This report is the exclusive property of this inspection company and the client(s) listed in the report title. Use of this report by any unauthorized persons is prohibited.
Property Inspection Report
||Boise ID 83702
||Thursday, July 20, 2017
This report published on Monday, October 30, 2017 4:40:53 PM MDT
Time started: 1700
Time finished: 2020
Present during inspection: Client, Property owner, Tenant
Client present for discussion at end of inspection: No
Weather conditions during inspection: Dry (no rain)
Temperature during inspection: Hot
Inspection fee: $200
Type of building: Single family, Multiplex, Duplex
Buildings inspected: One Duplex with two units.
Number of residential units inspected: 2
Age of main building: 1910
Source for main building age: Municipal records or property listing
Front of building faces: North
Main entrance faces: North
Occupied: Yes, Furniture or stored items were present
Limitations: Unless specifically included in the inspection, the following items and any related equipment, controls, electric systems and/or plumbing systems are excluded from this inspection: detached buildings or structures; fences and gates; retaining walls; underground drainage systems, catch basins or concealed sump pumps; swimming pools and related safety equipment, spas, hot tubs or saunas; whether deck, balcony and/or stair membranes are watertight; trees, landscaping, properties of soil, soil stability, erosion and erosion control; ponds, water features, irrigation or yard sprinkler systems; sport courts, playground, recreation or leisure equipment; areas below the exterior structures with less than 3 feet of vertical clearance; invisible fencing; sea walls, docks and boathouses; retractable awnings. Any comments made regarding these items are as a courtesy only.
Site profile: Level
Condition of driveway: Appeared serviceable
Driveway material: Poured in place concrete
Condition of sidewalks and/or patios: Appeared serviceable
Sidewalk material: Poured in place concrete
Condition of deck, patio and/or porch covers: Appeared serviceable
Condition of stairs, handrails and guardrails: Appeared serviceable
Exterior stair material: Metal
Minor deterioration (e.g. cracks, holes, settlement, heaving) was found in the driveway, but no trip hazards were found. The client may wish to have repairs made for cosmetic reasons.
Exterior and Foundation
Limitations: The inspector performs a visual inspection of accessible components or systems at the exterior. Items excluded from this inspection include below-grade foundation walls and footings; foundations, exterior surfaces or components obscured by vegetation, stored items or debris; wall structures obscured by coverings such as siding or trim. Some items such as siding, trim, soffits, vents and windows are often high off the ground, and may be viewed using binoculars from the ground or from a ladder. This may limit a full evaluation. Regarding foundations, some amount of cracking is normal in concrete slabs and foundation walls due to shrinkage and drying. Note that the inspector does not determine the adequacy of seismic reinforcement.
Wall inspection method: Viewed from ground, from a ladder
Condition of wall exterior covering: Appeared serviceable
Apparent wall structure: Wood frame
Wall covering: Stucco
Condition of foundation and footings: Appeared serviceable
Apparent foundation type: Unfinished basement
Foundation/stem wall material: Poured in place concrete
Footing material (under foundation stem wall): Poured in place concrete
Wires coming from roof appear to of come lose from wall. May not be in use any longer. Recommend securing to wall or removing.
Limitations: Structural components such as joists and beams, and other components such as piping, wiring and/or ducting that are obscured by under-floor insulation are also excluded from this inspection. Note that the inspector does not determine if support posts, columns, beams, joists, studs, trusses, etc. are of adequate size, spanning or spacing.
The inspector does not guarantee or warrant that water will not accumulate in the basement in the future. Access to the basement during all seasons and during prolonged periods of all types of weather conditions (e.g. heavy rain, melting snow) would be needed to do so. The inspector does not determine the adequacy of basement floor or stairwell drains, or determine if such drains are clear or clogged.
Note that all basement areas should be checked periodically for water intrusion, plumbing leaks and pest activity.
Condition of exterior entry doors: Appeared serviceable
Exterior door material: Wood
Condition of floor substructure above: Appeared serviceable
Pier or support post material: Wood
Beam material: Solid wood
Floor structure above: Solid wood joists
Condition of insulation underneath floor above: Appeared serviceable, Required repairs, replacement and/or evaluation (see comments below)
Insulation material underneath floor above: Fiberglass roll or batt
Evidence of prior water intrusion was found in one or more sections of the basement. For example, water stains or rust at support post bases, efflorescence on the foundation, etc. Accumulated water is a conducive condition for wood-destroying organisms and should not be present in the basement. Recommend reviewing any disclosure statements available and ask the property owner about past accumulation of water in the basement. The basement should be monitored in the future for accumulated water, especially after heavy and/or prolonged periods of rain. If water is found to accumulate, then recommend that a qualified contractor who specializes in drainage issues evaluate and repair as necessary. Typical repairs for preventing water from accumulating in basements include:
- Repairing, installing or improving rain run-off systems (gutters, downspouts and extensions or drain lines)
- Improving perimeter grading
- Repairing, installing or improving underground footing and/or curtain drains
Ideally, water should not enter basements, but if water must be controlled after it enters the basement, then typical repairs include installing a sump pump.
Basement of 711.
One or more joists were notched or had holes cut in them in such a way as to significantly weaken the joist(s). General guidelines for modifying joists made of dimensional lumber include these restrictions:
- Notches at ends should not exceed 1/4 of the joist's depth.
- Other notches should not exceed 1/6 of the joist's depth.
- Notches should not be cut in the middle 1/3 of the joist's span.
- Notches should not be longer than 1/3 of the joist's depth.
- Holes must be 2 inches or more from the joist's edge.
- The maximum hole diameter is 1/3 of the depth of the joist.
Recommend that a qualified contractor evaluate and repair as necessary, and per standard building practices.
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; solar roofing components. Any comments made regarding these items are made as a courtesy only. Note that the inspector does not provide an estimate of remaining life on the roof surface material, nor guarantee that leaks have not occurred in the roof surface, skylights or roof penetrations in the past. Regarding roof leaks, only active leaks, visible evidence of possible sources of leaks, and evidence of past leaks observed during the inspection are reported on as part of this inspection. The inspector does not guarantee or warrant that leaks will not occur in the future. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high wind and rain, melting snow) would be needed to do so. Occupants should monitor the condition of roofing materials in the future. For older roofs, recommend that a professional inspect the roof surface, flashings, appurtenances, etc. annually and maintain/repair as might be required. If needed, the roofer should enter attic space(s). Regarding the roof drainage system, unless the inspection was conducted during and after prolonged periods of heavy rain, the inspector was unable to determine if gutters, downspouts and extensions perform adequately or are leak-free.
Roof inspection method: Traversed
Condition of roof surface material: Appeared serviceable
Roof surface material: Asphalt or fiberglass composition shingles
Roof type: Gable
Apparent number of layers of roof surface material: One
Condition of exposed flashings: Appeared serviceable
Condition of gutters, downspouts and extensions: Appeared serviceable
Attic and Roof Structure
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; areas and components obscured by insulation. Any comments made regarding these items are made as a courtesy only. The inspector does not determine the adequacy of the attic ventilation system. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high/low temperatures, high/low humidity, high wind and rain, melting snow) would be needed to do so. The inspector is not a licensed engineer and does not determine the adequacy of roof structure components such as trusses, rafters or ceiling beams, or their spacing or sizing.
Attic inspection method: Traversed
Condition of roof structure: Appeared serviceable
Roof structure type: Rafters
Ceiling structure: Ceiling joists
Condition of insulation in attic (ceiling, skylight chase, etc.): Appeared serviceable
Ceiling insulation material: Fiberglass loose fill, Cellulose loose fill
Approximate attic insulation R value (may vary in areas): R-49
Vermiculite insulation present: None visible
Condition of roof ventilation: Appeared serviceable
Roof ventilation type: Box vents (roof jacks)
One or more exhaust ducts (e.g. bathroom fan, clothes dryer) in the attic have come apart, were loose or have fallen down. This can result in increased moisture levels inside the structure and is a conducive condition for wood-destroying organisms. Recommend that a qualified person make permanent repairs as necessary.
Garage or Carport
Limitations: The inspector does not determine the adequacy of firewall ratings. Requirements for ventilation in garages vary between municipalities.
Type: Detached, Garage
Condition of garage vehicle door(s): Appeared serviceable
Type of garage vehicle door: Roll
Condition of garage floor: Appeared serviceable
Condition of garage interior: Appeared serviceable
Garage ventilation: Adequate
Minor cracks were found in the concrete slab floor. These are common and appeared to be only a cosmetic issue.
Limitations: The following items are not included in this inspection: generator systems, transfer switches, surge suppressors, inaccessible or concealed wiring; underground utilities and systems; low-voltage lighting or lighting on timers or sensors. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of grounding or bonding, if this system has an adequate capacity for the client's specific or anticipated needs, or if this system has any reserve capacity for additions or expansion. The inspector does not operate circuit breakers as part of the inspection, and does not install or change light bulbs. The inspector does not evaluate every wall switch or receptacle, but instead tests a representative number of them per various standards of practice. When furnishings, stored items or child-protective caps are present some receptacles are usually inaccessible and are not tested; these are excluded from this inspection. Receptacles that are not of standard 110 volt configuration, including 240-volt dryer receptacles, are not tested and are excluded. The functionality of, power source for and placement of smoke and carbon monoxide alarms is not determined as part of this inspection. Upon taking occupancy, proper operating and placement of smoke and carbon monoxide alarms should be verified and batteries should be changed. These devices have a limited lifespan and should be replaced every 10 years. The inspector attempts to locate and evaluate all main and sub-panels. However, panels are often concealed. If panels are found after the inspection, a qualified electrician should evaluate and repair if necessary. The inspector attempts to determine the overall electrical service size, but such estimates are not guaranteed because the overall capacity may be diminished by lesser-rated components in the system. Any repairs recommended should be made by a licensed electrician.
Electric service condition: Appeared serviceable
Primary service type: Overhead
Number of service conductors: 2
Service voltage (volts): 120-240
Estimated service amperage: 60
Primary service overload protection type: Circuit breakers, Fuses
Service entrance conductor material: Stranded aluminum
Condition of main service panel: Near, at or beyond service life
Location of main service panel #A: Garage, 1701
Location of main service panel #B: Garage, 711
Location of sub-panel #C: Basement
Location of sub-panel #D: Basement
Location of main disconnect: Breaker at top of main service panel, Both main disconnects are located in the garage for 711 unit.
Branch circuit wiring type: knob and tube
Ground fault circuit interrupter (GFCI) protection present: No
Arc fault circuit interrupter (AFCI) protection present: No
Smoke alarms installed: Yes, but not tested
Energized "knob and tube" wiring was found at one or more locations. This type of wiring was commonly installed prior to 1950. It is ungrounded and considered unsafe by today's standards. Over time, the wire's insulation can become brittle and fall apart or wear thin, resulting in exposed conductors and a risk of shock and/or fire. This wiring is also easily damaged by covering it with insulation (a common practice), and incorrectly tapping new wiring into it.
It is not within the scope of this inspection to determine what percentage of this property's wiring is of the knob-and-tube type, or to determine what percentage of the knob and tube wiring is energized versus abandoned. Recommend that a qualified electrician evaluate this wiring and make repairs or replace wiring as necessary.
Note that some insurance companies may be unwilling to offer homeowner's insurance for properties with knob and tube wiring. Consult with your insurance carrier regarding this. For more information, visit:http://www.reporthost.com/?KNOBTUBE
The electric service was configured so that too many hand movements were necessary to turn off all power for the service. Six or fewer circuit breakers should be required to turn off all power to a residence. This is a potential safety hazard during an emergency when the power needs to be turned off quickly. Recommend that a qualified electrician repair per standard building practices.
One or more electrical components including receptacles appeared to be older than their intended service life. Such old components may pose a fire or shock hazard. Recommend consulting with a qualified electrician to determine which components should be replaced with newer, modern components.
The legend for circuit breakers or fuses in panel(s) #A and B was missing, incomplete, illegible or confusing. This is a potential shock or fire hazard in the event of an emergency when power needs to be turned off. Recommend correcting the legend so it's accurate, complete and legible. Evaluation by a qualified electrician may be necessary.
A "split bus" panel was installed as a main service panel. On such panels there is no single main disconnect switch to turn the power off. Instead, all breakers labeled "main" or "sub-main" (usually those on the upper half of the panel) must be turned off to turn all power off. These panels are common, but are no longer installed. The client should familiarize themselves with the operation of this panel and the procedure for turning all the power off in the event of an emergency. Consult with an electrician if necessary. Please see any other comments in this report related to the panel's legend.
Plumbing / Fuel Systems
Limitations: The following items are not included in this inspection: private/shared wells and related equipment; private sewage disposal systems; hot tubs or spas; main, side and lateral sewer lines; gray water systems; pressure boosting systems; trap primers; incinerating or composting toilets; fire suppression systems; water softeners, conditioners or filtering systems; plumbing components concealed within the foundation or building structure, or in inaccessible areas such as below tubs; underground utilities and systems; overflow drains for tubs and sinks; backflow prevention devices. Any comments made regarding these items are as a courtesy only. Note that the inspector does not operate water supply or shut-off valves due to the possibility of valves leaking or breaking when operated. The inspector does not test for lead in the water supply, the water pipes or solder, does not determine if plumbing and fuel lines are adequately sized, and does not determine the existence or condition of underground or above-ground fuel tanks.
Condition of service and main line: Appeared serviceable
Water service: Public
Location of main water shut-off: Basement
Condition of supply lines: Appeared serviceable
Supply pipe material: Galvanized steel, PEX plastic
Limitations: Evaluation of and determining the adequacy or completeness of the following items are not included in this inspection: water recirculation pumps; solar water heating systems; Energy Smart or energy saver controls; catch pan drains. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on water heaters, does not determine if water heaters are appropriately sized, or perform any evaluations that require a pilot light to be lit or a shut-off valve to be operated.
Condition of water heater: Appeared serviceable
Energy source: Natural gas
Capacity (in gallons): 40
Temperature-pressure relief valve installed: Yes
Location of water heater: Basement
Hot water temperature tested: Yes, 139deg F
Water temperature (degrees Fahrenheit): 139deg F
Condition of venting system: Appeared serviceable
Heating, Ventilation and Air Condition (HVAC)
Limitations: The following items are not included in this inspection: humidifiers, dehumidifiers, electronic air filters; solar, coal or wood-fired heat systems; thermostat or temperature control accuracy and timed functions; heating components concealed within the building structure or in inaccessible areas; underground utilities and systems; safety devices and controls (due to automatic operation). Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on heating or cooling system components, does not determine if heating or cooling systems are appropriately sized, does not test coolant pressure, or perform any evaluations that require a pilot light to be lit, a shut-off valve to be operated, a circuit breaker to be turned "on" or a serviceman's or oil emergency switch to be operated. It is beyond the scope of this inspection to determine if furnace heat exchangers are intact and free of leaks. Condensation pans and drain lines may clog or leak at any time and should be monitored while in operation in the future. Where buildings contain furnishings or stored items, the inspector may not be able to verify that a heat source is present in all "liveable" rooms (e.g. bedrooms, kitchens and living/dining rooms).
General heating system type(s): Forced air, Furnace
General heating distribution type(s): Ducts and registers
Forced air heating system fuel type: Natural gas
Location of forced air furnace: Basement
Condition of furnace filters: Appeared serviceable
Condition of forced air ducts and registers: Appeared serviceable, Required repair, replacement and/or evaluation (see comments below)
Cooling system and/or heat pump fuel type: Electric
Condition of controls: Appeared serviceable
Fireplaces, Stoves, Chimneys and Flues
Limitations: The following items are not included in this inspection: coal stoves, gas logs, chimney flues (except where visible). Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of drafting or sizing in fireplace and stove flues, and also does not determine if prefabricated or zero-clearance fireplaces are installed in accordance with the manufacturer's specifications. The inspector does not perform any evaluations that require a pilot light to be lit, and does not light fires. The inspector provides a basic visual examination of a chimney and any associated wood burning device. The National Fire Protection Association has stated that an in-depth Level 2 chimney inspection should be part of every sale or transfer of property with a wood-burning device. Such an inspection may reveal defects that are not apparent to the home inspector who is a generalist.
Condition of chimneys and flues: Appeared serviceable
Wood-burning chimney type: Masonry, with metal liner
One or more fireplace dampers were inoperable and/or missing. Recommend that a qualified contractor repair or replace dampers as necessary.
Fireplace in 1701 has lose bricks and missing a closable damper.
Limitations: The following items are not included in this inspection: household appliances such as stoves, ovens, cook tops, ranges, warming ovens, griddles, broilers, dishwashers, trash compactors, refrigerators, freezers, ice makers, hot water dispensers and water filters; appliance timers, clocks, cook functions, self and/or continuous cleaning operations, thermostat or temperature control accuracy, and lights. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of the remaining life of appliances, and does not determine the adequacy of operation of appliances. The inspector does not note appliance manufacturers, models or serial numbers and does not determine if appliances are subject to recalls. Areas and components behind and obscured by appliances are inaccessible and excluded from this inspection.
Condition of counters: Appeared serviceable
Condition of cabinets: Appeared serviceable
Condition of sinks and related plumbing: Appeared serviceable
Condition of under-sink food disposal: Appeared serviceable
Condition of dishwasher: Appeared serviceable
One or more cabinets, drawers and/or cabinet doors were damaged or deteriorated.
1701 unit had several drawers that were rough but functional along with cabinets that did not stay closed.
Water damage was found in shelving or cabinets below the sink. Recommend that a qualified contractor repair as necessary after any plumbing leaks have been repaired. If moisture is present then concealed areas should be dried thoroughly.
One or more cabinet drawers were difficult to open or close. Recommend that a qualified person repair as necessary.
Bathrooms, Laundry and Sinks
Limitations: The following items are not included in this inspection: overflow drains for tubs and sinks; heated towel racks, saunas, steam generators, clothes washers, clothes dryers. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of washing machine drain lines, washing machine catch pan drain lines, or clothes dryer exhaust ducts. The inspector does not operate water supply or shut-off valves for sinks, toilets, bidets, clothes washers, etc. due to the possibility of valves leaking or breaking when operated. The inspector does not determine if shower pans or tub and shower enclosures are water tight, or determine the completeness or operability of any gas piping to laundry appliances.
Location #A: Full bath, second floor, 1701
Condition of counters: Appeared serviceable
Condition of cabinets: Appeared serviceable
Condition of flooring: Appeared serviceable
Condition of sinks and related plumbing: Appeared serviceable
Condition of toilets: Appeared serviceable
Condition of bathtubs and related plumbing: Appeared serviceable
Condition of shower(s) and related plumbing: Appeared serviceable
Condition of ventilation systems: Appeared serviceable
The bathtub at location(s) #A drained slowly. Recommend clearing drain and/or that a qualified plumber repair if necessary.
One or more handles controlling water flow to the shower at location(s) #A were loose. Recommend that a qualified person repair or replace handles as necessary.
The exhaust fan at location(s) #A was noisy or vibrated excessively. Moisture may accumulate and result in mold, bacteria or fungal growth. Recommend that a qualified person clean, repair or replace fans as necessary.
The sink at location(s) #A was worn, blemished or deteriorated.
Interior, Doors and Windows
Limitations: The following items are not included in this inspection: security, intercom and sound systems; communications wiring; central vacuum systems; elevators and stair lifts; cosmetic deficiencies such as nail-pops, scuff marks, dents, dings, blemishes or issues due to normal wear and tear in wall, floor and ceiling surfaces and coverings, or in equipment; deficiencies relating to interior decorating; low voltage and gas lighting systems. Any comments made regarding these items are as a courtesy only. Note that the inspector does not evaluate any areas or items which require moving stored items, furnishings, debris, equipment, floor coverings, insulation or similar materials. The inspector does not test for asbestos, lead, radon, mold, hazardous waste, urea formaldehyde urethane, or any other toxic substance. Some items such as window, drawer, cabinet door or closet door operability are tested on a sampled basis. The client should be aware that paint may obscure wall and ceiling defects, floor coverings may obscure floor defects, and furnishings may obscure wall, floor and floor covering defects. If furnishings were present during the inspection, recommend a full evaluation of walls, floors and ceilings that were previously obscured when possible. Determining the cause and/or source of odors is not within the scope of this inspection.
Condition of exterior entry doors: Required repair, replacement and/or evaluation (see comments below)
Exterior door material: Wood, Glass panel
Condition of interior doors: Appeared serviceable
Condition of windows and skylights: Appeared serviceable
Type(s) of windows: Vinyl
Condition of walls and ceilings: Appeared serviceable
Wall type or covering: Drywall, Drywall or plaster
Ceiling type or covering: Drywall, Drywall or plaster
Condition of flooring: Appeared serviceable
Flooring type or covering: Carpet
Condition of stairs, handrails and guardrails: Appeared serviceable
Some interior door hardware (locksets) were loose. Recommend that a qualified person repair or replace as necessary.
Carpeting in one or more areas was damaged or deteriorated. Recommend that a qualified contractor replace as necessary.
Minor cracks, nail pops and/or blemishes were found in walls and/or ceilings in one or more areas. Cracks and nail pops are common, are often caused by lumber shrinkage or minor settlement, and can be more or less noticeable depending on changes in humidity. They did not appear to be a structural concern, but the client may wish to repair these for aesthetic reasons. For recurring cracks, consider using an elastic crack covering product:http://www.reporthost.com/?ECC
1701 Master Bedroom.
One or more exterior doors had minor damage and/or deterioration. Although serviceable, the client may wish to repair or replace such doors for appearances' sake.
Handle on 1701 front door is lose.
Thank you for choosing NorthWest Inspections.