This report published on Sunday, December 6, 2020 7:07:48 AM PST
This report is the exclusive property of this inspection company and the client(s) listed in the report title. Use of this report by any unauthorized persons is prohibited.
Thank you for choosing Alicante Home Inspections to perform the following inspection on the property you wish to purchase. This report is the exclusive property of Alicante Home Inspections and the individual/s paying for the inspection fee and report. Use of this report by any unauthorized persons is prohibited.
All findings should be made to Alicante Property Inspections.
This report represents our professional opinion of the condition of the inspected elements of the subject property, determine during a limited time inspection. This inspection was performed, where applicable, in a manner consistent with the standards of the home inspection industry, terms and conditions of the inspection agreement and limitations noted in the inspection agreement. Information contained herein was prepared exclusively for the named client and their authorized representatives.
We have inspected the subject property and must report to you exactly what we found. Because of the age, design and location of the home, we might find some hairline cracks on driveways or walls, see paint peeling off Walls, cracks on tiles, chipped bathtubs or some cracks over windows and doors. These are normal and cosmetic conditions.
While due care was exercised in the performance of this inspection, the company makes no representations or guarantees with respect to latent deficiencies or future conditions as part of the inspection or this report. This report is valid only for a period of thirty (30) days from the date of the inspection. This report, including any attachments, should be reviewed in its entirety. Any questions about the inspection or report should be resolved prior to title transfer.
If this property was unoccupied and the plumbing system has not been in continuous operation recently. It's possible for plumbing leaks to exist but not be apparent. Leaks can be small and take time to become visible. The inspector normally operates all accessible and operable plumbing fixtures, but this limited inspection may not reveal small leaks that only become visible after constant use of the plumbing system. After taking occupancy, monitor the plumbing system for leaks that may become apparent. Areas below the house should be evaluated after plumbing has been operated to check for leaks. Any problems that are found should be repaired by a qualified plumber.
This inspection report was prepared in a format specifically for the individual/s paying for the inspections fee and report and such transfer does not cover all potential areas of concern a third party may have. This report is transferable only with the consent of the individual/s paying for inspections fee and report and such transfer does not imply any warranty or guarantee regarding the report by inspection firm.
If you have any questions regarding this report, please feel free to call us.
How to Read this Report
This report is organized by the property's functional areas. Within each functional area, descriptive information is listed first and is shown in bold type. Items of concern follow descriptive information.
Concerns are shown and sorted according to these types:
Poses a safety hazard
Recommend repairing or replacing
Recommend repair and/or maintenance
Correction likely involves only a minor expense
Recommend ongoing maintenance
Recommend evaluation by a specialist
Recommend monitoring in the future
Item or component is in serviceable condition
For your information
Click here for a glossary of building construction terms.Contact your inspector If there are terms that you do not understand, or visit the glossary of construction terms at https://www.reporthost.com/glossary.asp
Limitations: Unless specifically included in the inspection, the following items and any related equipment, controls, electric systems and/or plumbing systems are excluded from this inspection: detached buildings or structures; fences and gates; retaining walls; underground drainage systems, catch basins or concealed sump pumps; swimming pools and related safety equipment, spas, hot tubs or saunas; whether deck, balcony and/or stair membranes are watertight; trees, landscaping, properties of soil, soil stability, erosion and erosion control; ponds, water features, irrigation or yard sprinkler systems; sport courts, playground, recreation or leisure equipment; areas below the exterior structures with less than 3 feet of vertical clearance; invisible fencing; sea walls, docks and boathouses; retractable awnings. Any comments made regarding these items are as a courtesy only.
Condition of fences and gates: Appeared serviceable
Fence and gate material: Wood, Wrought iron, Masonry
Condition of retaining walls: Appeared serviceable
Retaining wall material: Masonry block
Site profile: Minor slope
Condition of driveway: Appeared serviceable
Driveway material: Poured in place concrete
Condition of sidewalks and/or patios: Appeared serviceable
Sidewalk material: Poured in place concrete
Condition of deck, patio and/or porch covers: Appeared serviceable
Deck, patio, porch cover material and type: Open, Covered (Refer to Roof section)
Condition of decks, porches and/or balconies: Appeared serviceable
Deck, porch and/or balcony material: Waterproof coating or membrane
3) Recommend installing a drain screens on one or more decks, this helps to prevent clog ups and debris from entering and plugging up drain.
4) The condition of the drain(s) is unknown. It's beyond the scope of a home inspection to determine if these drains flow adequately during prolonged periods of heavy rain. Recommend consulting with the property owners about this if possible, and monitoring drains in the future. If water is found to accumulate, then recommend that a qualified contractor evaluate and repair as necessary. For example, by cleaning, repairing or installing drains.
Limitations: The inspector performs a visual inspection of accessible components or systems at the exterior. Items excluded from this inspection include below-grade foundation walls and footings; foundations, exterior surfaces or components obscured by vegetation, stored items or debris; wall structures obscured by coverings such as siding or trim. Some items such as siding, trim, soffits, vents and windows are often high off the ground, and may be viewed using binoculars from the ground or from a ladder. This may limit a full evaluation. Regarding foundations, some amount of cracking is normal in concrete slabs and foundation walls due to shrinkage and drying. Note that the inspector does not determine the adequacy of seismic reinforcement.
Wall inspection method: Viewed from ground
Condition of wall exterior covering: Appeared serviceable
Apparent wall structure: Wood frame
Wall covering: Stucco, Wood
Condition of foundation and footings: Appeared serviceable
Apparent foundation type: Concrete slab on grade
Footing material (under foundation stem wall): Poured in place concrete
6) Trees were in contact with or were close to the building at one or more locations. Damage to the building may occur, especially during high winds, or may have already occurred (see other comments in this report). Recommend that a qualified tree service contractor or certified arborist remove trees as necessary to prevent damage to the building exterior.
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; solar roofing components. Any comments made regarding these items are made as a courtesy only. Note that the inspector does not provide an estimate of remaining life on the roof surface material, nor guarantee that leaks have not occurred in the roof surface, skylights or roof penetrations in the past. Regarding roof leaks, only active leaks, visible evidence of possible sources of leaks, and evidence of past leaks observed during the inspection are reported on as part of this inspection. The inspector does not guarantee or warrant that leaks will not occur in the future. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high wind and rain, melting snow) would be needed to do so. Occupants should monitor the condition of roofing materials in the future. For older roofs, recommend that a professional inspect the roof surface, flashings, appurtenances, etc. annually and maintain/repair as might be required. If needed, the roofer should enter attic space(s). Regarding the roof drainage system, unless the inspection was conducted during and after prolonged periods of heavy rain, the inspector was unable to determine if gutters, downspouts and extensions perform adequately or are leak-free.
Roof inspection method: Scanned roof using aerial drone with HD camera
Condition of roof surface material: Appeared serviceable
Roof surface material: Concrete tile
Roof type: Gable
Apparent number of layers of roof surface material: One
Condition of exposed flashings: Appeared serviceable
9) General Roof Views: Roof was inspected and found to be in serviceable condition
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; areas and components obscured by insulation. Any comments made regarding these items are made as a courtesy only. The inspector does not determine the adequacy of the attic ventilation system. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high/low temperatures, high/low humidity, high wind and rain, melting snow) would be needed to do so. The inspector is not a licensed engineer and does not determine the adequacy of roof structure components such as trusses, rafters or ceiling beams, or their spacing or sizing.
Attic inspection method: Partially traversed
Location of attic: second floor
Condition of roof structure: Appeared serviceable
Roof structure type: Rafters
Ceiling structure: Ceiling joists
Condition of insulation in attic (ceiling, skylight chase, etc.): Appeared serviceable
Ceiling insulation material: Fiberglass roll or batt
Condition of roof ventilation: Appeared serviceable
10) The pull-down attic stairs did not close properly, and was missing weather stripping, in addition the foam insulation board that was glued in place and is slipping out of position. Recommend that a qualified person adjust to close properly, repair insulation and install weatherstripping per standard building practices for better energy efficiency. For more information, visit: https://www.reporthost.com/?INSATTSTRS
Limitations: The following items are not included in this inspection: generator systems, transfer switches, surge suppressors, inaccessible or concealed wiring; underground utilities and systems; low-voltage lighting or lighting on timers or sensors. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of grounding or bonding, if this system has an adequate capacity for the client's specific or anticipated needs, or if this system has any reserve capacity for additions or expansion. The inspector does not operate circuit breakers as part of the inspection, and does not install or change light bulbs. The inspector does not evaluate every wall switch or receptacle, but instead tests a representative number of them per various standards of practice. When furnishings, stored items or child-protective caps are present some receptacles are usually inaccessible and are not tested; these are excluded from this inspection. Receptacles that are not of standard 110 volt configuration, including 240-volt dryer receptacles, are not tested and are excluded. The functionality of, power source for and placement of smoke and carbon monoxide alarms is not determined as part of this inspection. Upon taking occupancy, proper operating and placement of smoke and carbon monoxide alarms should be verified and batteries should be changed. These devices have a limited lifespan and should be replaced every 10 years. The inspector attempts to locate and evaluate all main and sub-panels. However, panels are often concealed. If panels are found after the inspection, a qualified electrician should evaluate and repair if necessary. The inspector attempts to determine the overall electrical service size, but such estimates are not guaranteed because the overall capacity may be diminished by lesser-rated components in the system. Any repairs recommended should be made by a licensed electrician.
Electric service condition: Appeared serviceable
Service voltage (volts): 120-240
Estimated service amperage: 200
Primary service overload protection type: Circuit breakers
Main disconnect rating (amps): 200
Condition of main service panel: Appeared serviceable
Condition of branch circuit wiring: Serviceable
Branch circuit wiring type: Non-metallic sheathed
Ground fault circuit interrupter (GFCI) protection present: No
Arc fault circuit interrupter (AFCI) protection present: No
Smoke alarms installed: One or more not working
13) Carbon monoxide alarms were missing on one or more levels. This is a potential safety hazard. Some states and/or municipalities require CO alarms to be installed in the vicinity of each sleeping area, on each level and in accordance with the manufacturer's recommendations. Recommend installing additional carbon monoxide alarms per these standards. For more information, visit: https://www.reporthost.com/?COALRM
Missing CO upstairs in hallway.
14) One or more light fixtures under kitchen cabinets flicker when on. Recommend that a qualified electrician evaluate and repair or replace light fixtures as necessary.
Limitations: The following items are not included in this inspection: private/shared wells and related equipment; private sewage disposal systems; hot tubs or spas; main, side and lateral sewer lines; gray water systems; pressure boosting systems; trap primers; incinerating or composting toilets; fire suppression systems; water softeners, conditioners or filtering systems; plumbing components concealed within the foundation or building structure, or in inaccessible areas such as below tubs; underground utilities and systems; overflow drains for tubs and sinks; backflow prevention devices. Any comments made regarding these items are as a courtesy only. Note that the inspector does not operate water supply or shut-off valves due to the possibility of valves leaking or breaking when operated. The inspector does not test for lead in the water supply, the water pipes or solder, does not determine if plumbing and fuel lines are adequately sized, and does not determine the existence or condition of underground or above-ground fuel tanks.
Condition of service and main line: Appeared serviceable
Water service: Public
Location of main water meter: By street
Location of main water shut-off: Building exterior
Condition of supply lines: Appeared serviceable
Supply pipe material: Copper
Condition of drain pipes: Appeared serviceable
Drain pipe material: Plastic, Galvanized steel
Condition of waste lines: Appeared serviceable
Waste pipe material: Plastic
Location(s) of plumbing clean-outs: Building exterior
Vent pipe condition: Appeared serviceable
Vent pipe material: Plastic, Galvanized steel
Condition of fuel system: Appeared serviceable
Location of main fuel shut-off valve: At gas meter
17) If this property was unoccupied and the plumbing system has not been in continuous operation recently. It's possible for plumbing leaks to exist but not be apparent. Leaks can be small and take time to become visible. The inspector normally operates all accessible and operable plumbing fixtures, but this limited inspection may not reveal small leaks that only become visible after constant use of the plumbing system. After taking occupancy, monitor the plumbing system for leaks that may become apparent. Areas below the house should be evaluated after plumbing has been operated to check for leaks. Any problems that are found should be repaired by a qualified plumber.
Limitations: Evaluation of and determining the adequacy or completeness of the following items are not included in this inspection: water recirculation pumps; solar water heating systems; Energy Smart or energy saver controls; catch pan drains. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on water heaters, does not determine if water heaters are appropriately sized, or perform any evaluations that require a pilot light to be lit or a shut-off valve to be operated.
Condition of water heater: Appeared serviceable
Energy source: Natural gas
Capacity (in gallons): 40
19) General Water Heater Views:
20) One or more tankless water heaters were observed at this property. It is beyond the scope of this inspection to determine the adequacy of this system since demand varies significantly with water usage. For example, with simultaneous showers while washing clothes or dishes, etc. During such usage, tankless water heaters may not keep up with demand. This inspection includes a limited evaluation of the water heater to determine the following:
Does it supply hot water?
Is the water pressure adequate for the unit (typically minimum 30-50 psi)?
Is combustion air and the venting system serviceable?
Is the wiring for the electric supply safe?
Is a temperature-pressure relief valve and drain line installed?
Any concerns observed related to the above items are noted in this report.
Limitations: The following items are not included in this inspection: humidifiers, dehumidifiers, electronic air filters; solar, coal or wood-fired heat systems; thermostat or temperature control accuracy and timed functions; heating components concealed within the building structure or in inaccessible areas; underground utilities and systems; safety devices and controls (due to automatic operation). Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on heating or cooling system components, does not determine if heating or cooling systems are appropriately sized, does not test coolant pressure, or perform any evaluations that require a pilot light to be lit, a shut-off valve to be operated, a circuit breaker to be turned "on" or a serviceman's or oil emergency switch to be operated. It is beyond the scope of this inspection to determine if furnace heat exchangers are intact and free of leaks. Condensation pans and drain lines may clog or leak at any time and should be monitored while in operation in the future. Where buildings contain furnishings or stored items, the inspector may not be able to verify that a heat source is present in all "liveable" rooms (e.g. bedrooms, kitchens and living/dining rooms).
General heating system type(s): Forced air
General heating distribution type(s): Ducts and registers
Condition of forced air heating/(cooling) system: Appeared serviceable
Forced air heating system fuel type: Natural gas
Forced air heating system manufacturer: Payne
Location of forced air furnace: Attic
Condition of furnace filters: Appeared serviceable
Location for forced air filter(s): Behind return air grill(s)
Condition of forced air ducts and registers: Appeared serviceable
Condition of cooling system and/or heat pump: Appeared serviceable
Cooling system and/or heat pump fuel type: Electric
Limitations: The following items are not included in this inspection: coal stoves, gas logs, chimney flues (except where visible). Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of drafting or sizing in fireplace and stove flues, and also does not determine if prefabricated or zero-clearance fireplaces are installed in accordance with the manufacturer's specifications. The inspector does not perform any evaluations that require a pilot light to be lit, and does not light fires. The inspector provides a basic visual examination of a chimney and any associated wood burning device. The National Fire Protection Association has stated that an in-depth Level 2 chimney inspection should be part of every sale or transfer of property with a wood-burning device. Such an inspection may reveal defects that are not apparent to the home inspector who is a generalist.
Condition of wood-burning fireplaces, stoves: Appeared serviceable
Wood-burning fireplace type: Masonry
Fan or blower installed in wood-burning fireplace or stove: No
Condition of chimneys and flues: Appeared serviceable
Wood-burning chimney type: Masonry
23) A fireplace was equipped with a gas burner and the chimney damper could close. This is a safety hazard due to the possibility of burner or pilot light exhaust gases entering living spaces. The fire place damper needs to have the safety clip installed; the clip keeps the damper from closing 100% in case the gas is accidently left-turned on Modifications should be made to prevent the damper from ever closing to prevent this. A qualified contractor should repair per standard building practices so the damper cannot close.
24) One or more wood-burning fireplaces were found at the property. When such devices are used, they should be professionally inspected and cleaned annually to prevent creosote build-up and to determine if repairs are needed. The National Fire Protection Association states that a "Level 2" chimney inspection should be performed with every sale or transfer of property with a wood-burning device. Recommend consulting with the property owner about recent and past servicing and repairs to all wood-burning devices and chimneys or flues at this property. Recommend that a qualified specialist evaluate all wood-burning devices and chimneys, and clean and repair as necessary. Note that if a wood stove insert is installed, it may need to be removed for such an evaluation. For more information, search for "chimney inspection" at: https://www.reporthost.com/?CSIA
25) One or more fireplace dampers was difficult to open. Recommend that a qualified contractor repair or replace dampers as necessary.
Limitations: The following items are not included in this inspection: household appliances such as stoves, ovens, cook tops, ranges, warming ovens, griddles, broilers, dishwashers, trash compactors, refrigerators, freezers, ice makers, hot water dispensers and water filters; appliance timers, clocks, cook functions, self and/or continuous cleaning operations, thermostat or temperature control accuracy, and lights. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of the remaining life of appliances, and does not determine the adequacy of operation of appliances. The inspector does not note appliance manufacturers, models or serial numbers and does not determine if appliances are subject to recalls. Areas and components behind and obscured by appliances are inaccessible and excluded from this inspection.
Limitations: The following items are not included in this inspection: overflow drains for tubs and sinks; heated towel racks, saunas, steam generators, clothes washers, clothes dryers. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of washing machine drain lines, washing machine catch pan drain lines, or clothes dryer exhaust ducts. The inspector does not operate water supply or shut-off valves for sinks, toilets, bidets, clothes washers, etc. due to the possibility of valves leaking or breaking when operated. The inspector does not determine if shower pans or tub and shower enclosures are water tight, or determine the completeness or operability of any gas piping to laundry appliances.
Location #A: Bathroom#A
Location #B: Bathroom#B
Location #C: Bathroom#C
Location #D: Bathroom#D
Condition of counters: Appeared serviceable
Condition of cabinets: Appeared serviceable
Condition of flooring: Appeared serviceable
Condition of sinks and related plumbing: Appeared serviceable
Condition of toilets: Appeared serviceable
Condition of bathtubs and related plumbing: Appeared serviceable
Condition of shower(s) and related plumbing: Appeared serviceable
Condition of ventilation systems: Appeared serviceable
Bathroom and laundry ventilation type: Spot exhaust fans
Gas supply for laundry equipment present: Yes
240 volt receptacle for laundry equipment present: No
30) The toilet handle sticks in the open/flush position when used. This could be a problem when a guest uses the bathroom and pushes or pulls the lever to hard. Recommend that a qualified person should repair or adjust as components as necessary.
31) Bathroom/s was inspected and found to be in serviceable condition.
32) Laundry room need modifications in order to use. Gas only dryer connection.
Limitations: The following items are not included in this inspection: security, intercom and sound systems; communications wiring; central vacuum systems; elevators and stair lifts; cosmetic deficiencies such as nail-pops, scuff marks, dents, dings, blemishes or issues due to normal wear and tear in wall, floor and ceiling surfaces and coverings, or in equipment; deficiencies relating to interior decorating; low voltage and gas lighting systems. Any comments made regarding these items are as a courtesy only. Note that the inspector does not evaluate any areas or items which require moving stored items, furnishings, debris, equipment, floor coverings, insulation or similar materials. The inspector does not test for asbestos, lead, radon, mold, hazardous waste, urea formaldehyde urethane, or any other toxic substance. Some items such as window, drawer, cabinet door or closet door operability are tested on a sampled basis. The client should be aware that paint may obscure wall and ceiling defects, floor coverings may obscure floor defects, and furnishings may obscure wall, floor and floor covering defects. If furnishings were present during the inspection, recommend a full evaluation of walls, floors and ceilings that were previously obscured when possible. Determining the cause and/or source of odors is not within the scope of this inspection.
Condition of exterior entry doors: Appeared serviceable
Exterior door material: Glass panel
Condition of interior doors: Appeared serviceable
Type(s) of windows: Metal, Multi-pane
Condition of walls and ceilings: Appeared serviceable
Wall type or covering: Drywall or plaster
Ceiling type or covering: Drywall or plaster
Condition of flooring: Appeared serviceable
Condition of concrete slab floor(s): Appeared serviceable
Condition of stairs, handrails and guardrails: Appeared serviceable
33) Recommend cleaning all window and door tracks from new construction debris.
34) Interior Views:
35) Concrete slab floors were obscured by and couldn't be fully evaluated.
1.1. A Home Inspection is a non-invasive, visual examination of a residential dwelling, performed for a fee, which is designed to identify observed material defects within specific components of said dwelling. Components may include any combination of mechanical, structural, electrical, plumbing, or other essential systems or portions of the home, as identified and agreed to by the Client and Inspector, prior to the inspection process.
I. A home inspection is intended to assist in evaluation of the overall condition of the dwelling. The inspection is based on observation of the visible and apparent condition of the structure and its components on the date of the inspection, and not the prediction of future conditions.
II. A home inspection will not reveal every concern that exists or ever could exist, but only those material defects observed on the day of the inspection.
III. A home inspection can include a survey and/or analysis of energy flows and usage in a residential property if the client requests it.
1.2. A Material Defect is a condition of a residential real property, or any portion of it, that would have a significant, adverse impact on the value of the real property, or that involves an unreasonable risk to people on the property. The fact that a structural element, system or subsystem is near, at or beyond the end of the normal useful life of such a structural element, system or subsystem is not by itself a material defect.
1.3. An Inspection Report shall describe and identify, in written format, the inspected systems, structures, and components of the dwelling, and shall identify material defects observed. Inspection reports may contain recommendations regarding conditions reported or recommendations for correction, monitoring or further evaluation by professionals, but this is not required. A complete copy of the STANDARDS OF PRACTICE we adhere to can be found at the following link: http://www.nachi.org/sop.htm