Inspector's email: firstname.lastname@example.org
Phone: (360) 394-1667
Inspector's phone: (360) 394-1667
19408 Langaunet Ln NE
Poulsbo WA 98370-8510
Inspector: Jim Gallant
Washington State Home Inspector Cert/Lic #313
WSDA Certified structural pest inspector #63467
InterNACHI Member #NACHI04012337
This report published on Friday, October 05, 2012 7:42:53 AM PDT
Full General Home Inspection and Structural Pest Inspection|
WA State Dept. Agriculture ICN# 00000000
View report summary
This report is the exclusive property of this inspection company and the client(s) listed in the report title. Use of this report by any unauthorized persons is prohibited.
WAC 16-228-2045 requires that a diagram be prepared for WDO (Wood Destroying Organism) inspection reports. A copy is available upon request.
For information on follow-up inspections, please see the bottom section of this report.
Thank you for choosing All Point Home Inspections. We've made every effort to provide you with a thorough, high quality inspection, and hope that the information in this report proves to be valuable in your consideration of this property. If for any reason you are unsatisfied with this report, or have questions after reviewing it, please don't hesitate to call us. If you are satisfied, please tell your friends about us.
This inspection complies with the American Society of Home Inspectors' (ASHI) Standards of Practice and the National Association of Home Inspectors' (NAHI) Standards of Practice. This report is intended to identify major defects within a structure that significantly affect its habitability or that cost in excess of $500 to repair, although minor defects may be noted in the report. Cosmetic items such as damaged molding, trim, doors, cabinets, interior paint or carpet are generally excluded from this report.
Home inspection reports by nature focus on defects and may seem negative in tone. Some features of this property may be in excellent condition and of high quality but have not been mentioned, or been deemed adequate in the report. This is not meant to downplay this property's assets, but to focus on alerting you to potentially expensive problems. Bear in mind that all homes, regardless of their age, have some number of defects.
Areas of the property that are excluded due to lack of access are vulnerable to infestation and damage from wood destroying insects and organisms.
How to Read this Report
This report is organized by the property's functional areas. Within each functional area, descriptive information is listed first and is shown in bold type. Items of concern follow descriptive information.
Concerns are shown and sorted according to these types:
|Safety||Poses a risk of injury or death |
|Major defect||Correction likely involves a significant expense |
|Repair/Replace||Recommend repairing or replacing |
|Repair/Maintain||Recommend repair and/or maintenance |
|Maintain||Recommend ongoing maintenance |
|Evaluate||Recommend evaluation by a specialist |
|Comment||For your information |
Wood Destroying Organism Concerns
Concerns relating to wood destroying organisms are shown as follows:
|Conducive conditions||Conditions conducive for wood destroying insects or organisms (Wood-soil contact, shrubs in contact with siding, roof or plumbing leaks, etc.) |
Click here for a glossary of building construction terms.
Contact your inspector if there are terms that you do not understand, or visit the glossary of construction terms at http://www.reporthost.com/glossary.asp
Report number: 20120218-1
Time started: 1:00 PM
Time finished: 3:15 PM
Present during inspection: Client
Client present for discussion at end of inspection: Yes
Weather conditions during inspection: Rain
Temperature during inspection: Cold
Ground condition: Wet
Recent weather: Rain
Overnight temperature: Cold
Inspection fee: $395
Payment method: Check
Type of building: Single family
Buildings inspected: One house
Age of main building: 1991
Source for main building age: Realtor
Front of building faces: West
Main entrance faces: West
Evidence of rodent infestation was found in the form of feces and bait boxes in the crawl space. Recommend consulting with the property owner about this. A qualified person should make repairs to seal openings in the structure, set traps, and clean rodent waste as necessary. Recommend following guidelines in these Center for Disease Control articles:
Some areas and items at this property were obscured by furniture, stored items. This often includes but is not limited to walls, floors, windows, inside and under cabinets, under sinks, on counter tops, in closets, behind window coverings, under rugs or carpets, and under or behind furniture. Areas around the exterior, under the structure, in the garage and in the attic may also be obscured by stored items. The inspector in general does not move personal belongings, furnishings, carpets or appliances. When furnishings, stored items or debris are present, all areas or items that are obscured, concealed or not readily accessible are excluded from the inspection. The client should be aware that when furnishings, stored items or debris are eventually moved, damage or problems that were not noted during the inspection may be found.
Limitations: Unless specifically included in the inspection, the following items and any related equipment, controls, electric systems and/or plumbing systems are excluded from this inspection: detached buildings or structures; fences and gates; retaining walls; underground drainage systems, catch basins or concealed sump pumps; swimming pools and related safety equipment, spas, hot tubs or saunas; whether deck, balcony and/or stair membranes are watertight; trees, landscaping, properties of soil, soil stability, erosion and erosion control; ponds, water features, irrigation or yard sprinkler systems; sport courts, playground, recreation or leisure equipment; areas below the exterior structures with less than 3 feet of vertical clearance; invisible fencing; sea walls, docks and boathouses; retractable awnings. Any comments made regarding these items are as a courtesy only.
Site profile: Level
Condition of driveway: Appeared serviceable
Driveway material: Gravel
Condition of sidewalks and/or patios: Appeared serviceable
Sidewalk material: Paving stones
Condition of decks, porches and/or balconies: Appeared serviceable
Deck, porch and/or balcony material: Wood, Plastic fiber
Condition of exterior stairs: Appeared serviceable
Exterior stair material: Wood, Plastic fiber
Fungal rot was found in decking boards and trim at one or more decks or porches. Conducive conditions for this such as wood-soil contact should be corrected, and a qualified contractor should evaluate and repair as necessary. All rotten wood should be replaced.
Rot in trim at edge of deck near sliding glass door.
Rot in decking boards by sliding glass door.
Soil was in contact with or close to wooden stairs at one or more locations. This is a conducive condition for wood-destroying organisms. Soil should be graded and/or removed so no wood-soil contact is present, if possible. Otherwise, installing products such as borate-based Impel rods may help to prevent infestation and damage. For more information, visit:
All areas of the deck substructure were inaccessible due to limited space below. These areas couldn't be evaluated and are excluded from the inspection.
Limitations: The inspector performs a visual inspection of accessible components or systems at the exterior. Items excluded from this inspection include below-grade foundation walls and footings; foundations, exterior surfaces or components obscured by vegetation, stored items or debris; wall structures obscured by coverings such as siding or trim. Some items such as siding, trim, soffits, vents and windows are often high off the ground, and may be viewed using binoculars from the ground or from a ladder. This may limit a full evaluation. Regarding foundations, some amount of cracking is normal in concrete slabs and foundation walls due to shrinkage and drying. Note that the inspector does not determine the adequacy of seismic reinforcement.
Condition of wall exterior covering: Appeared serviceable
Apparent wall structure: Wood frame
Wall covering: Wood, Wood fiber
Condition of foundation and footings: Appeared serviceable
Apparent foundation type: Crawl space
Foundation/stem wall material: Poured in place concrete
Footing material (under foundation stem wall): Poured in place concrete
Anchor bolts or hold downs for seismic reinforcement: Installed
Shear panels for seismic reinforcement: Not determined (inaccessible or obscured)
This property was clad with composition wood-fiber siding. Various manufacturers (e.g. Louisiana Pacific, Weyerhaeuser and Masonite) have produced this type of siding, which is made from oriented strand board (OSB) or "hardboard." It is prone to deteriorate and/or fail prematurely due to moisture penetration. Failure is typically visible in the form of swelling, cracking, buckling, wafer pops, delamination and fungal growth.
Some areas of siding on this structure showed symptoms described above and need replacement and/or maintenance. Some manufacturers (e.g. Louisiana Pacific) recommend a repair process for this siding where affected areas are sealed with Permanizer Plus, a flexible primer made by Pittsburgh Paint, followed by two coats of 100% acrylic latex paint. This sealant must be applied to the bottom edges using a brush. The face of the siding can be sprayed. The Permanizer Plus sealer isn't required for edges that aren't swollen, cracked or deteriorated, but the acrylic latex should still be brushed on these edges.
Recommend that a qualified contractor evaluate and replace siding as necessary, and/or seal and repaint as necessary. Repairs should be made per the siding and/or sealant manufacturer's installation instructions, and per standard building practices.
For more information, visit:
Some delamination and swelling at siding on garage gable.
Some areas of the exterior paint finish were incomplete and/or substandard (e.g. primed only, too few coats). Siding and trim are more subject to damage from moisture with a failing finish. This is a conducive condition for wood-destroying organisms. Recommend that a qualified person prep if necessary (e.g. clean, scrape, sand, prime, caulk) and apply paint where necessary. Any repairs needed to the siding or trim should be made prior to repainting.
Limitations: Structural components such as joists and beams, and other components such as piping, wiring and/or ducting that are obscured by under-floor insulation are excluded from this inspection. The inspector does not determine if support posts, columns, beams, joists, studs, trusses, etc. are of adequate size, spanning or spacing.
Unpainted OSB sheathing near front door, at base of roof valley.
The inspector does not guarantee or warrant that water will not accumulate in the crawl spaces in the future. Complete access to all crawl space areas during all seasons and during prolonged periods of all types of weather conditions (e.g. heavy rain, melting snow) would be needed to do so.
The inspector attempts to locate all crawl space access points and areas. Access points may be obscured or otherwise hidden by furnishings or stored items. In such cases, the client should ask the property owner where all access points are that are not described in this inspection, and have those areas inspected. Note that crawl space areas should be checked at least annually for water intrusion, plumbing leaks and pest activity.
Crawl space inspection method: Partially traversed
Location of crawl space access point #A: Master bath closet
Crawl space access points that were opened and viewed, traversed or partially traversed: A
Condition of floor substructure above crawl space: Appeared serviceable
Pier or support post material: Wood
Beam material: Solid wood
Floor structure: 2x6 tongue and groove
Condition of insulation underneath floor above: Not applicable, none installed
Insulation material underneath floor above: None visible
Condition of vapor barrier: Appeared serviceable
Vapor barrier present: Yes, Full
Condition of crawl space ventilation: Appeared serviceable
Ventilation type: Unconditioned space, with vents
No insulation was installed under the floor above the crawl space. Recommend that a qualified person install insulation for better energy efficiency and per standard building practices. Typically this is R-19 rated fiberglass batt with the attached facing installed against the warm (floor) side.
No under-floor insulation.
One or more crawl space vents were blocked by debris. This restricts ventilation in the crawl space and can result in increased levels of moisture inside. This is a conducive condition for wood-destroying organisms. Materials or items blocking vents should be removed as necessary.
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; solar roofing components. Any comments made regarding these items are made as a courtesy only. Note that the inspector does not provide an estimate of remaining life on the roof surface material, nor guarantee that leaks have not occurred in the roof surface, skylights or roof penetrations in the past. Regarding roof leaks, only active leaks, visible evidence of possible sources of leaks, and evidence of past leaks observed during the inspection are reported on as part of this inspection. The inspector does not guarantee or warrant that leaks will not occur in the future. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high wind and rain, melting snow) would be needed to do so. Regarding the roof drainage system, unless the inspection was conducted during and after prolonged periods of heavy rain, the inspector was unable to determine if gutters, downspouts and extensions performed adequately or were leak-free.
Roof inspection method: Traversed
Roof surface material: Asphalt or fiberglass composition shingles
Roof type: Gable
Apparent number of layers of roof surface material: One
Condition of exposed flashings: Appeared serviceable
Condition of gutters, downspouts and extensions: Appeared serviceable
Gutter and downspout material: Metal
Gutter and downspout installation: Full
Vegetation such as trees, shrubs, and/or vines overhung the roof surface or were in contact with the roof edge. Organic debris such as leaves or needles are more likely to accumulate in gutters and on the roof surface. Gutters can overflow and cause water to come in contact with the building exterior or water can accumulate around the foundation. This is a conducive condition for wood-destroying organisms. Vegetation in contact with the roof can damage the roof surface and/or the roof drainage system. Vegetation should be pruned so as to not be in contact with the roof, and to not overhang the roof surface. If vegetation is too tall then it should be pruned at least 10 feet above the roof surface.
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; areas and components obscured by insulation. Any comments made regarding these items are made as a courtesy only. The inspector does not determine the adequacy of the attic ventilation system. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high/low temperatures, high/low humidity, high wind and rain, melting snow) would be needed to do so. The inspector is not a licensed engineer and does not determine the adequacy of roof structure components such as trusses, rafters or ceiling beams, or their spacing or sizing.
Attic inspection method: Viewed from hatch(es)
Location of attic access point #A: Main floor hallway
Attic access points that were opened and viewed, traversed or partially traversed: A
Condition of roof structure: Appeared serviceable
Roof structure type: Trusses
Ceiling structure: Trusses
Condition of insulation in attic (ceiling, skylight chase, etc.): Required repair, replacement and/or evaluation (see comments below)
Ceiling insulation material: Fiberglass loose fill
Approximate attic insulation R value (may vary in areas): R-19to R38
Condition of roof ventilation: Required repair, replacement and/or evaluation (see comments below)
Roof ventilation type: Ridge vent(s), Open soffit vents
One or more sections of the roof structure appeared to have substandard ventilation (ridge vent was too narrow). This can result in high attic and roof surface temperatures, reduce the life of the roof covering materials, and/or increase cooling costs. High levels of moisture are also likely to accumulate in the roof structure or attic, and can be a conducive condition for wood-destroying organisms. Standard building practices require one free square foot of ventilation for every 150 square feet of attic space, and that vents be evenly distributed between the lowest points of the roof structure and the highest points to promote air circulation. Often this means that both soffit vents and ridge or gable end vents are installed. Recommend that a qualified contractor evaluate and repair per standard building practices.
Narrow slot for continuous ridge venting.
The ceiling insulation in one or more areas of the attic was compacted or uneven. Heating and cooling costs may be higher due to reduced energy efficiency. Recommend that a qualified person repair, replace or install insulation as necessary and per standard building practices (typically R-38).
Uneven ceiling insulation.
Uneven ceiling insulation.
All attic areas and roof structures more than 10 feet from attic access point(s) A were inaccessible due to possible damage to insulation if traversed, lack of permanent walkways, limited height. These areas were not evaluated and are excluded from the inspection.
Microbial staining was visible on roof sheathing in the attic. Such staining usually occurs due to elevated humidity in the attic, and subsequent elevated moisture levels in the sheathing. When humid attic conditions have been corrected, it's likely that such staining will stop growing. Humid conditions often occur during construction when large volumes of water evaporate from paint and sheetrock mud, and can then return to normal, dryer levels. However, ongoing ventilation and/or insulation issues can also result in humid conditions. Please note any other comments in this report related to ventilation, insulation and/or moisture levels in the attic, and make any related recommended corrections. After issues related to the moisture conditions have been corrected, the clients may or may not wish to have mitigation work performed for the biological staining. Typically mold abatement specialists perform such work and may do the following:
Note that the inspector is not a mold specialist or industrial hygienist and provides no professional opinion on health issues related to microbial growth.
- Remove affected attic insulation
- Clean microbial staining from wood surfaces
- Treat wood surfaces with mildewcides
- Prime wood with special primers
- Install new attic insulation
Limitations: The inspector does not determine the adequacy of firewall ratings. Requirements for ventilation in garages vary between municipalities.
Dark staining (mold?) on roof sheathing.
Dark staining (mold?) on roof sheathing.
Type: Attached, Garage
Condition of garage: Required repair, replacement and/or evaluation (see comments below)
Type of door between garage and house: Metal
Condition of exterior entry doors: Appeared serviceable
Exterior door material: Metal, Glass panel
Type of garage vehicle door: Sectional
Number of vehicle doors: 1
Condition of automatic opener(s): Appeared serviceable
Condition of garage floor: Appeared serviceable
Condition of garage interior: Appeared serviceable
Garage ventilation: Exists
The door between the garage and the house has been modified with a pet door. Normally such doors are constructed with fire-resistant materials or in such a way as to prevent fire and fumes from spreading to interior living spaces. The fire resistance of this door appears to have been compromised.
Also this door had a door stop and a self closer that allowed the door to be propped open installed on it. Normally, such doors are required to prevent fire and fumes from spreading to interior living spaces. Such modifications compromise the door's ability to perform as intended.
Recommend that a qualified person replace the door with a fire-resistant door per standard building practices, or repair the door. Also recommend that unapproved hardware be removed if the door isn't replaced.
Pet door and door stop.
Self closer props door open.
No photo-electric sensors were installed for one or more garage vehicle doors' automatic opener. These have been required on all automatic door openers since 1993 and improve safety by triggering the door's auto-reverse feature without need for the door to come in contact with the object, person or animal that is preventing the door from closing. Recommend that a qualified contractor install "photo eye" sensors where missing for improved safety. For more information on garage door safety issues, visit:
No photo eyes.
One or more garage vehicle doors had an automatic opener installed, and the manual lock mechanism on the door hadn't been permanently disabled. The automatic opener can get damaged, or injury can occur if the automatic door opener is operated with the manual lock engaged. A qualified person should disable or remove the lock mechanism per standard building practices. For more information on garage door safety issues, visit:
Deadbolt not disabled.
The wall-mounted control for one or more automatic garage vehicle door openers was less than 5 feet off the floor, or within reach of children. This is a safety hazard. Children should not be able to operate automatic garage vehicle door openers. A qualified person should relocate controls for door openers so they are at least 5 feet above floors and/or out of reach of children. For more information on garage door safety issues, visit:
Low control button.
One or more garage vehicle doors weren't balanced. The door(s) wouldn't stay in place when opened half-way, and fell to the ground instead. This is a potential safety hazard since the door(s) can fall when open and cause injury. A qualified contractor should repair as necessary. For more information on garage door safety issues, visit:
Limitations: The following items are not included in this inspection: generator systems, surge suppressors, inaccessible or concealed wiring; underground utilities and systems; low voltage lighting or lighting on timers or sensors. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of grounding or bonding, does not determine if this system has an adequate capacity for the client's specific needs, nor determine if this system has any reserve capacity for additions or expansion. The inspector does not operate circuit breakers as part of the inspection, install or change light bulbs, nor determine the operability of every wall switch. The functionality of, power source for and placement of smoke detectors is not determined as part of this inspection. When taking occupancy, operability of smoke and carbon monoxide detectors should be verified and batteries should be changed. Smoke detectors have a limited lifespan and should be replaced every 10 years.
Electric service condition: Appeared serviceable
Primary service type: Underground
Service voltage (volts): 120-240
Service amperage (amps): 200
Primary service overload protection type: Circuit breakers
Service entrance conductor material: Aluminum
Main disconnect rating (amps): 200
System ground: Not determined, not readily apparent
Condition of main service panel: Required repair, replacement and/or evaluation (see comments below)
Location of main service panel #A: Garage
Location of main disconnect: Breaker at top of main service panel
Condition of branch circuit wiring: Required repair, replacement and/or evaluation (see comments below)
Branch circuit wiring type: Non-metallic sheathed
Solid strand aluminum branch circuit wiring present: None visible
Smoke detectors present: Yes, but not tested
Carbon monoxide detectors present: No
One or more screws used to secure the cover to panel #A were in contact with conductors at some point and appeared to have caused a short circuit. Scorch marks were visible and the wiring insulation was damaged. A qualified electrician should evaluate and repair as necessary.
Short-circuited wire in main service panel, with scorch marks visible.
One or more open ground, three-pronged grounding type receptacles were found. This is a safety hazard due to the risk of shock. A qualified electrician should evaluate and make repairs as necessary.
Grounding type receptacles were first required in residential structures during the 1960s. Based on the age of this structure and/or the absence of 2-pronged receptacles, repairs should be made by correcting wiring circuits as necessary so all receptacles are grounded as per standard building practices. Replacement of three-pronged receptacles with 2-pronged receptacles is not an acceptable solution.
One or more exterior electric receptacles were being used for appliances or systems that are constantly in use, and were not equipped with a "while in use" receptacle covers for wet locations[/url]. This is a safety hazard due to the risk of shock and fire. "While in use" covers should be installed where necessary. For more information, visit:
Based on the age of this structure and the appearance of existing smoke alarms, the alarms may have been installed more than 10 years ago. According to National Fire Protection Association, aging smoke alarms don't operate as efficiently and often are the source for nuisance alarms. Older smoke alarms are estimated to have a 30% probability of failure within the first 10 years. Newer smoke alarms do better, but should be replaced after 10 years. Unless you know that the smoke alarms are new, replacing them when moving into a new residence is also recommended by NFPA. For more information, visit:
Possible older smoke detector.
Smoke detectors were missing from bedrooms. Additional smoke detectors should be installed as necessary so a functioning one exists in each hallway leading to bedrooms, in each bedroom, and one each level of the building. For more information, visit:
This property had one or more fuel burning appliances and/or an attached garage, and no carbon monoxide detectors were visible. This is a safety hazard. Recommend installing one or more carbon monoxide detectors as necessary and as per the manufacturer's instructions (normally 1 per living level). For more information, visit:
Limitations: The following items are not included in this inspection: private wells and sewage disposal systems; main, side and lateral sewer lines; gray water systems; pressure boosting systems; incinerating or composting toilets; fire suppression sprinkler systems; water softeners, conditioners or filtering systems; plumbing components concealed within the foundation or building structure, or in inaccessible areas such as below tubs; underground utilities and systems; overflow drains for tubs and sinks; backflow prevention devices. Any comments made regarding these items are as a courtesy only. Note that the inspector does not operate water supply or shut-off valves due to the possibility of valves leaking or breaking when operated. The inspector does not test for lead in the water supply, the water pipes or solder, does not determine if plumbing and fuel lines are adequately sized, and does not determining the existence or condition of underground or above-ground fuel tanks.
Condition of service and main line: Appeared serviceable
Location of main water meter: By street
Water service: Public
Water pressure (psi): 60 psi
Service pipe material: Not determined (inaccessible or obscured)
Condition of supply lines: Appeared serviceable
Supply pipe material: Copper
Condition of drain pipes: Appeared serviceable
Drain pipe material: Plastic
Condition of waste lines: Appeared serviceable
Waste pipe material: Plastic
Vent pipe condition: Appeared serviceable
Vent pipe material: Plastic
Visible fuel storage systems: None
One or more water supply pipes in the crawl space were uninsulated. Recommend insulating pipes as per standard building practices for better energy efficiency and to prevent water pipes from freezing.
Some water supply pipes in crawl space not insulated.
The inspector did not determine the location of the main water shut-off valve. The client should consult with the property owner to determine if a shut-off valve exists, find it themselves, or hire a qualified plumber if necessary to find it. If no shut-off valve is found for the structure, then recommend having a qualified plumber install one to more easily allow the water supply to be turned off in the event of an emergency, such as when a supply pipe bursts.
Limitations: Evaluation of and determining the adequacy or completeness of the following items are not included in this inspection: water recirculation pumps; solar water heating systems; Energy Smart or energy saver controls; catch pan drains. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on water heaters, does not determine if water heaters are appropriately sized, or perform any evaluations that require a pilot light to be lit or a shut-off valve to be operated.
Condition of water heater: Appeared serviceable
Energy source: Electricity
Capacity (in gallons): Not determined
Location of water heater: Closet
The water heater did not have seismic straps or struts installed. This is a potential safety hazard in the event of an earthquake due to the risk of the water heater tipping over, gas lines breaking if it's gas-fired, or electric wiring being damaged if powered by electricity. Leaks can also occur in water-supply pipes. A qualified person should install seismic straps or struts as necessary and per standard building practices.
No seismic straps at water heater.
The estimated useful life for most water heaters is 8-12 years. The inspector was unable to determine the age of the water heater due to the manufacturer's label being obscured, no serial number being visible, or the serial number not clearly indicating the age. The client should be aware that this water heater may be near, at or beyond its useful life and may need replacing at any time. Recommend attempting to determine the water heater's age.
If found to be near, at or beyond its useful lifespan, recommend budgeting for a replacement in the near future, or considering replacement now before any leaks occur. The client should be aware that significant flooding can occur if the water heater does fail. If not replaced now, consider having a qualified person install a catch pan and drain or a water alarm to help prevent damage if water does leak.
A permanently installed insulated jacket was installed on the water heater. It obscured the manufacturer's information label and/or most of the water heater. The inspector was unable to fully evaluate the water heater.
Limitations: The following items are not included in this inspection: humidifiers, dehumidifiers, electronic air filters; solar, coal or wood fired heat systems; thermostat or temperature control accuracy and timed functions; heating components concealed within the building structure or in inaccessible areas; underground utilities and systems; safety devices and controls (due to automatic operation). Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on heating system components, does not determine if heating systems are appropriately sized, or perform any evaluations that require a pilot light to be lit. It is beyond the scope of this inspection to determine if furnace heat exchangers are intact and free of leaks.
Insulated blanket on water heater.
Condition of heating system: Appeared serviceable
Heating type: Convection
Fuel type: Electric
Condition of controls: Appeared serviceable
One or more windows in this structure were equipped with air supply ports (window vents). They're intended to improve indoor air quality in relatively air tight structures by supplying fresh air to living spaces and by reducing moisture accumulation. Air supply ports should be kept open at all times.
Limitations: The following items are not included in this inspection: household appliances such as stoves, ovens, cook tops, ranges, warming ovens, griddles, broilers, dishwashers, trash compactors, refrigerators, freezers, ice makers, hot water dispensers and water filters; appliance timers, clocks, cook functions, self and/or continuous cleaning operations, thermostat or temperature control accuracy, and lights. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of the remaining life of appliances, and does not determine the adequacy of operation of appliances. The inspector does not note appliance manufacturers, models or serial numbers and does not determine if appliances are subject to recalls. Areas and components behind and obscured by appliances are inaccessible and excluded from this inspection.
Kitchen appliances present during inspection: Range, Dishwasher, Refrigerator
Condition of counters: Appeared serviceable
Condition of cabinets: Appeared serviceable
Condition of sinks and related plumbing: Appeared serviceable
Condition of dishwasher: Required repair, replacement and/or evaluation (see comments below)
Condition of range, cooktop: Appeared serviceable
Range, cooktop type: Electric
Condition of refrigerator: Appeared serviceable
No high loop or air gap was visible for the dishwasher drain. A high loop is created by routing the drain line up to the bottom surface of the counter top above and securely fastening it to that surface. An air gap is a device that makes the drain line non-continuous. Both of these prevent waste-water backflow from entering the dishwasher, and possibly flooding out of the dishwasher if/when a siphon occurs. Some newer dishwashers have these devices built in. The client should try to determine if these devices are built in to this brand and model of dishwasher (e.g. review installation instructions). If not, or if this cannot be determined, then recommend that a qualified contractor install a high loop and air gap per standard building practices.
Limitations: The following items are not included in this inspection: overflow drains for tubs and sinks; bidets, heated towel racks, saunas, steam generators, clothes washers, clothes dryers. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of washing machine drain lines, washing machine catch pan drain lines, or clothes dryer exhaust ducts. The inspector does not operate water supply or shut-off valves for sinks, toilets, bidets, clothes washers, etc. due to the possibility of valves leaking or breaking when operated. The inspector does not determine if shower pans or tub and shower enclosures are water tight, or determine the completeness or operability of any gas piping to laundry appliances.
Location #A: Laundry room/area
Location #B: Main full bath
Location #C: Master bath
Condition of counters: Appeared serviceable
Condition of cabinets: Appeared serviceable
Condition of flooring: Required repairs, replacement and/or evaluation (see comments below)
Condition of sinks and related plumbing: Appeared serviceable
Condition of toilets: Required repair, replacement and/or evaluation (see comments below)
Condition of bathtubs and related plumbing: Appeared serviceable
Condition of shower(s) and related plumbing: Appeared serviceable
Condition of ventilation systems: Appeared serviceable
Gas supply for laundry equipment present: No
240 volt receptacle for laundry equipment present: Yes
The clothes dryer was equipped with a vinyl or mylar, accordion-type, flexible exhaust duct. The U.S. Consumer Product Safety Commission considers these types of ducts to be unsafe, and a fire hazard. They can trap lint and are susceptible to kinks or crushing, which can greatly reduce the air flow and cause overheating. Recommend that such ducts be replaced with a rigid or corrugated semi-rigid metal duct, and by a qualified contractor if necessary. For more information on dryer safety issues, visit:
Mylar clothes dryer exhaust duct.
Vinyl floor tiles was installed in the bathroom at location B. Spilled water may penetrate seams and damage the subfloor. Recommend that a qualified contractor install continuous waterproof flooring in wet areas such as bathrooms.
Vinyl floor tiles in main full bath.
Caulk was installed all the way around the base of the toilet at location B. Normally caulk is applied only 3/4 of the way around the toilet base for sanitary purposes and to prevent water intrusion. The back is normally left uncaulked so water can escape if a leak ever occurs. If the entire base is caulked and a leak develops in the seal at the base of the toilet, then water will leak down undetected into the floor and areas below. Recommend that caulk be removed from the back side of the toilet base(s) per standard building practices.
Limitations: The following items are not included in this inspection: security, intercom and sound systems; communications wiring; central vacuum systems; elevators and stair lifts; sources of obnoxious odors; cosmetic deficiencies such as nail-pops, scuff marks, dents, dings, blemishes or issues due to normal wear and tear in wall, floor and ceiling surfaces and coverings, or in equipment; deficiencies relating to interior decorating; low voltage and gas lighting systems. Any comments made regarding these items are as a courtesy only. Note that the inspector does not evaluate any areas or items which require moving stored items, furnishings, debris, equipment, floor coverings, insulation or similar materials. The inspector does not test for asbestos, lead, radon, mold, hazardous waste, urea formaldehyde urethane, or any other toxic substance. Some items such as window, drawer, cabinet door or closet door operability are tested on a sampled basis. The client should be aware that paint may obscure wall and ceiling defects, floor coverings may obscure floor defects, and furnishings may obscure wall, floor and floor covering defects. If furnishings were present during the inspection, recommend a full evaluation of walls, floors and ceilings that were previously obscured when possible. Determining the cause of odors is not within the scope of this inspection.
Toilet caulked all the way around base of toilet.
Condition of exterior entry doors: Appeared serviceable
Exterior door material: Metal, Sliding glass
Condition of interior doors: Appeared serviceable
Condition of windows and skylights: Appeared serviceable
Type of windows: Vinyl, Multi-pane, Sliding
Condition of walls and ceilings: Appeared serviceable
Wall type or covering: Drywall, Wallpaper
Ceiling type or covering: Drywall
Condition of flooring: Appeared serviceable
Flooring type or covering: Carpet, Laminate, Tile
Tile, stone and/or grout in the flooring in one or more areas was deteriorated (e.g. loose or cracked tiles, missing grout) or substandard. If in a wet area, water may damage the the subfloor. Recommend that a qualified contractor repair as necessary.
Limitations: This report only includes findings from accessible and visible areas on the day of the inspection. In addition to the inaccessible areas documented in this report, examples of other inaccessible areas include: sub areas less than 18 inches in height; attic areas less than five feet in height, areas blocked by ducts, pipes or insulation; areas where locks or permanently attached covers prevent access; areas where insulation would be damaged if traversed; areas obscured by vegetation. All inaccessible areas are subject to infestation or damage from wood destroying organisms. The inspector does not move furnishings, stored items, debris, floor or wall coverings, insulation, or other materials as part of the inspection, nor perform destructive testing. Wood destroying organisms may infest, reinfest or become active at anytime. No warranty is provided as part of this inspection.
Cracks in kitchen floor tiles.
Visible evidence of active wood destroying insects: No
Visible evidence of active wood decay fungi: Yes
Visible evidence of past wood destroying insects: No
Visible evidence of past wood decay fungi: Yes
Visible evidence of damage by wood destroying insects: No
Visible evidence of damage by wood decay fungi: Yes
Visible evidence of conditions conducive to wood destroying organisms: Yes
FOLLOW-UP INSPECTION POLICY
Generally we discourage follow-up inspections for these reasons
1. Quality of repairs
If repairs are made to a property based on the results of an inspection, the work should be performed by qualified contractors, not the seller. By qualified, we mean licensed, bonded, state-certified where applicable and with a reasonable amount of experience. Contractors providing repairs should provide legible documentation in the form of work orders and/or receipts. If repairs are made in this way, then there's generally no need for a follow-up inspection. Additionally, it may be better to negotiate a lower price on your home and have repairs made by contractors you choose rather than the seller making repairs as cheaply as possible.
2. Pest inspections required for some follow-up inspections
On occasion, some follow-up inspections may require a complete, new structural pest inspection. Examples include:Evaluating a crawl space after carpenter ant infestation was foundEvaluating numerous items throughout a structure after a significant amount of time has passed (original inspection in winter, follow-up in summer)
Our fees for follow-up inspections are as follows:
Follow-up inspection: $150Follow-up inspections with a structural pest (WDO/WDI) inspection: $250
Additional charges usually apply for travel outside of Kitsap County
SCOPE AND LIMITATIONS OF THIS INSPECTION
This inspection is limited to a visual observation of the exposed and readily accessible areas of the home. The concealed and inaccessible areas are not included. The following locations are considered inaccessible due to limited height and excluded from this inspection unless otherwise stated:
Crawl space areas less than 18 inches in heightAttic spaces less than 5 feet in heightSpaces under outdoor decks less than 5 feet high
Observation includes operation of the systems or components by means of the normal user controls. Dismantling of equipment, and destructive testing is not included. Some specific items are also excluded, and these are listed in the following section. If you feel there is a need for evaluation of any of these items, then you will need to arrange for specific inspections.
Items not Included
As a part of our service, we sometimes provide approximate, cost of repair estimates for particular items. These estimates should be considered as background information only. It is beyond the scope of this inspection and report to supply you with accurate repair costs. Such estimates should be supplied by contractors who specialize in this type of work. Our estimates should be used only as guidelines. If you intend to negotiate the price of this property based on defects found during this inspection, we strongly suggest you obtain one or more written bids from a licensed contractor(s). It is a conflict of interest for All Point Home Inspections to recommend any specific contractor.
- Recreational, leisure, playground or decorative equipment or appliances including but not limited to pools, hot tubs, saunas, steam baths, landscape lighting, fountains, shrubs, trees, and tennis courts;
- Cosmetic conditions (wallpapering, painting, carpeting, scratches, scrapes, dents, cracks, stains, soiled or faded surfaces on the structure or equipment, soiled, faded, torn, or dirty floor, wall or window coverings etc.);
- Noise pollution or air quality in the area;
- Earthquake hazard, liquefaction, flood plain, soil, slide potential or any other geological conditions or evaluations;
- Engineering level evaluations on any topic;
- Existence or non-existence of solder or lead in water pipes, asbestos, hazardous waste, radon, urea formaldehyde urethane, lead paint or any other environmental, flammable or toxic contaminants or the existence of water or airborne diseases or illnesses and all other similar or potentially harmful substances (although the inspector may note the possible existence of asbestos in ceiling texture and furnace duct tape);
- Zoning or municipal code (e.g. building, fire, housing (existing buildings), mechanical, electrical, plumbing, etc. code) restrictions or other legal requirements of any kind;
- Any repairs which relate to some standard of interior decorating;
- Cracked heat exchangers or similar devices in furnaces;
- Any evaluation which requires the calculation of the capacity of any system or item that is expected to be part of the inspection. Examples include but are not limited to the calculation of appropriate wattage or wiring of kitchen appliances, appropriate sizing of flues or chimneys, appropriate ventilation to combustion-based items (e.g. furnaces, water heaters, fireplaces etc.), appropriate sizing, spacing and spanning of joists, beams, columns, girders, trusses, rafters, studs etc., appropriate sizing of plumbing and fuel lines, etc.;
- Washers and dryers;
- Circuit breaker operation;
- Specialty evaluations such as private sewage, wells, solar heating systems, alarms, intercom systems, central vacuum systems, wood and coal stoves, pre-fab and zero clearance fireplaces, space heaters, sprinkler systems, gas logs, gas lights, elevators and common areas unless these have been specifically added to the inspection description above but only to the degree that the inspector is capable of evaluating these items;
- Items that are not visible and exposed including but not limited to concealed wiring, plumbing, water leaks, under bathtubs and shower stalls due to faulty pans or otherwise, vent lines, duct work, exterior foundation walls (below grade or covered by shrubs or wall/paneling, stored goods etc.) and footings, underground utilities, and systems and chimney flues;
- Evaluations involving destructive testing;
- Evaluation which requires moving personal goods, debris, furniture, equipment, floor covering, insulation or like materials;
- Design problems and adequacy or operational capacity, quality or suitability;
- Fireplace drafting;
- To prevent damages to units, air conditioning when outside temperature below 60 degrees F or if the unit has not been warmed up or on for at least 24 hours prior to inspection;
- Any evaluation which would involve scraping paint or other wall coverings;
- Heating system accessories (e.g. humidifiers, electronic air cleaners etc.);
- Legal description of property such as boundaries, egress/ingress, etc.;
- Quality of materials;
- Conformance with plan specifications or manufacturers specifications;
- Flood conditions or plains;
- Any other characteristics or items which are generally not included in a building inspection report on a regular basis.
Evaluations are made as to the present age, and remaining economic life of an item, i.e. water heaters, roofs, plumbing, furnaces, etc. These evaluations are based on visual observation, industry averages and prior experience. THEY ARE NOT OFFERED AS A WARRANTY OR CERTIFICATION OF REMAINING LIFE.
In some cases we may recommend your consulting a specialist such as a structural engineer or licensed electrician. Hiring a specialist can be a prudent means of providing some protection of your financial investment in this property. WE DO NOT MAKE ANY TYPE OF WARRANTY OR GUARANTEE AS TO THE CONDITION OF THE PROPERTY. SOME THINGS MAY REMAIN HIDDEN OR BECOME DEFECTIVE AFTER THE INSPECTION. IT IS NOT POSSIBLE TO DETECT EVERY DEFECT WITHIN A BUILDING DURING THE COURSE OF A GENERAL INSPECTION. THIS REPORT SHOULD BE USED IN CONJUNCTION WITH, AND NOT A REPLACEMENT FOR , A PRE-CLOSING WALK-THROUGH BY THE CLIENT.
THIS INSPECTION IS NOT AN INSURANCE POLICY AGAINST HIDDEN DEFECTS, OR CONDITIONS THAT ARE NOT VISIBLE AND READILY APPARENT AT THE TIME OF INSPECTION.
THE COST OF THIS INSPECTION DOES NOT ENTITLE YOU TO ANY TYPE OF PROTECTION FROM HIDDEN FLAWS AND DEFECTS. THIS INSPECTION DOES NOT TRANSFER YOUR ULTIMATE RESPONSIBILITY TO ALL POINT HOME INSPECTIONS.