Minor ceiling damage was found in one garage ceiling area. However, no elevated levels of moisture were found. The damage may be due to past roof leak. Recommend asking the property owner(s) about this, and monitoring the stained area(s) in the future, especially after heavy or prolonged rain. If elevated moisture is found in the future, a qualified contractor should evaluate and repair as necessary.
Garage interior aspects.
Primary service type: Underground
Primary service overload protection type: Circuit breakers
Service amperage (amps): 200
Service voltage (volts): 120/240
Location of main service switch: At the meter and main service located at the South West corner of the home
Location of sub panels: Two main service panels are located in the laundry room second level
Location of main disconnect: No single main disconnect, use all breakers in main service panel
Service entrance conductor material: Aluminum
System ground: Cold water supply pipes
Main disconnect rating (amps): 200
Branch circuit wiring type: Copper
Solid strand aluminum branch circuit wiring present: No
Smoke detectors present: Yes
Main electrical components and their locations.
Photo 11-1 Electric meter and main disconnect are located inside this enclosure
located at the South west hot tub deck.
Photo 11-2 Main service panels located in the laundry room.
Photo 11-3 Service panels were exposed and observed.
Photo 11-4 Existing smoke detector.
Photo 11-5 Existing CO detector.
Estimated age: < 6 years
Type: Tank Indirect fired storage tank
Energy source: Natural gas
Capacity (in gallons): 110
Model: Triangle Tube
Water temperature (degrees Fahrenheit): Approximately 130 degrees
Hot water tank and approximate water temperature.
Photo 12-1 Hot water storage tank in the mechanical room.
Photo 12-2 Approximate water temperature at this tub spout.
Heating and cooling
Estimated age: < 6 years
Primary heating system energy source: Natural gas
Primary heat system type: Hydronic radiant floors
Primary A/C energy source: N/A
Primary Air conditioning type: N/A
Distribution system: N/A
Manufacturer: Triangle Tube Wall Boiler
Model: Prestige Solo 175
The last service date of this system appears to be more than one year ago, or the inspector was unable to determine the last service date. The client(s) should ask the property owner(s) when it was last serviced. If unable to determine the last service date, or if this system was serviced more than one year ago, a qualified hydronic heating specialist should service this system and make repairs if necessary. This servicing should be performed annually in the future.
Photo 14-1 Boiler.
Photo 14-2 Boiler controls.
Photo 14-3 Heat zone valves, actuators, circulation pumps, expansion tank and other components.
Photo 14-4 Radiant heat manifolds and radiant tubing in the crawlspace.
Photo 14-5 Heating controls.
Plumbing and laundry
Water pressure (psi): < 80 psi
Location of main water shut-off valve: In the crawlspace at the water meter
Location of main water meter: In the crawlspace
Location of main fuel shut-off: At the North East corner of the home at the meter
Visible fuel storage systems: N/A
Water service: Public
Service pipe material: Copper
Supply pipe material: Copper
Vent pipe material: Plastic
Drain pipe material: Plastic
Waste pipe material: Plastic
The clothes dryer exhaust duct appears to may need cleaning. Significant amounts of lint build up was found. This is a safety hazard due to the risk of fire from decreased air flow. This duct should be cleaned now and annually, or more often if necessary in the future. Some chimney sweeps or heating/cooling duct cleaners perform this service. For more information, visit:http://www.cpsc.gov/CPSCPUB/PUBS/5022.htmlhttp://chimneykeepers.com/dryerclean.html
Main water shut off, water meter, gas meter and main disconnect and their locations.
Photo 16-1 Main water shut off located below the water meter.
Photo 16-2 Water meter.
Photo 16-3 Gas meter and disconnect are located at the North East corner of the home.
Fireplaces, woodstoves and chimneys
Fireplace type: Masonry with metal liner, Metal prefabricated
Chimney type: Metal
The North master suite gas fireplace did not respond when the controls were operated. This may be due to the pilot light being turned off, the gas supply being turned off, or any number of other reasons. As a result, these appliances were not fully evaluated. As per the Standards of Practice for both the National Association of Certified Home Inspectors (NACHI)
and the American Society of Home Inspectors (ASHI)
the inspector does not operate gas shut off valves or light pilot lights during inspections. Recommend consulting with the property owner(s) as to how the fireplace(s) and/or stove(s) operate, and/or having a gas appliance contractor evaluate and repair if necessary.
The home has a wood burning fireplace in the living area and gas burning fireplaces in the two master suites.
Photo 18-1 Living area wood burning fireplace.
Photo 18-2 South master suite gas fireplace.
Photo 18-3 South master suite gas fireplace with wall switch operation.
Photo 18-4 North master suite gas fireplace.
Inspection method: Traversed
Insulation material underneath floor above: Fiberglass roll or batt
Pier or support post material: Wood
Beam material: Solid wood
Floor structure above: Engineered wood joists
Vapor barrier present: Yes
Photo 19-1 Crawlspace access.
Photo 19-2 Crawlspace.
Photo 19-3 Crawlspace.
Photo 19-4 Crawlspace.
Photo 19-5 Crawlspace.
Photo 19-6 Crawlspace.
The top left stove top burner appears inoperable. A qualified appliance technician should evaluate and repair as necessary.
One or more light fixtures are slightly damaged and/or deteriorated in some way. A qualified electrician could evaluate and repair or replace light fixtures or components as necessary.
Photo 21-1 Broken sconce observed at the kitchen countertop lighting.
Kitchen aspects and appliances.
Photo 22-1 Kitchen.
Photo 22-2 Kitchen.
Photo 22-3 Lacanche brand gas stove.
Photo 22-4 Gas cooktop.
Photo 22-5 Dual gas ovens.
Photo 22-6 Professional grade ventilation system.
Photo 22-7 Bulb out at the cooktop vent lighting.
Photo 22-8 Kitchen sink and faucet.
Photo 22-9 The disposal and or sink drain plumbing had been removed
prior to the inspection, these components were not observed.
Photo 22-10 Installations for a refrigerator.
Photo 22-11 Installations for a dishwasher.
Photo 22-12 Installations for possibly a wine chiller.
The jet tub in the North master suite bathroom did not respond to normal operation of the controls. The inspector observed the GFCI circuits and tub components below the tub and could not determine the reason for the malfunction A qualified contractor could evaluate and repair as necessary.
Photo 24-1 South master suite bathroom.
Photo 24-2 South master suite bathroom.
Photo 24-3 South master suite bathroom jet tub.
Photo 24-4 North master suite bathroom.
Photo 24-5 North master suite bathroom.
Photo 24-6 Steam shower controls.
Photo 24-7 North master suite bathroom steam shower generator is located in the bedroom closet loft area.
Photo 24-8 Guest bathroom.
Photo 24-9 Guest bathroom.
Photo 24-10 Guest bathroom.
The ground fault circuit interrupter (GFCI) electric receptacle located at the South master suite wet bar is tripped and will not reset. A qualified electrician should evaluate and replace or make repairs as necessary.
One or more windows that were built to open, will not open, or open only minimally due to their being painted shut, damaged and/or deteriorated in some way. Repairs should be made as necessary, and by a qualified contractor if necessary so windows open fully, and open and close easily.
Batteries in all the smoke alarms should be replaced after taking occupancy, and annually in the future. "Chirping" noises emitted from smoke alarms typically indicate that batteries need replacing. For more information, visit:http://www.cpsc.gov/cpscpub/pubs/5077.html
The home is equipped with a residential grade elevator that services all three levels of the home. Recommend having the elevator serviced regularly as suggested by the manufacture and or a qualified elevator service contractor.
Photo 28-1 The elevator responded to normal operation of the controls.
Photo 28-2 Elevator interior.
Photo 28-3 Elevator controls.
Photo 28-4 Access to the main elevator components is located above the elevator on the third floor.
Photo 28-5 Main elevator components are located above the elevator.
Photo 28-6 Elevator components located above the elevator.
Photo 29-1 Main living area, dinning and kitchen.
Photo 29-2 Main living area.
Photo 29-4 Stairways.
Photo 29-5 South master suite.
Photo 29-6 North master suite.
Photo 29-7 Laundry room.
Photo 29-8 Hallways.
Photo 29-9 Sauna located in the lower level.
Photo 29-10 Lower level entertainment room.
Thank you for choosing Absolute Home Inspection.
I welcome any feedback or questions you may have throughout this process and wish you all the best in your new home.