Phone: (562) 565-5851
12314 Beverly Blvd
Whittier CA 90601-3030
Inspector: Raul Baeza, CPI
Property Inspection Report
||521 Kinley St, La Habra 90631
||Saturday, August 27, 2016
This report published on Saturday, August 27, 2016 8:50:54 PM PDT
Thank you for choosing R.B.Inspections to perform the following inspection on the property you wish to purchase. This report is the exclusive property of R.B.Inspections and the individual(s) paying for the inspection fee and report. Use of this report by any unauthorized persons is prohibited.
All findings should be made to R.B.Inspections.
This report represents our professional opinion of the condition of the inspected elements of the subject property, determine during a limited time inspection. This inspection was performed, where applicable, in a manner consistent with the standards of the home inspection industry, terms and conditions of the inspection agreement and limitations noted in the inspection agreement. Information contained herein was prepared exclusively for the named client and their authorized representatives.
We have inspected the subject property and must report to you exactly what we found. Because of the age, design and location of the home, we might find some hairline cracks on driveways or walls, see paint peeling off walls, cracks on tiles, chipped bathtubs or some cracks over windows and doors. These are normal and cosmetic conditions.
While due care was exercised in the performance of this inspection, the company makes no representations or guarantees with respect to latent deficiencies or future conditions as part of the inspection or this report. This report is valid only for a period of thirty (30) days from the date of the inspection. This report, including any attachments, should be reviewed in its entirety. Any questions about the inspection or report should be resolved prior to title transfer.
This inspection report was prepared in a format specifically for the individual/s paying for the inspections fee and report and such transfer does not cover all potential areas of concern a third party may have. This report is transferable only with the consent of the individual/s paying for inspections fee and report and such transfer does not imply any warranty or guarantee regarding the report by inspection firm.
No warranty, guarantee, or insurance by R.B.Inspections is expressed or implied. This report does not include inspection for wood destroying insects, mold, lead or asbestos. A representative sampling of the building components is viewed in areas that are accessible at the time of the inspection. No destructive testing or dismantling of components is performed. Not all defects will be identified during this inspection. Unexpected repairs should be anticipated.
The person conducting your inspection is not a licensed structural engineer or other professional whose license authorizes the rendering of an opinion as to the structural integrity of a building or its other component parts.
You are advised to seek two professional opinions and acquire estimates of repair as to any defects, comments, improvements or recommendations mentioned in this report. We recommend that the professional making any repairs inspect the property further, in order to discover and repair related problems that were not identified in the report. We recommend that all repairs, corrections, and cost estimates be completed and documented prior to closing or purchasing the property. Feel free to hire other professionals to inspect the property prior to closing, including HVAC professionals, electricians, plumbers, engineers, or roofers.
If you have any questions regarding this report, please feel free to call us.
Report number: 52190631
Time started: 12:00pm
Time finished: 3:00pm
Present during inspection: Client, Realtor
Client present for discussion at end of inspection: Yes
Inspector: Raul Baeza
Weather conditions during inspection: Dry (no rain), Sunny
Temperature during inspection: Warm
Ground condition: Dry
Recent weather: Dry (no rain), Sunny
Overnight temperature: Cool
Inspection fee: 330.00
Payment method: Cash
Type of building: Single family
Buildings inspected: One house
Number of residential units inspected: 1
Age of main building: 1961
Source for main building age: Realtor
Front of building faces: East
Main entrance faces: East
Occupied: Yes, Furniture or stored items were present
Structures built prior to the mid 1980s may contain lead and/or asbestos. Lead is commonly found in paint and in some plumbing components. The EPA does not recognize newer coats of paint as encapsulating older coats of lead-based paint. Asbestos is commonly found in various building materials such as insulation, siding, and/or floor and ceiling tiles. Laws were passed in 1978 to prohibit usage of lead and asbestos, but stocks of materials containing these substances remained in use for a number of years thereafter. Both lead and asbestos are known health hazards. Evaluating for the presence of lead and/or asbestos is beyond the scope of this inspection. Any mention of these materials in this report is made as a courtesy only, and meant to refer the client to a specialist. Consult with specialists as necessary, such as industrial hygienists, professional labs and/or abatement specialists for this type of evaluation. For information on lead, asbestos and other hazardous materials in homes, visit:http://www.reporthost.com/?EPAhttp://www.reporthost.com/?CPSChttp://www.reporthost.com/?CDC
What Really Matters
by Nick Gromicko (Founder of InterNACHI)
Buying a home? The process can be stressful. A home inspection is supposed to give you peace of mind, but often has the opposite effect. You will be asked to absorb a lot of information in a short time. This often includes a written report, a checklist, photographs, environmental reports, and what the inspector himself says during the inspection. All this, combined with the seller's disclosure and what you notice yourself, makes the experience even more overwhelming. What should you do?
Relax. Most of your inspection will be maintenance recommendations, life expectancies for various systems and components, and minor imperfections. These are useful to know about. However, the issues that really matter will fall into four categories:
1. major defects. An example of this would be a structural failure;
2. things that lead to major defects, such as a small roof-flashing leak, for example;
3. things that may hinder your ability to finance, legally occupy, or insure the home; and
4. safety hazards, such as an exposed, live buss bar at the electrical panel.
Anything in these categories should be addressed. Often, a serious problem can be corrected inexpensively to protect both life and property (especially in categories 2 and 4).
Most sellers are honest and are often surprised to learn of defects uncovered during an inspection. Realize that sellers are under no obligation to repair everything mentioned in the report. No home is perfect. Keep things in perspective. Do not kill your deal over things that do not matter. It is inappropriate to demand that a seller address deferred maintenance, conditions already listed on the seller's disclosure, or nit-picky items.
Some areas and items at this property were obscured by furniture and/or stored items. This often includes but is not limited to walls, floors, windows, inside and under cabinets, under sinks, on counter tops, in closets, behind window coverings, under rugs or carpets, and under or behind furniture. Areas around the exterior, under the structure, in the garage and in the attic may also be obscured by stored items. The inspector in general does not move personal belongings, furnishings, carpets or appliances. When furnishings, stored items or debris are present, all areas or items that are obscured, concealed or not readily accessible are excluded from the inspection. The client should be aware that when furnishings, stored items or debris are eventually moved, damage or problems that were not noted during the inspection may be found.
Limitations: Unless specifically included in the inspection, the following items and any related equipment, controls, electric systems and/or plumbing systems are excluded from this inspection: detached buildings or structures; fences and gates; retaining walls; underground drainage systems, catch basins or concealed sump pumps; swimming pools and related safety equipment, spas, hot tubs or saunas; whether deck, balcony and/or stair membranes are watertight; trees, landscaping, properties of soil, soil stability, erosion and erosion control; ponds, water features, irrigation or yard sprinkler systems; sport courts, playground, recreation or leisure equipment; areas below the exterior structures with less than 3 feet of vertical clearance; invisible fencing; sea walls, docks and boathouses; retractable awnings. Any comments made regarding these items are as a courtesy only.
Condition of fences and gates: Appeared serviceable
Fence and gate material: Wood, Brick
Condition of driveway: Appeared serviceable
Driveway material: Poured in place concrete, Brick
Condition of sidewalks and/or patios: Appeared serviceable
Sidewalk material: Poured in place concrete, Paving stones
Condition of deck, patio and/or porch covers: Appeared serviceable
Deck, patio, porch cover material and type: Covered (Refer to Roof section)
One or more gates were difficult to open and close and need repair.
Exterior and Foundation
Limitations: The inspector performs a visual inspection of accessible components or systems at the exterior. Items excluded from this inspection include below-grade foundation walls and footings; foundations, exterior surfaces or components obscured by vegetation, stored items or debris; wall structures obscured by coverings such as siding or trim. Some items such as siding, trim, soffits, vents and windows are often high off the ground, and may be viewed using binoculars from the ground or from a ladder. This may limit a full evaluation. Regarding foundations, some amount of cracking is normal in concrete slabs and foundation walls due to shrinkage and drying. Note that the inspector does not determine the adequacy of seismic reinforcement.
Wall inspection method: Viewed from ground
Condition of wall exterior covering: Appeared serviceable
Apparent wall structure: Wood frame
Wall covering: Wood, Stucco, Solid brick (not veneer)
Condition of foundation and footings: Appeared serviceable
Apparent foundation type: Crawl space
Limitations: Structural components such as joists and beams, and other components such as piping, wiring and/or ducting that are obscured by under-floor insulation are excluded from this inspection. The inspector does not determine if support posts, columns, beams, joists, studs, trusses, etc. are of adequate size, spanning or spacing.
The inspector does not guarantee or warrant that water will not accumulate in the crawl spaces in the future. Complete access to all crawl space areas during all seasons and during prolonged periods of all types of weather conditions (e.g. heavy rain, melting snow) would be needed to do so.
The inspector attempts to locate all crawl space access points and areas. Access points may be obscured or otherwise hidden by furnishings or stored items. In such cases, the client should ask the property owner where all access points are that are not described in this inspection, and have those areas inspected. Note that crawl space areas should be checked at least annually for water intrusion, plumbing leaks and pest activity.
Crawl space inspection method: Traversed
Location of crawl space access point #A: Building exterior
Location of crawl space access point #B: Building exterior
Condition of floor substructure above: Appeared serviceable
Pier or support post material: Wood, Concrete
Floor structure above: Solid wood joists
Evidence of prior water intrusion or accumulation was found in one or more sections of the crawl space. For example, sediment stains on the vapor barrier or foundation, and/or efflorescence on the foundation. Accumulated water is a conducive condition for wood-destroying organisms and should not be present in the crawl space. Recommend that the client review any disclosure statements available and ask the property owner about past accumulation of water in the crawl space. The crawl space should be monitored in the future for accumulated water, especially after heavy and/or prolonged periods of rain. If water is found to accumulate, then recommend that a qualified contractor who specializes in drainage issues evaluate and repair as necessary. Typical repairs for preventing water from accumulating in crawl spaces include:
- Repairing, installing or improving rain run-off systems (gutters, downspouts and extensions or drain lines)
- Improving perimeter grading
- Repairing, installing or improving underground footing and/or curtain drains
Ideally, water should not enter crawl spaces, but if water must be controlled after it enters the crawl space, then typical repairs include installing trenches, gravity drains and/or sump pump(s) in the crawl space.
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; solar roofing components. Any comments made regarding these items are made as a courtesy only. Note that the inspector does not provide an estimate of remaining life on the roof surface material, nor guarantee that leaks have not occurred in the roof surface, skylights or roof penetrations in the past. Regarding roof leaks, only active leaks, visible evidence of possible sources of leaks, and evidence of past leaks observed during the inspection are reported on as part of this inspection. The inspector does not guarantee or warrant that leaks will not occur in the future. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high wind and rain, melting snow) would be needed to do so. Occupants should monitor the condition of roofing materials in the future. For older roofs, recommend that a professional inspect the roof surface, flashings, appurtenances, etc. annually and maintain/repair as might be required. If needed, the roofer should enter attic space(s). Regarding the roof drainage system, unless the inspection was conducted during and after prolonged periods of heavy rain, the inspector was unable to determine if gutters, downspouts and extensions perform adequately or are leak-free.
Roof inspection method: Traversed
Condition of roof surface material: Appeared serviceable
Roof surface material: Asphalt or fiberglass composition shingles
Roof type: Gable
Apparent number of layers of roof surface material: One
Condition of exposed flashings: Appeared serviceable
Condition of gutters, downspouts and extensions: Appeared serviceable
Gutter and downspout material: Plastic
Gutter and downspout installation: Full
Attic and Roof Structure
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; areas and components obscured by insulation. Any comments made regarding these items are made as a courtesy only. The inspector does not determine the adequacy of the attic ventilation system. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high/low temperatures, high/low humidity, high wind and rain, melting snow) would be needed to do so. The inspector is not a licensed engineer and does not determine the adequacy of roof structure components such as trusses, rafters or ceiling beams, or their spacing or sizing.
Attic inspection method: Viewed from hatch(es)
Location of attic access point #A: Hallway
Condition of roof structure: Appeared serviceable
Roof structure type: Trusses
Ceiling structure: Trusses
Condition of insulation in attic (ceiling, skylight chase, etc.): Appeared serviceable
Ceiling insulation material: Fiberglass loose fill
Condition of roof ventilation: Appeared serviceable
Garage or Carport
Limitations: The inspector does not determine the adequacy of firewall ratings. Requirements for ventilation in garages vary between municipalities.
Condition of exterior entry doors: Appeared serviceable
Exterior door material: Wood
Condition of garage vehicle door(s): Appeared serviceable
Type of garage vehicle door: Sectional
Number of vehicle doors: 1
Condition of automatic opener(s): Appeared serviceable
Mechanical auto-reverse operable (reverses when meeting reasonable resistance during closing): Yes
Condition of garage floor: Appeared serviceable
Condition of garage interior: Appeared serviceable
Garage ventilation: Exists
One or more exterior doors were difficult to open or close. Recommend that a qualified person repair as necessary.
Weatherstripping around one or more exterior doors was missing. Water may enter the building, or energy efficiency may be reduced. Recommend that a qualified person repair or replace weatherstripping as necessary.
Limitations: The following items are not included in this inspection: generator systems, transfer switches, surge suppressors, inaccessible or concealed wiring; underground utilities and systems; low-voltage lighting or lighting on timers or sensors. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of grounding or bonding, if this system has an adequate capacity for the client's specific or anticipated needs, or if this system has any reserve capacity for additions or expansion. The inspector does not operate circuit breakers as part of the inspection, and does not install or change light bulbs. The inspector does not evaluate every wall switch or receptacle, but instead tests a representative number of them per various standards of practice. When furnishings, stored items or child-protective caps are present some receptacles are usually inaccessible and are not tested; these are excluded from this inspection. Receptacles that are not of standard 110 volt configuration, including 240-volt dryer receptacles, are not tested and are excluded. The functionality of, power source for and placement of smoke and carbon monoxide alarms is not determined as part of this inspection. Upon taking occupancy, proper operating and placement of smoke and carbon monoxide alarms should be verified and batteries should be changed. These devices have a limited lifespan and should be replaced every 10 years. The inspector attempts to locate and evaluate all main and sub-panels. However, panels are often concealed. If panels are found after the inspection, a qualified electrician should evaluate and repair if necessary. The inspector attempts to determine the overall electrical service size, but such estimates are not guaranteed because the overall capacity may be diminished by lesser-rated components in the system. Any repairs recommended should be made by a licensed electrician.
Electric service condition: Appeared serviceable
Primary service type: Overhead
Number of service conductors: 2
Service voltage (volts): 120-240
Estimated service amperage: 100
Primary service overload protection type: Circuit breakers
Service entrance conductor material: Stranded copper
Main disconnect rating (amps): 100
System ground: Copper
Condition of main service panel: Appeared serviceable
Location of main service panel #A: Building exterior, North
Condition of branch circuit wiring: Serviceable
Branch circuit wiring type: copper
One or more modern, 3-slot electric receptacles were found with an open ground. Three-slot receptacles should have a hot, a neutral and a ground wire connected. Homeowners often install new 3-slot receptacles on older, 2-wire circuits that only have hot and neutral wires. This is a shock hazard when appliances that require a ground are used with these receptacles. Examples of such appliances include computers and related hardware, refrigerators, freezers, portable air conditioners, clothes washers, aquarium pumps, and electrically operated gardening tools. Where the electric system was installed prior to when grounded circuits were required (1960s), it is permissible to replace 3-slot receptacles with 2-slot receptacles to prevent appliances that require a ground from being plugged in to an ungrounded circuit. However, the client should be aware of this limitation when planning use for various rooms, such as an office. For newer electric systems, circuits should be repaired so grounded, 3-wire cables provide power to 3-slot receptacles. Recommend that a qualified electrician repair per standard building practices.
Smoke alarms were missing from one or more bedrooms. Smoke alarms should be installed as necessary so a functioning alarm exists in each hallway leading to bedrooms, in each bedroom, on each level and in any attached garage. For more information, visit:http://www.reporthost.com/?SMKALRM
No permanently installed carbon monoxide alarms were found. This is a potential safety hazard. Some states and/or municipalities require CO alarms to be installed for new construction and/or for homes being sold. Recommend installing approved CO alarms outside of each separate sleeping area in the immediate vicinity of the bedrooms on each level and in accordance with the manufacturer's recommendations. For more information, visit:http://www.reporthost.com/?COALRM
Plumbing / Fuel Systems
Limitations: The following items are not included in this inspection: private/shared wells and related equipment; private sewage disposal systems; hot tubs or spas; main, side and lateral sewer lines; gray water systems; pressure boosting systems; trap primers; incinerating or composting toilets; fire suppression systems; water softeners, conditioners or filtering systems; plumbing components concealed within the foundation or building structure, or in inaccessible areas such as below tubs; underground utilities and systems; overflow drains for tubs and sinks; backflow prevention devices. Any comments made regarding these items are as a courtesy only. Note that the inspector does not operate water supply or shut-off valves due to the possibility of valves leaking or breaking when operated. The inspector does not test for lead in the water supply, the water pipes or solder, does not determine if plumbing and fuel lines are adequately sized, and does not determine the existence or condition of underground or above-ground fuel tanks.
Condition of service and main line: Appeared serviceable
Water service: Public
Water pressure (psi): 40psi
Location of main water meter: By street, East
Location of main water shut-off: Building exterior, North
Condition of supply lines: Appeared serviceable
Supply pipe material: Copper
Condition of drain pipes: Appeared serviceable
Drain pipe material: Plastic
Condition of waste lines: Appeared serviceable
Waste pipe material: Plastic, Cast iron
Location(s) of plumbing clean-outs: Not determined (obscured, inaccessible or none found)
Condition of fuel system: Appeared serviceable
Visible fuel storage systems: Above ground
Location of main fuel shut-off valve: At gas meter, At building exterior, North
Water pressure (psi): 40psi
Main water meter.
Main water shut-off.
Location of main fuel shut-off valve: At gas meter.
Limitations: Evaluation of and determining the adequacy or completeness of the following items are not included in this inspection: water recirculation pumps; solar water heating systems; Energy Smart or energy saver controls; catch pan drains. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on water heaters, does not determine if water heaters are appropriately sized, or perform any evaluations that require a pilot light to be lit or a shut-off valve to be operated.
Condition of water heater: Appeared serviceable
Energy source: Natural gas
Estimated age: 2011
Capacity (in gallons): Not determined (label obscure or inaccessible)
Temperature-pressure relief valve installed: Yes
Manufacturer: General Electric
Location of water heater: Garage
Hot water temperature tested: Yes
At the time of inspection the water heater appeared to be in serviceable condition, except as noted.
Hot water temp.
Heating, Ventilation and Air Condition (HVAC)
Limitations: The following items are not included in this inspection: humidifiers, dehumidifiers, electronic air filters; solar, coal or wood-fired heat systems; thermostat or temperature control accuracy and timed functions; heating components concealed within the building structure or in inaccessible areas; underground utilities and systems; safety devices and controls (due to automatic operation). Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on heating or cooling system components, does not determine if heating or cooling systems are appropriately sized, does not test coolant pressure, or perform any evaluations that require a pilot light to be lit, a shut-off valve to be operated, a circuit breaker to be turned "on" or a serviceman's or oil emergency switch to be operated. It is beyond the scope of this inspection to determine if furnace heat exchangers are intact and free of leaks. Condensation pans and drain lines may clog or leak at any time and should be monitored while in operation in the future. Where buildings contain furnishings or stored items, the inspector may not be able to verify that a heat source is present in all "liveable" rooms (e.g. bedrooms, kitchens and living/dining rooms).
General heating system type(s): Forced air
General heating distribution type(s): Ducts and registers
Condition of forced air heating/(cooling) system: Appeared serviceable
Forced air heating system fuel type: Natural gas
Estimated age of forced air furnace: 2009
Forced air heating system manufacturer: Concord
Location of forced air furnace: Closet, Exterior
Condition of furnace filters: Appeared serviceable
Location for forced air filter(s): At base of air handler
Condition of forced air ducts and registers: Appeared serviceable
Condition of cooling system and/or heat pump: Appeared serviceable
Cooling system and/or heat pump fuel type: Electric
Location of heat pump or air conditioning unit: Building exterior
Type: Split system
Estimated age of heat pump or air conditioning unit: 2010
Condition of cooling system and/or heat pump: Concord
The pad for the heat pump or air conditioning condensing unit was substandard or missing. This unit requires adequate support. The compressor may be damaged if this unit is tilted 10 degrees or more. Also, the pad should elevate the unit above the soil to prevent corrosion. Recommend that a qualified person repair as necessary.
At the time of inspection the heating and air conditioning unit appeared to be in serviceable condition, except as noted.
Fireplaces, Stoves, Chimneys and Flues
Limitations: The following items are not included in this inspection: coal stoves, gas logs, chimney flues (except where visible). Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of drafting or sizing in fireplace and stove flues, and also does not determine if prefabricated or zero-clearance fireplaces are installed in accordance with the manufacturer's specifications. The inspector does not perform any evaluations that require a pilot light to be lit, and does not light fires. The inspector provides a basic visual examination of a chimney and any associated wood burning device. The National Fire Protection Association has stated that an in-depth Level 2 chimney inspection should be part of every sale or transfer of property with a wood-burning device. Such an inspection may reveal defects that are not apparent to the home inspector who is a generalist.
Condition of gas-fired fireplaces or stoves: Appeared serviceable
Gas fireplace or stove type: Metal pre-fab fireplace
Condition of chimneys and flues: Appeared serviceable
Limitations: The following items are not included in this inspection: household appliances such as stoves, ovens, cook tops, ranges, warming ovens, griddles, broilers, dishwashers, trash compactors, refrigerators, freezers, ice makers, hot water dispensers and water filters; appliance timers, clocks, cook functions, self and/or continuous cleaning operations, thermostat or temperature control accuracy, and lights. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of the remaining life of appliances, and does not determine the adequacy of operation of appliances. The inspector does not note appliance manufacturers, models or serial numbers and does not determine if appliances are subject to recalls. Areas and components behind and obscured by appliances are inaccessible and excluded from this inspection.
Permanently installed kitchen appliances present during inspection: Range, Under-sink food disposal, Microwave oven
Condition of counters: Appeared serviceable
Condition of cabinets: Appeared serviceable
Condition of sinks and related plumbing: Appeared serviceable
Condition of under-sink food disposal: Appeared serviceable
Condition of dishwasher: Appeared serviceable
Condition of range, cooktop or oven: Appeared serviceable
Type of ventilation: Hood or built into microwave over range or cooktop, ducted to exterior
Condition of built-in microwave oven: Appeared serviceable
Bathrooms, Laundry and Sinks
Limitations: The following items are not included in this inspection: overflow drains for tubs and sinks; heated towel racks, saunas, steam generators, clothes washers, clothes dryers. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of washing machine drain lines, washing machine catch pan drain lines, or clothes dryer exhaust ducts. The inspector does not operate water supply or shut-off valves for sinks, toilets, bidets, clothes washers, etc. due to the possibility of valves leaking or breaking when operated. The inspector does not determine if shower pans or tub and shower enclosures are water tight, or determine the completeness or operability of any gas piping to laundry appliances.
Location #A: Full bath, Master bath
Location #B: Full bath, Hallway
Condition of counters: Appeared serviceable
Condition of cabinets: Appeared serviceable
Condition of flooring: Appeared serviceable
Condition of sinks and related plumbing: Appeared serviceable
Condition of toilets: Appeared serviceable
Condition of bathtubs and related plumbing: Appeared serviceable
Condition of shower(s) and related plumbing: Appeared serviceable
Condition of ventilation systems: Appeared serviceable
Bathroom and laundry ventilation type: Windows, Spot exhaust fans
Gas supply for laundry equipment present: Yes
240 volt receptacle for laundry equipment present: No
Interior, Doors and Windows
Limitations: The following items are not included in this inspection: security, intercom and sound systems; communications wiring; central vacuum systems; elevators and stair lifts; cosmetic deficiencies such as nail-pops, scuff marks, dents, dings, blemishes or issues due to normal wear and tear in wall, floor and ceiling surfaces and coverings, or in equipment; deficiencies relating to interior decorating; low voltage and gas lighting systems. Any comments made regarding these items are as a courtesy only. Note that the inspector does not evaluate any areas or items which require moving stored items, furnishings, debris, equipment, floor coverings, insulation or similar materials. The inspector does not test for asbestos, lead, radon, mold, hazardous waste, urea formaldehyde urethane, or any other toxic substance. Some items such as window, drawer, cabinet door or closet door operability are tested on a sampled basis. The client should be aware that paint may obscure wall and ceiling defects, floor coverings may obscure floor defects, and furnishings may obscure wall, floor and floor covering defects. If furnishings were present during the inspection, recommend a full evaluation of walls, floors and ceilings that were previously obscured when possible. Determining the cause and/or source of odors is not within the scope of this inspection.
Condition of exterior entry doors: Appeared serviceable
Exterior door material: Wood, Glass panel, Sliding glass
Condition of interior doors: Appeared serviceable
Condition of windows and skylights: Appeared serviceable
Type(s) of windows: Vinyl
Condition of walls and ceilings: Appeared serviceable
Wall type or covering: Drywall
Ceiling type or covering: Drywall
Condition of flooring: Appeared serviceable
Flooring type or covering: Carpet, Wood or wood products, Tile
Some exterior door hardware, including door bell were inoperable. Recommend that a qualified person repair or replace as necessary.
Limitations: The following items are not included in this inspection: swimming pool bodies; equipment on timers, remote controls or sensors; underground or concealed piping; motorized covers; waterfalls and related equipment; Ozone generators; ultraviolate light systems; filter backflushing mechanisms. Any comments made regarding these items are as a courtesy only. Note that the inspector does not disassemble filters, remove pool covers, nor determine if swimming pool bodies, filters or skimmers leak, nor determine if swimming pool bodies are level.
Water level: Full
Condition of body: Appeared serviceable
Body material: Plaster-Gunite ~
Condition of deck: Appeared serviceable
Deck material: Concrete, Brick
Condition of coping: Appeared serviceable
Coping material: Concrete
Condition of pumps, lines and valves: Appeared serviceable
Water is refilled through: Hose
Types of pumps installed: Circulation
Line material: PVC
Condition of filter and related equipment: Appeared serviceable
Filter type: Sand
Condition of skimmers: Appeared serviceable
Condition of electrical equipment: Appeared serviceable
Fencing around the pool in one or more areas was missing. This is a safety hazard because they are intended to control access to areas with a drowning hazard. Standard building practices require that fencing:
- Be a minimum of five feet in height
- Not be climbable by children
- Not have gaps or voids that allow climbing or access to gate latch mechanisms
A qualified person should evaluate and repair or replace as necessary, and as per standard building practices. For more information, visit:http://www.reporthost.com/?POOLBARR
No removable cover was installed for the pool. Recommend that one be installed to maintain water quality and for safety purposes.
Wood Destroying Organism Findings
Limitations: This report only includes findings from accessible and visible areas on the day of the inspection. In addition to the inaccessible areas documented in this report, examples of other inaccessible areas include: sub areas less than 18 inches in height; attic areas less than 5 feet in height, areas blocked by ducts, pipes or insulation; areas where locks or permanently attached covers prevent access; areas where insulation would be damaged if traversed; areas obscured by vegetation. All inaccessible areas are subject to infestation or damage from wood-destroying organisms. The inspector does not move furnishings, stored items, debris, floor or wall coverings, insulation, or other materials as part of the inspection, nor perform destructive testing. Wood-destroying organisms may infest, re-infest or become active at any time. No warranty is provided as part of this inspection.
1.1. A Home Inspection is a non-invasive, visual examination of a residential dwelling, performed for a fee, which is designed to identify observed material defects within specific components of said dwelling. Components may include any combination of mechanical, structural, electrical, plumbing, or other essential systems or portions of the home, as identified and agreed to by the Client and Inspector, prior to the inspection process.
I. A home inspection is intended to assist in evaluation of the overall condition of the dwelling. The inspection is based on observation of the visible and apparent condition of the structure and its components on the date of the inspection, and not the prediction of future conditions.
II. A home inspection will not reveal every concern that exists or ever could exist, but only those material defects observed on the day of the inspection.
III. A home inspection can include a survey and/or analysis of energy flows and usage in a residential property if the client requests it.
1.2. A Material Defect is a condition of a residential real property, or any portion of it, that would have a significant, adverse impact on the value of the real property, or that involves an unreasonable risk to people on the property. The fact that a structural element, system or subsystem is near, at or beyond the end of the normal useful life of such a structural element, system or subsystem is not by itself a material defect.
1.3. An Inspection Report shall describe and identify, in written format, the inspected systems, structures, and components of the dwelling, and shall identify material defects observed. Inspection reports may contain recommendations regarding conditions reported or recommendations for correction, monitoring or further evaluation by professionals, but this is not required.
This inspection was performed in accordance with the current Standards of Practice and Code of Ethics of the International Association of Certified Home Inspectors (InterNACHI). The Standards contain certain and very important limitations, exceptions, and exclusions to the inspection. A complete copy of the STANDARDS OF PRACTICE we adhere to can be found at the following link: http://www.nachi.org/sop.htm