Top Rated Home InspectionWebsite: http://www.topratedhomeinspection.com
Phone: (323) 494-5774
Inspector's phone: (323) 494-5774
Inspector: Julio Montiel
This report published on Monday, January 28, 2013 12:43:56 AM PST
Property Inspection Report|
||5730 3rd Ave, Los Angeles, CA 90043
View report summary
This report is the exclusive property of this inspection company and the client(s) listed in the report title. Use of this report by any unauthorized persons is prohibited.
How to Read this Report
This report is organized by the property's functional areas. Within each functional area, descriptive information is listed first and is shown in bold type. Items of concern follow descriptive information.
Concerns are shown and sorted according to these types:
|Safety||Poses a safety hazard |
|Repair/Replace||Recommend repairing or replacing |
|Repair/Maintain||Recommend repair and/or maintenance |
|Maintain||Recommend ongoing maintenance |
|Evaluate||Recommend evaluation by a specialist |
|Monitor||Recommend monitoring in the future |
|Serviceable||Item or component is in serviceable condition |
|Comment||For your information |
Click here for a glossary of building construction terms.
Contact your inspector if there are terms that you do not understand, or visit the glossary of construction terms at http://www.reporthost.com/glossary.asp
Time started: 10am
Time finished: 1pm
Present during inspection: Client, Realtor
Client present for discussion at end of inspection: Yes
Weather conditions during inspection: Rain
Temperature during inspection: Cool
Inspection fee: $200.00
Payment method: Cash
Type of building: Single family, Detached garage
Buildings inspected: One house, One detached garage
Front of building faces: West
Main entrance faces: West
Occupied: Furniture or stored items were presentminimal
Structures built prior to the mid 1980s may contain lead and/or asbestos. Lead is commonly found in paint and in some plumbing components. The EPA does not recognize newer coats of paint as encapsulating older coats of lead-based paint. Asbestos is commonly found in various building materials such as insulation, siding, and/or floor and ceiling tiles. Laws were passed in 1978 to prohibit usage of lead and asbestos, but stocks of materials containing these substances remained in use for a number of years thereafter. Both lead and asbestos are known health hazards. Evaluating for the presence of lead and/or asbestos is beyond the scope of this inspection. Any mention of these materials in this report is made as a courtesy only, and meant to refer the client to a specialist. Consult with specialists as necessary, such as industrial hygienists, professional labs and/or abatement specialists for this type of evaluation. For information on lead, asbestos and other hazardous materials in homes, visit:
Limitations: Unless specifically included in the inspection, the following items and any related equipment, controls, electric systems and/or plumbing systems are excluded from this inspection: detached buildings or structures; fences and gates; retaining walls; underground drainage systems, catch basins or concealed sump pumps; swimming pools and related safety equipment, spas, hot tubs or saunas; whether deck, balcony and/or stair membranes are watertight; trees, landscaping, properties of soil, soil stability, erosion and erosion control; ponds, water features, irrigation or yard sprinkler systems; sport courts, playground, recreation or leisure equipment; areas below the exterior structures with less than 3 feet of vertical clearance; invisible fencing; sea walls, docks and boathouses; retractable awnings. Any comments made regarding these items are as a courtesy only.
Site profile: Level
Condition of driveway: Appeared serviceable
Driveway material: Poured in place concrete
Condition of sidewalks and/or patios: Appeared serviceable
Sidewalk material: Poured in place concrete, Paving stones
Condition of deck, patio and/or porch covers: Appeared serviceable
Deck, patio, porch cover material and type: Covered (Refer to Roof section)
Condition of decks, porches and/or balconies: Appeared serviceable
Deck, porch and/or balcony material: Tile
Limitations: The inspector performs a visual inspection of accessible components or systems at the exterior. Items excluded from this inspection include below-grade foundation walls and footings; foundations, exterior surfaces or components obscured by vegetation, stored items or debris; wall structures obscured by coverings such as siding or trim. Some items such as siding, trim, soffits, vents and windows are often high off the ground, and may be viewed using binoculars from the ground or from a ladder. This may limit a full evaluation. Regarding foundations, some amount of cracking is normal in concrete slabs and foundation walls due to shrinkage and drying. Note that the inspector does not determine the adequacy of seismic reinforcement.
Condition of wall exterior covering: Appeared serviceable
Apparent wall structure: Wood frame
Wall covering: Stucco
Condition of foundation and footings: Appeared serviceable
Apparent foundation type: Crawl space
Foundation/stem wall material: Post and pier construction, no stem wall
Limitations: Structural components such as joists and beams, and other components such as piping, wiring and/or ducting that are obscured by under-floor insulation are excluded from this inspection. The inspector does not determine if support posts, columns, beams, joists, studs, trusses, etc. are of adequate size, spanning or spacing.
The inspector does not guarantee or warrant that water will not accumulate in the crawl spaces in the future. Complete access to all crawl space areas during all seasons and during prolonged periods of all types of weather conditions (e.g. heavy rain, melting snow) would be needed to do so.
The inspector attempts to locate all crawl space access points and areas. Access points may be obscured or otherwise hidden by furnishings or stored items. In such cases, the client should ask the property owner where all access points are that are not described in this inspection, and have those areas inspected. Note that crawl space areas should be checked at least annually for water intrusion, plumbing leaks and pest activity.
Crawl space inspection method: Partially traversed
Condition of floor substructure above crawl space: Appeared serviceable
Pier or support post material: Wood
Beam material: Solid wood
Floor structure: Solid wood joists
Condition of insulation underneath floor above: Not applicable, none installed
Condition of crawl space ventilation: Appeared serviceable
Pier / Post connector support in crawl space
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; solar roofing components. Any comments made regarding these items are made as a courtesy only. Note that the inspector does not provide an estimate of remaining life on the roof surface material, nor guarantee that leaks have not occurred in the roof surface, skylights or roof penetrations in the past. Regarding roof leaks, only active leaks, visible evidence of possible sources of leaks, and evidence of past leaks observed during the inspection are reported on as part of this inspection. The inspector does not guarantee or warrant that leaks will not occur in the future. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high wind and rain, melting snow) would be needed to do so. Regarding the roof drainage system, unless the inspection was conducted during and after prolonged periods of heavy rain, the inspector was unable to determine if gutters, downspouts and extensions performed adequately or were leak-free.
Roof inspection method: Viewed from eaves on ladder
Condition of roof surface material: Appeared serviceable
Roof surface material: Asphalt or fiberglass composition shingles
Apparent number of layers of roof surface material: 3
Condition of exposed flashings: Appeared serviceable
Flashings at the base of one or more chimneys were missing. Leaks can occur as a result. This is a conducive condition for wood-destroying organisms. Recommend that a qualified contractor evaluate and repair as necessary.
Chimney rain / spark cap missing and north side ( external ) of chimney compartment needs future maintenance cleaning.
Chimney flashing missing
Cleaning & maintenance needed
Rain / spark cap missing
One or more gutters, downspouts were missing. Rainwater can come in contact with the building exterior or accumulate around the building foundation as a result. This is a conducive condition for wood-destroying organisms. Recommend that a qualified person repair as necessary.
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; areas and components obscured by insulation. Any comments made regarding these items are made as a courtesy only. The inspector does not determine the adequacy of the attic ventilation system. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high/low temperatures, high/low humidity, high wind and rain, melting snow) would be needed to do so. The inspector is not a licensed engineer and does not determine the adequacy of roof structure components such as trusses, rafters or ceiling beams, or their spacing or sizing.
Attic inspection method: Traversed
Condition of roof structure: Appeared serviceable
Condition of insulation in attic (ceiling, skylight chase, etc.): Appeared serviceable
Condition of roof ventilation: Appeared serviceable
Roof ventilation type: Gable end vents
One or more exhaust fans in the attic had no duct to route the exhaust air outside. As a result, conditioned air will enter the attic when the fan is operated. This can result in excessive moisture in the attic. Recommend that a qualified contractor install ducting per standard building practices. Typically, this includes a duct with R-4 rated insulation permanently attached to a vent hood or cap installed on the roof or at an exterior wall.
Both bathrooms A, B & kitchen have no ducted vents.
Limitations: The inspector does not determine the adequacy of firewall ratings. Requirements for ventilation in garages vary between municipalities.
Kitchen hood vent missing
Bath B missing ducts
Bath A missing ducts
Condition of garage interior: Appeared serviceable
Garage ventilation: Adequate
Garage bathroom GFCI outlet non operational
Limitations: The following items are not included in this inspection: generator systems, transfer switches, surge suppressors, inaccessible or concealed wiring; underground utilities and systems; low-voltage lighting or lighting on timers or sensors. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of grounding or bonding, if this system has an adequate capacity for the client's specific or anticipated needs, or if this system has any reserve capacity for additions or expansion. The inspector does not operate circuit breakers as part of the inspection, and does not install or change light bulbs. The inspector does not evaluate every wall switch or receptacle, but instead tests a representative number of them per various standards of practice. When furnishings, stored items or child-protective caps are present some receptacles are usually inaccessible and are not tested; these are excluded from this inspection. Receptacles that are not of standard 110 volt configuration, including 240-volt dryer receptacles, are not tested and are excluded. The functionality of, power source for and placement of smoke and carbon monoxide alarms is not determined as part of this inspection. Upon taking occupancy, proper operating and placement of smoke and carbon monoxide alarms should be verified and batteries should be changed. These devices have a limited lifespan and should be replaced every 10 years. The inspector attempts to locate and evaluate all main and sub-panels. However, panels are often concealed. If panels are found after the inspection, a qualified electrician should evaluate and repair if necessary. The inspector attempts to determine the overall electrical service size, but such estimates are not guaranteed because the overall capacity may be diminished by lesser-rated components in the system. Any repairs recommended should be made by a licensed electrician.
Electric service condition: Appeared serviceable
Service voltage (volts): 120-240
Primary service overload protection type: Circuit breakers
Main disconnect rating (amps): 200
System ground: Ground rod(s) in soil, Cold water supply pipes
Condition of main service panel: Appeared serviceable
Condition of sub-panel(s): Appeared serviceable
Location of main service panel #A: Bedroom
Location of sub-panel #B: Garage
Location of main disconnect: Breaker at mid of main service panel
Condition of branch circuit wiring: Serviceable
Smoke alarms installed: Yes, but not tested
Carbon monoxide alarms installed: Yes, but not tested
One or more ground fault circuit interrupter (GFCI) receptacles (outlets) wouldn't trip at the garage. This is a potential shock hazard. Recommend that a qualified electrician evaluate and repair as necessary.
Garage bathroom GFCI non responsive when tested
Smoke and CO2 detectors installed and appeared serviceable.
All receptacles are grounded and functioning in the house and garage. All GFCI in the house tripped properly.
Limitations: The following items are not included in this inspection: private/shared wells and related equipment; private sewage disposal systems; hot tubs or spas; main, side and lateral sewer lines; gray water systems; pressure boosting systems; trap primers; incinerating or composting toilets; fire suppression systems; water softeners, conditioners or filtering systems; plumbing components concealed within the foundation or building structure, or in inaccessible areas such as below tubs; underground utilities and systems; overflow drains for tubs and sinks; backflow prevention devices. Any comments made regarding these items are as a courtesy only. Note that the inspector does not operate water supply or shut-off valves due to the possibility of valves leaking or breaking when operated. The inspector does not test for lead in the water supply, the water pipes or solder, does not determine if plumbing and fuel lines are adequately sized, and does not determine the existence or condition of underground or above-ground fuel tanks.
Condition of service and main line: Appeared serviceable
Water service: Public
Water pressure (psi): 100psi
Location of main water shut-off: west of main house
Condition of supply lines: Appeared serviceable
Supply pipe material: Galvanized steel
Condition of drain pipes: Appeared serviceable
Drain pipe material: Plastic, Galvanized steel
Condition of waste lines: Appeared serviceable
Vent pipe condition: Appeared serviceable
Vent pipe material: Plastic
Condition of fuel system: Appeared serviceable
Location of main fuel shut-off valve: At gas meter
No earthquake shut-off valve located-Red.
Gas shut off valve located-Green.
One or more sections of galvanized steel gas supply piping were routed underground. This type of piping is likely to corrode underground. Steel pipes with a factory coating other than galvanized zinc, or approved plastic pipe, should be used. Recommend that a qualified contractor repair per standard building practices.
The water supply pressure was greater than 80 psi ( tested at 100 pounds per square inch (PSI)). Pressures above 80 PSI may void warranties for some appliances such as water heaters or washing machines. Flexible supply lines to washing machines are likely to burst with higher pressures. 40-80 PSI is considered the normal range for water pressure in a home, and most plumbers recommend 50-60 PSI . Typically, the pressure cannot be regulated at the water meter. Recommend that a qualified plumber evaluate and make modifications to reduce the pressure to below 80 PSI . Installing a pressure reducing valve on the main service pipe is a common solution to this problem. If one exists, then it should be adjusted, repaired or replaced as necessary to maintain lower pressures. Note that installing a pressure reducing valve creates a "closed system," which may require installing an expansion tank at the water heater if one is not already installed.
Water main valve located at west of house (front)
The gas meter was in contact with or too close to the soil below and is likely to rust as a result. Gas meters should be located 10 inches or more above the soil below. Soil should be graded or removed as necessary.
Limitations: Evaluation of and determining the adequacy or completeness of the following items are not included in this inspection: water recirculation pumps; solar water heating systems; Energy Smart or energy saver controls; catch pan drains. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on water heaters, does not determine if water heaters are appropriately sized, or perform any evaluations that require a pilot light to be lit or a shut-off valve to be operated.
Condition of water heater: Appeared serviceable
Energy source: Natural gas
Estimated age: 2001
Capacity (in gallons): 40
Temperature-pressure relief valve installed: Yes
Location of water heater: Exterior closet
Hot water temperature tested: Yes 74 degrees
Water temperature (degrees Fahrenheit): needs further evaluation or adjustment
The estimated useful life for most water heaters is 8-12 years. This water heater appeared to be near 10 years this age and/or its useful lifespan and may need replacing at any time. Recommend budgeting for a replacement in the near future, or considering replacement now before any leaks occur. The client should be aware that significant flooding can occur if the water heater fails. If not replaced now, consider having a qualified person install a catch pan and drain or a water alarm to help prevent damage if water does leak.
Properly strapped. Needs adjustment as water heat tested at 74 degrees at all faucets.
Limitations: The following items are not included in this inspection: humidifiers, dehumidifiers, electronic air filters; solar, coal or wood-fired heat systems; thermostat or temperature control accuracy and timed functions; heating components concealed within the building structure or in inaccessible areas; underground utilities and systems; safety devices and controls (due to automatic operation). Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on heating or cooling system components, does not determine if heating or cooling systems are appropriately sized, does not test coolant pressure, or perform any evaluations that require a pilot light to be lit, a shut-off valve to be operated, a circuit breaker to be turned "on" or a serviceman's or oil emergency switch to be operated. It is beyond the scope of this inspection to determine if furnace heat exchangers are intact and free of leaks. Condensation pans and drain lines may clog or leak at any time and should be monitored while in operation in the future. Where buildings contain furnishings or stored items, the inspector may not be able to verify that a heat source is present in all "liveable" rooms (e.g. bedrooms, kitchens and living/dining rooms).
General heating system type(s): Forced air
General heating distribution type(s): Ducts and registers
Condition of forced air heating/(cooling) system: Appeared serviceable
Forced air heating system fuel type: Natural gas
Location of forced air furnace: Attic
Condition of furnace filters: Appeared serviceable
Condition of forced air ducts and registers: Appeared serviceable
Condition of venting system: Appeared serviceable
Condition of controls: Appeared serviceable
Heating and cooling was serviceable. New filter installed.
Hallway filter compartment
East bedroom has no vents for heater nor cooling. Has a ceiling fan
Limitations: The following items are not included in this inspection: coal stoves, gas logs, chimney flues (except where visible). Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of drafting or sizing in fireplace and stove flues, and also does not determine if prefabricated or zero-clearance fireplaces are installed in accordance with the manufacturer's specifications. The inspector does not perform any evaluations that require a pilot light to be lit, and does not light fires. The inspector provides a basic visual examination of a chimney and any associated wood burning device. The National Fire Protection Association has stated that an in-depth Level 2 chimney inspection should be part of every sale or transfer of property with a wood-burning device. Such an inspection may reveal defects that are not apparent to the home inspector who is a generalist.
Condition of wood-burning fireplaces, stoves: Appeared serviceable
Wood-burning fireplace type: Masonry
Condition of chimneys and flues: Appeared serviceable
Wood-burning chimney type: Masonry
Limitations: The following items are not included in this inspection: household appliances such as stoves, ovens, cook tops, ranges, warming ovens, griddles, broilers, dishwashers, trash compactors, refrigerators, freezers, ice makers, hot water dispensers and water filters; appliance timers, clocks, cook functions, self and/or continuous cleaning operations, thermostat or temperature control accuracy, and lights. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of the remaining life of appliances, and does not determine the adequacy of operation of appliances. The inspector does not note appliance manufacturers, models or serial numbers and does not determine if appliances are subject to recalls. Areas and components behind and obscured by appliances are inaccessible and excluded from this inspection.
Condition of counters: Appeared serviceable
Condition of cabinets: Appeared serviceable
Condition of sinks and related plumbing: Appeared serviceable
Condition of under-sink food disposal: Appeared serviceable
See Attic and Roof Structure
Limitations: The following items are not included in this inspection: overflow drains for tubs and sinks; heated towel racks, saunas, steam generators, clothes washers, clothes dryers. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of washing machine drain lines, washing machine catch pan drain lines, or clothes dryer exhaust ducts. The inspector does not operate water supply or shut-off valves for sinks, toilets, bidets, clothes washers, etc. due to the possibility of valves leaking or breaking when operated. The inspector does not determine if shower pans or tub and shower enclosures are water tight, or determine the completeness or operability of any gas piping to laundry appliances.
Location #A: Full bathwest
Location #B: Full batheast
Location #C: Full bathgarage
Condition of counters: Appeared serviceable
Condition of cabinets: Appeared serviceable
Condition of flooring: Appeared serviceable
Condition of sinks and related plumbing: Appeared serviceable
Condition of toilets: Required repair, replacement and/or evaluation (see comments below)
Condition of bathtubs and related plumbing: Appeared serviceable
Condition of shower(s) and related plumbing: Required repair, replacement and/or evaluation (see comments below)
Condition of ventilation systems: Appeared serviceable
The hot and cold water supply flow for the bathtub at location(s) #B is inoperable. Recommend that a qualified plumber evaluate and repair as necessary.
The shower enclosure at location(s) #C was missing. Water can damage the wall structure as a result. Recommend that a qualified contractor repair or replace the surround as necessary.
Missing shower door at bath #C
The toilet at location(s) #B & C was loose where it attached to the floor. Leaks can occur. Flooring, the sub-floor or areas below may get damaged. Sewer gases can enter living spaces. Recommend that a qualified contractor remove the toilet(s) for further evaluation and repair if necessary. A new wax ring should be installed and toilet(s) should be securely anchored to the floor to prevent movement and leaking.
Toilets in east bath B and garage bath C need slight tightening.
It is recommended that bath #B needs minor caulking on the sinks back-splash and tub fixture.
Moisture tested on all under sink dry walls ( plumbing prone leaks ). No detection.
Limitations: The following items are not included in this inspection: security, intercom and sound systems; communications wiring; central vacuum systems; elevators and stair lifts; cosmetic deficiencies such as nail-pops, scuff marks, dents, dings, blemishes or issues due to normal wear and tear in wall, floor and ceiling surfaces and coverings, or in equipment; deficiencies relating to interior decorating; low voltage and gas lighting systems. Any comments made regarding these items are as a courtesy only. Note that the inspector does not evaluate any areas or items which require moving stored items, furnishings, debris, equipment, floor coverings, insulation or similar materials. The inspector does not test for asbestos, lead, radon, mold, hazardous waste, urea formaldehyde urethane, or any other toxic substance. Some items such as window, drawer, cabinet door or closet door operability are tested on a sampled basis. The client should be aware that paint may obscure wall and ceiling defects, floor coverings may obscure floor defects, and furnishings may obscure wall, floor and floor covering defects. If furnishings were present during the inspection, recommend a full evaluation of walls, floors and ceilings that were previously obscured when possible. Determining the cause and/or source of odors is not within the scope of this inspection.
Condition of exterior entry doors: Appeared serviceable
Exterior door material: Wood, Metal
Condition of interior doors: Appeared serviceable
Condition of windows and skylights: Appeared serviceable
Type(s) of windows: Metal, Sliding
Condition of walls and ceilings: Appeared serviceable
Wall type or covering: Drywall
Ceiling type or covering: Drywall
Condition of flooring: Appeared serviceable
Flooring type or covering: Wood or wood products, Laminate, Tile
www.TopRatedHomeInspection.com - 323 494 5774 - email@example.com