This report published on Wednesday, October 31, 2018 6:30:03 AM PDT
This report is the exclusive property of this inspection company and the client listed in the report title. Use of this report by any unauthorized persons is prohibited.
How to Read this Report
This report is organized by the property's functional areas. Within each functional area, descriptive information is listed first and is shown in bold type. Items of concern follow descriptive information.
Concerns are shown and sorted according to these types:
Poses a safety concern
Recommend repairing or replacing
Recommend repair and/or maintenance
Correction usually involves a minor expense
Recommend ongoing maintenance
Recommend evaluation by a specialist
Recommend monitoring in the future
For your information
Conditions conducive for wood destroying insects or organisms (Wood-soil contact, shrubs in contact with siding, roof or plumbing leaks, etc.)
Click here for a glossary of building construction terms.Contact your inspector If there are terms that you do not understand, or visit the glossary of construction terms at https://www.reporthost.com/glossary.asp
Client present for discussion at end of inspection: Yes
Weather conditions during inspection: Dry (no rain)
Temperature during inspection: Cool
Ground condition: Wet
Recent weather: Dry (no rain), Rain
Overnight temperature: Cold
Inspection fee: $000.00
Payment method: Check 1851
Type of building: Single family
Buildings inspected: One house
Age of main building: 2013
Source for main building age: Municipal records or property listing
1) The client should be aware that a break-in period occurs during the first year or two after a building is constructed. Some amount of settlement and shrinkage is inevitable as temperature and humidity varies during the seasons. Systems may need adjustment or repair after experiencing constant, prolonged and/or heavy usage. Overall performance of the building exterior has not yet been tested by a wide variety of weather conditions.
Also, it is beyond the scope of this inspection to determine if all permits have been approved or signed off. Consult with the builder and/or municipality to determine if all necessary permits have been approved.
Limitations: Unless specifically included in the inspection, the following items and any related equipment, controls, electric systems and/or plumbing systems are excluded from this inspection: detached buildings or structures; fences and gates; retaining walls; underground drainage systems, catch basins or concealed sump pumps; swimming pools and related safety equipment, spas, hot tubs or saunas; whether deck, balcony and/or stair membranes are watertight; trees, landscaping, properties of soil, soil stability, erosion and erosion control; ponds, water features, irrigation or yard sprinkler systems; sport courts, playground, recreation or leisure equipment; areas below the exterior structures with less than 3 feet of vertical clearance; invisible fencing; sea walls, docks and boathouses; retractable awnings. Any comments made regarding these items are as a courtesy only.
Site profile: Moderate slope
Condition of driveway: Appeared serviceable
Driveway material: Poured in place concrete
Condition of sidewalks and/or patios: Appeared serviceable
Sidewalk material: Poured in place concrete
Condition of decks, porches and/or balconies: Appeared serviceable
Deck, porch and/or balcony material: Concrete
2) Significant amounts of standing water or evidence of past accumulated water were found at one or more locations in the yard or landscaped areas, and no drain was visible. If evidence of past water was found (e.g. silt accumulation or staining), monitor these areas in the future during periods of heavy rain. If standing water exists, recommend that a qualified person repair as necessary. For example, installing one or more drains, or grading soil.
3) The soil or grading sloped down towards building perimeters in one or more areas. This can result in water accumulating around building foundations or underneath buildings. It is a conducive condition for wood-destroying organisms. Recommend grading soil so it slopes down and away from buildings with a slope of at least 1 inch per horizontal foot for at least 6 feet out from buildings.
Limitations: The inspector performs a visual inspection of accessible components or systems at the exterior. Items excluded from this inspection include below-grade foundation walls and footings; foundations, exterior surfaces or components obscured by vegetation, stored items or debris; wall structures obscured by coverings such as siding or trim. Some items such as siding, trim, soffits, vents and windows are often high off the ground, and may be viewed using binoculars from the ground or from a ladder. This may limit a full evaluation. Regarding foundations, some amount of cracking is normal in concrete slabs and foundation walls due to shrinkage and drying. Note that the inspector does not determine the adequacy of seismic reinforcement.
Condition of wall exterior covering: Appeared serviceable
Apparent wall structure: Wood frame
Wall covering: Wood fiber, Cement fiber
Condition of foundation and footings: Appeared serviceable, Required repairs, replacement and/or evaluation (see comments below)
Apparent foundation type: Crawl space
Foundation/stem wall material: Poured in place concrete
Footing material (under foundation stem wall): Poured in place concrete
Anchor bolts or hold downs for seismic reinforcement: Installed
4) It appeared that the exterior foundation walls did not have a waterproof protective coating on them. A qualified contractor should evaluate and repair as necessary.
Limitations: Structural components such as joists and beams, and other components such as piping, wiring and/or ducting that are obscured by under-floor insulation are excluded from this inspection. The inspector does not determine if support posts, columns, beams, joists, studs, trusses, etc. are of adequate size, spanning or spacing.
The inspector does not guarantee or warrant that water will not accumulate in the crawl spaces in the future. Complete access to all crawl space areas during all seasons and during prolonged periods of all types of weather conditions (e.g. heavy rain, melting snow) would be needed to do so.
The inspector attempts to locate all crawl space access points and areas. Access points may be obscured or otherwise hidden by furnishings or stored items. In such cases, the client should ask the property owner where all access points are that are not described in this inspection, and have those areas inspected. Note that crawl space areas should be checked at least annually for water intrusion, plumbing leaks and pest activity.
Crawl space inspection method: Traversed
Location of crawl space access point: Hall closet
Condition of floor substructure above crawl space: Appeared serviceable
Pier or support post material: Wood
Beam material: Solid wood
Floor structure: Solid wood joists
Condition of insulation underneath floor above: Appeared serviceable
Insulation material underneath floor above: Fiberglass roll or batt
Condition of vapor barrier: Appeared serviceable, Required repairs, replacement and/or evaluation (see comments below)
Vapor barrier present: Partial
Condition of crawl space ventilation: Appeared serviceable
Ventilation type: Unconditioned space with vents
5) Water was found at one or more locations in the crawl space. Water from crawl spaces can evaporate and enter the structure above causing high levels of moisture in the structure. This is a conducive condition for wood-destroying organisms. While a minor amount of seasonal water is commonly found in crawl spaces, significant amounts should not be present.
Rain runoff is the most common cause of wet crawl spaces, but water can come from other sources such as groundwater or underground springs. Recommend that a qualified person correct any issues related to outside perimeter grading and/or roof drainage (see any other comments about this in this report). If standing water persists, then recommend that a qualified contractor who specializes in drainage issues evaluate and repair as necessary. Typically such repairs include:
Repairing, installing or improving underground footing and/or curtain drains
Applying waterproof coatings to foundation walls
Digging trenches in the crawl space to collect or divert water
Installing sump pumps
6) The vapor barrier in some areas of the crawl space was loose or askew and substandard. Soil was exposed as a result and will allow water from the soil to evaporate up into the structure. This is a conducive condition for wood-destroying organisms. A 6 mil black plastic sheet should be placed over all exposed soil with seams overlapped to 24 inches, and not in contact with any wood structural components. The sheeting should be held in place with bricks or stones, not wood. Recommend that a qualified person replace or repair the vapor barrier where necessary and per standard building practices.
7) Cellulose material such as scrap wood was found in the crawl space. This is a conducive condition for wood-destroying organisms. Recommend removing all cellulose-based debris or stored items.
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; solar roofing components. Any comments made regarding these items are made as a courtesy only. Note that the inspector does not provide an estimate of remaining life on the roof surface material, nor guarantee that leaks have not occurred in the roof surface, skylights or roof penetrations in the past. Regarding roof leaks, only active leaks, visible evidence of possible sources of leaks, and evidence of past leaks observed during the inspection are reported on as part of this inspection. The inspector does not guarantee or warrant that leaks will not occur in the future. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high wind and rain, melting snow) would be needed to do so. Regarding the roof drainage system, unless the inspection was conducted during and after prolonged periods of heavy rain, the inspector was unable to determine if gutters, downspouts and extensions performed adequately or were leak-free.
Inspector's estimate of roof surface age: 2013
Roof inspection method: Viewed from ground with binoculars
Condition of roof surface material: Appeared serviceable
Roof surface material: Asphalt or fiberglass composition shingles
Roof type: Gable
Apparent number of layers of roof surface material: One
Condition of exposed flashings: Appeared serviceable
Condition of gutters, downspouts and extensions: Appeared serviceable
Gutter and downspout material: Metal
Gutter and downspout installation: Full
8) One or more downspouts terminated above a roof surface, and rainwater from the downspouts washes over the roof surface below. This is a common configuration, but in some cases large quantities of rainwater can damage shingles by removing granules and reduce the life of the roof surface. Consider installing extensions to route the rainwater directly to the closest gutter below to prevent such damage.
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; areas and components obscured by insulation. Any comments made regarding these items are made as a courtesy only. The inspector does not determine the adequacy of the attic ventilation system. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high/low temperatures, high/low humidity, high wind and rain, melting snow) would be needed to do so. The inspector is not a licensed engineer and does not determine the adequacy of roof structure components such as trusses, rafters or ceiling beams, or their spacing or sizing.
Attic inspection method: Partially traversed
Location of attic access point: Master bedroom closet, second floor
Condition of roof structure: Appeared serviceable
Condition of insulation in attic (ceiling, skylight chase, etc.): Appeared serviceable
Ceiling insulation material: Mineral wool loose fill
Approximate attic insulation R value (may vary in areas): More than R-38
Condition of roof ventilation: Required repair, replacement and/or evaluation (see comments below)
9) The roof structure had no visible venting. This can result in high attic and roof surface temperatures, reduce the life of the roof covering materials, and/or increase cooling costs. High levels of moisture are also likely to accumulate in the roof structure or attic, and can be a conducive condition for wood-destroying organisms. Standard building practices require one free square foot of ventilation for every 150 square feet of attic space, and that vents be evenly distributed between the lowest points of the roof structure and the highest points to promote air circulation. Often this means that both soffit vents and ridge or gable end vents are installed. Recommend that a qualified contractor evaluate and install vents per standard building practices.
Limitations: The inspector does not determine the adequacy of firewall ratings. Requirements for ventilation in garages vary between municipalities.
Type: Attached garage
Condition of garage to house door: Required repair, replacement and/or evaluation (see comments below)
Type of door between garage and house: Solid core
Condition of garage vehicle doors: Appeared serviceable
Type of garage vehicle door: Sectional
Number of vehicle doors: 2
Condition of automatic openers: Appeared serviceable
Mechanical auto-reverse operable (reverses when meeting reasonable resistance during closing): Yes
Condition of garage floor: Appeared serviceable
Condition of garage interior: Appeared serviceable
Garage ventilation: Adequate
11) The self-closing device on the door between the garage and the house didn't close and latch the door. These devices are installed to keep the door closed to prevent possible fire and fumes from the garage from spreading to the house. Recommend that a qualified person repair as necessary.
12) The door between the garage and the house didn't self-latch when closed via the self-closing device because of damage or deterioration to the door hardware. House to garage doors prevent fire and fumes from spreading from the garage to the house. Self-closing devices keep the door closed for this purpose. Recommend that a qualified person repair as necessary.
Limitations: The following items are not included in this inspection: generator systems, transfer switches, surge suppressors, inaccessible or concealed wiring; underground utilities and systems; low-voltage lighting or lighting on timers or sensors. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of grounding or bonding, if this system has an adequate capacity for the client's specific or anticipated needs, or if this system has any reserve capacity for additions or expansion. The inspector does not operate circuit breakers as part of the inspection, and does not install or change light bulbs. The inspector does not evaluate every wall switch or receptacle, but instead tests a representative number of them per various standards of practice. When furnishings, stored items or child-protective caps are present some receptacles are usually inaccessible and are not tested; these are excluded from this inspection. Receptacles that are not of standard 110 volt configuration, including 240-volt dryer receptacles, are not tested and are excluded. The functionality of, power source for and placement of smoke and carbon monoxide detectors is not determined as part of this inspection. Upon taking occupancy, proper operating and placement of smoke and carbon monoxide detectors should be verified and batteries should be changed. These devices have a limited lifespan and should be replaced every 10 years. The inspector attempts to locate and evaluate all main and sub-panels. However, panels are often concealed. If panels are found after the inspection, a qualified electrician should evaluate and repair if necessary. The inspector attempts to determine the overall electrical service size, but such estimates are not guaranteed because the overall capacity may be diminished by lesser-rated components in the system. Any repairs recommended should be made by a licensed electrician.
Electric service condition: Appeared serviceable
Primary service type: Underground
Number of service conductors: 3
Service voltage (volts): 120-240
Estimated service amperage: 200
Primary service overload protection type: Circuit breakers
System ground: Ground rod(s) in soil
Condition of main service panel: Appeared serviceable
Location of main service panel: Garage
Location of main disconnect: Breaker at bottom of main service panel
Limitations: The following items are not included in this inspection: private/shared wells and related equipment; private sewage disposal systems; hot tubs or spas; main, side and lateral sewer lines; gray water systems; pressure boosting systems; trap primers; incinerating or composting toilets; fire suppression systems; water softeners, conditioners or filtering systems; plumbing components concealed within the foundation or building structure, or in inaccessible areas such as below tubs; underground utilities and systems; overflow drains for tubs and sinks; backflow prevention devices. Any comments made regarding these items are as a courtesy only. Note that the inspector does not operate water supply or shut-off valves due to the possibility of valves leaking or breaking when operated. The inspector does not test for lead in the water supply, the water pipes or solder, does not determine if plumbing and fuel lines are adequately sized, and does not determine the existence or condition of underground or above-ground fuel tanks.
Condition of service and main line: Appeared serviceable
Location of main water meter: By street
Location of main water shut-off: Garage
Water service: Public
Service pipe material: Not determined (inaccessible or obscured)
Condition of supply lines: Appeared serviceable
Supply pipe material: PEX plastic
Condition of drain pipes: Appeared serviceable
Drain pipe material: Plastic
Condition of waste lines: Appeared serviceable
Waste pipe material: Plastic
Location of plumbing clean-out: Crawl space
Vent pipe condition: Appeared serviceable
Vent pipe material: Plastic
Sump pump installed: No
Sewage ejector pump installed: No
Condition of fuel system: Appeared serviceable
Location of main fuel shut-off valve: At gas meter
14) Photo of main water shut-off in garage, for your information
Limitations: Evaluation of and determining the adequacy or completeness of the following items are not included in this inspection: water recirculation pumps; solar water heating systems; Energy Smart or energy saver controls; catch pan drains. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on water heaters, does not determine if water heaters are appropriately sized, or perform any evaluations that require a pilot light to be lit or a shut-off valve to be operated.
Condition of water heater: Appeared serviceable
Energy source: Natural gas
Estimated age: 2013
Capacity (in gallons): 50
Temperature-pressure relief valve installed: Yes
Manufacturer: Bradford White
Model number: M15036FBN
Serial number: KE18245720
Location of water heater: Garage
Hot water temperature tested: No
Condition of burners: Appeared serviceable
Condition of venting system: Appeared serviceable, Required repair, replacement and/or evaluation (see comments below)
Condition of combustion air supply: Appeared serviceable
15) No thermal expansion tank was installed at the water heater, and the plumbing system may be "closed" based on the inspector's observation of a pressure-reducing valve installed in this system. Some pressure-reducing valves have an integrated bypass check valve that allows water under high pressure from thermal expansion to flow back to the supply main. However, the inspector was unable to determine if the pressure-reducing valve in this system was equipped with such a bypass check valve. If none is present then the system is "closed," and an expansion tank should be installed to allow room for water in the system to expand. Without one, the water heater's temperature-pressure relief valve can leak or become damaged, or toilets can "run" due to excess pressure overcoming the fill valve. Recommend that a qualified plumber evaluate further and install an expansion tank per standard building practices if necessary.
16) The water heater was installed in an unheated space on a concrete floor and was not resting on an insulated pad. The bottom of the casing is likely to rust, and energy efficiency may be reduced. Recommend installing an insulated pad under the water heater.
Limitations: The following items are not included in this inspection: humidifiers, dehumidifiers, electronic air filters; solar, coal or wood-fired heat systems; thermostat or temperature control accuracy and timed functions; heating components concealed within the building structure or in inaccessible areas; underground utilities and systems; safety devices and controls (due to automatic operation). Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on heating or cooling system components, does not determine if heating or cooling systems are appropriately sized, does not test coolant pressure, or perform any evaluations that require a pilot light to be lit, a shut-off valve to be operated, a circuit breaker to be turned "on" or a serviceman's or oil emergency switch to be operated. It is beyond the scope of this inspection to determine if furnace heat exchangers are intact and free of leaks. Condensation pans and drain lines may clog or leak at any time and should be monitored while in operation in the future. Where buildings contain furnishings or stored items, the inspector may not be able to verify that a heat source is present in all "liveable" rooms (e.g. bedrooms, kitchens and living/dining rooms).
General heating system type: Forced air
General heating distribution type: Ducts and registers
Condition of forced air heating/(cooling) system: Appeared serviceable
Forced air heating system fuel type: Natural gas
Estimated age of forced air furnace: 2013
Forced air furnace model number: TG91S060B 12MP11A
Forced air furnace serial number: W1A3385363
Location of forced air furnace: Attic
Forced air system capacity in BTUs or kilowatts: 60,000
Condition of furnace filters: Appeared serviceable
Location for forced air filter: Behind return air grill
Condition of forced air ducts and registers: Appeared serviceable
Condition of controls: Appeared serviceable
Condition of whole house fan: Appeared serviceable
18) Drywall dust, and construction debris such as drywall dust and/or sawdust was found behind or below heating or cooling air supply registers. Drywall dust in particular can reduce the life of heating and cooling equipment if left to circulate. At a minimum, recommend vacuuming ducts at each register. Consider having a qualified contractor clean the ducts.
19) Recommend replacing or washing HVAC filters upon taking occupancy depending on the type of filters installed. Regardless of the type, recommend checking filters monthly in the future and replacing or washing them as necessary. How frequently they need replacing or washing depends on the type and quality of the filter, how the system is configured (e.g. always on vs. "Auto"), and on environmental factors (e.g. pets, smoking, frequency of house cleaning, number of occupants, the season).
Limitations: The following items are not included in this inspection: coal stoves, gas logs, chimney flues (except where visible). Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of drafting or sizing in fireplace and stove flues, and also does not determine if prefabricated or zero-clearance fireplaces are installed in accordance with the manufacturer's specifications. The inspector does not perform any evaluations that require a pilot light to be lit, and does not light fires. The inspector provides a basic visual examination of a chimney and any associated wood burning device. The National Fire Protection Association has stated that an in-depth Level 2 chimney inspection should be part of every sale or transfer of property with a wood-burning device. Such an inspection may reveal defects that are not apparent to the home inspector who is a generalist.
Condition of gas-fired fireplace: Appeared serviceable, Required repair, replacement and/or evaluation (see comments below)
Gas fireplace type: Metal pre-fab fireplace
Fan or blower installed in gas-fired fireplace: No
Condition of chimneys and flues: Appeared serviceable, Required repair, replacement and/or evaluation (see comments below)
Chimney type: Metal
21) The metal water heater chimney extended higher than 5 feet above the roof surface, and supports for the flue were missing and/or substandard. This is a potential safety hazard due to the risk of the flue pipe moving and possibly being damaged or becoming loose. Surrounding flashing, roof sheathing and/or roof surface materials may also be overstressed during chimney movement. Recommend that a qualified person install bracing per standard building practices.
22) The electric receptacle for the fireplace was lying loose. A qualified electrician should install as necessary and according to standard building practices.
23) Photos of the gas fireplace, for your information
Limitations: The following items are not included in this inspection: household appliances such as stoves, ovens, cook tops, ranges, warming ovens, griddles, broilers, dishwashers, trash compactors, refrigerators, freezers, ice makers, hot water dispensers and water filters; appliance timers, clocks, cook functions, self and/or continuous cleaning operations, thermostat or temperature control accuracy, and lights. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of the remaining life of appliances, and does not determine the adequacy of operation of appliances. The inspector does not note appliance manufacturers, models or serial numbers and does not determine if appliances are subject to recalls. Areas and components behind and obscured by appliances are inaccessible and excluded from this inspection.
Condition of counters: Appeared serviceable
Condition of cabinets: Appeared serviceable
Condition of sinks and related plumbing: Appeared serviceable
Condition of under-sink food disposal: Appeared serviceable
Condition of dishwasher: Appeared serviceable
Condition of range, cooktop: Appeared serviceable
Range, cooktop type: Natural gas
Condition of refrigerator: Appeared serviceable
Condition of built in microwave: Appeared serviceable
24) The refrigerator door handle was loose. Recommend that a qualified person repair or replace as necessary.
Limitations: The following items are not included in this inspection: overflow drains for tubs and sinks; heated towel racks, saunas, steam generators, clothes washers, clothes dryers. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of washing machine drain lines, washing machine catch pan drain lines, or clothes dryer exhaust ducts. The inspector does not operate water supply or shut-off valves for sinks, toilets, bidets, clothes washers, etc. due to the possibility of valves leaking or breaking when operated. The inspector does not determine if shower pans or tub and shower enclosures are water tight, or determine the completeness or operability of any gas piping to laundry appliances.
Location A: Half bath
Location B: Full bath
Location C: Master bath
Condition of counters: Appeared serviceable
Condition of cabinets: Appeared serviceable
Condition of flooring: Appeared serviceable
Condition of sinks and related plumbing: Appeared serviceable
Condition of toilets: Appeared serviceable
Condition of bathtubs and related plumbing: Appeared serviceable
Condition of showers and related plumbing: Appeared serviceable
Condition of ventilation systems: Appeared serviceable
Gas supply for laundry equipment present: No
240 volt receptacle for laundry equipment present: Yes
26) A significant amount of water came out of the bathtub spout when the shower at location B was turned on. The diverter valve is likely defective, or may be encrusted with mineral deposits. Water will be wasted as a result. Recommend that a qualified plumber repair or replace components as necessary.
27) Rubber water supply hoses installed at the clothes washer are prone to bursting when deteriorated, which can result in flooding and significant water damage. Recommend upgrading to braided, stainless steel hoses.
Limitations: The following items are not included in this inspection: security, intercom and sound systems; communications wiring; central vacuum systems; elevators and stair lifts; cosmetic deficiencies such as nail-pops, scuff marks, dents, dings, blemishes or issues due to normal wear and tear in wall, floor and ceiling surfaces and coverings, or in equipment; deficiencies relating to interior decorating; low voltage and gas lighting systems. Any comments made regarding these items are as a courtesy only. Note that the inspector does not evaluate any areas or items which require moving stored items, furnishings, debris, equipment, floor coverings, insulation or similar materials. The inspector does not test for asbestos, lead, radon, mold, hazardous waste, urea formaldehyde urethane, or any other toxic substance. Some items such as window, drawer, cabinet door or closet door operability are tested on a sampled basis. The client should be aware that paint may obscure wall and ceiling defects, floor coverings may obscure floor defects, and furnishings may obscure wall, floor and floor covering defects. If furnishings were present during the inspection, recommend a full evaluation of walls, floors and ceilings that were previously obscured when possible. Determining the cause and/or source of odors is not within the scope of this inspection.
Condition of exterior entry doors: Appeared serviceable
Condition of interior doors: Appeared serviceable
Condition of windows and skylights: Appeared serviceable
Types of windows: Vinyl, Multi-pane, Sliding, Fixed
Condition of walls and ceilings: Appeared serviceable
Wall type or covering: Drywall
Ceiling type or covering: Drywall
Condition of flooring: Appeared serviceable, Required repairs, replacement and/or evaluation (see comments below)
Flooring type or covering: Carpet, Laminate
Condition of stairs, handrails and guardrails: Appeared serviceable, Required repairs, replacement and/or evaluation (see comments below)
28) Handrails at one or more flights of stairs were loose. This is a safety hazard. Recommend that a qualified person repair as necessary.
29) Squeaking or creaking noises occur when walking on one or more sections of flooring in the kitchen and TV room. This is usually caused by substandard construction practices where the sub-floor decking is not adequately fastened to the framing below. For example, not enough glue was used and/or nails were used rather than screws. In most cases, this is only an annoyance rather than a structural problem. Various solutions such as Squeeeeek No More and Counter Snap fasteners exist to correct this. Repairs to eliminate the squeaks or creaks may be more or less difficult depending on the floor covering and the access to the underside of the sub-floor. Recommend that a qualified contractor evaluate and repair as necessary. For more information, visit: http://www.google.com/search?hl=en&q=squeaky+f
This completes your home inspection report. Thank you for your business.