This report is the exclusive property of this inspection company and the client(s) listed in the report title. Use of this report by any unauthorized persons is prohibited.
Hudson Home Inspections, LLC
Inspector: Dmitriy Chimirev
Property Inspection Report
||123 ABC Lane
||Thursday, July 27, 2017
This report published on Tuesday, August 22, 2017 3:51:18 PM EDT
How to Read this Report
This report is organized by the property's functional areas. Within each functional area, descriptive information is listed first and is shown in bold type. Items of concern follow descriptive information.
Concerns are shown and sorted according to these types:
|Safety||Poses a safety hazard|
|Major Defect||Correction likely involves a significant expense|
|Repair/Replace||Recommend repairing or replacing|
|Repair/Maintain||Recommend repair and/or maintenance|
|Minor Defect||Correction likely involves only a minor expense|
|Maintain||Recommend ongoing maintenance|
|Evaluate||Recommend evaluation by a specialist|
|Monitor||Recommend monitoring in the future|
|Comment||For your information|
Click here for a glossary of building construction terms.Contact your inspector If there are terms that you do not understand, or visit the glossary of construction terms at http://www.reporthost.com/glossary.asp
Report number: 1230
Time started: 10am
Time finished: 12am
Present during inspection: Client, Realtor
Client present for discussion at end of inspection: Yes
Weather conditions during inspection: Dry (no rain)
Temperature during inspection: Warm
Type of building: Single family, Detached garage
Buildings inspected: One house, One detached garage
Age of main building: 64
Source for main building age: Municipal records or property listing
Front of building faces: South
Main entrance faces: South
1) Safety, Comment
Structures built prior to the mid 1980s may contain lead and/or asbestos. Lead is commonly found in paint and in some plumbing components. The EPA does not recognize newer coats of paint as encapsulating older coats of lead-based paint. Asbestos is commonly found in various building materials such as insulation, siding, and/or floor and ceiling tiles. Laws were passed in 1978 to prohibit usage of lead and asbestos, but stocks of materials containing these substances remained in use for a number of years thereafter. Both lead and asbestos are known health hazards. Evaluating for the presence of lead and/or asbestos is beyond the scope of this inspection. Any mention of these materials in this report is made as a courtesy only, and meant to refer the client to a specialist. Consult with specialists as necessary, such as industrial hygienists, professional labs and/or abatement specialists for this type of evaluation. For information on lead, asbestos and other hazardous materials in homes, visit:http://www.reporthost.com/?EPAhttp://www.reporthost.com/?CPSChttp://www.reporthost.com/?CDC
2) Evaluate, Comment
The water service was not fully functional during the inspection*. The inspector operates only "normal" controls such as faucets, and does not operate shut-off valves to the water meter or house. As a result, plumbing supply, drain waste and vent lines, traps, pumps, fixtures, and some appliances such as water heaters weren't fully evaluated. The water pressure was not determined. Recommend that a qualified person make a full evaluation of the plumbing system after the water supply is turned back on. Areas below the house should be evaluated after plumbing has been operated to check for leaks. Any problems that are found after this evaluation should be repaired by a qualified plumber.
*It appears the water pressure regulator on the well pump was malfunctioning.
Limitations: Unless specifically included in the inspection, the following items and any related equipment, controls, electric systems and/or plumbing systems are excluded from this inspection: detached buildings or structures; fences and gates; retaining walls; underground drainage systems, catch basins or concealed sump pumps; swimming pools and related safety equipment, spas, hot tubs or saunas; whether deck, balcony and/or stair membranes are watertight; trees, landscaping, properties of soil, soil stability, erosion and erosion control; ponds, water features, irrigation or yard sprinkler systems; sport courts, playground, recreation or leisure equipment; areas below the exterior structures with less than 3 feet of vertical clearance; invisible fencing; sea walls, docks and boathouses; retractable awnings. Any comments made regarding these items are as a courtesy only.
Site profile: Level
Condition of driveway: Appeared serviceable
Driveway material: Gravel
Condition of sidewalks and/or patios: Appeared serviceable
Sidewalk material: Poured in place concrete, Paving stones
Condition of deck, patio and/or porch covers: Appeared serviceable
Deck, patio, porch cover material and type: Covered (Refer to Roof section)
Condition of decks, porches and/or balconies: Appeared serviceable
Deck, porch and/or balcony material: Wood
Condition of stairs, handrails and guardrails: Required repairs, replacement and/or evaluation (see comments below)
Exterior stair material: Wood, Masonry
3) Safety, Repair/Replace -
The risers for stairs at one or more locations varied in height and pose a fall or trip hazard. Risers within the same flight of stairs should vary by no more than 3/8 inch. At a minimum, be aware of this hazard, especially when guests who are not familiar with the stairs are present. Recommend that a qualified contractor repair per standard building practices.
4) Safety, Repair/Replace
Guardrails at one or more locations with drop-offs higher than 30 inches were missing. This poses a fall hazard. Guardrails should be installed where walking surfaces are more than 30 inches above the surrounding grade or surfaces below. Recommend that a qualified contractor install guardrails where missing and per standard building practices.
5) Safety, Repair/Replace
Perimeter bench seating was installed at one or more decks, porches or balconies where walking surfaces were more than 30 inches above the surrounding grade. Bench seating is not a safe substitute for standard guardrails, and is a potential fall hazard. Gaps in such seating often allow small children to climb underneath and fall. People sitting or standing on benches may also fall. The clients should at least be aware of this hazard, especially if small children are present. Recommend having a qualified contractor repair as necessary to eliminate fall hazards around bench seating.
6) Repair/Maintain -
The soil or grading sloped down towards building perimeters in one or more areas. This can result in water accumulating around building foundations or underneath buildings. It can be a conducive condition for wood-destroying organisms. Recommend grading soil so it slopes down and away from buildings with a slope of at least 1 inch per horizontal foot for at least 6 feet out from buildings.
Wooden deck or porch surfaces were overdue for normal maintenance. Recommend that a qualified person clean and preserve as necessary. Where decks have been coated with a finish such as opaque stains or paint, it may be too difficult to strip the finish and apply anything but paint or opaque stain. Where transparent stain or penetrating oil has been applied in the past, recommend that a penetrating oil be used. For more information, visit:http://www.reporthost.com/?PENOILhttp://www.reporthost.com/?DKMAIN
Exterior and Foundation
Limitations: The inspector performs a visual inspection of accessible components or systems at the exterior. Items excluded from this inspection include below-grade foundation walls and footings; foundations, exterior surfaces or components obscured by vegetation, stored items or debris; wall structures obscured by coverings such as siding or trim. Some items such as siding, trim, soffits, vents and windows are often high off the ground, and may be viewed using binoculars from the ground or from a ladder. This may limit a full evaluation. Regarding foundations, some amount of cracking is normal in concrete slabs and foundation walls due to shrinkage and drying. Note that the inspector does not determine the adequacy of seismic reinforcement.
Wall inspection method: Viewed from ground
Condition of wall exterior covering: Appeared serviceable
Apparent wall structure: Wood frame
Wall covering: Vinyl
Condition of foundation and footings: Appeared serviceable
Apparent foundation type: Unfinished basement
Foundation/stem wall material: Concrete block
Soil was in contact with or less than 6 inches from siding or trim. Regardless of what material is used for siding, it should not be in contact with the soil. If made of wood, siding or trim will eventually rot. For other materials, ground or surface water can infiltrate siding or trim and cause damage to the wall structure. Wood-destroying insects are likely to infest and damage the wall structure. This is a conducive condition for wood-destroying organisms. Recommend grading or removing soil as necessary to maintain a 6-inch clearance. Note that damage from fungal rot and/or insects may be found when soil is removed, and repairs may be necessary.
@ the Garage.
Vegetation such as trees, shrubs and/or vines was in contact with or close to the building exterior. Vegetation can serve as a pathway for wood-destroying insects and can retain moisture against the exterior after it rains. This is a conducive condition for wood-destroying organisms. Recommend pruning, moving or removing vegetation as necessary to maintain at least 6 inches of space between it and the building exterior. A 1-foot clearance is better.
The paint or stain finish in some areas was failing (e.g. peeling, faded, worn, thinning). Siding and trim with a failing finish can be damaged by moisture. Recommend that a qualified contractor prep (e.g. clean, scrape, sand, prime, caulk) and repaint or restain the building exterior where necessary and per standard building practices. Any repairs needed to the siding or trim should be made prior to this.
Limitations: Structural components such as joists and beams, and other components such as piping, wiring and/or ducting that are obscured by under-floor insulation are also excluded from this inspection. Note that the inspector does not determine if support posts, columns, beams, joists, studs, trusses, etc. are of adequate size, spanning or spacing.
The inspector does not guarantee or warrant that water will not accumulate in the basement in the future. Access to the basement during all seasons and during prolonged periods of all types of weather conditions (e.g. heavy rain, melting snow) would be needed to do so. The inspector does not determine the adequacy of basement floor or stairwell drains, or determine if such drains are clear or clogged.
Note that all basement areas should be checked periodically for water intrusion, plumbing leaks and pest activity.
Condition of exterior entry doors: Limited evaluation. Not accessible
Exterior door material: Metal
Condition of floor substructure above: Appeared serviceable
Pier or support post material: Steel
Beam material: Built-up wood
Floor structure above: Solid wood joists
11) Repair/Replace, Evaluate, Monitor
Evidence of prior water intrusion was found in one or more sections of the basement. For example, water stains or rust at support post bases, efflorescence on the foundation, etc. Accumulated water is a conducive condition for wood-destroying organisms and should not be present in the basement. Recommend reviewing any disclosure statements available and ask the property owner about past accumulation of water in the basement. The basement should be monitored in the future for accumulated water, especially after heavy and/or prolonged periods of rain. If water is found to accumulate, then recommend that a qualified contractor who specializes in drainage issues evaluate and repair as necessary. Typical repairs for preventing water from accumulating in basements include:
- Repairing, installing or improving rain run-off systems (gutters, downspouts and extensions or drain lines)
- Improving perimeter grading
- Repairing, installing or improving underground footing and/or curtain drains
Ideally, water should not enter basements, but if water must be controlled after it enters the basement, then typical repairs include installing a sump pump.
Wet stains and moisture absorption products present.
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; solar roofing components. Any comments made regarding these items are made as a courtesy only. Note that the inspector does not provide an estimate of remaining life on the roof surface material, nor guarantee that leaks have not occurred in the roof surface, skylights or roof penetrations in the past. Regarding roof leaks, only active leaks, visible evidence of possible sources of leaks, and evidence of past leaks observed during the inspection are reported on as part of this inspection. The inspector does not guarantee or warrant that leaks will not occur in the future. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high wind and rain, melting snow) would be needed to do so. Occupants should monitor the condition of roofing materials in the future. For older roofs, recommend that a professional inspect the roof surface, flashings, appurtenances, etc. annually and maintain/repair as might be required. If needed, the roofer should enter attic space(s). Regarding the roof drainage system, unless the inspection was conducted during and after prolonged periods of heavy rain, the inspector was unable to determine if gutters, downspouts and extensions perform adequately or are leak-free.
Roof inspection method: Viewed from ground with binoculars, Viewed from windows
Condition of roof surface material: Near, at or beyond service life
Roof surface material: Asphalt or fiberglass composition shingles
Roof type: Gable
Apparent number of layers of roof surface material: One
Condition of exposed flashings: Appeared serviceable
Condition of gutters, downspouts and extensions: Required repair, replacement and/or evaluation (see comments below)
12) Major Defect, Evaluate -
The roof surface appeared to be near the end of its service life and will likely need replacing in the near future even if repairs are made now. Recommend discussing replacement options with a qualified contractor, and budgeting for a replacement roof surface in the near future. The client may also wish to consider having a qualified contractor attempt to issue a "5 year roof certificate."
13) Repair/Replace -
Extensions such as splash blocks or drain pipes for one or more downspouts were substandard. Water can accumulate around the building foundation or inside crawl spaces or basements as a result. Recommend that a qualified person install, replace or repair extensions as necessary so rainwater drains away from the structure.
Moss was growing on the roof. As a result, shingles can lift or be damaged. Leaks can result and/or the roof surface can fail prematurely. Efforts should be made to kill the moss during its growing season (wet months). Typically, zinc or phosphate-based chemicals are used for this and must be applied periodically. For information on various moss treatment products and their pros and cons, visit:http://www.reporthost.com/?MOSS
Attic and Roof Structure
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; areas and components obscured by insulation. Any comments made regarding these items are made as a courtesy only. The inspector does not determine the adequacy of the attic ventilation system. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high/low temperatures, high/low humidity, high wind and rain, melting snow) would be needed to do so. The inspector is not a licensed engineer and does not determine the adequacy of roof structure components such as trusses, rafters or ceiling beams, or their spacing or sizing.
Attic inspection method: Partially traversed
Condition of roof structure: Appeared serviceable
Roof structure type: Rafters
Ceiling structure: Ceiling joists
Condition of insulation in attic (ceiling, skylight chase, etc.): Appeared serviceable
Ceiling insulation material: Fiberglass roll or batt
Garage or Carport
Limitations: The inspector does not determine the adequacy of firewall ratings. Requirements for ventilation in garages vary between municipalities.
Condition of garage vehicle door(s): Appeared serviceable
Type of garage vehicle door: Sectional
Number of vehicle doors: 2
Condition of automatic opener(s): Appeared serviceable
Mechanical auto-reverse operable (reverses when meeting reasonable resistance during closing): Yes
Condition of garage floor: Appeared serviceable
Condition of garage interior: Appeared serviceable
Garage ventilation: Exists
15) Comment -
Minor cracks were found in the concrete slab floor. These are common and appeared to be only a cosmetic issue.
Limitations: The following items are not included in this inspection: generator systems, transfer switches, surge suppressors, inaccessible or concealed wiring; underground utilities and systems; low-voltage lighting or lighting on timers or sensors. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of grounding or bonding, if this system has an adequate capacity for the client's specific or anticipated needs, or if this system has any reserve capacity for additions or expansion. The inspector does not operate circuit breakers as part of the inspection, and does not install or change light bulbs. The inspector does not evaluate every wall switch or receptacle, but instead tests a representative number of them per various standards of practice. When furnishings, stored items or child-protective caps are present some receptacles are usually inaccessible and are not tested; these are excluded from this inspection. Receptacles that are not of standard 110 volt configuration, including 240-volt dryer receptacles, are not tested and are excluded. The functionality of, power source for and placement of smoke and carbon monoxide alarms is not determined as part of this inspection. Upon taking occupancy, proper operating and placement of smoke and carbon monoxide alarms should be verified and batteries should be changed. These devices have a limited lifespan and should be replaced every 10 years. The inspector attempts to locate and evaluate all main and sub-panels. However, panels are often concealed. If panels are found after the inspection, a qualified electrician should evaluate and repair if necessary. The inspector attempts to determine the overall electrical service size, but such estimates are not guaranteed because the overall capacity may be diminished by lesser-rated components in the system. Any repairs recommended should be made by a licensed electrician.
Electric service condition: Appeared serviceable
Primary service type: Overhead
Number of service conductors: 3
Service voltage (volts): 120-240
Estimated service amperage: 60
Primary service overload protection type: Circuit breakers
Service entrance conductor material: Stranded aluminum
Main disconnect rating (amps): 60
System ground: Ground rod(s) in soil, Cold water supply pipes
Condition of main service panel: Required repair, replacement and/or evaluation (see comments below)
Location of main service panel #A: Basement
Location of main disconnect: Top right
Condition of branch circuit wiring: Required repair, replacement and/or evaluation (see comments below)
Branch circuit wiring type: Non-metallic sheathed, (BX) Armor clad flexible, Aluminum solid-strand
Solid strand aluminum branch circuit wiring present: Yes
Ground fault circuit interrupter (GFCI) protection present: No
Arc fault circuit interrupter (AFCI) protection present: No
Smoke alarms installed: Yes, but not tested
Carbon monoxide alarms installed: Yes, but not tested
16) Safety, Repair/Replace, Evaluate
One or more branch circuits with solid-strand aluminum wires were found. Problems due to expansion and contraction with this type of wiring can cause overheating at connections between the wire and devices such as switches and receptacles, or at splices. This is a potential fire hazard. The Consumer Products Safety Commission recommends either discontinuing use of circuits with aluminum wiring, removing the wiring, or that an electrician determine if copper wire can be pig-tailed onto the ends of the aluminum wire. A qualified electrician should evaluate the full electrical system and repair as necessary. For more information, visit:http://www.reporthost.com/?ALWIRE1http://www.reporthost.com/?ALWIRE2
17) Safety, Repair/Replace, Evaluate
One or more electric receptacles at the kitchen, bathroom(s), laundry area, utility sink, garage and/or exterior had no visible ground fault circuit interrupter (GFCI) protection, or the inspector was unable to determine if GFCI protection was present. If not GFCI-protected, receptacles in wet areas pose a shock hazard. Recommend that a qualified electrician evaluate and install GFCI protection if necessary and per standard building practices. General guidelines for GFCI-protected receptacles include the following locations:
- Outdoors (since 1973)
- Bathrooms (since 1975)
- Garages (since 1978)
- Kitchens (since 1987)
- Crawl spaces and unfinished basements (since 1990)
- Wet bar sinks (since 1993)
- Laundry and utility sinks (since 2005)
For more information, visit:http://www.reporthost.com/?GFCI
18) Safety, Repair/Replace
One or more circuit breakers in panel(s) #A were "double tapped," where two or more wires were installed in the breaker's lug. Most breakers are designed for only one wire to be connected. This is a safety hazard since the lug bolt can tighten securely against one wire but leave other(s) loose. Arcing, sparks and fires can result. Recommend that a qualified electrician repair as necessary. For more information, visit:http://www.reporthost.com/?DBLTAP
19) Safety, Repair/Replace
Wire splices were exposed and were not contained in a covered junction box. This is a potential shock or fire hazard. Recommend that a qualified electrician repair per standard building practices. For example, by installing permanently mounted junction boxes with cover plates where needed to contain wiring splices.
20) Safety, Evaluate -
Branch circuit wiring installed in buildings built prior to the mid 1980s is typically rated for a maximum temperature of only 60 degrees Celsius. This includes non-metallic sheathed (Romex) wiring, and both BX and AC metal-clad flexible wiring. Knob and tube wiring, typically installed in homes built prior to 1950, may be rated for even lower maximum temperatures. Newer electric fixtures including lighting and fans typically require wiring rated for 90 degrees Celsius. Connecting newer fixtures to older, 60-degree-rated wiring is a potential fire hazard. Repairs for such conditions may involve replacing the last few feet of wiring to newer fixtures with new 90-degree-rated wire, and installing a junction box to join the old and new wiring.
It is beyond the scope of this inspection to determine if such incompatible components are installed, or to determine the extent to which they're installed. Based on the age of this building, the client should be aware of this safety hazard, both for existing fixtures and when planning to upgrade with newer fixtures. Consult with a qualified electrician for repairs as necessary.
21) Safety, Evaluate -
2-slot receptacles rather than 3-slot, grounded receptacles were installed in one or more areas. These do not have an equipment ground and are considered unsafe by today's standards. Appliances that require a ground should not be used with 2-slot receptacles. Examples of such appliances include computers and related hardware, refrigerators, freezers, portable air conditioners, clothes washers, aquarium pumps, and electrically operated gardening tools. The client should be aware of this limitation when planning use for various rooms, such as an office. Upgrading to grounded receptacles typically requires installing new wiring from the main service panel or sub-panel to the receptacle(s), in addition to replacing the receptacle(s). Consult with a qualified electrician about upgrading to 3-wire, grounded circuits.
22) Safety, Comment
The functionality of, power source for and placement of smoke alarms is not determined as part of this inspection. Smoke alarms should be installed in each bedroom, in hallways leading to bedrooms, on each level and in attached garages. They have a limited lifespan and should be replaced every 10 years. For home buyers, batteries in smoke alarms should be changed when taking occupancy. Batteries should be replaced annually in the future. Carbon monoxide alarms should be installed in the vicinity of sleeping areas and on each level. For more information, visit:http://www.reporthost.com/?SMKALRMhttp://www.reporthost.com/?COALRM
23) Repair/Replace, Evaluate -
One or more electric receptacles appeared to have no power. Recommend asking the property owner about this. Switches may need to be operated or GFCI/AFCI protection may need to be reset to make some receptacles energized. If necessary, recommend that a qualified electrician evaluate and repair.
24) Evaluate -
The electric service to this property appeared to be rated at substantially less than 200 amps and may be inadequate. Depending on the client's needs, recommend consulting with a qualified electrician about upgrading to a 200 amp service. Note that the electric service's rating is based on the lowest rating for the meter base, the service conductors, the main service panel and the main disconnect switch. One or more of these components may need replacing to upgrade.
Plumbing / Fuel Systems
Limitations: The following items are not included in this inspection: private/shared wells and related equipment; private sewage disposal systems; hot tubs or spas; main, side and lateral sewer lines; gray water systems; pressure boosting systems; trap primers; incinerating or composting toilets; fire suppression systems; water softeners, conditioners or filtering systems; plumbing components concealed within the foundation or building structure, or in inaccessible areas such as below tubs; underground utilities and systems; overflow drains for tubs and sinks; backflow prevention devices. Any comments made regarding these items are as a courtesy only. Note that the inspector does not operate water supply or shut-off valves due to the possibility of valves leaking or breaking when operated. The inspector does not test for lead in the water supply, the water pipes or solder, does not determine if plumbing and fuel lines are adequately sized, and does not determine the existence or condition of underground or above-ground fuel tanks.
Condition of service and main line: Appeared serviceable
Water service: Private well
Location of main water shut-off: Basement
Condition of supply lines: Appeared serviceable
Supply pipe material: Copper
Condition of drain pipes: Appeared serviceable
Drain pipe material: Plastic, Copper
Condition of waste lines: Required repair, replacement and/or evaluation (see comments below)
Waste pipe material: Cast iron
Vent pipe condition: Appeared serviceable
Vent pipe material: Galvanized steel, Copper
Condition of fuel system: Appeared serviceable
Visible fuel storage systems: oil tank, in basement
Location of main fuel shut-off valve: At oil tank
25) Repair/Replace, Evaluate
Corrosion was found in some waste pipes or fittings. This can indicate past leaks, or that leaks are likely to occur in the future. Recommend that a qualified plumber evaluate and repair as necessary.
26) Maintain, Evaluate
Based on visible components or information provided to the inspector, this property appeared to have a private sewage disposal (septic) system. These are specialty systems and are excluded from this inspection. Comments in this report related to this system are made as a courtesy only and are not meant to be a substitute for a full evaluation by a qualified specialist. Generally, septic tanks should be pumped and inspected every 3 years. Depending on the type of system and municipal regulations, inspection and maintenance may be required more frequently, often annually. Recommend the following:
- Consult with the property owner about this system's maintenance and repair history
- Review any documentation available for this system
- Review inspection and maintenance requirements for this system
- That a qualified specialist evaluate, perform maintenance and make repairs if necessary
For more information, visit:http://www.reporthost.com/?SEPTIC
Based on visible equipment or information provided to the inspector, the water supply to this property appeared to be from a private well. Private well water supplies are specialty systems and are excluded from this inspection. Comments in this report related to this system are made as a courtesy only and are not meant to be a substitute for a full evaluation by a qualified specialist. The inspector does not test private well water for contamination or pollutants, determine if the supply and/or flow are adequate, or provide an estimate for remaining life of well pumps, pressure tanks or equipment. Only visible and accessible components are evaluated. Recommend the following:
- That a qualified well contractor fully evaluate the well, including a pump/flow test
- That the well water be tested per the client's concerns (coliforms, pH, contaminants, etc.)
- Research the well's history (how/when constructed, how/when maintained or repaired, past performance, past health issues)
- Document the current well capacity and water quality for future reference
For more information, visit:http://www.reporthost.com/?WELL
A water filtration system was installed on the premises. These are specialty systems and are excluded from this inspection. Comments in this report related to this system are made as a courtesy only and are not meant to be a substitute for a full evaluation by a qualified specialist. Filter cartridges typically need replacing periodically. Cleaning and other maintenance may also be needed. Recommend consulting with the property owner about this system to determine its condition, required maintenance, age, expected remaining life, etc. For more information, visit:http://www.reporthost.com/?WTRFLTR
Limitations: Evaluation of and determining the adequacy or completeness of the following items are not included in this inspection: water recirculation pumps; solar water heating systems; Energy Smart or energy saver controls; catch pan drains. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on water heaters, does not determine if water heaters are appropriately sized, or perform any evaluations that require a pilot light to be lit or a shut-off valve to be operated.
Condition of water heater: Appeared serviceable
Energy source: Oil
Capacity (in gallons): 50
Temperature-pressure relief valve installed: Yes
Location of water heater: Basement
Hot water temperature tested: No
Condition of burners: Appeared serviceable
Condition of venting system: Appeared serviceable
29) Safety, Repair/Replace
No drain line was installed for the temperature-pressure relief valve. This is a potential safety hazard due to the risk of scalding if someone is standing next to the water heater when the valve opens. Recommend that a qualified plumber install a drain line per standard building practices.
Heating, Ventilation and Air Condition (HVAC)
Limitations: The following items are not included in this inspection: humidifiers, dehumidifiers, electronic air filters; solar, coal or wood-fired heat systems; thermostat or temperature control accuracy and timed functions; heating components concealed within the building structure or in inaccessible areas; underground utilities and systems; safety devices and controls (due to automatic operation). Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on heating or cooling system components, does not determine if heating or cooling systems are appropriately sized, does not test coolant pressure, or perform any evaluations that require a pilot light to be lit, a shut-off valve to be operated, a circuit breaker to be turned "on" or a serviceman's or oil emergency switch to be operated. It is beyond the scope of this inspection to determine if furnace heat exchangers are intact and free of leaks. Condensation pans and drain lines may clog or leak at any time and should be monitored while in operation in the future. Where buildings contain furnishings or stored items, the inspector may not be able to verify that a heat source is present in all "liveable" rooms (e.g. bedrooms, kitchens and living/dining rooms).
General heating system type(s): Forced air
General heating distribution type(s): Ducts and registers
Last service date of primary heat source: 9/14. And 10/10
Source for last service date of primary heat source: Label
Condition of forced air heating/(cooling) system: Appeared serviceable
Forced air heating system fuel type: Oil
Location of forced air furnace: Basement
Condition of furnace filters: Required replacement
Condition of forced air ducts and registers: Appeared serviceable
Condition of burners: Appeared serviceable, Not determined (inaccessible, obscured)
Type of combustion air supply: No dedicated source visible, uses room air
Condition of venting system: Appeared serviceable
Condition of controls: Appeared serviceable
30) Safety, Repair/Maintain, Evaluate
The last service date of the gas or oil-fired forced air furnace appeared to be more than 1 year ago, or the inspector was unable to determine the last service date. Ask the property owner when it was last serviced. If unable to determine the last service date, or if this system was serviced more than 1 year ago, recommend that a qualified HVAC contractor inspect, clean, and service this system, and make repairs if necessary. For safety reasons, and because this system is fueled by gas or oil, this servicing should be performed annually in the future. Any needed repairs noted in this report should be brought to the attention of the HVAC contractor when it's serviced. For more information visit:http://www.reporthost.com/?ANFURINSP
Fireplaces, Stoves, Chimneys and Flues
Limitations: The following items are not included in this inspection: coal stoves, gas logs, chimney flues (except where visible). Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of drafting or sizing in fireplace and stove flues, and also does not determine if prefabricated or zero-clearance fireplaces are installed in accordance with the manufacturer's specifications. The inspector does not perform any evaluations that require a pilot light to be lit, and does not light fires. The inspector provides a basic visual examination of a chimney and any associated wood burning device. The National Fire Protection Association has stated that an in-depth Level 2 chimney inspection should be part of every sale or transfer of property with a wood-burning device. Such an inspection may reveal defects that are not apparent to the home inspector who is a generalist.
Condition of wood-burning fireplaces, stoves: Appeared serviceable
Wood-burning fireplace type: Masonry with metal liner
Condition of chimneys and flues: Required repair, replacement and/or evaluation (see comments below)
Wood-burning chimney type: Masonry
Gas-fired flue type: Not determined (obscured or inaccessible)
31) Safety, Repair/Replace
No spark screen or rain cap was installed at one or more chimney flue terminations. Spark screens reduce the chance of embers exiting the flue and causing fires. They also prevent wildlife (e.g. birds, rodents, raccoons) from entering flues. Rain caps prevent water from entering flues, mixing with combustion deposits and creating caustic chemicals which can corrode flues. They also prevent damage to masonry from freeze-thaw cycles and prevent metal components (e.g. dampers, metal firebox liners) from rusting. Recommend that a qualified person install rain caps with spark screens per standard building practices where missing.
Limitations: The following items are not included in this inspection: household appliances such as stoves, ovens, cook tops, ranges, warming ovens, griddles, broilers, dishwashers, trash compactors, refrigerators, freezers, ice makers, hot water dispensers and water filters; appliance timers, clocks, cook functions, self and/or continuous cleaning operations, thermostat or temperature control accuracy, and lights. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of the remaining life of appliances, and does not determine the adequacy of operation of appliances. The inspector does not note appliance manufacturers, models or serial numbers and does not determine if appliances are subject to recalls. Areas and components behind and obscured by appliances are inaccessible and excluded from this inspection.
Condition of counters: Required repair, replacement and/or evaluation (see comments below)
Condition of cabinets: Appeared serviceable
Condition of sinks and related plumbing: Required repair, replacement and/or evaluation (see comments below)
Condition of dishwasher: Appeared serviceable
Condition of range, cooktop or oven: Appeared serviceable
Range, cooktop or oven type: Electric
Type of ventilation: Hood or built into microwave over range or cooktop
Condition of refrigerator: Not determined
Condition of built-in microwave oven: N/A (none installed)
32) Repair/Replace, Evaluate -
The exhaust fan over the range recirculated the exhaust air back into the kitchen. This may be due to no duct being installed, baffles not being installed, or problems with duct work. This can be a nuisance for odor and grease accumulation. Where a gas-fired range or cook top is installed, carbon monoxide and excessive levels of moisture can accumulate in living spaces. Recommend that a qualified contractor evaluate and repair as necessary so exhaust air is ducted outdoors.
33) Repair/Replace -
Countertops and/or backsplashes were damaged or deteriorated. Recommend repairing or replacing as necessary.
34) Repair/Replace -
The kitchen sink drain pipe used an S-trap rather than a P-trap, or no P-trap was visible. Siphons and sudden flows of water in S-Traps can drain all the water out of the trap, leaving it dry. Sewer gases can then enter living areas. Recommend that a qualified plumber repair per standard building practices.
Water was leaking at the sink faucet base or handles. Recommend that a qualified plumber repair as necessary.
36) Minor Defect -
The light in the exhaust hood was inoperable. Recommend replacing light bulb(s) or that repairs be made by a qualified person if necessary.
Bathrooms, Laundry and Sinks
Limitations: The following items are not included in this inspection: overflow drains for tubs and sinks; heated towel racks, saunas, steam generators, clothes washers, clothes dryers. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of washing machine drain lines, washing machine catch pan drain lines, or clothes dryer exhaust ducts. The inspector does not operate water supply or shut-off valves for sinks, toilets, bidets, clothes washers, etc. due to the possibility of valves leaking or breaking when operated. The inspector does not determine if shower pans or tub and shower enclosures are water tight, or determine the completeness or operability of any gas piping to laundry appliances.
Location #A: Half bath, first floor
Location #B: Full bath, second floor
Condition of counters: Appeared serviceable
Condition of cabinets: Appeared serviceable
Condition of flooring: Required repairs, replacement and/or evaluation (see comments below)
Condition of sinks and related plumbing: Appeared serviceable
Condition of toilets: Appeared serviceable
Condition of bathtubs and related plumbing: Appeared serviceable
Condition of shower(s) and related plumbing: Appeared serviceable
Condition of ventilation systems: Required repair, replacement and/or evaluation (see comments below)
Bathroom and laundry ventilation type: Windows, Central exhaust fan
Gas supply for laundry equipment present: No
240 volt receptacle for laundry equipment present: Yes
The exhaust fan at location(s) #B was inoperable. Moisture may accumulate and result in mold, bacteria or fungal growth. Recommend that a qualified person clean, repair or replace fans as necessary.
Tile, stone and/or grout in the flooring at location(s) #A was deteriorated (e.g. loose or cracked tiles, missing grout) or substandard. Water can damage the sub-floor as a result. Recommend that a qualified contractor repair as necessary.
Interior, Doors and Windows
Limitations: The following items are not included in this inspection: security, intercom and sound systems; communications wiring; central vacuum systems; elevators and stair lifts; cosmetic deficiencies such as nail-pops, scuff marks, dents, dings, blemishes or issues due to normal wear and tear in wall, floor and ceiling surfaces and coverings, or in equipment; deficiencies relating to interior decorating; low voltage and gas lighting systems. Any comments made regarding these items are as a courtesy only. Note that the inspector does not evaluate any areas or items which require moving stored items, furnishings, debris, equipment, floor coverings, insulation or similar materials. The inspector does not test for asbestos, lead, radon, mold, hazardous waste, urea formaldehyde urethane, or any other toxic substance. Some items such as window, drawer, cabinet door or closet door operability are tested on a sampled basis. The client should be aware that paint may obscure wall and ceiling defects, floor coverings may obscure floor defects, and furnishings may obscure wall, floor and floor covering defects. If furnishings were present during the inspection, recommend a full evaluation of walls, floors and ceilings that were previously obscured when possible. Determining the cause and/or source of odors is not within the scope of this inspection.
Condition of exterior entry doors: Appeared serviceable
Exterior door material: Wood, Glass panel
Condition of interior doors: Appeared serviceable
Condition of windows and skylights: Appeared serviceable
Type(s) of windows: Vinyl, Wood, Metal, Multi-pane, Single-pane, Single-hung, Double-hung, Jalousie
Condition of walls and ceilings: Appeared serviceable
Wall type or covering: Drywall or plaster
Ceiling type or covering: Drywall or plaster
Condition of flooring: Appeared serviceable
Condition of concrete slab floor(s): Appeared serviceable
Flooring type or covering: Carpet, Vinyl, linoleum or marmoleum, Wood or wood products
Condition of stairs, handrails and guardrails: Repair/Replace
39) Safety, Repair/Maintain
Guardrails at one or more locations with drop-offs higher than 30 inches were wobbly, and pose a fall hazard. Recommend that a qualified person repair guardrails as necessary.
One or more windows that were designed to open and close were stuck shut and/or difficult to open and close. Recommend that a qualified person repair windows as necessary so they open and close easily.
Glass in one or more windows was cracked, broken and/or missing. Recommend that a qualified contractor replace glass where necessary.
42) Minor Defect
Minor cracks, nail pops and/or blemishes were found in walls and/or ceilings in one or more areas. Cracks and nail pops are common, are often caused by lumber shrinkage or minor settlement, and can be more or less noticeable depending on changes in humidity. They did not appear to be a structural concern, but the client may wish to repair these for aesthetic reasons. For recurring cracks, consider using an elastic crack covering product:http://www.reporthost.com/?ECC
The backyard fence was leaning and had partially separated from its support posts. Recommend a qualified contractor make any necessary repairs.
Stand alone heater in the 2nd floor bathroom was not functional.
Staining was noted in the toilet at the second floor bathroom.
Hudson Home Inspections, LLC.