(s) #B didn't flush or had a weak flush. Recommend that a qualified plumber evaluate and repair or replace the toilet as necessary.
I know you are aware of the toilet flush in Hall bath
One or more sink drains were leaking at location(s) #A. A qualified person should repair as necessary.
Drip pan at Master bath vanity. Not leaking at time of inspection
Interior, Doors and Windows
Limitations: The following items are not included in this inspection: security, intercom and sound systems; communications wiring; central vacuum systems; elevators and stair lifts; cosmetic deficiencies such as nail-pops, scuff marks, dents, dings, blemishes or issues due to normal wear and tear in wall, floor and ceiling surfaces and coverings, or in equipment; deficiencies relating to interior decorating; low voltage and gas lighting systems. Any comments made regarding these items are as a courtesy only. Note that the inspector does not evaluate any areas or items which require moving stored items, furnishings, debris, equipment, floor coverings, insulation or similar materials. The inspector does not test for asbestos, lead, radon, mold, hazardous waste, urea formaldehyde urethane, or any other toxic substance. Some items such as window, drawer, cabinet door or closet door operability are tested on a sampled basis. The client should be aware that paint may obscure wall and ceiling defects, floor coverings may obscure floor defects, and furnishings may obscure wall, floor and floor covering defects. If furnishings were present during the inspection, recommend a full evaluation of walls, floors and ceilings that were previously obscured when possible. Determining the cause and/or source of odors is not within the scope of this inspection.
Condition of exterior entry doors: Appeared serviceable
Exterior door material: Wood
Condition of interior doors: Required repair, replacement and/or evaluation (see comments below)
Condition of windows and skylights: Appeared serviceable
Type(s) of windows: Vinyl, Wood, Metal, Sliding
Condition of walls and ceilings: Appeared serviceable
Wall type or covering: Drywall
Ceiling type or covering: Drywall
Condition of flooring: Appeared serviceable
Flooring type or covering: Carpet, Vinyl, linoleum or marmoleum, Laminate, Tile
One or more interior doors wouldn't latch or were difficult to latch. Recommend that a qualified person repair as necessary. For example, by adjusting latch plates or locksets.
One or more interior doors were sticking in the door jamb and were difficult to operate. Recommend that a qualified person repair as necessary. For example, by trimming doors.
Your default report footer here...