This report is the exclusive property of this inspection company and the client(s) listed in the report title. Use of this report by any unauthorized persons is prohibited.
GOLDEN RULE HOME INSPECTIONS, LLCWebsite: http://www.reporthost.com/goldenrule
Phone: (928) 600-6491
4160 W Willis
Show Low AZ 85901-3228
Inspector: WILLIAM EASTMAN
Property Inspection Report
||1000 Some St
Lakeside, AZ 85929
||Thursday, April 06, 2017
This report published on Thursday, May 04, 2017 12:34:50 PM MDT
How to Read this Report
This report is organized by the property's functional areas. Within each functional area, descriptive information is listed first and is shown in bold type. Items of concern follow descriptive information.
Concerns are shown and sorted according to these types:
|Safety||Poses a safety hazard|
|Repair/Replace||Recommend repairing or replacing|
|Repair/Maintain||Recommend repair and/or maintenance|
|Minor Defect||Correction likely involves only a minor expense|
|Maintain||Recommend ongoing maintenance|
|Evaluate||Recommend evaluation by a specialist|
|Monitor||Recommend monitoring in the future|
|Serviceable||Item or component is in servicable condition|
|Comment||For your information|
Click here for a glossary of building construction terms.Contact your inspector If there are terms that you do not understand, or visit the glossary of construction terms at http://www.reporthost.com/glossary.asp
Time started: 11:00am
Weather conditions during inspection: Dry (no rain)
Inspection fee: 220
Payment method: Check
Type of building: Single family, Detached garage
Age of main building: Built 2005
Source for main building age: Realtor
Front of building faces: North
Occupied: Yes, Furniture or stored items were present
Some areas and items at this property were obscured by furniture and/or stored items. This often includes but is not limited to walls, floors, windows, inside and under cabinets, under sinks, on counter tops, in closets, behind window coverings, under rugs or carpets, and under or behind furniture. Areas around the exterior, under the structure, in the garage and in the attic may also be obscured by stored items. The inspector in general does not move personal belongings, furnishings, carpets or appliances. When furnishings, stored items or debris are present, all areas or items that are obscured, concealed or not readily accessible are excluded from the inspection. The client should be aware that when furnishings, stored items or debris are eventually moved, damage or problems that were not noted during the inspection may be found.
Limitations: Unless specifically included in the inspection, the following items and any related equipment, controls, electric systems and/or plumbing systems are excluded from this inspection: detached buildings or structures; fences and gates; retaining walls; underground drainage systems, catch basins or concealed sump pumps; swimming pools and related safety equipment, spas, hot tubs or saunas; whether deck, balcony and/or stair membranes are watertight; trees, landscaping, properties of soil, soil stability, erosion and erosion control; ponds, water features, irrigation or yard sprinkler systems; sport courts, playground, recreation or leisure equipment; areas below the exterior structures with less than 3 feet of vertical clearance; invisible fencing; sea walls, docks and boathouses; retractable awnings. Any comments made regarding these items are as a courtesy only.
Site profile: Moderate slope, Stairstepped
Condition of driveway: Appeared serviceable
Driveway material: Poured in place concrete, Gravel
Condition of sidewalks and/or patios: Appeared serviceable
Sidewalk material: Paving stones, Wood
Condition of deck, patio and/or porch covers: Appeared serviceable
Deck, patio, porch cover material and type: Covered (Refer to Roof section)
Condition of decks, porches and/or balconies: Appeared serviceable
Deck, porch and/or balcony material: Wood
Condition of stairs, handrails and guardrails: Appeared serviceable
Exterior stair material: Wood
The soil or grading sloped down towards building perimeters in one or more areas. This can result in water accumulating around building foundations or underneath buildings. At a minimum, monitor these areas, and areas under the structure in the future for accumulated water. If water does accumulate, recommend grading soil so it slopes down and away from buildings with a slope of at least 1 inch per horizontal foot for at least 6 feet out from buildings.
Exterior and Foundation
Limitations: The inspector performs a visual inspection of accessible components or systems at the exterior. Items excluded from this inspection include below-grade foundation walls and footings; foundations, exterior surfaces or components obscured by vegetation, stored items or debris; wall structures obscured by coverings such as siding or trim. Some items such as siding, trim, soffits, vents and windows are often high off the ground, and may be viewed using binoculars from the ground or from a ladder. This may limit a full evaluation. Regarding foundations, some amount of cracking is normal in concrete slabs and foundation walls due to shrinkage and drying. Note that the inspector does not determine the adequacy of seismic reinforcement.
Wall inspection method: Viewed from ground
Condition of wall exterior covering: Appeared serviceable
Apparent wall structure: Wood frame
Wall covering: Wood
Condition of foundation and footings: Appeared serviceable
Apparent foundation type: Crawl space, Concrete garage slab
Foundation/stem wall material: Concrete block
Footing material (under foundation stem wall): Poured in place concrete
Limitations: Structural components such as joists and beams, and other components such as piping, wiring and/or ducting that are obscured by under-floor insulation are excluded from this inspection. The inspector does not determine if support posts, columns, beams, joists, studs, trusses, etc. are of adequate size, spanning or spacing.
The inspector does not guarantee or warrant that water will not accumulate in the crawl spaces in the future. Complete access to all crawl space areas during all seasons and during prolonged periods of all types of weather conditions (e.g. heavy rain, melting snow) would be needed to do so.
The inspector attempts to locate all crawl space access points and areas. Access points may be obscured or otherwise hidden by furnishings or stored items. In such cases, the client should ask the property owner where all access points are that are not described in this inspection, and have those areas inspected. Note that crawl space areas should be checked at least annually for water intrusion, plumbing leaks and pest activity.
Crawl space inspection method: Traversed
Condition of floor substructure above: Appeared serviceable
Pier or support post material: Wood, Concrete block, Steel
Beam material: Built-up wood
Floor structure above: Engineered wood joists
Condition of insulation underneath floor above: Not applicable, none installed
Condition of vapor barrier: Not applicable, none installed
Condition of crawl space ventilation: Appeared serviceable
Ventilation type: Unconditioned space, with vents
3) Repair/Replace -
No under-floor insulation was installed in the crawl space. Recommend that a qualified person install insulation for better energy efficiency and per standard building practices. Typically this is R-19 rated fiberglass batt with the attached facing installed against the warm (floor) side.
4) Minor Defect
Cellulose material such as cardboard or paper was found in the crawl space. This is a conducive condition for wood-destroying organisms. Recommend removing all cellulose-based debris or stored items.
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; solar roofing components. Any comments made regarding these items are made as a courtesy only. Note that the inspector does not provide an estimate of remaining life on the roof surface material, nor guarantee that leaks have not occurred in the roof surface, skylights or roof penetrations in the past. Regarding roof leaks, only active leaks, visible evidence of possible sources of leaks, and evidence of past leaks observed during the inspection are reported on as part of this inspection. The inspector does not guarantee or warrant that leaks will not occur in the future. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high wind and rain, melting snow) would be needed to do so. Occupants should monitor the condition of roofing materials in the future. For older roofs, recommend that a professional inspect the roof surface, flashings, appurtenances, etc. annually and maintain/repair as might be required. If needed, the roofer should enter attic space(s). Regarding the roof drainage system, unless the inspection was conducted during and after prolonged periods of heavy rain, the inspector was unable to determine if gutters, downspouts and extensions perform adequately or are leak-free.
Roof inspection method: Traversed
Condition of roof surface material: Appeared serviceable
Roof surface material: Asphalt or fiberglass composition shingles, Rolled composition
Roof type: Gable, Hipped, Flat or low slope
Apparent number of layers of roof surface material: One
Condition of exposed flashings: Appeared serviceable
Condition of gutters, downspouts and extensions: Appeared serviceable
Attic and Roof Structure
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; areas and components obscured by insulation. Any comments made regarding these items are made as a courtesy only. The inspector does not determine the adequacy of the attic ventilation system. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high/low temperatures, high/low humidity, high wind and rain, melting snow) would be needed to do so. The inspector is not a licensed engineer and does not determine the adequacy of roof structure components such as trusses, rafters or ceiling beams, or their spacing or sizing.
Attic inspection method: Partially traversed
Condition of roof structure: Appeared serviceable
Roof structure type: Trusses
Ceiling structure: Trusses
Condition of insulation in attic (ceiling, skylight chase, etc.): Appeared serviceable
Ceiling insulation material: Fiberglass loose fill, Fiberglass roll or batt
Approximate attic insulation R value (may vary in areas): R-30
Vermiculite insulation present: None visible
Vapor retarder: None visible
Condition of roof ventilation: Appeared serviceable
Roof ventilation type: Ridge vent(s), Gable end vents, Enclosed soffit vents
One or more exhaust fan ducts in the attic were not attached to a vent hood or cap. As a result, conditioned air will enter the attic when the fan is operated. Ducts terminating near an attic vent but without a dedicated vent hood or cap will likely blow conditioned air back into the attic. This can result in excessive moisture in the attic. Recommend that a qualified contractor repair per standard building practices, so exhaust fan ducts are permanently fastened to vent hoods or caps.
6-1 - Above garage - two exhaust vents hung next to ridge vents
6-2 - Above bedroom - bathroom exhaust vent attached to gable vent
Cardboard baffles that are intended to keep insulation from blocking soffit vents in the attic were loose and had fallen down. Attic and/or roof structure ventilation can be reduced as a result. The service life for the roof surface materials can also be reduced because of high temperatures. Moisture from condensation is also likely to accumulate in the roof structure and/or attic and can be a conducive condition for wood-destroying organisms. Recommend that a qualified person repair or reattach baffles as necessary.
Garage or Carport
Limitations: The inspector does not determine the adequacy of firewall ratings. Requirements for ventilation in garages vary between municipalities.
Condition of door between garage and house: Appeared serviceable
Type of door between garage and house: Hollow core
Condition of garage vehicle door(s): Appeared serviceable
Type of garage vehicle door: Sectional
Number of vehicle doors: 1
Condition of automatic opener(s): Appeared serviceable
Mechanical auto-reverse operable (reverses when meeting reasonable resistance during closing): Yes
Condition of garage floor: Appeared serviceable
Condition of garage interior: Appeared serviceable
Garage ventilation: None visible, Only window
9) Safety, Repair/Replace
The door between the garage and the house did not appear to be fire resistant, or the inspector was unable to verify that it was via a label. This is a potential safety hazard. House to garage doors, to prevent fire and fumes from spreading from the garage into interior living space, should be constructed of fire-resistant materials. Doors, generally considered to be suitable for the purpose, are solid core wood, steel, honeycomb steel or a door that has been factory labeled as fire rated. Recommend that a qualified contractor replace or repair the door and, at that time, make any other corrections that might be required to provide suitable fire resistance between the garage and the dwelling per standard building practices. For more information, visit:http://www.reporthost.com/?AGFR
Also recommend installing self closing hinges
10) Repair/Maintain, Evaluate
One or more gas-fired appliances were installed in the garage, and no combustion air vent was visible. This can result in inadequate combustion air for the appliance(s), reduced efficiency, and possible safety issues related to carbon monoxide poisoning. Recommend that a qualified person evaluate further and repair per standard building practices. For example, by installing one or more vents.
Limitations: The following items are not included in this inspection: generator systems, transfer switches, surge suppressors, inaccessible or concealed wiring; underground utilities and systems; low-voltage lighting or lighting on timers or sensors. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of grounding or bonding, if this system has an adequate capacity for the client's specific or anticipated needs, or if this system has any reserve capacity for additions or expansion. The inspector does not operate circuit breakers as part of the inspection, and does not install or change light bulbs. The inspector does not evaluate every wall switch or receptacle, but instead tests a representative number of them per various standards of practice. When furnishings, stored items or child-protective caps are present some receptacles are usually inaccessible and are not tested; these are excluded from this inspection. Receptacles that are not of standard 110 volt configuration, including 240-volt dryer receptacles, are not tested and are excluded. The functionality of, power source for and placement of smoke and carbon monoxide alarms is not determined as part of this inspection. Upon taking occupancy, proper operating and placement of smoke and carbon monoxide alarms should be verified and batteries should be changed. These devices have a limited lifespan and should be replaced every 10 years. The inspector attempts to locate and evaluate all main and sub-panels. However, panels are often concealed. If panels are found after the inspection, a qualified electrician should evaluate and repair if necessary. The inspector attempts to determine the overall electrical service size, but such estimates are not guaranteed because the overall capacity may be diminished by lesser-rated components in the system. Any repairs recommended should be made by a licensed electrician.
Electric service condition: Appeared serviceable
Primary service type: Overhead
Number of service conductors: 3
Service voltage (volts): 120-240
Estimated service amperage: 200
Primary service overload protection type: Circuit breakers
Service entrance conductor material: Stranded copper
Main disconnect rating (amps): 200
System ground: Ground rod(s) in soil
Condition of main service panel: Appeared serviceable
Condition of sub-panel(s): Required repair, replacement and/or evaluation (see comments below)
Location of main service panel #A: Building exterior
Location of sub-panel #C: Shop
Location of main disconnect: Breaker at top of main service panel
Condition of branch circuit wiring: Serviceable
Branch circuit wiring type: Non-metallic sheathed
Solid strand aluminum branch circuit wiring present: None visible
Ground fault circuit interrupter (GFCI) protection present: Yes
Arc fault circuit interrupter (AFCI) protection present: No
11) Safety, Repair/Replace, Evaluate
Substandard wiring was found at the building exterior. For example, exposed wiring. This is a safety hazard. Recommend that a qualified electrician evaluate and repair as necessary and per standard building practices.
Under deck for exterior outlet
12) Safety, Repair/Replace
Neutral and equipment ground wires were bonded (connected) at sub-panel(s) # C. This should only occur in the main service panel, not sub-panels, and is a shock hazard. Neutral wires should be attached to a "floating" neutral bar not bonded to the panel, and grounding wires should be attached to a separate grounding bar bonded to the sub-panel. Recommend that a qualified electrician repair per standard building practices. For more information, visit:http://www.reporthost.com/?SUBGRND
13) Safety, Repair/Replace
One or more cover plates installed outside were not rated for exterior use. This is a potential shock and fire hazard. Recommend that a qualified electrician repair per standard building practices.
under eave on north side - heat strip for sat dish
14) Safety, Comment
The functionality of, power source for and placement of smoke alarms is not determined as part of this inspection. Smoke alarms should be installed in each bedroom, in hallways leading to bedrooms, on each level and in attached garages. They have a limited lifespan and should be replaced every 10 years. For home buyers, batteries in smoke alarms should be changed when taking occupancy. Batteries should be replaced annually in the future. Carbon monoxide alarms should be installed in the vicinity of sleeping areas and on each level. For more information, visit:http://www.reporthost.com/?SMKALRMhttp://www.reporthost.com/?COALRM
Floor outlet in living room should have cover to prevent contamination and/or moisture from contaminating the outlet.
The service drop wires were in contact with trees or vegetation. This can result in damage to wiring insulation or broken wires during high winds. Recommend pruning trees or vegetation as necessary. The utility company may prune trees at no charge.
One or more switches were taped so that they're inoperable. Consult with the property owner regarding this. If necessary, recommend that a qualified electrician repair.
Per owner, this switch has never been operational and no wires are attached.
Plumbing / Fuel Systems
Limitations: The following items are not included in this inspection: private/shared wells and related equipment; private sewage disposal systems; hot tubs or spas; main, side and lateral sewer lines; gray water systems; pressure boosting systems; trap primers; incinerating or composting toilets; fire suppression systems; water softeners, conditioners or filtering systems; plumbing components concealed within the foundation or building structure, or in inaccessible areas such as below tubs; underground utilities and systems; overflow drains for tubs and sinks; backflow prevention devices. Any comments made regarding these items are as a courtesy only. Note that the inspector does not operate water supply or shut-off valves due to the possibility of valves leaking or breaking when operated. The inspector does not test for lead in the water supply, the water pipes or solder, does not determine if plumbing and fuel lines are adequately sized, and does not determine the existence or condition of underground or above-ground fuel tanks.
Condition of service and main line: Appeared serviceable
Water service: Community well
Water pressure (psi): 50
Location of main water shut-off: Building exterior, At meter
Condition of supply lines: Appeared serviceable
Supply pipe material: Copper, PEX plastic
Condition of drain pipes: Appeared serviceable
Drain pipe material: Plastic
Condition of waste lines: Appeared serviceable
Waste pipe material: Plastic
Vent pipe condition: Appeared serviceable
Vent pipe material: Plastic
Sump pump installed: None visible
Sewage ejector pump installed: None visible
Condition of fuel system: Appeared serviceable
Visible fuel storage systems: None visible
Location of main fuel shut-off valve: At gas meter
19) Repair/Replace, Evaluate
The copper water service pipe was embedded in concrete or masonry where it was routed through the foundation, and no protection from damage due to thermal expansion was visible. Copper pipes embedded in concrete or masonry should be wrapped with an approved tape or installed through a sleeve for abrasion and corrosion protection. Recommend that a qualified contractor evaluate further to verify that no tape or sleeve is installed, and repair per standard building practices if necessary.
20) Repair/Maintain, Evaluate -
Based on visible equipment or information provided to the inspector, this property appeared to have a yard irrigation (sprinkler) system. These are specialty systems and are excluded from this inspection. Comments in this report related to this system are made as a courtesy only and are not meant to be a substitute for a full evaluation by a qualified specialist. When this system is operated, recommend verifying that water is not directed at building exteriors, or directed so water accumulates around building foundations. Sprinkler heads may need to be adjusted, replaced or disabled. Consider having a qualified plumber verify that a backflow prevention device is installed per standard building practices to prevent cross-contamination of potable water. Recommend that a qualified specialist evaluate the irrigation system for other defects (e.g. leaks, damaged or malfunctioning sprinkler heads) and repair if necessary.
A water softener system was installed on the premises. These are specialty systems and are excluded from this inspection. Comments in this report related to this system are made as a courtesy only and are not meant to be a substitute for a full evaluation by a qualified specialist. Water softeners typically work by removing unwanted minerals (e.g. calcium, magnesium) from the water supply. They prevent build-up of scale inside water supply pipes, improve lathering while washing, and prevent spots on dishes. Recommend consulting with the property owner about this system to determine its condition, required maintenance, age, expected remaining life, etc. For more information, visit:http://www.reporthost.com/?WTRSFThttp://www.reporthost.com/?HRDWTR
Limitations: Evaluation of and determining the adequacy or completeness of the following items are not included in this inspection: water recirculation pumps; solar water heating systems; Energy Smart or energy saver controls; catch pan drains. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on water heaters, does not determine if water heaters are appropriately sized, or perform any evaluations that require a pilot light to be lit or a shut-off valve to be operated.
Condition of water heater: Appeared serviceable
Energy source: Natural gas
Capacity (in gallons): 50
Temperature-pressure relief valve installed: Yes
Location of water heater: Garage
Hot water temperature tested: Yes
Water temperature (degrees Fahrenheit): 130
Condition of burners: Appeared serviceable
Condition of venting system: Appeared serviceable
22) Safety, Repair/Replace
One or more flexible connectors were used for the temperature-pressure relief valve drain line. Flex connectors can be bent or kinked so as to restrict the flow of the drain line and impair the operation of the valve. They typically are not rated for the temperature and pressure of water being discharged (potentially 150 psi and 210 degrees F). Flex connectors used this way pose a potential safety hazard for explosion. Recommend that a qualified plumber repair per standard building practices. For example, by installing a drain line made of rigid copper or CPVC plastic pipe.
The hot water temperature was greater than 120 degrees Fahrenheit. This is a safety hazard due to the risk of scalding. The thermostat should be adjusted so the water temperature doesn't exceed 120 degrees. If the water heater is powered by electricity, a qualified person should perform the adjustment, since covers that expose energized equipment normally need to be removed. For more information on scalding dangers, visit:http://www.reporthost.com/?SCALD
MFR DATE 06.2012
Heating, Ventilation and Air Condition (HVAC)
Limitations: The following items are not included in this inspection: humidifiers, dehumidifiers, electronic air filters; solar, coal or wood-fired heat systems; thermostat or temperature control accuracy and timed functions; heating components concealed within the building structure or in inaccessible areas; underground utilities and systems; safety devices and controls (due to automatic operation). Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on heating or cooling system components, does not determine if heating or cooling systems are appropriately sized, does not test coolant pressure, or perform any evaluations that require a pilot light to be lit, a shut-off valve to be operated, a circuit breaker to be turned "on" or a serviceman's or oil emergency switch to be operated. It is beyond the scope of this inspection to determine if furnace heat exchangers are intact and free of leaks. Condensation pans and drain lines may clog or leak at any time and should be monitored while in operation in the future. Where buildings contain furnishings or stored items, the inspector may not be able to verify that a heat source is present in all "liveable" rooms (e.g. bedrooms, kitchens and living/dining rooms).
General heating system type(s): Forced air, Gas fireplace or stove
General heating distribution type(s): Ducts and registers
Last service date of primary heat source: Fall 2016
Source for last service date of primary heat source: Property owner
Condition of forced air heating/(cooling) system: Appeared serviceable
Forced air heating system fuel type: Natural gas
Estimated age of forced air furnace: 16 years
Location of forced air furnace: Crawl space
Forced air system capacity in BTUs or kilowatts: 75,000 BTU
Condition of furnace filters: Required replacement
Location for forced air filter(s): Behind return air grill(s), Hall ceiling
Condition of forced air ducts and registers: Appeared serviceable
Condition of burners: Appeared serviceable
Type of combustion air supply: Intake duct
Condition of venting system: Appeared serviceable
Recommend that home buyers replace or clean HVAC filters upon taking occupancy depending on the type of filters installed. Regardless of the type, recommend checking filters monthly in the future and replacing or cleaning them as necessary. How frequently they need replacing or cleaning depends on the type and quality of the filter, how the system is configured (e.g. always on vs. "Auto"), and on environmental factors (e.g. pets, smoking, frequency of house cleaning, number of occupants, the season).
The estimated useful life for most forced air furnaces is 15-20 years. This furnace appeared to be near this age and/or its useful lifespan and may need replacing or significant repairs at any time. Recommend budgeting for a replacement in the near future.
Manufactured June 2001 (16 yrs) per http://www.buildingcenter.org/ruud-hvac
Measured heat rise approximately 35 degrees Fahrenheit
Fireplaces, Stoves, Chimneys and Flues
Limitations: The following items are not included in this inspection: coal stoves, gas logs, chimney flues (except where visible). Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of drafting or sizing in fireplace and stove flues, and also does not determine if prefabricated or zero-clearance fireplaces are installed in accordance with the manufacturer's specifications. The inspector does not perform any evaluations that require a pilot light to be lit, and does not light fires. The inspector provides a basic visual examination of a chimney and any associated wood burning device. The National Fire Protection Association has stated that an in-depth Level 2 chimney inspection should be part of every sale or transfer of property with a wood-burning device. Such an inspection may reveal defects that are not apparent to the home inspector who is a generalist.
Condition of gas-fired fireplaces or stoves: Appeared serviceable
Gas fireplace or stove type: Metal pre-fab fireplace
Condition of chimneys and flues: Appeared serviceable
Gas-fired flue type: B-vent
27) Safety, Repair/Maintain
One or more sections of B-vent or L-vent metal flue pipe were too close to combustible materials and/or insulation. This type of vent requires a minimum of 1 inch clearance to such materials. This is a fire hazard. Recommend that a qualified person repair as necessary. For example, by moving insulation, moving the flue pipe, installing a shield or making modifications to surrounding structures.
Water heater vent pipe above garage
Limitations: The following items are not included in this inspection: household appliances such as stoves, ovens, cook tops, ranges, warming ovens, griddles, broilers, dishwashers, trash compactors, refrigerators, freezers, ice makers, hot water dispensers and water filters; appliance timers, clocks, cook functions, self and/or continuous cleaning operations, thermostat or temperature control accuracy, and lights. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of the remaining life of appliances, and does not determine the adequacy of operation of appliances. The inspector does not note appliance manufacturers, models or serial numbers and does not determine if appliances are subject to recalls. Areas and components behind and obscured by appliances are inaccessible and excluded from this inspection.
Condition of counters: Appeared serviceable
Condition of cabinets: Appeared serviceable
Condition of sinks and related plumbing: Appeared serviceable
Condition of under-sink food disposal: Appeared serviceable
Condition of dishwasher: Appeared serviceable
Condition of range, cooktop or oven: Appeared serviceable
Range, cooktop or oven type: Electric
Type of ventilation: Hood or built into microwave over range or cooktop
Condition of refrigerator: Appeared serviceable
Condition of built-in microwave oven: Appeared serviceable
28) Safety, Repair/Replace
The range could tip forward. An anti-tip bracket may not be installed. This is a potential safety hazard since the range can tip forward when weight is applied to the open door, such as when a small child climbs on it or if heavy objects are dropped on it. Anti-tip brackets have been sold with all free-standing ranges since 1985. Recommend installing an anti-tip bracket to eliminate this safety hazard. For more information, visit:http://www.reporthost.com/?ATB
29) Repair/Replace, Evaluate
The exhaust fan over the range recirculated the exhaust air back into the kitchen. This may be due to no duct being installed, baffles not being installed, or problems with duct work. This can be a nuisance for odor and grease accumulation. Where a gas-fired range or cook top is installed, carbon monoxide and excessive levels of moisture can accumulate in living spaces. Recommend that a qualified contractor evaluate and repair as necessary so exhaust air is ducted outdoors.
Bathrooms, Laundry and Sinks
Limitations: The following items are not included in this inspection: overflow drains for tubs and sinks; heated towel racks, saunas, steam generators, clothes washers, clothes dryers. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of washing machine drain lines, washing machine catch pan drain lines, or clothes dryer exhaust ducts. The inspector does not operate water supply or shut-off valves for sinks, toilets, bidets, clothes washers, etc. due to the possibility of valves leaking or breaking when operated. The inspector does not determine if shower pans or tub and shower enclosures are water tight, or determine the completeness or operability of any gas piping to laundry appliances.
Location #A: Full bath, east
Location #B: Full bath, Master bath, west
Location #C: Laundry room/area
Condition of counters: Appeared serviceable
Condition of cabinets: Appeared serviceable
Condition of flooring: Appeared serviceable, Tile
Condition of sinks and related plumbing: Appeared serviceable
Condition of toilets: Appeared serviceable
Condition of bathtubs and related plumbing: Appeared serviceable
Condition of shower(s) and related plumbing: Appeared serviceable
Condition of ventilation systems: Appeared serviceable
Bathroom and laundry ventilation type: Windows, Spot exhaust fans
Gas supply for laundry equipment present: Yes
240 volt receptacle for laundry equipment present: No
Caulk was missing around the base of the bathtub spout, or there was a gap behind it, at location(s) #A. Water may enter the wall structure behind the bathtub. Recommend that a qualified person repair as necessary to eliminate the gap. For example, by installing or replacing caulk if the gap is small enough. For larger gaps, a shorter spout nipple or an escutcheon plate can be installed.
Tile and/or grout in the bathtub surround at location(s) #B was deteriorated (e.g. loose or cracked tiles, missing grout) or substandard. Water can damage the wall structure as a result. Recommend that a qualified contractor repair as necessary.
Gaps, no caulk, or substandard caulking were found between the shower enclosure and the floor at location(s) #B. Water can penetrate these areas and cause damage. Recommend that a qualified person re-caulk or install caulking as necessary.
Gaps, no caulk, or substandard caulking were found between countertops and backsplashes at location(s) #B. Water can penetrate these areas and cause damage. Recommend that a qualified person repair as necessary. For example, by installing or replacing caulk.
Left vanity in MBR
Substandard caulking or grout was found between the bathtub and the floor at location (A). Water may penetrate these areas and cause damage. Recommend that a qualified person re-caulk or re-grout as necessary.
Interior, Doors and Windows
Limitations: The following items are not included in this inspection: security, intercom and sound systems; communications wiring; central vacuum systems; elevators and stair lifts; cosmetic deficiencies such as nail-pops, scuff marks, dents, dings, blemishes or issues due to normal wear and tear in wall, floor and ceiling surfaces and coverings, or in equipment; deficiencies relating to interior decorating; low voltage and gas lighting systems. Any comments made regarding these items are as a courtesy only. Note that the inspector does not evaluate any areas or items which require moving stored items, furnishings, debris, equipment, floor coverings, insulation or similar materials. The inspector does not test for asbestos, lead, radon, mold, hazardous waste, urea formaldehyde urethane, or any other toxic substance. Some items such as window, drawer, cabinet door or closet door operability are tested on a sampled basis. The client should be aware that paint may obscure wall and ceiling defects, floor coverings may obscure floor defects, and furnishings may obscure wall, floor and floor covering defects. If furnishings were present during the inspection, recommend a full evaluation of walls, floors and ceilings that were previously obscured when possible. Determining the cause and/or source of odors is not within the scope of this inspection.
Condition of exterior entry doors: Appeared serviceable
Exterior door material: Metal, Sliding glass
Condition of interior doors: Appeared serviceable
Condition of windows and skylights: Appeared serviceable
Type(s) of windows: Metal, Multi-pane, Sliding, Single-hung
Condition of walls and ceilings: Appeared serviceable
Wall type or covering: Drywall
Ceiling type or covering: Drywall, Wood
Condition of flooring: Appeared serviceable
Flooring type or covering: Carpet, Wood or wood products, Tile
One or more interior doors wouldn't latch or were difficult to latch. Recommend that a qualified person repair as necessary. For example, by adjusting latch plates or locksets.
BR 2, 3 and Master Bath
Proudly serving Show Low, Pinetop-Lakeside and the surrounding White Mountains communities. *** AZ License #61673