This report is the exclusive property of this inspection company and the client(s) listed in the report
ProStar Inspection LLCWebsite: http://www.prostarinspection.com
Inspector's email: email@example.com
Phone: (800) 769-0136
Inspector's phone: (909) 736-5800
PO Box 2284
Rancho Cucamonga CA 91729-2284
Inspector: Brandon Ash
Property Inspection Report
||123 MAIN ST
Nowhere, CA 91730
||Saturday, July 23, 2016
This report published on Saturday, September 23, 2017 2:11:51 PM PDT
title. Use of this report by any unauthorized persons is prohibited.This report has been issued for
the exclusive use of our client [Happy Customer] and his/her authorized agents in this transaction. Any
third party use of this report without the express permission of the client and inspection firm is
prohibited and may result in legal liability.
Report number: 1607231
Time started: 9:00am
Time finished: 11:00am
Present during inspection: Client, Realtor, Current Home Owner
Weather conditions during inspection: Sunny
Temperature during inspection: Hot, 90 degrees
Inspection fee: $200.00
Type of building: Single family
Buildings inspected: One house
Age of main building: 1953
Source for main building age: MLS
Payment method: Check
Front of building faces: East
Main entrance faces: East
Structures built prior to the mid 1980s may contain lead and/or asbestos. Lead is commonly found in paint and in some plumbing components. The EPA does not recognize newer coats of paint as encapsulating older coats of lead-based paint. Asbestos is commonly found in various building materials such as insulation, siding, and/or floor and ceiling tiles. Laws were passed in 1978 to prohibit usage of lead and asbestos, but stocks of materials containing these substances remained in use for a number of years thereafter. Both lead and asbestos are known health hazards. Evaluating for the presence of lead and/or asbestos is beyond the scope of this inspection. Any mention of these materials in this report is made as a courtesy only, and meant to refer the client to a specialist. Consult with specialists as necessary, such as industrial hygienists, professional labs and/or abatement specialists for this type of evaluation. For information on lead, asbestos and other hazardous materials in homes, visit:http://www.reporthost.com/?EPAhttp://www.reporthost.com/?CPSChttp://www.reporthost.com/?CDC
Some areas and items at this property were obscured by furniture and/or stored items. This often includes but is not limited to walls, floors, windows, inside and under cabinets, under sinks, on counter tops, in closets, behind window coverings, under rugs or carpets, and under or behind furniture. Areas around the exterior, under the structure, in the garage and in the attic may also be obscured by stored items. The inspector in general does not move personal belongings, furnishings, carpets or appliances. When furnishings, stored items or debris are present, all areas or items that are obscured, concealed or not readily accessible are excluded from the inspection. The client should be aware that when furnishings, stored items or debris are eventually moved, damage or problems that were not noted during the inspection may be found.
Limitations: Unless specifically included in the inspection, the following items and any related equipment, controls, electric systems and/or plumbing systems are excluded from this inspection: detached buildings or structures; fences and gates; retaining walls; underground drainage systems, catch basins or concealed sump pumps; swimming pools and related safety equipment, spas, hot tubs or saunas; whether deck, balcony and/or stair membranes are watertight; trees, landscaping, properties of soil, soil stability, erosion and erosion control; ponds, water features, irrigation or yard sprinkler systems; sport courts, playground, recreation or leisure equipment; areas below the exterior structures with less than 3 feet of vertical clearance; invisible fencing; sea walls, docks and boathouses; retractable awnings. Any comments made regarding these items are as a courtesy only.
Site profile: Level
Driveway material: Poured in place concrete
Condition of driveway: Appeared serviceable, Required repair, replacement and/or evaluation (see comments below)
Condition of sidewalks and/or patios: Appeared serviceable
Sidewalk material: Poured in place concrete
Minor deterioration (e.g. cracks, holes, settlement, heaving) was found in sidewalks or patios, but no trip hazards were found. The client may wish to have repairs made for cosmetic reasons.
Exterior and Foundation
Limitations: The inspector performs a visual inspection of accessible components or systems at the exterior. Items excluded from this inspection include below-grade foundation walls and footings; foundations, exterior surfaces or components obscured by vegetation, stored items or debris; wall structures obscured by coverings such as siding or trim. Some items such as siding, trim, soffits, vents and windows are often high off the ground, and may be viewed using binoculars from the ground or from a ladder. This may limit a full evaluation. Regarding foundations, some amount of cracking is normal in concrete slabs and foundation walls due to shrinkage and drying. Note that the inspector does not determine the adequacy of seismic reinforcement.
Wall inspection method: Viewed from ground
Condition of wall exterior covering: Appeared serviceable
Apparent wall structure: Wood frame
Wall covering: Stucco
Condition of foundation and footings: Appeared serviceable
Apparent foundation type: Crawl space
Foundation/stem wall material: Poured in place concrete
Soil was in contact with or less than 6 inches from siding or trim. Regardless of what material is used for siding, it should not be in contact with the soil. If made of wood, siding or trim will eventually rot. For other materials, ground or surface water can infiltrate siding or trim and cause damage to the wall structure. Wood-destroying insects are likely to infest and damage the wall structure. This is a conducive condition for wood-destroying organisms. Recommend grading or removing soil as necessary to maintain a 6-inch clearance. Note that damage from fungal rot and/or insects may be found when soil is removed, and repairs may be necessary.
Vegetation such as trees, shrubs and/or vines was in contact with or close to the building exterior. Vegetation can serve as a pathway for wood-destroying insects and can retain moisture against the exterior after it rains. This is a conducive condition for wood-destroying organisms. Recommend pruning, moving or removing vegetation as necessary to maintain at least 6 inches of space between it and the building exterior. A 1-foot clearance is better.
Limitations: Structural components such as joists and beams, and other components such as piping, wiring and/or ducting that are obscured by under-floor insulation are excluded from this inspection. The inspector does not determine if support posts, columns, beams, joists, studs, trusses, etc. are of adequate size, spanning or spacing.
The inspector does not guarantee or warrant that water will not accumulate in the crawl spaces in the future. Complete access to all crawl space areas during all seasons and during prolonged periods of all types of weather conditions (e.g. heavy rain, melting snow) would be needed to do so.
The inspector attempts to locate all crawl space access points and areas. Access points may be obscured or otherwise hidden by furnishings or stored items. In such cases, the client should ask the property owner where all access points are that are not described in this inspection, and have those areas inspected. Note that crawl space areas should be checked at least annually for water intrusion, plumbing leaks and pest activity.
Crawl space inspection method: Partially traversed
Pier or support post material: Concrete
Beam material: Solid wood
Floor structure above: Solid wood joists
Condition of insulation underneath floor above: Not applicable, none installed
Condition of vapor barrier: Not applicable, none installed
Condition of crawl space ventilation: Appeared serviceable
Ventilation type: Unconditioned space, with vents
No under-floor insulation was installed in the crawl space. Recommend that a qualified person install insulation for better energy efficiency and per standard building practices. Typically this is R-19 rated fiberglass batt with the attached facing installed against the warm (floor) side.
No vapor barrier was installed in the crawl space. This is a conducive condition for wood-destroying organisms due to the likelihood of water evaporating from the soil below up into the structure. A 6 mil black plastic sheet should be placed over all exposed soil with seams overlapped to 24 inches, and not in contact with any wood structural components. The sheeting should be held in place with bricks or stones, not wood. Recommend that a qualified contractor install a vapor barrier per standard building practices.
One or more outdoor crawl space access hatches or doors were missing, damaged, deteriorated or substandard. Water and/or vermin can enter the crawl space. Recommend that a qualified person replace, install or repair hatches or doors where necessary.
Crawlspace entrance south side of home
Attic and Roof Structure
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; areas and components obscured by insulation. Any comments made regarding these items are made as a courtesy only. The inspector does not determine the adequacy of the attic ventilation system. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high/low temperatures, high/low humidity, high wind and rain, melting snow) would be needed to do so. The inspector is not a licensed engineer and does not determine the adequacy of roof structure components such as trusses, rafters or ceiling beams, or their spacing or sizing.
Attic inspection method: Partially traversed
Condition of roof structure: Appeared serviceable
Roof structure type: Rafters
Condition of insulation in attic (ceiling, skylight chase, etc.): Appeared serviceable
Ceiling insulation material: Fiberglass loose fill
Approximate attic insulation R value (may vary in areas): R-38
Condition of roof ventilation: Appeared serviceable
Roof ventilation type: Gable end vents
One or more attic access hatches or doors were not insulated, or had substandard insulation. Recommend installing insulation as necessary and per current standards at hatches or doors for better energy efficiency. For more information, visit:http://www.reporthost.com/?ATTACC
Garage or Carport
Limitations: The inspector does not determine the adequacy of firewall ratings. Requirements for ventilation in garages vary between municipalities.
Type: Attached, Garage
Condition of garage vehicle door(s): Appeared serviceable
Type of garage vehicle door: Sectional
Number of vehicle doors: 1
Condition of automatic opener(s): Appeared serviceable
Mechanical auto-reverse operable (reverses when meeting reasonable resistance during closing): Yes
Condition of garage floor: Appeared serviceable
Condition of garage interior: Appeared serviceable
Garage ventilation: Adequate
Limitations: The following items are not included in this inspection: generator systems, transfer switches, surge suppressors, inaccessible or concealed wiring; underground utilities and systems; low-voltage lighting or lighting on timers or sensors. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of grounding or bonding, if this system has an adequate capacity for the client's specific or anticipated needs, or if this system has any reserve capacity for additions or expansion. The inspector does not operate circuit breakers as part of the inspection, and does not install or change light bulbs. The inspector does not evaluate every wall switch or receptacle, but instead tests a representative number of them per various standards of practice. When furnishings, stored items or child-protective caps are present some receptacles are usually inaccessible and are not tested; these are excluded from this inspection. Receptacles that are not of standard 110 volt configuration, including 240-volt dryer receptacles, are not tested and are excluded. The functionality of, power source for and placement of smoke and carbon monoxide alarms is not determined as part of this inspection. Upon taking occupancy, proper operating and placement of smoke and carbon monoxide alarms should be verified and batteries should be changed. These devices have a limited lifespan and should be replaced every 10 years. The inspector attempts to locate and evaluate all main and sub-panels. However, panels are often concealed. If panels are found after the inspection, a qualified electrician should evaluate and repair if necessary. The inspector attempts to determine the overall electrical service size, but such estimates are not guaranteed because the overall capacity may be diminished by lesser-rated components in the system. Any repairs recommended should be made by a licensed electrician.
Electric service condition: Appeared serviceable
Primary service type: Overhead
Service voltage (volts): 120-240
Estimated service amperage: 100
Primary service overload protection type: Circuit breakers
Service entrance conductor material: Stranded copper
Main disconnect rating (amps): 100
Condition of main service panel: Appeared serviceable
Location of main service panel #A: Building exterior
Location of main disconnect: Breaker at top of main service panel
Condition of branch circuit wiring: Serviceable
Branch circuit wiring type: non-metallic sheathed
Smoke alarms installed: Yes, but not tested
Ground fault circuit interrupter (GFCI) protection present: Yes
Wire splices were exposed and were not contained in a covered junction box. This is a potential shock or fire hazard. Recommend that a qualified electrician repair per standard building practices. For example, by installing permanently mounted junction boxes with cover plates where needed to contain wiring splices.
Open circuit box with live wiring in attic
The functionality of, power source for and placement of smoke alarms is not determined as part of this inspection. Smoke alarms should be installed in each bedroom, in hallways leading to bedrooms, on each level and in attached garages. They have a limited lifespan and should be replaced every 10 years. For home buyers, batteries in smoke alarms should be changed when taking occupancy. Batteries should be replaced annually in the future. Carbon monoxide alarms should be installed in the vicinity of sleeping areas and on each level. For more information, visit:http://www.reporthost.com/?SMKALRMhttp://www.reporthost.com/?COALRM
One or more light fixtures were inoperable (didn't turn on when nearby switches were operated). Recommend further evaluation by replacing bulbs and/or consulting with the property owner. If replacing bulbs doesn't work and/or no other switch(es) can be found, then recommend that a qualified electrician evaluate and repair or replace light fixtures as necessary.
Lights in the main bathroom, above shower
Electric meter - South side of house
Circuit Breaker for Air Conditioning Compressor - South side of home
Circuit breaker box for A/C compressor - located on South side of house
Circuit breaker for A/C compressor
Plumbing / Fuel Systems
Limitations: The following items are not included in this inspection: private/shared wells and related equipment; private sewage disposal systems; hot tubs or spas; main, side and lateral sewer lines; gray water systems; pressure boosting systems; trap primers; incinerating or composting toilets; fire suppression systems; water softeners, conditioners or filtering systems; plumbing components concealed within the foundation or building structure, or in inaccessible areas such as below tubs; underground utilities and systems; overflow drains for tubs and sinks; backflow prevention devices. Any comments made regarding these items are as a courtesy only. Note that the inspector does not operate water supply or shut-off valves due to the possibility of valves leaking or breaking when operated. The inspector does not test for lead in the water supply, the water pipes or solder, does not determine if plumbing and fuel lines are adequately sized, and does not determine the existence or condition of underground or above-ground fuel tanks.
Water service: Public
Condition of supply lines: Appeared serviceable
Supply pipe material: Galvanized steel
Condition of drain pipes: Appeared serviceable
Condition of waste lines: Appeared serviceable
Vent pipe condition: Appeared serviceable
Condition of fuel system: Appeared serviceable
Location of main fuel shut-off valve: At gas meter
Heating, Ventilation and Air Condition (HVAC)
Limitations: The following items are not included in this inspection: humidifiers, dehumidifiers, electronic air filters; solar, coal or wood-fired heat systems; thermostat or temperature control accuracy and timed functions; heating components concealed within the building structure or in inaccessible areas; underground utilities and systems; safety devices and controls (due to automatic operation). Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on heating or cooling system components, does not determine if heating or cooling systems are appropriately sized, does not test coolant pressure, or perform any evaluations that require a pilot light to be lit, a shut-off valve to be operated, a circuit breaker to be turned "on" or a serviceman's or oil emergency switch to be operated. It is beyond the scope of this inspection to determine if furnace heat exchangers are intact and free of leaks. Condensation pans and drain lines may clog or leak at any time and should be monitored while in operation in the future. Where buildings contain furnishings or stored items, the inspector may not be able to verify that a heat source is present in all "liveable" rooms (e.g. bedrooms, kitchens and living/dining rooms).
General heating system type(s): Forced air
General heating distribution type(s): Ducts and registers
Condition of forced air heating/(cooling) system: Appeared serviceable
Forced air heating system fuel type: Natural gas
Location of forced air furnace: Attic
Condition of furnace filters: Appeared serviceable
Condition of forced air ducts and registers: Appeared serviceable
Condition of cooling system and/or heat pump: Appeared serviceable
Cooling system and/or heat pump fuel type: Electric
Location of heat pump or air conditioning unit: South side of house
Condition of controls: Appeared serviceable
A/C compressor - South side of house
Side view of A/C compressor - South side of house
Forced air unit located in attic
Forced air unit - located in attic
Gas shutoff valve for furnace - located in attic
Fireplaces, Stoves, Chimneys and Flues
Limitations: The following items are not included in this inspection: coal stoves, gas logs, chimney flues (except where visible). Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of drafting or sizing in fireplace and stove flues, and also does not determine if prefabricated or zero-clearance fireplaces are installed in accordance with the manufacturer's specifications. The inspector does not perform any evaluations that require a pilot light to be lit, and does not light fires. The inspector provides a basic visual examination of a chimney and any associated wood burning device. The National Fire Protection Association has stated that an in-depth Level 2 chimney inspection should be part of every sale or transfer of property with a wood-burning device. Such an inspection may reveal defects that are not apparent to the home inspector who is a generalist.
Condition of wood-burning fireplaces, stoves: Appeared serviceable
Wood-burning fireplace type: Masonry
Condition of chimneys and flues: Appeared serviceable, Required repair, replacement and/or evaluation (see comments below)
One or more masonry chimney crowns were cracked. Crowns are meant to keep water off of the chimney structure and prevent damage from freeze-thaw cycles. Chimney crowns are commonly constructed by mounding concrete or mortar on the top chimney surface, however this is substandard. A properly constructed chimney crown should:
- Be constructed using either precast concrete slabs, cast-in-place steel reinforced concrete, solid stone, or metal
- Be sloped down from the flue a minimum of 3 inches of fall per foot of run
- Extend a minimum of 2 1/2 inches beyond the face of the chimney on all sides
- Not directly contact the flue liner (if installed), with the gap filled with flexible caulk
- Have flashing installed between the bottom of the crown and the top of the brick chimney
Recommend that a qualified contractor repair or replace crowns as necessary, and per standard building practices.
Limitations: The following items are not included in this inspection: household appliances such as stoves, ovens, cook tops, ranges, warming ovens, griddles, broilers, dishwashers, trash compactors, refrigerators, freezers, ice makers, hot water dispensers and water filters; appliance timers, clocks, cook functions, self and/or continuous cleaning operations, thermostat or temperature control accuracy, and lights. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of the remaining life of appliances, and does not determine the adequacy of operation of appliances. The inspector does not note appliance manufacturers, models or serial numbers and does not determine if appliances are subject to recalls. Areas and components behind and obscured by appliances are inaccessible and excluded from this inspection.
Type of ventilation: Hood or built into microwave over range or cooktop
Condition of counters: Appeared serviceable
Condition of cabinets: Appeared serviceable
Condition of sinks and related plumbing: Appeared serviceable
Condition of under-sink food disposal: Appeared serviceable
Condition of dishwasher: Appeared serviceable
Condition of range, cooktop or oven: Appeared serviceable
Range, cooktop or oven type: Natural gas
Condition of refrigerator: Appeared serviceable
Cabinet hardware such as hinges, latches, closers, magnets or pulls were loose, missing or damaged at one or more cabinet drawers, doors or turntables. Recommend that a qualified person repair as necessary.
One knob on the cabinet below the kitchen sink is broken and comes off. Others are loose.
Garbage disposal under kitchen sink
Bathrooms, Laundry and Sinks
Limitations: The following items are not included in this inspection: overflow drains for tubs and sinks; heated towel racks, saunas, steam generators, clothes washers, clothes dryers. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of washing machine drain lines, washing machine catch pan drain lines, or clothes dryer exhaust ducts. The inspector does not operate water supply or shut-off valves for sinks, toilets, bidets, clothes washers, etc. due to the possibility of valves leaking or breaking when operated. The inspector does not determine if shower pans or tub and shower enclosures are water tight, or determine the completeness or operability of any gas piping to laundry appliances.
Location #A: Full bath
Location #B: Half bath
Condition of counters: Appeared serviceable
Condition of cabinets: Appeared serviceable
Condition of flooring: Appeared serviceable
Condition of sinks and related plumbing: Appeared serviceable
Condition of toilets: Appeared serviceable
Condition of bathtubs and related plumbing: Appeared serviceable
Condition of shower(s) and related plumbing: Appeared serviceable
Condition of ventilation systems: Appeared serviceable
Gas supply for laundry equipment present: No
240 volt receptacle for laundry equipment present: Yes
Water shutoff valves for washer- south wall in garage
Hot and cold water shutoff valves to washer - located in garage
Interior, Doors and Windows
Limitations: The following items are not included in this inspection: security, intercom and sound systems; communications wiring; central vacuum systems; elevators and stair lifts; cosmetic deficiencies such as nail-pops, scuff marks, dents, dings, blemishes or issues due to normal wear and tear in wall, floor and ceiling surfaces and coverings, or in equipment; deficiencies relating to interior decorating; low voltage and gas lighting systems. Any comments made regarding these items are as a courtesy only. Note that the inspector does not evaluate any areas or items which require moving stored items, furnishings, debris, equipment, floor coverings, insulation or similar materials. The inspector does not test for asbestos, lead, radon, mold, hazardous waste, urea formaldehyde urethane, or any other toxic substance. Some items such as window, drawer, cabinet door or closet door operability are tested on a sampled basis. The client should be aware that paint may obscure wall and ceiling defects, floor coverings may obscure floor defects, and furnishings may obscure wall, floor and floor covering defects. If furnishings were present during the inspection, recommend a full evaluation of walls, floors and ceilings that were previously obscured when possible. Determining the cause and/or source of odors is not within the scope of this inspection.
Condition of exterior entry doors: Appeared serviceable
Exterior door material: Wood
Condition of interior doors: Appeared serviceable
Condition of windows and skylights: Appeared serviceable
Type(s) of windows: Vinyl
Condition of walls and ceilings: Appeared serviceable
Wall type or covering: Drywall
Ceiling type or covering: Drywall
Condition of flooring: Appeared serviceable
Flooring type or covering: Carpet, Wood or wood products
One or more hinged exterior doors had no deadbolt lock installed and relied solely on the entry lockset for security. Recommend installing locksets on exterior doors where missing for added security.
Exterior door in back room
Roof inspection method: Traversed
Apparent number of layers of roof surface material: Multiple, 2
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; solar roofing components. Any comments made regarding these items are made as a courtesy only. Note that the inspector does not provide an estimate of remaining life on the roof surface material, nor guarantee that leaks have not occurred in the roof surface, skylights or roof penetrations in the past. Regarding roof leaks, only active leaks, visible evidence of possible sources of leaks, and evidence of past leaks observed during the inspection are reported on as part of this inspection. The inspector does not guarantee or warrant that leaks will not occur in the future. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high wind and rain, melting snow) would be needed to do so. Occupants should monitor the condition of roofing materials in the future. For older roofs, recommend that a professional inspect the roof surface, flashings, appurtenances, etc. annually and maintain/repair as might be required. If needed, the roofer should enter attic space(s). Regarding the roof drainage system, unless the inspection was conducted during and after prolonged periods of heavy rain, the inspector was unable to determine if gutters, downspouts and extensions perform adequately or are leak-free.
Condition of roof surface material: Appeared serviceable
Roof surface material: Asphalt or fiberglass composition shingles
Roof type: Gable
Apparent number of layers of roof surface material: Multiple
Condition of exposed flashings: Appeared serviceable
Condition of gutters, downspouts and extensions: Appeared serviceable
Some composition shingles were damaged. Leaks can occur as a result. This is a conducive condition for wood-destroying organisms. Recommend that a qualified contractor repair as necessary. For example, by replacing shingles.
Appeared to be a possible prior repair to roof
Gutters were missing over one or more entrances. People entering and exiting the building are likely to get wet during periods of rain as a result. Most buildings benefit from having a complete drainage system installed, but at a minimum, recommend installing gutters over entrances.
Found some debris in kick flashing on the roof. Recommend cleaning for proper functionality.
This asphalt or fiberglass composition roof surface appeared to have two or more layers of shingles. Additional layers of composition shingles typically last only 80% of their rated life, and the shingle manufacturer's warranty may be voided. The client should be aware that all layers of roofing will need to be removed when this roof surface needs replacing.
Energy source: Natural gas
Capacity (in gallons): 38
Location of water heater: Utility room, Outside
Limitations: Evaluation of and determining the adequacy or completeness of the following items are not included in this inspection: water recirculation pumps; solar water heating systems; Energy Smart or energy saver controls; catch pan drains. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on water heaters, does not determine if water heaters are appropriately sized, or perform any evaluations that require a pilot light to be lit or a shut-off valve to be operated.
Condition of water heater: Appeared serviceable
Estimated age: approx 3 years old - Manufacture Date on water heater 21 NOV 2013
Temperature-pressure relief valve installed: Yes
Location of water heater: Mechanical room, Outside Behind Garage
Hot water temperature tested: Yes
Water temperature (degrees Fahrenheit): 119
Condition of burners: Appeared serviceable
Condition of venting system: Appeared serviceable
Water Heater in outside utility closet
Water Heater Serial/Model # Information
Dear [Happy Customer],
Thank you for using ProStar Inspection, LLC. We hope that our inspection and testing services have been
helpful to you. If you have any questions about your report or need further information, please call us at
(800) 769-0136. We would like to take this opportunity to suggest that a periodic re-inspection of the
dwelling’s structural and mechanical systems can help you efficiently maintain the building and prevent minor
deficiencies from becoming serious and expensive problems. Our satisfied customers are our best referral
network. If you feel that our services have been beneficial, please inform your real estate agent, lawyer,
banker, or anyone you may know who is purchasing a new home or commercial building. Thank you for your
patronage and best wishes.
ProStar Inspection, LLC provides, at a minimum, services as outlined in InterNACHI Standards of Practice. https://www.nachi.org/sop.htm
The International Association of Certified Home Inspectors (InterNACHI) promotes a high standard of professionalism, business ethics and inspection procedures. At ProStar Inspection,LLC; we subscribe to the InterNACHI Code of Ethics, https://www.nachi.org/code_of_ethics.htm
in the course of our business.
Please contact us if there are any questions or concerns regarding the report. We will do our best to help! We thank you again for choosing ProStar Inspection.