Phone: (505) 913-7067
369 Montezuma Ave # 430
Santa Fe NM 87501-2835
Inspector: Erik Alstad
Property Inspection Report |
||Mark Kuykendall and Bruce Bullard
||34973 Hwy 285
New Mexico 87549
||Saturday, August 24, 2013
This report published on Monday, August 26, 2013 6:49:43 AM MDT
View report summary
This report is the exclusive property of this inspection company and the client(s) listed in the report title. Use of this report by any unauthorized persons is prohibited.
How to Read this Report
This report is organized by the property's functional areas. Within each functional area, descriptive information is listed first and is shown in bold type. Items of concern follow descriptive information.
Concerns are shown and sorted according to these types:
|Safety||Poses a safety hazard |
|Repair/Replace||Recommend repairing or replacing |
|Repair/Maintain||Recommend repair and/or maintenance |
|Minor Defect||Correction likely involves only a minor expense |
|Maintain||Recommend ongoing maintenance |
|Evaluate||Recommend evaluation by a specialist |
|Monitor||Recommend monitoring in the future |
|Comment||For your information |
Click here for a glossary of building construction terms.Contact your inspector If there are terms that you do not understand, or visit the glossary of construction terms at http://www.reporthost.com/glossary.asp
Report number: 402
Time started: 12:30
Time finished: 3:00
Present during inspection: Realtor
Weather conditions during inspection: Dry (no rain)
Temperature during inspection: Warm
Inspection fee: 567.98
Payment method: Check
Type of building: Single family
Buildings inspected: One house
Number of residential units inspected: 1
Age of main building:
Front of building faces: East
Main entrance faces: East
Evidence of rodent infestation was found in the form of feces, poison in the attic, above master bath. Consult with the property owner about this. A qualified person should make repairs to seal openings in the structure, set traps, and clean rodent waste as necessary.
Some areas and items at this property were obscured by furniture, stored items. This often includes but is not limited to walls, floors, windows, inside and under cabinets, under sinks, on counter tops, in closets, behind window coverings, under rugs or carpets, and under or behind furniture. Areas around the exterior, under the structure, in the garage and in the attic may also be obscured by stored items. The inspector in general does not move personal belongings, furnishings, carpets or appliances. When furnishings, stored items or debris are present, all areas or items that are obscured, concealed or not readily accessible are excluded from the inspection. The client should be aware that when furnishings, stored items or debris are eventually moved, damage or problems that were not noted during the inspection may be found.
Limitations: Unless specifically included in the inspection, the following items and any related equipment, controls, electric systems and/or plumbing systems are excluded from this inspection: detached buildings or structures; fences and gates; retaining walls; underground drainage systems, catch basins or concealed sump pumps; swimming pools and related safety equipment, spas, hot tubs or saunas; whether deck, balcony and/or stair membranes are watertight; trees, landscaping, properties of soil, soil stability, erosion and erosion control; ponds, water features, irrigation or yard sprinkler systems; sport courts, playground, recreation or leisure equipment; areas below the exterior structures with less than 3 feet of vertical clearance; invisible fencing; sea walls, docks and boathouses; retractable awnings. Any comments made regarding these items are as a courtesy only.
Site profile: Minor slope
Condition of driveway: Appeared serviceable
Driveway material: Dirt
Condition of deck, patio and/or porch covers: Appeared serviceable
Condition of decks, porches and/or balconies: Appeared serviceable
Deck, porch and/or balcony material: Concrete
Yard wall has minor stucco debonding on the east inside wall above window opening. Some minor cracks were also observed around window openings and other areas. It is advised these be sealed by a qualified stucco person.
Minor stucco cracks.
Erosion on the north and west side of the house, outside the master bedroom and other areas has resulted in the foundation insulation being exposed. It is advised this area be covered by replacing the eroded soil or other means.
A larger than normal crack in the front east side concrete deck was noted. This crack appears to be stable and does not present a tripping hazard. It is advised that this condition be monitored into the future.
Limitations: The inspector performs a visual inspection of accessible components or systems at the exterior. Items excluded from this inspection include below-grade foundation walls and footings; foundations, exterior surfaces or components obscured by vegetation, stored items or debris; wall structures obscured by coverings such as siding or trim. Some items such as siding, trim, soffits, vents and windows are often high off the ground, and may be viewed using binoculars from the ground or from a ladder. This may limit a full evaluation. Regarding foundations, some amount of cracking is normal in concrete slabs and foundation walls due to shrinkage and drying. Note that the inspector does not determine the adequacy of seismic reinforcement.
Wall inspection method: Viewed from ground
Condition of wall exterior covering: Appeared serviceable
Apparent wall structure: Wood frame
Wall covering: Stucco Elastimeric stucco
Apparent foundation type: Concrete slab on grade
Foundation/stem wall material: Not determined (inaccessible or obscured)
Footing material (under foundation stem wall): Not determined (inaccessible or obscured)
Bathroom vent on exterior of north wall is stuck in the open position. It is advised that this be repaired or replaced by qualified person.
Some minor stucco cracks (1/8" or less) were found in the south east corner were the yard wall meets the house, around portal beams, vigas, windows, doors and other areas on the house. It is advised these cracks be caulked or other wise sealed by a qualified contractor.
Minor stucco cracks.
Minor stucco cracks.
Portions of all exposed exterior wood (beams, vigas, columns, lintals etc.) need to be resealed or coated.
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; solar roofing components. Any comments made regarding these items are made as a courtesy only. Note that the inspector does not provide an estimate of remaining life on the roof surface material, nor guarantee that leaks have not occurred in the roof surface, skylights or roof penetrations in the past. Regarding roof leaks, only active leaks, visible evidence of possible sources of leaks, and evidence of past leaks observed during the inspection are reported on as part of this inspection. The inspector does not guarantee or warrant that leaks will not occur in the future. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high wind and rain, melting snow) would be needed to do so. Regarding the roof drainage system, unless the inspection was conducted during and after prolonged periods of heavy rain, the inspector was unable to determine if gutters, downspouts and extensions performed adequately or were leak-free.
Roof inspection method: Partially traversed
Condition of roof surface material: Appeared serviceable
Roof surface material: Metal panel
Roof type: Gable
One vent rain cap is missing on the west side near the ridge of the roof. It is advised this be replaced as soon as possible.
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; areas and components obscured by insulation. Any comments made regarding these items are made as a courtesy only. The inspector does not determine the adequacy of the attic ventilation system. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high/low temperatures, high/low humidity, high wind and rain, melting snow) would be needed to do so. The inspector is not a licensed engineer and does not determine the adequacy of roof structure components such as trusses, rafters or ceiling beams, or their spacing or sizing.
Attic inspection method: Partially traversed
Condition of roof structure: Appeared serviceable
Condition of insulation in attic (ceiling, skylight chase, etc.): Appeared serviceable
Ceiling insulation material: Fiberglass roll or batt
Approximate attic insulation R value (may vary in areas): R-30
Vapor retarder: Installed
Condition of roof ventilation: Appeared serviceable
Roof ventilation type: Gable end vents
The ceiling insulation in one or more areas of the attic was falling. Heating and cooling costs may be higher due to reduced energy efficiency. Recommend that a qualified person repair, replace or install insulation as necessary. This falling insulation is located over the kitchen area.
Insulation falling from ceiling in attic above kitchen.
One or more attic access hatches or doors were not insulated, or had substandard insulation. Weatherstripping was also missing or substandard. Recommend installing weatherstripping and insulation per current standards at hatches or doors for better energy efficiency.
The attic area above the master bedroom was not inspected. There was evidence of rodent infestation and rodent poison was spilled in and on the insulation making it dangerous to enter.
Limitations: The following items are not included in this inspection: generator systems, transfer switches, surge suppressors, inaccessible or concealed wiring; underground utilities and systems; low-voltage lighting or lighting on timers or sensors. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of grounding or bonding, if this system has an adequate capacity for the client's specific or anticipated needs, or if this system has any reserve capacity for additions or expansion. The inspector does not operate circuit breakers as part of the inspection, and does not install or change light bulbs. The inspector does not evaluate every wall switch or receptacle, but instead tests a representative number of them per various standards of practice. When furnishings, stored items or child-protective caps are present some receptacles are usually inaccessible and are not tested; these are excluded from this inspection. Receptacles that are not of standard 110 volt configuration, including 240-volt dryer receptacles, are not tested and are excluded. The functionality of, power source for and placement of smoke and carbon monoxide alarms is not determined as part of this inspection. Upon taking occupancy, proper operating and placement of smoke and carbon monoxide alarms should be verified and batteries should be changed. These devices have a limited lifespan and should be replaced every 10 years. The inspector attempts to locate and evaluate all main and sub-panels. However, panels are often concealed. If panels are found after the inspection, a qualified electrician should evaluate and repair if necessary. The inspector attempts to determine the overall electrical service size, but such estimates are not guaranteed because the overall capacity may be diminished by lesser-rated components in the system. Any repairs recommended should be made by a licensed electrician.
Electric service condition: Appeared serviceable
Primary service type: Underground
Number of service conductors: 3
Service voltage (volts): 120-240
Estimated service amperage: 200
Primary service overload protection type: Circuit breakers
Service entrance conductor material: Stranded aluminum
Main disconnect rating (amps): 200
System ground: Ground rod(s) in soil
Condition of main service panel: Appeared serviceable
Location of main service panel #A: Family room/ office
Location of main disconnect: Breaker at top of main service panel
Condition of branch circuit wiring: Serviceable
Branch circuit wiring type: Copper
Solid strand aluminum branch circuit wiring present: None visible
Ground fault circuit interrupter (GFCI) protection present: Yes
Arc fault circuit interrupter (AFCI) protection present: No
One or more ground fault circuit interrupter (GFCI) receptacles (outlets) wouldn't reset at the bathroom(s). This is a potential shock hazard. GFCI outlet in master bedroom is defective and reset button falls out. This GFCI also controls the outlet in the hall bedroom. Recommend that a qualified electrician evaluate and repair as necessary.
GFCI master bath not working.
No arc fault circuit interrupter (AFCI) breakers were installed for bedroom circuits. These are relatively new devices, and reduce the risk of fire by protecting against overheated or arcing receptacles (outlets) or light fixtures. Consult with a qualified electrician about upgrading circuits to AFCI protection per standard building practices.
One or more knockouts were missing from panel(s) #A. Holes in panels are a potential fire hazard if a malfunction ever occurs inside the panel. Rodents can also enter panels through holes. Recommend that a qualified person install knockout covers where missing and per standard building practices.
Kitchen recessed lighting has a dimmer switch but does not dim. It is advised that a qualified electrician evaluate this condition.
Limitations: The following items are not included in this inspection: private/shared wells and related equipment; private sewage disposal systems; hot tubs or spas; main, side and lateral sewer lines; gray water systems; pressure boosting systems; trap primers; incinerating or composting toilets; fire suppression systems; water softeners, conditioners or filtering systems; plumbing components concealed within the foundation or building structure, or in inaccessible areas such as below tubs; underground utilities and systems; overflow drains for tubs and sinks; backflow prevention devices. Any comments made regarding these items are as a courtesy only. Note that the inspector does not operate water supply or shut-off valves due to the possibility of valves leaking or breaking when operated. The inspector does not test for lead in the water supply, the water pipes or solder, does not determine if plumbing and fuel lines are adequately sized, and does not determine the existence or condition of underground or above-ground fuel tanks.
Condition of service and main line: Appeared serviceable
Water service: Private well
Condition of supply lines: Appeared serviceable
Supply pipe material: PEX plastic
Condition of drain pipes: Appeared serviceable
Drain pipe material: Plastic
Condition of waste lines: Not determined (inaccessible, obscured, or water service off)
Waste pipe material: Plastic
Vent pipe condition: Appeared serviceable
Vent pipe material: Plastic
Condition of fuel system: Appeared serviceable
Visible fuel storage systems: propane tank
Location of main fuel shut-off valve: At propane tank
Exterior water spigot on east wall near office/family room is loose. It is advised a qualified plumber evaluate this problem.
Based on visible components or information provided to the inspector, this property appeared to have a private sewage disposal (septic) system. These are specialty systems and are excluded from this inspection. Comments in this report related to this system are made as a courtesy only and are not meant to be a substitute for a full evaluation by a qualified specialist. Generally, septic tanks should be pumped and inspected every 3 years. Depending on the type of system and municipal regulations, inspection and maintenance may be required more frequently, often annually. Recommend the following:
- Consult with the property owner about this system's maintenance and repair history
- Review any documentation available for this system
- Review inspection and maintenance requirements for this system
- That a qualified specialist evaluate, perform maintenance and make repairs if necessary
Based on visible equipment or information provided to the inspector, the water supply to this property appeared to be from a private well. Private well water supplies are specialty systems and are excluded from this inspection. Comments in this report related to this system are made as a courtesy only and are not meant to be a substitute for a full evaluation by a qualified specialist. The inspector does not test private well water for contamination or pollutants, determine if the supply and/or flow are adequate, or provide an estimate for remaining life of well pumps, pressure tanks or equipment. Only visible and accessible components are evaluated. Recommend the following:
- That a qualified well contractor fully evaluate the well, including a pump/flow test
- That the well water be tested per the client's concerns (coliforms, pH, contaminants, etc.)
- Research the well's history (how/when constructed, how/when maintained or repaired, past performance, past health issues)
- Document the current well capacity and water quality for future reference
The inspector did not determine the location of the main water shut-off valve, or verify that a readily accessible shut-off valve in the building exists. Recommend consulting with the property owner to determine if a main shut-off valve exists, locating it yourself, or that a qualified plumber find it if necessary. If no readily accessible main shut-off valve is found in the building, then recommend that a qualified plumber install one so the water supply can be quickly turned off in the event of an emergency, such as when a supply pipe bursts.
Jetted tub in master bath was filled and appeared to work correctly. However the access panel across the front of the tub was caulked shut. The pump, plumbing and other mechanical parts were not able to be inspected.
Limitations: Evaluation of and determining the adequacy or completeness of the following items are not included in this inspection: water recirculation pumps; solar water heating systems; Energy Smart or energy saver controls; catch pan drains. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on water heaters, does not determine if water heaters are appropriately sized, or perform any evaluations that require a pilot light to be lit or a shut-off valve to be operated.
Condition of water heater: Appeared serviceable
Energy source: Propane
Capacity (in gallons): 40
Temperature-pressure relief valve installed: Yes
Location of water heater: Utility room
Limitations: The following items are not included in this inspection: humidifiers, dehumidifiers, electronic air filters; solar, coal or wood-fired heat systems; thermostat or temperature control accuracy and timed functions; heating components concealed within the building structure or in inaccessible areas; underground utilities and systems; safety devices and controls (due to automatic operation). Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on heating or cooling system components, does not determine if heating or cooling systems are appropriately sized, does not test coolant pressure, or perform any evaluations that require a pilot light to be lit, a shut-off valve to be operated, a circuit breaker to be turned "on" or a serviceman's or oil emergency switch to be operated. It is beyond the scope of this inspection to determine if furnace heat exchangers are intact and free of leaks. Condensation pans and drain lines may clog or leak at any time and should be monitored while in operation in the future. Where buildings contain furnishings or stored items, the inspector may not be able to verify that a heat source is present in all "liveable" rooms (e.g. bedrooms, kitchens and living/dining rooms).
General heating system type(s): Forced air
General heating distribution type(s): Ducts and registers
Condition of forced air heating/(cooling) system: May need to be serviced.
Forced air heating system fuel type: Propane
Location of forced air furnace: Exterior, back of house, outside laundry room.
Location for forced air filter(s): Behind return air grill(s) in laundry room
Condition of forced air ducts and registers: Required repair, replacement and/or evaluation (see comments below)
Cooling system and/or heat pump fuel type: Electric
Location: Outside on west side of house.
Type: Packaged unit
Condition of controls: Appeared serviceable
One or more heating or cooling air supply registers had a weak air flow. This may result in an inadequate air supply. Recommend asking the property owner about this. Adjustable damper(s) in ducts may exist and be reducing the flow. If dampers exist, then they should be opened to attempt to improve the air flow. If the property owner is unaware of such dampers, or if adjusting dampers does not improve the air flow, then recommend that a qualified HVAC contractor evaluate and repair or make modifications as necessary.
The estimated useful life for most forced air furnaces is 15-20 years. The inspector was unable to determine the age of the furnace. Be aware that this furnace may be near, at, or beyond its useful life and may need replacing or significant repairs at any time. Recommend attempting to determine the furnace's age (ask property owner or service technician), and budgeting for a replacement if necessary.
The estimated useful life for most heat pumps and air conditioning condensing units is 10-15 years. The inspector was unable to determine the age of this unit. Be aware that it may be near, at, or beyond its useful life and may need replacing or significant repairs at any time. Recommend attempting to determine the age (ask property owner or service technician), and budgeting for a replacement if necessary.
It is advised that the heating and cooling system and ducts be inspected by a qualified contractor to be sure the system is operating properly and for possible cleaning.
The current homeowner stated that the return register in the wall near the front door is not part of the existing heating and cooling system.
Limitations: The following items are not included in this inspection: coal stoves, gas logs, chimney flues (except where visible). Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of drafting or sizing in fireplace and stove flues, and also does not determine if prefabricated or zero-clearance fireplaces are installed in accordance with the manufacturer's specifications. The inspector does not perform any evaluations that require a pilot light to be lit, and does not light fires. The inspector provides a basic visual examination of a chimney and any associated wood burning device. The National Fire Protection Association has stated that an in-depth Level 2 chimney inspection should be part of every sale or transfer of property with a wood-burning device. Such an inspection may reveal defects that are not apparent to the home inspector who is a generalist.
One or more wood-burning fireplaces or stoves were found at the property. When such devices are used, they should be professionally inspected and cleaned annually to prevent creosote build-up and to determine if repairs are needed. It is advised that a qualified contractor evaluate this system.
Limitations: The following items are not included in this inspection: household appliances such as stoves, ovens, cook tops, ranges, warming ovens, griddles, broilers, dishwashers, trash compactors, refrigerators, freezers, ice makers, hot water dispensers and water filters; appliance timers, clocks, cook functions, self and/or continuous cleaning operations, thermostat or temperature control accuracy, and lights. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of the remaining life of appliances, and does not determine the adequacy of operation of appliances. The inspector does not note appliance manufacturers, models or serial numbers and does not determine if appliances are subject to recalls. Areas and components behind and obscured by appliances are inaccessible and excluded from this inspection.
Condition of counters: Appeared serviceable
Condition of cabinets: Appeared serviceable
Condition of under-sink food disposal: Appeared serviceable
Range, cooktop or oven type: Electric
Inspector did not fully inspect cabinet under kitchen sink because of excessive items stored in cabinet.
Limitations: The following items are not included in this inspection: overflow drains for tubs and sinks; heated towel racks, saunas, steam generators, clothes washers, clothes dryers. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of washing machine drain lines, washing machine catch pan drain lines, or clothes dryer exhaust ducts. The inspector does not operate water supply or shut-off valves for sinks, toilets, bidets, clothes washers, etc. due to the possibility of valves leaking or breaking when operated. The inspector does not determine if shower pans or tub and shower enclosures are water tight, or determine the completeness or operability of any gas piping to laundry appliances.
Inspector could not fully inspect cabinet under kitchen sink.
Location #A: Full bath, Master bath
Location #B: Full bath hall bath
Condition of counters: Appeared serviceable
Condition of cabinets: Appeared serviceable
Condition of flooring: Appeared serviceable
Condition of sinks and related plumbing: Appeared serviceable
Condition of toilets: Appeared serviceable
Condition of shower(s) and related plumbing: Appeared serviceable
Bathroom and laundry ventilation type: Spot exhaust fans
Gas supply for laundry equipment present: Yes
240 volt receptacle for laundry equipment present: Yes
Corrosion and scale on metal shower door frame in the master bedroom indicates it is nearing the end of its useful life. This may need to be replaced in the near future.
Corrosion and water damage to shower door master bath.
Significant corrosion or rust was found at the hall bathroom toilet supply valve. This can indicate past leaks, or that leaks are likely to occur in the future. Recommend that a qualified plumber repair as necessary. For example, by replacing valves or fittings.
Toilet water supply in hall bathroom shows signs of leaking.
There was no fresh air exhaust fan or operable window installed in the laundry room as required. It is advised that a qualified contractor evaluate and repair.
Limitations: The following items are not included in this inspection: security, intercom and sound systems; communications wiring; central vacuum systems; elevators and stair lifts; cosmetic deficiencies such as nail-pops, scuff marks, dents, dings, blemishes or issues due to normal wear and tear in wall, floor and ceiling surfaces and coverings, or in equipment; deficiencies relating to interior decorating; low voltage and gas lighting systems. Any comments made regarding these items are as a courtesy only. Note that the inspector does not evaluate any areas or items which require moving stored items, furnishings, debris, equipment, floor coverings, insulation or similar materials. The inspector does not test for asbestos, lead, radon, mold, hazardous waste, urea formaldehyde urethane, or any other toxic substance. Some items such as window, drawer, cabinet door or closet door operability are tested on a sampled basis. The client should be aware that paint may obscure wall and ceiling defects, floor coverings may obscure floor defects, and furnishings may obscure wall, floor and floor covering defects. If furnishings were present during the inspection, recommend a full evaluation of walls, floors and ceilings that were previously obscured when possible. Determining the cause and/or source of odors is not within the scope of this inspection.
Condition of exterior entry doors: Appeared serviceable. See notes and exceptions below.
Exterior door material: Wood
Condition of interior doors: Appeared serviceable
Condition of windows and skylights: Appeared serviceable
Type(s) of windows: Multi-pane, Double-hung
Condition of walls and ceilings: Appeared serviceable
Wall type or covering: Drywall
Ceiling type or covering: Drywall
Condition of flooring: Appeared serviceable
Condensation or staining was visible between multi-pane glass in the picture window in the office/family room (east wall). This usually indicates that the seal between the panes of glass has failed or that the desiccant material that absorbs moisture is saturated. As a result, the view through the window may be obscured, the window's R-value will be reduced, and accumulated condensation may leak into the wall structure below. Recommend that a qualified contractor evaluate and repair windows as necessary. Usually, this means replacing the glass in window frames.
Be aware that evidence of failed seals or desiccant may be more or less visible depending on the temperature, humidity, sunlight, etc. Windows or glass-paneled doors other than those that the inspector identified may also have failed seals and need glass replaced. It is beyond the scope of this inspection to identify every window with failed seals or desiccant.
The dead bolt in the office exterior door does not work. Recommend that a qualified person repair or replace as necessary.
Excessive debonding of paint and stucco on and around exterior laundry door, door frame and surrounding area on west wall. It is advised this be evaluated and repaired by a qualified contractor.
Paint and stucco debonding, exterior of laundry room door.
Paint and stucco debonding, exterior of laundry room door.
Your default report footer here...