On The Money Home Inspection, LLC
Phone: (812) 987-8453
1104 Stonelilly Dr
Jeffersonville IN 47130-8468
Inspector: Wayne Money
Property Inspection Report
||2098 Highway 337 NW
Corydon IN 47112-2080
||Wednesday, March 16, 2016
This report published on Thursday, April 07, 2016 10:25:43 PM EDT
In this report I will identify any aspect that I see that is not operating as it should. Keep in mind that no home is wihout at least some of these issues - or something comparable. Most things in the main body of this repost will be minor maintenance issues and not a reason for concern, but may need to be addressed in the near future. At the bottom of the report I will include any serious defects and/or safety issues that I believe should be looked at by a qualified contractor. This report is the exclusive property of this inspection company and the client(s) listed in the report title. Use of this report by any unauthorized persons is prohibited.
How to Read this Report
This report is organized by the property's functional areas. Within each functional area, descriptive information is listed first and is shown in bold type. Items of concern follow descriptive information.
Concerns are shown and sorted according to these types:
|Safety||Poses a safety hazard|
|Repair/Replace||Recommend repairing or replacing|
|Repair/Maintain||Recommend repair and/or maintenance|
|Minor Defect||Correction likely involves only a minor expense|
|Maintain||Recommend ongoing maintenance|
|Evaluate||Recommend evaluation by a specialist|
|Monitor||Recommend monitoring in the future|
|Serviceable||Item or component is in servicable condition|
|Comment||For your information|
Click here for a glossary of building construction terms.Contact your inspector If there are terms that you do not understand, or visit the glossary of construction terms at http://www.reporthost.com/glossary.asp
Limitations: Unless specifically included in the inspection, the following items and any related equipment, controls, electric systems and/or plumbing systems are excluded from this inspection: detached buildings or structures; fences and gates; retaining walls; underground drainage systems, catch basins or concealed sump pumps; swimming pools and related safety equipment, spas, hot tubs or saunas; whether deck, balcony and/or stair membranes are watertight; trees, landscaping, properties of soil, soil stability, erosion and erosion control; ponds, water features, irrigation or yard sprinkler systems; sport courts, playground, recreation or leisure equipment; areas below the exterior structures with less than 3 feet of vertical clearance; invisible fencing; sea walls, docks and boathouses; retractable awnings. Any comments made regarding these items are as a courtesy only.
Site profile: Minor slope
Condition of driveway: Appeared serviceable
Driveway material: Poured in place concrete
Condition of sidewalks and/or patios: Appeared serviceable
Sidewalk material: Poured in place concrete
Condition of decks, porches and/or balconies: Appeared serviceable
Deck, porch and/or balcony material: Wood
Condition of stairs, handrails and guardrails: Appeared serviceable
Exterior stair material: Wood
1) Safety, Comment
Since this railing was built, guidelines have changed and the new suggestion is that guardrails with a drop-off higher than 30 inches now have gaps that are too large. This poses a safety hazard for children (e.g. falling, getting stuck in railing). Guardrails should not have gaps or voids that allow passage of a sphere equal to or greater than 4 inches in diameter, or 6 inches in diameter at triangular spaces between stair edges and guardrails. This is just a new safety warning and I'm making you aware.
Exterior and Foundation
Limitations: The inspector performs a visual inspection of accessible components or systems at the exterior. Items excluded from this inspection include below-grade foundation walls and footings; foundations, exterior surfaces or components obscured by vegetation, stored items or debris; wall structures obscured by coverings such as siding or trim. Some items such as siding, trim, soffits, vents and windows are often high off the ground, and may be viewed using binoculars from the ground or from a ladder. This may limit a full evaluation. Regarding foundations, some amount of cracking is normal in concrete slabs and foundation walls due to shrinkage and drying. Note that the inspector does not determine the adequacy of seismic reinforcement.
Wall inspection method: Viewed from ground
Condition of wall exterior covering: Appeared serviceable
Apparent wall structure: Wood frame
Wall covering: Vinyl, Brick veneer
Condition of foundation and footings: Appeared serviceable
Apparent foundation type: Concrete slab on grade
2) Maintain, Comment
Make sure gutters and downspouts are clear of debris and operate as they should.
Check the downspouts when it's raining to verify they are working correctly.
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; solar roofing components. Any comments made regarding these items are made as a courtesy only. Note that the inspector does not provide an estimate of remaining life on the roof surface material, nor guarantee that leaks have not occurred in the roof surface, skylights or roof penetrations in the past. Regarding roof leaks, only active leaks, visible evidence of possible sources of leaks, and evidence of past leaks observed during the inspection are reported on as part of this inspection. The inspector does not guarantee or warrant that leaks will not occur in the future. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high wind and rain, melting snow) would be needed to do so. Regarding the roof drainage system, unless the inspection was conducted during and after prolonged periods of heavy rain, the inspector was unable to determine if gutters, downspouts and extensions performed adequately or were leak-free.
Roof inspection method: Viewed from ground with binoculars
Condition of roof surface material: Appeared serviceable
Roof surface material: Asphalt or fiberglass composition shingles
Roof type: Gable
Apparent number of layers of roof surface material: One
Condition of gutters, downspouts and extensions: Appeared serviceable
One or more roof flashings were missing. Leaks can occur as a result. This is a conducive condition for wood-destroying organisms. Recommend that a qualified person repair as necessary.
4) Maintain, Monitor, Comment
One or more rubber or neoprene pipe flashings were showing some age and from my experience, these never last as long as the shingles do. They develop cracks where the plastic meets the pipe and leaks can occur as a result. This is a conducive condition for wood-destroying organisms. Recommend that a qualified contractor replace flashings when necessary.
Limitations: The following items are not included in this inspection: household appliances such as stoves, ovens, cook tops, ranges, warming ovens, griddles, broilers, dishwashers, trash compactors, refrigerators, freezers, ice makers, hot water dispensers and water filters; appliance timers, clocks, cook functions, self and/or continuous cleaning operations, thermostat or temperature control accuracy, and lights. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of the remaining life of appliances, and does not determine the adequacy of operation of appliances. The inspector does not note appliance manufacturers, models or serial numbers and does not determine if appliances are subject to recalls. Areas and components behind and obscured by appliances are inaccessible and excluded from this inspection.
Condition of counters: Appeared serviceable
Condition of cabinets: Appeared serviceable
Condition of sinks and related plumbing: Appeared serviceable
Condition of under-sink food disposal: Appeared serviceable
Condition of dishwasher: Appeared serviceable
Condition of range, cooktop or oven: Appeared serviceable
Range, cooktop or oven type: Electric
5) Minor Defect, Maintain, Comment
One sink drain was leaking. A qualified plumber should repair as necessary.
Bathrooms, Laundry and Sinks
Limitations: The following items are not included in this inspection: overflow drains for tubs and sinks; heated towel racks, saunas, steam generators, clothes washers, clothes dryers. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of washing machine drain lines, washing machine catch pan drain lines, or clothes dryer exhaust ducts. The inspector does not operate water supply or shut-off valves for sinks, toilets, bidets, clothes washers, etc. due to the possibility of valves leaking or breaking when operated. The inspector does not determine if shower pans or tub and shower enclosures are water tight, or determine the completeness or operability of any gas piping to laundry appliances.
Location #A: Full bath
Location #B: Full bath
Condition of counters: Appeared serviceable
Condition of cabinets: Appeared serviceable
Condition of flooring: Appeared serviceable
Condition of toilets: Appeared serviceable
Condition of bathtubs and related plumbing: Appeared serviceable
Condition of shower(s) and related plumbing: Appeared serviceable
Condition of ventilation systems: Appeared serviceable
Bathroom and laundry ventilation type: Spot exhaust fans
Gas supply for laundry equipment present: No
240 volt receptacle for laundry equipment present: Yes
6) Safety, Evaluate, Monitor, Comment
The clothes dryer was equipped with a vinyl or mylar, accordion-type, flexible exhaust duct. The U.S. Consumer Product Safety Commission considers these types of ducts to be unsafe, and a fire hazard. They can trap lint and are susceptible to kinks or crushing, which can greatly reduce the air flow and cause overheating. Recommend that such ducts be replaced with a rigid or corrugated semi-rigid metal duct, and by a qualified contractor if necessary. For more information, visit:http://www.reporthost.com/?DRYER
7) Minor Defect, Comment
The bathtub drain stopper mechanism at locations #A and B were missing.
8) Maintain, Evaluate, Monitor, Comment
Stains were found in the shelving or cabinets below the sink at location #A. Plumbing leaks may have occurred in the past. Maintain as needed.
Interior, Doors and Windows
Limitations: The following items are not included in this inspection: security, intercom and sound systems; communications wiring; central vacuum systems; elevators and stair lifts; cosmetic deficiencies such as nail-pops, scuff marks, dents, dings, blemishes or issues due to normal wear and tear in wall, floor and ceiling surfaces and coverings, or in equipment; deficiencies relating to interior decorating; low voltage and gas lighting systems. Any comments made regarding these items are as a courtesy only. Note that the inspector does not evaluate any areas or items which require moving stored items, furnishings, debris, equipment, floor coverings, insulation or similar materials. The inspector does not test for asbestos, lead, radon, mold, hazardous waste, urea formaldehyde urethane, or any other toxic substance. Some items such as window, drawer, cabinet door or closet door operability are tested on a sampled basis. The client should be aware that paint may obscure wall and ceiling defects, floor coverings may obscure floor defects, and furnishings may obscure wall, floor and floor covering defects. If furnishings were present during the inspection, recommend a full evaluation of walls, floors and ceilings that were previously obscured when possible. Determining the cause and/or source of odors is not within the scope of this inspection.
Condition of exterior entry doors: Appeared serviceable
Exterior door material: Wood, Sliding glass
Condition of interior doors: Appeared serviceable
Condition of windows and skylights: Appeared serviceable
Type(s) of windows: Vinyl, Wood, Multi-pane, Single-hung, Fixed
Condition of walls and ceilings: Appeared serviceable
Wall type or covering: Drywall
Ceiling type or covering: Drywall
Condition of flooring: Appeared serviceable
Flooring type or covering: Carpet, Vinyl, linoleum or marmoleum
Glass in one or more windows was cracked. Recommend that a qualified contractor replace glass where necessary.
10) Minor Defect, Evaluate, Comment
The seal between multi-pane glass in one or more sliding glass doors appeared to have failed based on condensation or stains between the panes of glass. Recommend that a qualified contractor evaluate and replace glass where necessary.
Be aware that evidence of broken seals may be more or less visible from one day to the next depending on the temperature, humidity, sunlight, etc. Glass doors or windows other than those that the inspector identified may also have failed seals and need glass replaced too.
11) Minor Defect, Evaluate, Comment
Condensation or staining was visible between multi-pane glass in windows. This usually indicates that the seal between the panes of glass has failed or that the desiccant material that absorbs moisture is saturated. As a result, the view through the window may be obscured, the window's R-value will be reduced, and accumulated condensation may leak into the wall structure below. Recommend that a qualified contractor evaluate and repair windows as necessary. Usually, this means replacing the glass in window frames.
Be aware that evidence of failed seals or desiccant may be more or less visible depending on the temperature, humidity, sunlight, etc. Windows or glass-paneled doors other than those that the inspector identified may also have failed seals and need glass replaced. It is beyond the scope of this inspection to identify every window with failed seals or desiccant.
Limitations: The following items are not included in this inspection: generator systems, transfer switches, surge suppressors, inaccessible or concealed wiring; underground utilities and systems; low-voltage lighting or lighting on timers or sensors. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of grounding or bonding, if this system has an adequate capacity for the client's specific or anticipated needs, or if this system has any reserve capacity for additions or expansion. The inspector does not operate circuit breakers as part of the inspection, and does not install or change light bulbs. The inspector does not evaluate every wall switch or receptacle, but instead tests a representative number of them per various standards of practice. When furnishings, stored items or child-protective caps are present some receptacles are usually inaccessible and are not tested; these are excluded from this inspection. Receptacles that are not of standard 110 volt configuration, including 240-volt dryer receptacles, are not tested and are excluded. The functionality of, power source for and placement of smoke and carbon monoxide alarms is not determined as part of this inspection. Upon taking occupancy, proper operating and placement of smoke and carbon monoxide alarms should be verified and batteries should be changed. These devices have a limited lifespan and should be replaced every 10 years. The inspector attempts to locate and evaluate all main and sub-panels. However, panels are often concealed. If panels are found after the inspection, a qualified electrician should evaluate and repair if necessary. The inspector attempts to determine the overall electrical service size, but such estimates are not guaranteed because the overall capacity may be diminished by lesser-rated components in the system. Any repairs recommended should be made by a licensed electrician.
Electric service condition: Appeared serviceable
Primary service type: Underground
Number of service conductors: 3
Service voltage (volts): 120-240
Estimated service amperage: 200
Primary service overload protection type: Circuit breakers
Main disconnect rating (amps): 200
Condition of main service panel: Appeared serviceable
Location of main service panel #A: Garage
Location of main disconnect: Breaker at top of main service panel
Condition of branch circuit wiring: Serviceable
Branch circuit wiring type: Non-metallic sheathed
Arc fault circuit interrupter (AFCI) protection present: No
12) Safety, Repair/Maintain
Based on the age of this structure and the appearance of existing smoke alarms, the alarms may have been installed more than 10 years ago. According to National Fire Protection Association
, aging smoke alarms don't operate as efficiently and often are the source for nuisance alarms. Older smoke alarms are estimated to have a 30% probability of failure within the first 10 years. Newer smoke alarms do better, but should be replaced after 10 years. Unless you know that the smoke alarms are new, replacing them when moving into a new residence is also recommended by NFPA. For more information, visit:http://www.reporthost.com/?SMKALRMLS
13) Safety, Evaluate, Comment
One electric receptacle (outlets) at the garage had no visible ground fault circuit interrupter (GFCI) protection, or the inspector was unable to determine if GFCI protection was present. If not GFCI-protected, receptacles in wet areas pose a shock hazard. Recommend that a qualified electrician evaluate and install GFCI protection if necessary and per standard building practices. General guidelines for GFCI-protected receptacles include the following locations:
- Outdoors (since 1973)
- Bathrooms (since 1975)
- Garages (since 1978)
- Kitchens (since 1987)
- Crawl spaces and unfinished basements (since 1990)
- Wet bar sinks (since 1993)
- Laundry and utility sinks (since 2005)
For more information, visit:http://www.reporthost.com/?GFCI
14) Safety, Evaluate, Comment
Smoke alarms were missing in the attached garage. Additional smoke alarms should be installed as necessary so a functioning alarm exists in each hallway leading to bedrooms, in each bedroom, on each level and in any attached garage. For more information, visit:http://www.reporthost.com/?SMKALRM
15) Evaluate, Monitor, Comment
Not sure where this wire goes to, but end could be damaged.
The breaker box was installed correctly.
Main shut off for entire house is at the top.
Plumbing / Fuel Systems
Limitations: The following items are not included in this inspection: private/shared wells and related equipment; private sewage disposal systems; hot tubs or spas; main, side and lateral sewer lines; gray water systems; pressure boosting systems; trap primers; incinerating or composting toilets; fire suppression systems; water softeners, conditioners or filtering systems; plumbing components concealed within the foundation or building structure, or in inaccessible areas such as below tubs; underground utilities and systems; overflow drains for tubs and sinks; backflow prevention devices. Any comments made regarding these items are as a courtesy only. Note that the inspector does not operate water supply or shut-off valves due to the possibility of valves leaking or breaking when operated. The inspector does not test for lead in the water supply, the water pipes or solder, does not determine if plumbing and fuel lines are adequately sized, and does not determine the existence or condition of underground or above-ground fuel tanks.
Water service: Public
Location of main water shut-off: Not determined (obscured, inaccessible or none found)
Condition of drain pipes: Appeared serviceable
Drain pipe material: Plastic
Vent pipe condition: Appeared serviceable
Vent pipe material: Plastic
17) Evaluate, Comment
A water softener system was installed on the premises. These are specialty systems and are excluded from this inspection. Comments in this report related to this system are made as a courtesy only and are not meant to be a substitute for a full evaluation by a qualified specialist. Water softeners typically work by removing unwanted minerals (e.g. calcium, magnesium) from the water supply. They prevent build-up of scale inside water supply pipes, improve lathering while washing, and prevent spots on dishes. Recommend consulting with the property owner about this system to determine its condition, required maintenance, age, expected remaining life, etc. For more information, visit:http://www.reporthost.com/?WTRSFThttp://www.reporthost.com/?HRDWTR
Limitations: Evaluation of and determining the adequacy or completeness of the following items are not included in this inspection: water recirculation pumps; solar water heating systems; Energy Smart or energy saver controls; catch pan drains. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on water heaters, does not determine if water heaters are appropriately sized, or perform any evaluations that require a pilot light to be lit or a shut-off valve to be operated.
Condition of water heater: Appeared serviceable, Near service life
Energy source: Electricity
Estimated age: mfr 2004
Temperature-pressure relief valve installed: Yes
Location of water heater: Utility room
Hot water temperature tested: Yes
Water temperature (degrees Fahrenheit): 99
18) Maintain, Evaluate, Monitor, Comment
The hot water temperature was significantly lower than the standard temperature range of 110-120 degrees Fahrenheit. The thermostat should be adjusted to a higher setting. If the water temperature doesn't reach 120 degrees, then recommend that a qualified plumber evaluate and repair or replace the water heater as necessary.
Heating, Ventilation and Air Condition (HVAC)
Limitations: The following items are not included in this inspection: humidifiers, dehumidifiers, electronic air filters; solar, coal or wood-fired heat systems; thermostat or temperature control accuracy and timed functions; heating components concealed within the building structure or in inaccessible areas; underground utilities and systems; safety devices and controls (due to automatic operation). Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on heating or cooling system components, does not determine if heating or cooling systems are appropriately sized, does not test coolant pressure, or perform any evaluations that require a pilot light to be lit, a shut-off valve to be operated, a circuit breaker to be turned "on" or a serviceman's or oil emergency switch to be operated. It is beyond the scope of this inspection to determine if furnace heat exchangers are intact and free of leaks. Condensation pans and drain lines may clog or leak at any time and should be monitored while in operation in the future. Where buildings contain furnishings or stored items, the inspector may not be able to verify that a heat source is present in all "liveable" rooms (e.g. bedrooms, kitchens and living/dining rooms).
General heating system type(s): Forced air, Furnace, Heat pump
General heating distribution type(s): Ducts and registers
Condition of forced air heating/(cooling) system: Appeared serviceable
Forced air heating system fuel type: Electric
Estimated age of forced air furnace: Mfr 11/2004
Location of forced air furnace: Laundry room
Condition of furnace filters: Required replacement
Location for forced air filter(s): At base of air handler
Condition of forced air ducts and registers: Appeared serviceable
Condition of cooling system and/or heat pump: Appeared serviceable
Cooling system and/or heat pump fuel type: Electric
Location: Right side.
Type: Split system
Condition of controls: Appeared serviceable
19) Evaluate, Comment
The outdoor air temperature was below 65 degrees Fahrenheit during the inspection. Air conditioning systems can be damaged if operated during such low temperatures. Because of this, the inspector was unable to operate and fully evaluate the cooling system.
The AC is about two years old.
Furnace is 11 years old. Average life is 15-20 years.
Garage or Carport
Limitations: The inspector does not determine the adequacy of firewall ratings. Requirements for ventilation in garages vary between municipalities.
Condition of door between garage and house: Appeared serviceable
Type of door between garage and house: Metal
Condition of garage vehicle door(s): Appeared serviceable
Type of garage vehicle door: Sectional
Number of vehicle doors: 1
Condition of automatic opener(s): Appeared serviceable
Mechanical auto-reverse operable (reverses when meeting reasonable resistance during closing): Yes
Condition of garage floor: Appeared serviceable
Condition of garage interior: Appeared serviceable
21) Safety, Comment
The pull-down attic stairs installed in the attached garage ceiling had no visible fire-resistance rating. Current standard building practices call for wooden-framed ceilings that divide the house and garage to have a fire-resistance rating. Installing pull-down attic stairs intended for interior spaces compromises the ceiling's fire resistance. Recommend that a qualified person repair as necessary to restore the ceiling's fire resistance. For example, by modifying, replacing or removing the stairs. Note that commercially made, fire resistance-rated stairs are available. For more information, visit:http://www.reporthost.com/?FIREATTSTR
Attic and Roof Structure
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; areas and components obscured by insulation. Any comments made regarding these items are made as a courtesy only. The inspector does not determine the adequacy of the attic ventilation system. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high/low temperatures, high/low humidity, high wind and rain, melting snow) would be needed to do so. The inspector is not a licensed engineer and does not determine the adequacy of roof structure components such as trusses, rafters or ceiling beams, or their spacing or sizing.
Attic inspection method: Partially traversed
Condition of roof structure: Appeared serviceable
Roof structure type: Trusses
Ceiling structure: Trusses
Condition of insulation in attic (ceiling, skylight chase, etc.): Appeared serviceable
Ceiling insulation material: Cellulose loose fill
Condition of roof ventilation: Appeared serviceable
Roof ventilation type: Ridge vent(s), Enclosed soffit vents
23) Evaluate, Comment
These joist hangers should have nails in every hole. All located at the garage intersection.
After a complete inspection of this house here is a list of my concerns:
1. Picture #12-15 Suggest discussing these issues with a qualified electrician.
2. Picture #22-23 Suggest having qualified contractor evaluate the repairs made to the three trusses that have been altered on the jobsite.
Thank you for your trust in On The Money Home Inspection, LLC.
Please like us on Facebook at On The Money Home Inspection.
If you have any concerns or questions about this report please don't hesitate to contact me.