This report published on Friday, May 10, 2019 12:11:16 PM EDT
This report is the exclusive property of this inspection company and the client(s) listed in the report title. Use of this report by any unauthorized persons is prohibited.
How to Read this Report
This report is organized by the property's functional areas. Within each functional area, descriptive information is listed first and is shown in bold type. Items of concern follow descriptive information.
Concerns are shown and sorted according to these types:
Poses a safety hazard
Recommend repairing or replacing
Recommend repair and/or maintenance
Recommend ongoing maintenance
Recommend evaluation by a specialist
For your information
Click here for a glossary of building construction terms.Contact your inspector If there are terms that you do not understand, or visit the glossary of construction terms at https://www.reporthost.com/glossary.asp
Client present for discussion at end of inspection: Yes
Weather conditions during inspection: Dry (no rain)
Temperature during inspection: Warm
Ground condition: Dry
Recent weather: Dry (no rain)
Overnight temperature: Warm
Inspection fee: 325.00
Payment method: Cash
Buildings inspected: One house
Number of residential units inspected: 1
Age of main building: 1974
Source for main building age: Municipal records or property listing
1) Possible Microbial growths were found at one or more locations in interior rooms. It is beyond the scope of this inspection to identify what substance or organism this staining is. However such staining is normally caused by excessively moist conditions, which in turn can be caused by plumbing or building envelope leaks and/or substandard ventilation. These conducive conditions should be corrected before making any attempts to remove or correct the staining. Normally affected materials such as drywall are removed, enclosed affected spaces are allowed to dry thoroughly, a mildewcide may be applied, and only then is drywall reinstalled. For evaluation and possible mitigation, consult with a qualified industrial hygienist or mold/moisture mitigation specialist. For more information, visit: http://www.reporthost.com/?MOLDCDC http://www.reporthost.com/?MOLDEPA
Limitations: Unless specifically included in the inspection, the following items and any related equipment, controls, electric systems and/or plumbing systems are excluded from this inspection: detached buildings or structures; fences and gates; retaining walls; underground drainage systems, catch basins or concealed sump pumps; swimming pools and related safety equipment, spas, hot tubs or saunas; whether deck, balcony and/or stair membranes are watertight; trees, landscaping, properties of soil, soil stability, erosion and erosion control; ponds, water features, irrigation or yard sprinkler systems; sport courts, playground, recreation or leisure equipment; areas below the exterior structures with less than 3 feet of vertical clearance; invisible fencing; sea walls, docks and boathouses; retractable awnings. Any comments made regarding these items are as a courtesy only.
Site profile: Level
Condition of driveway: Appeared serviceable
Driveway material: Poured in place concrete
Condition of sidewalks and/or patios: Appeared serviceable
Sidewalk material: Poured in place concrete
Condition of deck, patio and/or porch covers: Appeared serviceable
Deck, patio, porch cover material and type: Covered (Refer to Roof section)
Condition of decks, porches and/or balconies: Appeared serviceable
Deck, porch and/or balcony material: Concrete
2) Some porches were obscured by carpeting and couldn't be fully evaluated.
Limitations: The inspector performs a visual inspection of accessible components or systems at the exterior. Items excluded from this inspection include below-grade foundation walls and footings; foundations, exterior surfaces or components obscured by vegetation, stored items or debris; wall structures obscured by coverings such as siding or trim. Some items such as siding, trim, soffits, vents and windows are often high off the ground, and may be viewed using binoculars from the ground or from a ladder. This may limit a full evaluation. Regarding foundations, some amount of cracking is normal in concrete slabs and foundation walls due to shrinkage and drying. Note that the inspector does not determine the adequacy of seismic reinforcement.
Wall inspection method: Viewed from ground
Condition of wall exterior covering: Appeared serviceable
Apparent wall structure: Concrete block
Wall covering: Stucco
Condition of foundation and footings: Appeared serviceable
Apparent foundation type: Concrete slab on grade
4) Cracks, deterioration and/or damage were found in one or more areas of the exterior stucco finish. In damp climates, moisture may enter cracks or damaged areas and further deteriorate the stucco. Also the wall behind the stucco may become damaged from moisture. Note that areas behind the stucco are inaccessible and excluded from this inspection. Recommend that a qualified contractor repair or replace stucco as necessary.
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; solar roofing components. Any comments made regarding these items are made as a courtesy only. Note that the inspector does not provide an estimate of remaining life on the roof surface material, nor guarantee that leaks have not occurred in the roof surface, skylights or roof penetrations in the past. Regarding roof leaks, only active leaks, visible evidence of possible sources of leaks, and evidence of past leaks observed during the inspection are reported on as part of this inspection. The inspector does not guarantee or warrant that leaks will not occur in the future. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high wind and rain, melting snow) would be needed to do so. Regarding the roof drainage system, unless the inspection was conducted during and after prolonged periods of heavy rain, the inspector was unable to determine if gutters, downspouts and extensions performed adequately or were leak-free.
Roof inspection method: Traversed
Condition of roof surface material: Appeared serviceable
Roof surface material: Asphalt or fiberglass composition shingles
Roof type: Gable
Condition of exposed flashings: Appeared serviceable
Condition of gutters, downspouts and extensions: Appeared serviceable
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; areas and components obscured by insulation. Any comments made regarding these items are made as a courtesy only. The inspector does not determine the adequacy of the attic ventilation system. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high/low temperatures, high/low humidity, high wind and rain, melting snow) would be needed to do so. The inspector is not a licensed engineer and does not determine the adequacy of roof structure components such as trusses, rafters or ceiling beams, or their spacing or sizing.
Attic inspection method: Traversed
Location of attic access point #A: Garage
Location of attic access point #B: Hallway
Attic access points that were opened and viewed, traversed or partially traversed: A
Condition of roof structure: Appeared serviceable
Roof structure type: Trusses
Ceiling structure: Trusses
Condition of insulation in attic (ceiling, skylight chase, etc.): Appeared serviceable
Ceiling insulation material: Fiberglass loose fill, Cellulose loose fill
Approximate attic insulation R value (may vary in areas): Not determined (inaccessible or obscured)
Condition of roof ventilation: Appeared serviceable
Limitations: The inspector does not determine the adequacy of firewall ratings. Requirements for ventilation in garages vary between municipalities.
Type: Attached, Garage
Condition of door between garage and house: Appeared serviceable
Type of door between garage and house: Solid core, Wood
Condition of exterior entry doors: Appeared serviceable
Exterior door material: Metal
Condition of garage vehicle door(s): Appeared serviceable
Type of garage vehicle door: Sectional
Number of vehicle doors: 1
Condition of automatic opener(s): Appeared serviceable
Mechanical auto-reverse operable (reverses when meeting reasonable resistance during closing): Yes
Condition of garage floor: Appeared serviceable
Condition of garage interior: Appeared serviceable
Garage ventilation: Adequate
8) The door between the garage and the house did not appear to be fire resistant, or the inspector was unable to verify that it was via a label. This is a potential safety hazard. House to garage doors, to prevent fire and fumes from spreading from the garage into interior living space, should be constructed of fire-resistant materials. Doors, generally considered to be suitable for the purpose, are solid core wood, steel, honeycomb steel or a door that has been factory labeled as fire rated. Recommend that a qualified contractor replace or repair the door and, at that time, make any other corrections that might be required to provide suitable fire resistance between the garage and the dwelling per standard building practices. For more information, visit: http://www.reporthost.com/?AGFR
Limitations: The following items are not included in this inspection: generator systems, transfer switches, surge suppressors, inaccessible or concealed wiring; underground utilities and systems; low-voltage lighting or lighting on timers or sensors. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of grounding or bonding, if this system has an adequate capacity for the client's specific or anticipated needs, or if this system has any reserve capacity for additions or expansion. The inspector does not operate circuit breakers as part of the inspection, and does not install or change light bulbs. The inspector does not evaluate every wall switch or receptacle, but instead tests a representative number of them per various standards of practice. When furnishings, stored items or child-protective caps are present some receptacles are usually inaccessible and are not tested; these are excluded from this inspection. Receptacles that are not of standard 110 volt configuration, including 240-volt dryer receptacles, are not tested and are excluded. The functionality of, power source for and placement of smoke and carbon monoxide alarms is not determined as part of this inspection. Upon taking occupancy, proper operating and placement of smoke and carbon monoxide alarms should be verified and batteries should be changed. These devices have a limited lifespan and should be replaced every 10 years. The inspector attempts to locate and evaluate all main and sub-panels. However, panels are often concealed. If panels are found after the inspection, a qualified electrician should evaluate and repair if necessary. The inspector attempts to determine the overall electrical service size, but such estimates are not guaranteed because the overall capacity may be diminished by lesser-rated components in the system. Any repairs recommended should be made by a licensed electrician.
Electric service condition: Appeared serviceable
Primary service type: Overhead
Service voltage (volts): 120-240
Estimated service amperage: 150
Primary service overload protection type: Circuit breakers
Main disconnect rating (amps): 150
Condition of main service panel: Appeared serviceable
Location of main service panel #A: Living room
Location of main disconnect: Top bank of breakers in main service panel (split bus)
10) One or more electric receptacles (outlets) at the kitchen had no visible ground fault circuit interrupter (GFCI) protection, or the inspector was unable to determine if GFCI protection was present. If not GFCI-protected, receptacles in wet areas pose a shock hazard. Recommend that a qualified electrician evaluate and install GFCI protection if necessary and per standard building practices. General guidelines for GFCI-protected receptacles include the following locations:
Outdoors (since 1973)
Bathrooms (since 1975)
Garages (since 1978)
Kitchens (since 1987)
Crawl spaces and unfinished basements (since 1990)
11) Wire splices were exposed and were not contained in a covered junction box. This is a potential shock or fire hazard. Recommend that a qualified electrician repair per standard building practices. For example, by installing permanently mounted junction boxes with cover plates where needed to contain wiring splices.
12) A "split bus" panel was installed as a main service panel. On such panels there is no single main disconnect switch to turn the power off. Instead, all breakers labeled "main" or "sub-main" (usually those on the upper half of the panel) must be turned off to turn all power off. These panels are common, but are no longer installed. The client should familiarize themselves with the operation of this panel and the procedure for turning all the power off in the event of an emergency. Consult with an electrician if necessary. Please see any other comments in this report related to the panel's legend.
Limitations: The following items are not included in this inspection: private/shared wells and related equipment; private sewage disposal systems; hot tubs or spas; main, side and lateral sewer lines; gray water systems; pressure boosting systems; trap primers; incinerating or composting toilets; fire suppression systems; water softeners, conditioners or filtering systems; plumbing components concealed within the foundation or building structure, or in inaccessible areas such as below tubs; underground utilities and systems; overflow drains for tubs and sinks; backflow prevention devices. Any comments made regarding these items are as a courtesy only. Note that the inspector does not operate water supply or shut-off valves due to the possibility of valves leaking or breaking when operated. The inspector does not test for lead in the water supply, the water pipes or solder, does not determine if plumbing and fuel lines are adequately sized, and does not determine the existence or condition of underground or above-ground fuel tanks.
Condition of service and main line: Appeared serviceable
Water service: Public
Location of main water meter: By street
Location of main water shut-off: Building exterior
Service pipe material: Not determined (inaccessible or obscured)
Condition of supply lines: Appeared serviceable
Supply pipe material: Copper
Condition of drain pipes: Appeared serviceable
Drain pipe material: Plastic
Condition of waste lines: Appeared serviceable
Waste pipe material: Plastic, Not determined (inaccessible or obscured)
Location(s) of plumbing clean-outs: Building exterior
Vent pipe condition: Appeared serviceable
Vent pipe material: Plastic
Sump pump installed: Yes
Condition of sump pump: Required repairs, replacement and/or evaluation (see comments below)
14) During inspection the water was ran to check plumbing. The water started to backup from septic to home. A licensed septic tank company should be contacted to evaluate drain system and tank.
15) One or more leaks were found in waste pipes or fittings. A qualified plumber should evaluate and repair as necessary.
16) One or more hose bib (outside faucets) handles were broken. Recommend that a qualified person replace handles or make repairs as necessary.
17) One or more hose bibs (outside faucets) leaked while off. When hose bibs leak while turned off, it's often caused by a worn valve seat or a loose bonnet. When hose bibs leak while turned on, it may be due to worn "packing" around the stem or a defective backflow prevention device. Recommend that a qualified plumber repair as necessary.
18) Based on visible components or information provided to the inspector, this property appeared to have a private sewage disposal (septic) system. These are specialty systems and are excluded from this inspection. Comments in this report related to this system are made as a courtesy only and are not meant to be a substitute for a full evaluation by a qualified specialist. Generally, septic tanks should be pumped and inspected every 3 years. Depending on the type of system and municipal regulations, inspection and maintenance may be required more frequently, often annually. Recommend the following:
Consult with the property owner about this system's maintenance and repair history
Review any documentation available for this system
Review inspection and maintenance requirements for this system
That a qualified specialist evaluate, perform maintenance and make repairs if necessary
19) The inspector was unable to fully evaluate the sump pump because unplugged. Its condition was not determined. Recommend that conditions that prevented evaluation be corrected, and that a qualified person test the pump and make repairs if necessary.
Limitations: Evaluation of and determining the adequacy or completeness of the following items are not included in this inspection: water recirculation pumps; solar water heating systems; Energy Smart or energy saver controls; catch pan drains. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on water heaters, does not determine if water heaters are appropriately sized, or perform any evaluations that require a pilot light to be lit or a shut-off valve to be operated.
Condition of water heater: Appeared serviceable
Energy source: Electricity
Estimated age: 6yrs
Capacity (in gallons): 50
Temperature-pressure relief valve installed: Yes
Location of water heater: Garage
Hot water temperature tested: Yes
Water temperature (degrees Fahrenheit): 118.3
21) One or more active leaks were found at the water heater's supply pipes or fittings. A qualified plumber should evaluate and repair as necessary.
Limitations: The following items are not included in this inspection: humidifiers, dehumidifiers, electronic air filters; solar, coal or wood-fired heat systems; thermostat or temperature control accuracy and timed functions; heating components concealed within the building structure or in inaccessible areas; underground utilities and systems; safety devices and controls (due to automatic operation). Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on heating or cooling system components, does not determine if heating or cooling systems are appropriately sized, does not test coolant pressure, or perform any evaluations that require a pilot light to be lit, a shut-off valve to be operated, a circuit breaker to be turned "on" or a serviceman's or oil emergency switch to be operated. It is beyond the scope of this inspection to determine if furnace heat exchangers are intact and free of leaks. Condensation pans and drain lines may clog or leak at any time and should be monitored while in operation in the future. Where buildings contain furnishings or stored items, the inspector may not be able to verify that a heat source is present in all "liveable" rooms (e.g. bedrooms, kitchens and living/dining rooms).
General heating system type(s): Heat pump
General heating distribution type(s): Ducts and registers
Condition of furnace filters: Appeared serviceable
Location for forced air filter(s): Behind return air grill(s)
Condition of forced air ducts and registers: Appeared serviceable
Condition of cooling system and/or heat pump: Appeared serviceable
Cooling system and/or heat pump fuel type: Electric
Type: Split system, Heat pump
Estimated age: 4yrs
Condition of controls: Appeared serviceable
23) A/C unit appears to be less than 10 yrs old but no service record could be found. Recommend having a licensed a/c contractor come out and service the unit and ask owner about any warranties it may be under and ask a/c company about purchasing and extended warranty.
Limitations: The following items are not included in this inspection: coal stoves, gas logs, chimney flues (except where visible). Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of drafting or sizing in fireplace and stove flues, and also does not determine if prefabricated or zero-clearance fireplaces are installed in accordance with the manufacturer's specifications. The inspector does not perform any evaluations that require a pilot light to be lit, and does not light fires. The inspector provides a basic visual examination of a chimney and any associated wood burning device. The National Fire Protection Association has stated that an in-depth Level 2 chimney inspection should be part of every sale or transfer of property with a wood-burning device. Such an inspection may reveal defects that are not apparent to the home inspector who is a generalist.
Condition of wood-burning fireplaces, stoves: Appeared serviceable
Wood-burning fireplace type: Masonry with metal liner
24) Spark screen or rain cap was loose at one or more chimney flue terminations. Spark screens reduce the chance of embers exiting the flue and causing fires. They also prevent wildlife (e.g. birds, rodents, raccoons) from entering flues. Rain caps prevent water from entering flues, mixing with combustion deposits and creating caustic chemicals which can corrode flues. They also prevent damage to masonry from freeze-thaw cycles and prevent metal components (e.g. dampers, metal firebox liners) from rusting. Recommend that a qualified person install rain caps with spark screens per standard building practices where missing.
25) One or more wood-burning fireplaces or stoves were found at the property. When such devices are used, they should be professionally inspected and cleaned annually to prevent creosote build-up and to determine if repairs are needed. The National Fire Protection Association states that a "Level 2" chimney inspection should be performed with every sale or transfer of property with a wood-burning device. Recommend consulting with the property owner about recent and past servicing and repairs to all wood-burning devices and chimneys or flues at this property. Recommend that a qualified specialist evaluate all wood-burning devices and chimneys, and clean and repair as necessary. Note that if a wood stove insert is installed, it may need to be removed for such an evaluation. For more information, search for "chimney inspection" at: http://www.reporthost.com/?CSIA
Limitations: The following items are not included in this inspection: household appliances such as stoves, ovens, cook tops, ranges, warming ovens, griddles, broilers, dishwashers, trash compactors, refrigerators, freezers, ice makers, hot water dispensers and water filters; appliance timers, clocks, cook functions, self and/or continuous cleaning operations, thermostat or temperature control accuracy, and lights. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of the remaining life of appliances, and does not determine the adequacy of operation of appliances. The inspector does not note appliance manufacturers, models or serial numbers and does not determine if appliances are subject to recalls. Areas and components behind and obscured by appliances are inaccessible and excluded from this inspection.
Condition of sinks and related plumbing: Appeared serviceable
Condition of under-sink food disposal: N/A (none installed)
Condition of dishwasher: Near, at or beyond service life
Condition of range, cooktop or oven: Near, at or beyond service life
Range, cooktop or oven type: Electric
Type of ventilation: Hood or built into microwave over range or cooktop
Condition of refrigerator: Near, at or beyond service life
Condition of built-in microwave oven: Near, at or beyond service life
26) An exhaust hood was installed over the cook top or range, but the fan recirculated the exhaust air back into the kitchen. This may be due to no duct being installed, baffles at the front of the hood not being installed, or a problem with the duct. This can be a nuisance for odor and grease accumulation. Where a gas-fired range or cook top is installed, carbon monoxide and excessive levels of moisture can accumulate in living spaces. Recommend that a qualified contractor evaluate and repair as necessary so exhaust air is ducted outdoors.
Limitations: The following items are not included in this inspection: overflow drains for tubs and sinks; heated towel racks, saunas, steam generators, clothes washers, clothes dryers. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of washing machine drain lines, washing machine catch pan drain lines, or clothes dryer exhaust ducts. The inspector does not operate water supply or shut-off valves for sinks, toilets, bidets, clothes washers, etc. due to the possibility of valves leaking or breaking when operated. The inspector does not determine if shower pans or tub and shower enclosures are water tight, or determine the completeness or operability of any gas piping to laundry appliances.
Location #A: Full bath
Location #B: 3/4 bath, Master bath
Condition of counters: Appeared serviceable
Condition of cabinets: Appeared serviceable
Condition of flooring: Appeared serviceable
Condition of sinks and related plumbing: Appeared serviceable
Condition of toilets: Appeared serviceable
Condition of bathtubs and related plumbing: Appeared serviceable
Condition of shower(s) and related plumbing: Appeared serviceable
Condition of ventilation systems: Appeared serviceable
Bathroom and laundry ventilation type: Windows
240 volt receptacle for laundry equipment present: Yes
28) The jetting system for the bathtub was not evaluated.
Limitations: The following items are not included in this inspection: security, intercom and sound systems; communications wiring; central vacuum systems; elevators and stair lifts; cosmetic deficiencies such as nail-pops, scuff marks, dents, dings, blemishes or issues due to normal wear and tear in wall, floor and ceiling surfaces and coverings, or in equipment; deficiencies relating to interior decorating; low voltage and gas lighting systems. Any comments made regarding these items are as a courtesy only. Note that the inspector does not evaluate any areas or items which require moving stored items, furnishings, debris, equipment, floor coverings, insulation or similar materials. The inspector does not test for asbestos, lead, radon, mold, hazardous waste, urea formaldehyde urethane, or any other toxic substance. Some items such as window, drawer, cabinet door or closet door operability are tested on a sampled basis. The client should be aware that paint may obscure wall and ceiling defects, floor coverings may obscure floor defects, and furnishings may obscure wall, floor and floor covering defects. If furnishings were present during the inspection, recommend a full evaluation of walls, floors and ceilings that were previously obscured when possible. Determining the cause and/or source of odors is not within the scope of this inspection.
Condition of exterior entry doors: Appeared serviceable
Exterior door material: Metal
Condition of interior doors: Appeared serviceable
Condition of windows and skylights: Required repair, replacement and/or evaluation (see comments below)
Type(s) of windows: Metal, Single-pane, Single-hung
Condition of walls and ceilings: Appeared serviceable
Wall type or covering: Drywall or plaster
Ceiling type or covering: Drywall or plaster
Condition of flooring: Appeared serviceable
Flooring type or covering: Tile
30) Windows are deteriorated and in need of repair or replacement.
31) One or more windows that were designed to open and close were difficult to open and close. Recommend that a qualified person repair windows as necessary so they open and close easily.
32) Glass in one or more windows was cracked, broken and/or missing. Recommend that a qualified contractor replace glass where necessary.
33) One or more walls . Recommend that a qualified person repair as necessary.
34) The sash-side spring mechanisms in one or more windows were broken, loose or disconnected. The window(s) were difficult to operate as a result, and not square in their frames or tracks. Recommend that a qualified contractor or service technician repair as necessary so windows open and close easily, and stay open without support.
35) Screens were missing from many windows. These windows may not provide ventilation during months when insects are active.