This report is the exclusive property of this inspection company and the client(s) listed in the report title. Use of this report by any unauthorized persons is prohibited.
Washington Home Inspection Company
214 S Washington St
Spokane WA 99201-4318
Inspector: Gregg Morin
Washington State Home Inspector License # 1137
Property Inspection Report
||John and Jane Silverman
||4388 Mountain View Lane
Spokane WA 99208
||Friday, November 06, 2015
This report published on Saturday, January 09, 2016 1:04:44 PM PST
Report number: 220611062015
Time started: 10:45
Time finished: 2:30
Present during inspection: Client, Property owner, Realtor
Client present for discussion at end of inspection: Yes
Weather conditions during inspection: Dry (no rain)
Temperature during inspection: Cool, 36 Degrees
Inspection fee: 330.00
Payment method: Check
Type of building: Single family
Buildings inspected: One house
Number of residential units inspected: 4
Age of main building: 1927
Source for main building age: Municipal records or property listing
Front of building faces: North
Main entrance faces: North
Occupied: No, Partially occupied
Structures built prior to the mid 1980s may contain lead and/or asbestos. Lead is commonly found in paint and in some plumbing components. The EPA does not recognize newer coats of paint as encapsulating older coats of lead-based paint. Asbestos is commonly found in various building materials such as insulation, siding, and/or floor and ceiling tiles. Laws were passed in 1978 to prohibit usage of lead and asbestos, but stocks of materials containing these substances remained in use for a number of years thereafter. Both lead and asbestos are known health hazards. Evaluating for the presence of lead and/or asbestos is beyond the scope of this inspection. Any mention of these materials in this report is made as a courtesy only, and meant to refer the client to a specialist. Consult with specialists as necessary, such as industrial hygienists, professional labs and/or abatement specialists for this type of evaluation. For information on lead, asbestos and other hazardous materials in homes, visit:http://www.reporthost.com/?EPAhttp://www.reporthost.com/?CPSChttp://www.reporthost.com/?CDC
Evidence of rodent infestation was found in the form of dead rodents in the basement and exterior facia gap. Consult with the property owner about this. A qualified person should make repairs to seal openings in the structure, set traps, and clean rodent waste as necessary. Recommend following guidelines in these Center for Disease Control articles:http://www.reporthost.com/?SEALUPhttp://www.reporthost.com/?TRAPUPhttp://www.reporthost.com/?CLEANUP
As this properties rural location is prone to some small rodent past infestation, and only 2 small dead mice were found, it is purely the potential homeowners discretion if they want to consult with a licensed pest inspector.
Limitations: Unless specifically included in the inspection, the following items and any related equipment, controls, electric systems and/or plumbing systems are excluded from this inspection: detached buildings or structures; fences and gates; retaining walls; underground drainage systems, catch basins or concealed sump pumps; swimming pools and related safety equipment, spas, hot tubs or saunas; whether deck, balcony and/or stair membranes are watertight; trees, landscaping, properties of soil, soil stability, erosion and erosion control; ponds, water features, irrigation or yard sprinkler systems; sport courts, playground, recreation or leisure equipment; areas below the exterior structures with less than 3 feet of vertical clearance; invisible fencing; sea walls, docks and boathouses; retractable awnings. Any comments made regarding these items are as a courtesy only.
Site profile: Minor slope
Condition of driveway: Appeared serviceable
Driveway material: Gravel
Condition of decks, porches and/or balconies: Required repairs, replacement and/or evaluation (see comments below)
Deck, porch and/or balcony material: Wood
Condition of stairs, handrails and guardrails: Required repairs, replacement and/or evaluation (see comments below)
Exterior stair material: Wood
Guardrails at one or more locations with drop-offs higher than 30 inches were missing. This poses a fall hazard. Guardrails should be installed where walking surfaces are more than 30 inches above the surrounding grade or surfaces below. Recommend that a qualified contractor install guardrails where missing and per standard building practices.
Guardrails at one or more locations with drop-offs higher than 30 inches were missing, and pose a fall hazard. Recommend that a qualified person repair guardrails as necessary.
Additionally some areas with under 30 inch drop-offs exist that pose a safety hazard due to the location being between the pool and deck. These areas should have decking and bracing installed.
One or more deck or porch beams were not positively secured to the support posts below. Deck or porch beams are commonly connected to support posts by "toenailing," which is inadequate, however at this specific location the 4x4 wood support post is "face nailed" to the rim joist. Decks and porches are subject to movement under live loads and require a positive connection between their support posts and beams. Recommend that a qualified contractor repair per standard building practices. For example, by installing metal plates, plywood gussets or dimensional lumber to connect posts and beams.
This property was accessed by a driveway shared with nearby properties. Shared driveways or access roads are excluded from this inspection. Comments in this report related to them are made as a courtesy only and are not meant to be a substitute for a evaluation by a specialist if repairs are needed. Recommend that the client review the recorded agreements regarding the driveway, the deeds of the property owners involved, and easements permitting access to, use of, and maintenance of the driveway.
Exterior and Foundation
Limitations: The inspector performs a visual inspection of accessible components or systems at the exterior. Items excluded from this inspection include below-grade foundation walls and footings; foundations, exterior surfaces or components obscured by vegetation, stored items or debris; wall structures obscured by coverings such as siding or trim. Some items such as siding, trim, soffits, vents and windows are often high off the ground, and may be viewed using binoculars from the ground or from a ladder. This may limit a full evaluation. Regarding foundations, some amount of cracking is normal in concrete slabs and foundation walls due to shrinkage and drying. Note that the inspector does not determine the adequacy of seismic reinforcement.
Wall inspection method: Viewed from ground
Condition of wall exterior covering: Appeared serviceable
Apparent wall structure: Wood frame
Wall covering: Wood fiber
Condition of foundation and footings: Appeared serviceable
Apparent foundation type: Unfinished basement
Foundation/stem wall material: Poured in place concrete, Stone
Soil was in contact with or less than 6 inches from siding, trim or structural wood. This is a conducive condition for wood-destroying organisms. Recommend grading or removing soil as necessary to maintain a 6-inch clearance. If not possible, then recommend replacing untreated wood with pressure-treated wood. Installation of borate-based products such as Impel rods can also reduce the likelihood of rot or infestation if soil cannot be removed. Note that damage from fungal rot and/or insects may be found when soil is removed, and repairs may be necessary.
Limitations: Structural components such as joists and beams, and other components such as piping, wiring and/or ducting that are obscured by under-floor insulation are also excluded from this inspection. Note that the inspector does not determine if support posts, columns, beams, joists, studs, trusses, etc. are of adequate size, spanning or spacing.
The inspector does not guarantee or warrant that water will not accumulate in the basement in the future. Access to the basement during all seasons and during prolonged periods of all types of weather conditions (e.g. heavy rain, melting snow) would be needed to do so. The inspector does not determine the adequacy of basement floor or stairwell drains, or determine if such drains are clear or clogged.
Note that all basement areas should be checked periodically for water intrusion, plumbing leaks and pest activity.
Condition of exterior entry doors: Required repair, replacement and/or evaluation (see comments below)
Exterior door material: Wood
Condition of insulation underneath floor above: Not applicable, none installed
The ceiling height over stairs at one or more locations was too low and poses a safety hazard, especially for tall people. Ceilings over stairs should be at least 6 feet 8 inches high. At a minimum, be aware of this hazard, especially when guests who are not familiar with the stairs are present. Recommend that a qualified contractor repair per standard building practices.
This occurs at the basement stair leading from the kitchen to the basement.
Handrails at one or more flights of stairs were missing. This is a safety hazard. Recommend that a qualified person repair as necessary.
A handrail should be installed at the staircase from the kitchen to the basement.
One or more exterior doors Didnt have functioning locking mechanism. Recommend that a qualified person repair as necessary.
A nail as opposed to a pad lock was used to secure one on the basement doors.
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; solar roofing components. Any comments made regarding these items are made as a courtesy only. Note that the inspector does not provide an estimate of remaining life on the roof surface material, nor guarantee that leaks have not occurred in the roof surface, skylights or roof penetrations in the past. Regarding roof leaks, only active leaks, visible evidence of possible sources of leaks, and evidence of past leaks observed during the inspection are reported on as part of this inspection. The inspector does not guarantee or warrant that leaks will not occur in the future. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high wind and rain, melting snow) would be needed to do so. Regarding the roof drainage system, unless the inspection was conducted during and after prolonged periods of heavy rain, the inspector was unable to determine if gutters, downspouts and extensions performed adequately or were leak-free.
Roof inspection method: Traversed
Condition of roof surface material: Appeared serviceable
Roof surface material: Asphalt or fiberglass composition shingles
Roof type: Gable
Condition of exposed flashings: Appeared serviceable
One or more downspouts were incomplete. Rainwater can come in contact with the building exterior or accumulate around the building foundation as a result. This is a conducive condition for wood-destroying organisms. Recommend that a qualified person repair as necessary.
A 90 degree downspout elbow and splash block should be installed adjacent to the back laundry room door to carry water away from the home. Picture shown above in this report.
Attic and Roof Structure
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; areas and components obscured by insulation. Any comments made regarding these items are made as a courtesy only. The inspector does not determine the adequacy of the attic ventilation system. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high/low temperatures, high/low humidity, high wind and rain, melting snow) would be needed to do so. The inspector is not a licensed engineer and does not determine the adequacy of roof structure components such as trusses, rafters or ceiling beams, or their spacing or sizing.
Attic inspection method: Viewed from hatch(es)
Roof structure type: Rafters
Ceiling structure: Ceiling joists
Condition of insulation in attic (ceiling, skylight chase, etc.): Appeared serviceable
Ceiling insulation material: Cellulose loose fill
Approximate attic insulation R value (may vary in areas): R-13
Vermiculite insulation present: None visible
Condition of roof ventilation: Appeared serviceable
Roof ventilation type: Gable end vents
One or more attic access hatches or doors were too small to allow easy access. Such hatches should be at least 22 x 30 inches in size, and in safely accessed areas. Recommend that a qualified person modify attic access points per standard building practices.
The ceiling insulation installed in the attic was substandard and appeared to have an R rating that's significantly less than current standards (R-38). Heating and cooling costs will likely be higher due to poor energy efficiency. Recommend that a qualified contractor install insulation for better energy efficiency and per standard building practices.
One or more attic access hatches or doors were not insulated, or had substandard insulation. Weatherstripping was also missing or substandard. Recommend installing weatherstripping and insulation per current standards at hatches or doors for better energy efficiency. For more information, visit:http://www.reporthost.com/?ATTACC
Limitations: The following items are not included in this inspection: generator systems, transfer switches, surge suppressors, inaccessible or concealed wiring; underground utilities and systems; low-voltage lighting or lighting on timers or sensors. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of grounding or bonding, if this system has an adequate capacity for the client's specific or anticipated needs, or if this system has any reserve capacity for additions or expansion. The inspector does not operate circuit breakers as part of the inspection, and does not install or change light bulbs. The inspector does not evaluate every wall switch or receptacle, but instead tests a representative number of them per various standards of practice. When furnishings, stored items or child-protective caps are present some receptacles are usually inaccessible and are not tested; these are excluded from this inspection. Receptacles that are not of standard 110 volt configuration, including 240-volt dryer receptacles, are not tested and are excluded. The functionality of, power source for and placement of smoke and carbon monoxide alarms is not determined as part of this inspection. Upon taking occupancy, proper operating and placement of smoke and carbon monoxide alarms should be verified and batteries should be changed. These devices have a limited lifespan and should be replaced every 10 years. The inspector attempts to locate and evaluate all main and sub-panels. However, panels are often concealed. If panels are found after the inspection, a qualified electrician should evaluate and repair if necessary. The inspector attempts to determine the overall electrical service size, but such estimates are not guaranteed because the overall capacity may be diminished by lesser-rated components in the system. Any repairs recommended should be made by a licensed electrician.
Electric service condition: Appeared serviceable
Primary service type: Overhead
Number of service conductors: 2
Service voltage (volts): 120-240
Primary service overload protection type: Circuit breakers
Service entrance conductor material: Stranded copper
System ground: Not determined, not readily apparent
Condition of main service panel: Required repair, replacement and/or evaluation (see comments below)
Condition of sub-panel(s): Required repair, replacement and/or evaluation (see comments below)
Location of main service panel #A: Laundry room
Location of main service panel #B: Barn
Location of main disconnect: Breaker at top of main service panel
Condition of branch circuit wiring: Serviceable
Branch circuit wiring type: Non-metallic sheathed
Solid strand aluminum branch circuit wiring present: None visible
Ground fault circuit interrupter (GFCI) protection present: No
Arc fault circuit interrupter (AFCI) protection present: No
Smoke alarms installed: Yes, but not tested
Carbon monoxide alarms installed: No, recommend install
Modifications were made to panel(s) #A or to equipment inside. Electric panels and equipment inside are Underwriter Laboratory rated devices, and modifications to them are not allowed. Recommend that a qualified electrician evaluate and replace components or make repairs as necessary.
The main breaker panel needs a cover to be in compliance with local codes and ordinances. At a minimum here a metal UL cover needs to be installed.
Extension cords were being used as permanent wiring at one or more locations. They should only be used for portable equipment on a temporary basis. Using extension cords as permanent wiring is a potential fire and shock hazard, and indicates that wiring is inadequate and needs updating. Extension cords may be undersized. Connections may not be secure resulting in power fluctuations, damage to equipment, overheating and sparks that could start a fire. Recommend that a qualified electrician repair per standard building practices and eliminate extension cords for permanently installed equipment.
This occurs at the ceiling fan in the dining room.
Smoke alarms were missing from one or more bedrooms. Additional smoke alarms should be installed as necessary so a functioning alarm exists in each hallway leading to bedrooms, in each bedroom, on each level and in any attached garage. For more information, visit:http://www.reporthost.com/?SMKALRM
No carbon monoxide alarms were visible. This is a potential safety hazard. Some states and/or municipalities require CO alarms to be installed for new construction and/or for homes being sold. Recommend installing approved CO alarms outside of each separate sleeping area in the immediate vicinity of the bedrooms on each level and in accordance with the manufacturer's recommendations. For more information, visit:http://www.reporthost.com/?COALRM
Carbon monoxide alarms were missing from one or more sleeping areas. This is a potential safety hazard. Some states and/or municipalities require CO alarms to be installed in the vicinity of each sleeping area, on each level and in accordance with the manufacturer's recommendations. Recommend installing additional carbon monoxide alarms per these standards. For more information, visit:http://www.reporthost.com/?COALRM
Branch circuit wiring installed in buildings built prior to the mid 1980s is typically rated for a maximum temperature of only 60 degrees Celsius. This includes non-metallic sheathed (Romex) wiring, and both BX and AC metal-clad flexible wiring. Knob and tube wiring, typically installed in homes built prior to 1950, may be rated for even lower maximum temperatures. Newer electric fixtures including lighting and fans typically require wiring rated for 90 degrees Celsius. Connecting newer fixtures to older, 60-degree-rated wiring is a potential fire hazard. Repairs for such conditions may involve replacing the last few feet of wiring to newer fixtures with new 90-degree-rated wire, and installing a junction box to join the old and new wiring.
It is beyond the scope of this inspection to determine if such incompatible components are installed, or to determine the extent to which they're installed. Based on the age of this building, the client should be aware of this safety hazard, both for existing fixtures and when planning to upgrade with newer fixtures. Consult with a qualified electrician for repairs as necessary.
Few receptacles (outlets) were installed in one or more areas by modern standards. This can result in "octopus" wiring with extension cords, which is a fire hazard. Also, 2-slot receptacles (outlets) rather than 3-slot, grounded receptacles were installed in one or more areas. These do not have an equipment ground and are considered to be unsafe by today's standards. Appliances that require a ground should not be used with 2-slot receptacles. Examples of such appliances include computers and related hardware, refrigerators, freezers, portable air conditioners, clothes washers, aquarium pumps, and electrically operated gardening tools. The client should be aware of this limitation when planning use for various rooms, such as an office. Upgrading to grounded receptacles typically requires installing new wiring from the main service panel or sub-panel to the receptacle(s), in addition to replacing the receptacle(s). Consult with a qualified electrician about upgrading circuits with additional receptacles and 3-wire, grounded receptacles per standard building practices.
Plumbing / Fuel Systems
Limitations: The following items are not included in this inspection: private/shared wells and related equipment; private sewage disposal systems; hot tubs or spas; main, side and lateral sewer lines; gray water systems; pressure boosting systems; trap primers; incinerating or composting toilets; fire suppression systems; water softeners, conditioners or filtering systems; plumbing components concealed within the foundation or building structure, or in inaccessible areas such as below tubs; underground utilities and systems; overflow drains for tubs and sinks; backflow prevention devices. Any comments made regarding these items are as a courtesy only. Note that the inspector does not operate water supply or shut-off valves due to the possibility of valves leaking or breaking when operated. The inspector does not test for lead in the water supply, the water pipes or solder, does not determine if plumbing and fuel lines are adequately sized, and does not determine the existence or condition of underground or above-ground fuel tanks.
Condition of service and main line: Appeared serviceable
Water service: Private well
Location of main water shut-off: Basement
Condition of supply lines: Appeared serviceable
Supply pipe material: Copper, Galvanized steel
Condition of drain pipes: Appeared serviceable
Drain pipe material: Plastic
Condition of waste lines: Appeared serviceable
Waste pipe material: Plastic
Vent pipe condition: Appeared serviceable
Vent pipe material: Plastic
Sump pump installed: No
Visible fuel storage systems: oil tank
Location of main fuel shut-off valve: At oil tank
Copper water supply pipes were installed. Copper pipes installed prior to the late 1980s may be joined with solder that contains lead, which is a known health hazard especially for children. Laws were passed in 1985 prohibiting the use of lead in solder, but prior to that solder normally contained approximately 50% lead. The client should be aware of this, especially if children will be using this water supply system. Note that the inspector does not test for toxic materials such as lead. The client should consider having a qualified lab test for lead, and if necessary take steps to reduce or remove lead from the water supply. Various solutions include:
- Flush water taps or faucets. Do not drink water that has been sitting in the plumbing lines for more than 6 hours
- Install appropriate filters at points of use
- Use only cold water for cooking and drinking, as hot water dissolves lead more quickly than cold water
- Use bottled or distilled water
- Treat well water to make it less corrosive
- Have a qualified plumber replace supply pipes and/or plumbing components as necessary
For more information visit:http://www.reporthost.com/?LEADDWhttp://www.reporthost.com/?LEAD
Based on visible equipment or information provided to the inspector, this property appeared to have a yard irrigation (sprinkler) system. These are specialty systems and are excluded from this inspection. Comments in this report related to this system are made as a courtesy only and are not meant to be a substitute for a full evaluation by a qualified specialist. When this system is operated, recommend verifying that water is not directed at building exteriors, or directed so water accumulates around building foundations. Sprinkler heads may need to be adjusted, replaced or disabled. Consider having a qualified plumber verify that a backflow prevention device is installed per standard building practices to prevent cross-contamination of potable water. Recommend that a qualified specialist evaluate the irrigation system for other defects (e.g. leaks, damaged or malfunctioning sprinkler heads) and repair if necessary.
Significant corrosion or rust was found at one or more water supply valves. This can indicate past leaks, or that leaks are likely to occur in the future. Recommend that a qualified plumber repair as necessary. For example, by replacing valves or fittings.
Upstairs bathroom vanity.
Based on visible components or information provided to the inspector, this property appeared to have a private sewage disposal (septic) system. These are specialty systems and are excluded from this inspection. Comments in this report related to this system are made as a courtesy only and are not meant to be a substitute for a full evaluation by a qualified specialist. Generally, septic tanks should be pumped and inspected every 3 years. Depending on the type of system and municipal regulations, inspection and maintenance may be required more frequently, often annually. Recommend the following:
- Consult with the property owner about this system's maintenance and repair history
- Review any documentation available for this system
- Review inspection and maintenance requirements for this system
- That a qualified specialist evaluate, perform maintenance and make repairs if necessary
For more information, visit:http://www.reporthost.com/?SEPTIC
Based on visible equipment or information provided to the inspector, the water supply to this property appeared to be from a private well. Private well water supplies are specialty systems and are excluded from this inspection. Comments in this report related to this system are made as a courtesy only and are not meant to be a substitute for a full evaluation by a qualified specialist. The inspector does not test private well water for contamination or pollutants, determine if the supply and/or flow are adequate, or provide an estimate for remaining life of well pumps, pressure tanks or equipment. Only visible and accessible components are evaluated. Recommend the following:
- That a qualified well contractor fully evaluate the well, including a pump/flow test
- That the well water be tested per the client's concerns (coliforms, pH, contaminants, etc.)
- Research the well's history (how/when constructed, how/when maintained or repaired, past performance, past health issues)
- Document the current well capacity and water quality for future reference
For more information, visit:http://www.reporthost.com/?WELL
Limitations: Evaluation of and determining the adequacy or completeness of the following items are not included in this inspection: water recirculation pumps; solar water heating systems; Energy Smart or energy saver controls; catch pan drains. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on water heaters, does not determine if water heaters are appropriately sized, or perform any evaluations that require a pilot light to be lit or a shut-off valve to be operated.
Condition of water heater: Required repair, replacement and/or evaluation (see comments below)
Energy source: Electricity
Estimated age: 2004
Capacity (in gallons): 50
Location of water heater: Basement
Hot water temperature tested: Yes
Water temperature (degrees Fahrenheit): 115
Condition of burners: Appeared serviceable
No drain line was installed for the temperature-pressure relief valve. Drain lines are normally installed to prevent water from accumulating if/when the valve eventually leaks, and to prevent scalding if someone is standing next to the water heater when the valve opens. Recommend that a qualified plumber install a drain line so it drains outside and per standard building practices.
The estimated useful life for most water heaters is 8-12 years. This water heater appeared to be near this age and/or its useful lifespan and may need replacing at any time. Recommend budgeting for a replacement in the near future, or considering replacement now before any leaks occur. The client should be aware that significant flooding can occur if the water heater fails. If not replaced now, consider having a qualified person install a catch pan and drain or a water alarm to help prevent damage if water does leak.
Heating, Ventilation and Air Condition (HVAC)
Limitations: The following items are not included in this inspection: humidifiers, dehumidifiers, electronic air filters; solar, coal or wood-fired heat systems; thermostat or temperature control accuracy and timed functions; heating components concealed within the building structure or in inaccessible areas; underground utilities and systems; safety devices and controls (due to automatic operation). Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on heating or cooling system components, does not determine if heating or cooling systems are appropriately sized, does not test coolant pressure, or perform any evaluations that require a pilot light to be lit, a shut-off valve to be operated, a circuit breaker to be turned "on" or a serviceman's or oil emergency switch to be operated. It is beyond the scope of this inspection to determine if furnace heat exchangers are intact and free of leaks. Condensation pans and drain lines may clog or leak at any time and should be monitored while in operation in the future. Where buildings contain furnishings or stored items, the inspector may not be able to verify that a heat source is present in all "liveable" rooms (e.g. bedrooms, kitchens and living/dining rooms).
General heating system type(s): Forced air, Furnace, Wood-burning fireplace or stove
General heating distribution type(s): Ducts and registers
Last service date of primary heat source: 10-8-13
Source for last service date of primary heat source: Label
Condition of forced air heating/(cooling) system: Appeared serviceable
Forced air heating system fuel type: Oil
Estimated age of forced air furnace: Unknown, very old
Location of forced air furnace: Basement
Location for forced air filter(s): At top of air handler
Condition of forced air ducts and registers: Appeared serviceable
One or more "livable" rooms had no visible source of heat. Examples of livable rooms include bedrooms, kitchens and living/dining rooms, NOT hallways, closets or bathrooms. Livable rooms without heat (e.g. heat register, radiator, baseboard or wall heater) can be uncomfortable and have high levels of moisture. Depending on the client's needs, recommend consulting with a qualified heating contractor to determine options for modifying or improving the heating system per standard building practices.
The only heating supply duct in the upstairs area in in the hallway, none in the bedrooms.
Fireplaces, Stoves, Chimneys and Flues
Limitations: The following items are not included in this inspection: coal stoves, gas logs, chimney flues (except where visible). Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of drafting or sizing in fireplace and stove flues, and also does not determine if prefabricated or zero-clearance fireplaces are installed in accordance with the manufacturer's specifications. The inspector does not perform any evaluations that require a pilot light to be lit, and does not light fires. The inspector provides a basic visual examination of a chimney and any associated wood burning device. The National Fire Protection Association has stated that an in-depth Level 2 chimney inspection should be part of every sale or transfer of property with a wood-burning device. Such an inspection may reveal defects that are not apparent to the home inspector who is a generalist.
Condition of wood-burning fireplaces, stoves: Required repair, replacement and/or evaluation (see comments below)
Wood-burning fireplace type: Masonry, Metal pre-fab
Wood-burning stove type: Freestanding, Insert, Pellet stove
Condition of chimneys and flues: Appeared serviceable
Wood-burning chimney type: Masonry
Bathrooms, Laundry and Sinks
Limitations: The following items are not included in this inspection: overflow drains for tubs and sinks; heated towel racks, saunas, steam generators, clothes washers, clothes dryers. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of washing machine drain lines, washing machine catch pan drain lines, or clothes dryer exhaust ducts. The inspector does not operate water supply or shut-off valves for sinks, toilets, bidets, clothes washers, etc. due to the possibility of valves leaking or breaking when operated. The inspector does not determine if shower pans or tub and shower enclosures are water tight, or determine the completeness or operability of any gas piping to laundry appliances.
Location #A: Full bath
Location #B: 3/4 bath
Condition of counters: Appeared serviceable
Condition of cabinets: Appeared serviceable
Condition of flooring: Appeared serviceable
Condition of sinks and related plumbing: Required repair, replacement and/or evaluation (see comments below)
Condition of toilets: Appeared serviceable
Condition of bathtubs and related plumbing: Appeared serviceable
Condition of shower(s) and related plumbing: Required repair, replacement and/or evaluation (see comments below)
Condition of ventilation systems: Appeared serviceable
The shower enclosure at location(s) #B was deteriorated, damaged or substandard. Water can damage the wall structure as a result. Recommend that a qualified contractor repair or replace the surround as necessary.
Holes appear around the supply handles at the upstairs metal shower enclosure
Gaps, no caulk, or substandard caulking were found around the sink at location(s) #A. Water can penetrate these areas and cause damage. Recommend that a qualified person repair as necessary. For example, by installing or replacing caulk.
One or more sink drains were leaking at location(s) #A. A qualified person should repair as necessary.
Main floor eastern most bathroom sink drain lines appear to be leaking.
The toilet at the main floor bathroom as well as the basement bathroom had no caulk at he base and floor location. We recommend caulk be applied at the front and sides of the base of the toilet but not at the back. This is a sanitary issue but by leaving the back un-caulked any waste line leaks at the wax ring will not go unnoticed.
Interior, Doors and Windows
Limitations: The following items are not included in this inspection: security, intercom and sound systems; communications wiring; central vacuum systems; elevators and stair lifts; cosmetic deficiencies such as nail-pops, scuff marks, dents, dings, blemishes or issues due to normal wear and tear in wall, floor and ceiling surfaces and coverings, or in equipment; deficiencies relating to interior decorating; low voltage and gas lighting systems. Any comments made regarding these items are as a courtesy only. Note that the inspector does not evaluate any areas or items which require moving stored items, furnishings, debris, equipment, floor coverings, insulation or similar materials. The inspector does not test for asbestos, lead, radon, mold, hazardous waste, urea formaldehyde urethane, or any other toxic substance. Some items such as window, drawer, cabinet door or closet door operability are tested on a sampled basis. The client should be aware that paint may obscure wall and ceiling defects, floor coverings may obscure floor defects, and furnishings may obscure wall, floor and floor covering defects. If furnishings were present during the inspection, recommend a full evaluation of walls, floors and ceilings that were previously obscured when possible. Determining the cause and/or source of odors is not within the scope of this inspection.
Condition of exterior entry doors: Required repair, replacement and/or evaluation (see comments below)
Exterior door material: Metal
Condition of interior doors: Required repair, replacement and/or evaluation (see comments below)
Condition of windows and skylights: Appeared serviceable
Type(s) of windows: Vinyl, Metal, Sliding, Single-hung, Fixed
Condition of walls and ceilings: Appeared serviceable
Wall type or covering: Drywall, Paneling
Ceiling type or covering: Drywall
Condition of flooring: Appeared serviceable
Some exterior door hardware, including deadbolts were missing. Recommend that a qualified person repair or replace as necessary.
The north facing exterior entry door has no deadbolt.
Thank you for using Washington Home Inspection for your home inspection. I know your home inspection is very important to you and your business is very important to me. If I can help in anyway after the inspection, please call or Email me at the Email address or telephone number provided on this report. If you are happy with Washington Home Inspection please refer my company to your friends, your realtor and anyone you believe could benefit from my services. Washington Home Inspection not only performs inspections for purchasers, but also for people planning to sell a home who wish to estimate the amount of work that needs to be completed before listing the house.
A home inspection is a visual, and not an exhaustive or invasive, inspection of a home by a trained and impartial inspector. Washington Home Inspection adheres to the standards of the practice of the state of Washington.