This report is the exclusive property of this inspection company and the client(s) listed in the report title. Use of this report by any unauthorized persons is prohibited.
2816 Charleston St NE
Albuquerque NM 87110-2702
Inspector: Henry Schichtel
Property Inspection Report
||Friday, April 22, 2016
This report published on Monday, May 09, 2016 9:11:00 PM MDT
How to Read this Report
This report is organized by the property's functional areas. Within each functional area, descriptive information is listed first and is shown in bold type. Items of concern follow descriptive information.
Concerns are shown and sorted according to these types:
|Safety||Poses a safety hazard|
|Major Defect||Correction likely involves a significant expense|
|Repair/Replace||Recommend repairing or replacing|
|Repair/Maintain||Recommend repair and/or maintenance|
|Maintain||Recommend ongoing maintenance|
|Evaluate||Recommend evaluation by a specialist|
|Monitor||Recommend monitoring in the future|
|Comment||For your information|
Click here for a glossary of building construction terms.Contact your inspector If there are terms that you do not understand, or visit the glossary of construction terms at http://www.reporthost.com/glossary.asp
Time started: 2:50
Time finished: 4:30
Present during inspection: Client
Client present for discussion at end of inspection: No
Weather conditions during inspection: Dry (no rain), Sunny
Temperature during inspection: Warm, 81 degrees
Inspection fee: 0.00
Payment method: Check
Type of building: Townhouse
Buildings inspected: One condominium unit
Number of residential units inspected: 1
Age of main building: 1985
Source for main building age: Client
Front of building faces: North
Main entrance faces: North
Limitations: Unless specifically included in the inspection, the following items and any related equipment, controls, electric systems and/or plumbing systems are excluded from this inspection: detached buildings or structures; fences and gates; retaining walls; underground drainage systems, catch basins or concealed sump pumps; swimming pools and related safety equipment, spas, hot tubs or saunas; whether deck, balcony and/or stair membranes are watertight; trees, landscaping, properties of soil, soil stability, erosion and erosion control; ponds, water features, irrigation or yard sprinkler systems; sport courts, playground, recreation or leisure equipment; areas below the exterior structures with less than 3 feet of vertical clearance; invisible fencing; sea walls, docks and boathouses; retractable awnings. Any comments made regarding these items are as a courtesy only.
Site profile: Level
Condition of driveway: Appeared serviceable
Driveway material: Poured in place concrete
Exterior and Foundation
Limitations: The inspector performs a visual inspection of accessible components or systems at the exterior. Items excluded from this inspection include below-grade foundation walls and footings; foundations, exterior surfaces or components obscured by vegetation, stored items or debris; wall structures obscured by coverings such as siding or trim. Some items such as siding, trim, soffits, vents and windows are often high off the ground, and may be viewed using binoculars from the ground or from a ladder. This may limit a full evaluation. Regarding foundations, some amount of cracking is normal in concrete slabs and foundation walls due to shrinkage and drying. Note that the inspector does not determine the adequacy of seismic reinforcement.
Wall inspection method: Viewed from ground
Condition of wall exterior covering: Required repairs, replacement and/or evaluation (see comments below)
Apparent wall structure: Wood frame
Wall covering: Stucco
Apparent foundation type: Concrete slab on grade
2) Repair/Replace, Comment
Flashing at one or more locations was substandard. Leaks can occur as a result. Recommend that a qualified person repair, replace or install flashing as necessary, and per standard building practices.
Flashing type undetermined at second story deck around walls. Flashing can be seen under door threshold. Flashings need to be installed around all deck areas (especially with roof material underneath) to shed water away from structure.
3) Repair/Maintain, Evaluate
Moderate cracks (1/8 inch - 3/4 inch) and/or leaning were found in the foundation. This may be a structural concern or an indication that settlement is ongoing. The client should consider hiring qualified contractors and/or engineers as necessary for further evaluation. Such contractors may include:
- Foundation repair contractors who may prescribe repairs, and will give cost estimates for such repairs
- Masonry contractors who repair and/or replace brick veneer
- Geotechnical engineers who attempt to determine if settlement is ongoing, and the cause of the settlement
- Structural engineers who determine if repairs are necessary, and prescribe those repairs
At a minimum, recommend sealing cracks to prevent water infiltration. Numerous products exist to seal such cracks including hydraulic cement, resilient caulks and epoxy sealants.
further cracking was witnessed along the tiles. See other picture.
4) Repair/Maintain, Evaluate
Roof structure located under the second story deck to not shedding water adequately and is collecting dirt and debris. This condition will cause the roof materials to deteriorate at an accelerated rate. The situation can be greatly avoided by repairing the open skylight area in roof (see in other section). Recommend cleaning and further evaluation after roof repairs.
Cracks, deterioration and/or damage were found in one or more areas of the exterior stucco finish. In damp climates, moisture can enter cracks or damaged areas and further deteriorate the stucco. Also the wall behind the stucco can become damaged from moisture. Note that areas behind the stucco are inaccessible and excluded from this inspection. Recommend that a qualified contractor repair or replace stucco as necessary.
Vegetation such as trees, shrubs and/or vines was in contact with or close to the building exterior. Vegetation can serve as a pathway for wood-destroying insects and can retain moisture against the exterior after it rains. This is a conducive condition for wood-destroying organisms. Recommend pruning, moving or removing vegetation as necessary to maintain at least 6 inches of space between it and the building exterior. A 1-foot clearance is better.
8) Evaluate, Monitor
It was difficult to determine whether or not one or more windows or doors were installed with "drip cap" or "Z" flashings installed above them. Better building practices call for such flashings, which greatly reduce the chance of leaks above windows and doors. Without this flashing, caulk and paint must be maintained or water can enter the wall structure and cause rot and possible structural damage. Depending on the exposure (e.g. roof overhang, height of exterior wall, direction of prevailing rain) this may or may not be an issue. The client should monitor these areas in the future and maintain caulk and paint as necessary. Consult with a qualified contractor about installing flashings where needed, and per standard building practices. Note that when trim or siding is removed to install flashing, damaged wood may be found and additional repairs may be needed.
Railing for second floor deck are too far apart for child safety. At this spacing smaller children can fit through and therefore may fall. Recommend reattaching upright railing with a spacing no more than 4".
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; solar roofing components. Any comments made regarding these items are made as a courtesy only. Note that the inspector does not provide an estimate of remaining life on the roof surface material, nor guarantee that leaks have not occurred in the roof surface, skylights or roof penetrations in the past. Regarding roof leaks, only active leaks, visible evidence of possible sources of leaks, and evidence of past leaks observed during the inspection are reported on as part of this inspection. The inspector does not guarantee or warrant that leaks will not occur in the future. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high wind and rain, melting snow) would be needed to do so. Occupants should monitor the condition of roofing materials in the future. For older roofs, recommend that a professional inspect the roof surface, flashings, appurtenances, etc. annually and maintain/repair as might be required. If needed, the roofer should enter attic space(s). Regarding the roof drainage system, unless the inspection was conducted during and after prolonged periods of heavy rain, the inspector was unable to determine if gutters, downspouts and extensions perform adequately or are leak-free.
Roof inspection method: Traversed
Condition of roof surface material: Appeared serviceable
Roof surface material: Built up tar and felt, Synthetic plasticized or rubberized single-ply membrane
Roof type: Flat or low slope
Condition of exposed flashings: Not determined (inaccessible or obscured), Covered
Condition of gutters, downspouts and extensions: Appeared serviceable
10) Repair/Replace, Evaluate
The outer corner of the lower front roof structure seems to be missing some roofing tile, or possibly the tile has moved. This condition has left a portion off the roof structure and eaves to be unprotected from water and pest intrusion. Recommend replacing/fixing tiles.
12) Repair/Replace -
Gutters were missing over one or more entrances. People entering and exiting the building are likely to get wet during periods of rain as a result. Most buildings benefit from having a complete drainage system installed, but at a minimum, recommend installing gutters over entrances.
13) Repair/Replace -
Glass in one or more skylights was cracked, broken and/or missing. Recommend that a qualified contractor replace glass as necessary.
14) Maintain, Monitor, Comment
Alligatoring, crazing, fissures and/or cracks in the sealant were found in one or more areas of the parapet vents. This is often caused by exposure to ultraviolet light (the sun), and eventually results in water penetrating the underlying roof membrane and causing leaks. This is a conducive condition for wood-destroying organisms. Recommend that a qualified contractor evaluate and repair as necessary.
16) Evaluate, Comment
Evidence of ponding (pools of standing water) was found at one or more locations on the flat or low-slope roof surface. Even on a flat roof, water should be removed by a drainage system so that any remaining water evaporates within 48 hours after it rains. Prolonged standing water can result in roof leaks. This is a conducive condition for wood-destroying organisms. Recommend that a qualified contractor evaluate and repair as necessary to prevent ponding.
The roof was dry during roof inspection, therefore inspector was unable to confirm ponding on roof. Recommend evaluating after rainfall and determine whether or not water sheds of the roof efficiently.
Attic and Roof Structure
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; areas and components obscured by insulation. Any comments made regarding these items are made as a courtesy only. The inspector does not determine the adequacy of the attic ventilation system. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high/low temperatures, high/low humidity, high wind and rain, melting snow) would be needed to do so. The inspector is not a licensed engineer and does not determine the adequacy of roof structure components such as trusses, rafters or ceiling beams, or their spacing or sizing.
Attic inspection method: Not inspected because no access was found, No attic space, vaulted ceilings.
Garage or Carport
Limitations: The inspector does not determine the adequacy of firewall ratings. Requirements for ventilation in garages vary between municipalities.
Condition of door between garage and house: Appeared serviceable
Type of door between garage and house: Wood
Condition of garage vehicle door(s): Appeared serviceable
Type of garage vehicle door: Sectional
Number of vehicle doors: 1
Condition of automatic opener(s): Appeared serviceable
Mechanical auto-reverse operable (reverses when meeting reasonable resistance during closing): Yes
Condition of garage floor: Appeared serviceable
Condition of garage interior: Appeared serviceable
Garage ventilation: None
17) Repair/Replace, Evaluate -
One or more automatic door openers were noisy. Recommend that a qualified contractor evaluate and repair or replace opener(s) as necessary.
As stated by tenants, not inspected by home inspector.
Garage door was not inspected during this inspection due to tenants cars blocking door. Tenants advised the door works but is noisy. Further evaluation is recommended.
Limitations: The following items are not included in this inspection: generator systems, transfer switches, surge suppressors, inaccessible or concealed wiring; underground utilities and systems; low-voltage lighting or lighting on timers or sensors. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of grounding or bonding, if this system has an adequate capacity for the client's specific or anticipated needs, or if this system has any reserve capacity for additions or expansion. The inspector does not operate circuit breakers as part of the inspection, and does not install or change light bulbs. The inspector does not evaluate every wall switch or receptacle, but instead tests a representative number of them per various standards of practice. When furnishings, stored items or child-protective caps are present some receptacles are usually inaccessible and are not tested; these are excluded from this inspection. Receptacles that are not of standard 110 volt configuration, including 240-volt dryer receptacles, are not tested and are excluded. The functionality of, power source for and placement of smoke and carbon monoxide alarms is not determined as part of this inspection. Upon taking occupancy, proper operating and placement of smoke and carbon monoxide alarms should be verified and batteries should be changed. These devices have a limited lifespan and should be replaced every 10 years. The inspector attempts to locate and evaluate all main and sub-panels. However, panels are often concealed. If panels are found after the inspection, a qualified electrician should evaluate and repair if necessary. The inspector attempts to determine the overall electrical service size, but such estimates are not guaranteed because the overall capacity may be diminished by lesser-rated components in the system. Any repairs recommended should be made by a licensed electrician.
Electric service condition: Appeared serviceable
Primary service type: Underground
Service voltage (volts): 120-240
Estimated service amperage: 100
Primary service overload protection type: Circuit breakers
Main disconnect rating (amps): 100
System ground: Not determined, not readily apparent, Not visible
Condition of main service panel: Appeared serviceable
Location of main service panel #A: Garage
Location of main disconnect: Breaker at top of main service panel
Condition of branch circuit wiring: Serviceable
Branch circuit wiring type: Non-metallic sheathed
Solid strand aluminum branch circuit wiring present: None visible
Ground fault circuit interrupter (GFCI) protection present: Yes
Arc fault circuit interrupter (AFCI) protection present: No
Smoke alarms installed: Yes, but not tested
Carbon monoxide alarms installed: Yes, but not tested
20) Safety, Repair/Replace
Ceiling in master bedroom was noted to be hanging form its wiring. This is a safety hazard and needs to be repaired/wired correctly.
21) Repair/Replace, Evaluate
One or more electric receptacles appeared to have no power. Recommend asking the property owner about this. Switches may need to be operated or GFCI/AFCI protection may need to be reset to make some receptacles energized. If necessary, recommend that a qualified electrician evaluate and repair.
Located outside front porch area.
Ceiling fan located in main living area is wired to a dimmer switch. This may be considered incorrect if the switch and fan are not rated. This is mentioned because many times these components are not correct for this application. Recommend further evaluation by a electrician.
23) Repair/Maintain, Evaluate
The legend for circuit breakers or fuses in panel(s) #A was missing, incomplete, illegible or confusing. This is a potential shock or fire hazard in the event of an emergency when power needs to be turned off. Recommend correcting the legend so it's accurate, complete and legible. Evaluation by a qualified electrician may be necessary.
Plumbing / Fuel Systems
Limitations: The following items are not included in this inspection: private/shared wells and related equipment; private sewage disposal systems; hot tubs or spas; main, side and lateral sewer lines; gray water systems; pressure boosting systems; trap primers; incinerating or composting toilets; fire suppression systems; water softeners, conditioners or filtering systems; plumbing components concealed within the foundation or building structure, or in inaccessible areas such as below tubs; underground utilities and systems; overflow drains for tubs and sinks; backflow prevention devices. Any comments made regarding these items are as a courtesy only. Note that the inspector does not operate water supply or shut-off valves due to the possibility of valves leaking or breaking when operated. The inspector does not test for lead in the water supply, the water pipes or solder, does not determine if plumbing and fuel lines are adequately sized, and does not determine the existence or condition of underground or above-ground fuel tanks.
Water service: Public
Condition of drain pipes: Appeared serviceable
Drain pipe material: Not determined (inaccessible or obscured)
Condition of waste lines: Not determined (inaccessible, obscured, or water service off)
Vent pipe condition: Appeared serviceable
Vent pipe material: Plastic
Condition of fuel system: Appeared serviceable
Location of main fuel shut-off valve: At gas meter
No sediment trap was installed in the gas supply line at the water heater. Sediment traps prevent damage to gas-fired appliances by trapping oil, scale, water condensation and/or debris. Recommend that a qualified contractor install a sediment trap per standard building practices.
Limitations: Evaluation of and determining the adequacy or completeness of the following items are not included in this inspection: water recirculation pumps; solar water heating systems; Energy Smart or energy saver controls; catch pan drains. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on water heaters, does not determine if water heaters are appropriately sized, or perform any evaluations that require a pilot light to be lit or a shut-off valve to be operated.
Condition of water heater: Appeared serviceable
Energy source: Natural gas
Estimated age: <2 years
Capacity (in gallons): 40
Temperature-pressure relief valve installed: Yes
Location of water heater: Garage
Hot water temperature tested: No
Condition of burners: Not determined (inaccessible, obscured, or gas service off)
Condition of venting system: Appeared serviceable
Heating, Ventilation and Air Condition (HVAC)
Limitations: The following items are not included in this inspection: humidifiers, dehumidifiers, electronic air filters; solar, coal or wood-fired heat systems; thermostat or temperature control accuracy and timed functions; heating components concealed within the building structure or in inaccessible areas; underground utilities and systems; safety devices and controls (due to automatic operation). Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on heating or cooling system components, does not determine if heating or cooling systems are appropriately sized, does not test coolant pressure, or perform any evaluations that require a pilot light to be lit, a shut-off valve to be operated, a circuit breaker to be turned "on" or a serviceman's or oil emergency switch to be operated. It is beyond the scope of this inspection to determine if furnace heat exchangers are intact and free of leaks. Condensation pans and drain lines may clog or leak at any time and should be monitored while in operation in the future. Where buildings contain furnishings or stored items, the inspector may not be able to verify that a heat source is present in all "liveable" rooms (e.g. bedrooms, kitchens and living/dining rooms).
Condition of cooling system and/or heat pump: Appeared serviceable
Cooling system and/or heat pump fuel type: Electric
Location of heat pump or air conditioning unit: Roof
Type: Split system, Evaporative cooler
Condition of controls: Appeared serviceable
Condition of forced air heating/(cooling) system: Appeared serviceable
Forced air heating system fuel type: Natural gas
Location of forced air furnace: Garage
Condition of furnace filters: Required replacement, Required repair and/or evaluation (see comments below), Need to be installed properly.
Location for forced air filter(s): At base of air handler
Condition of forced air ducts and registers: Appeared serviceable
Condition of burners: Appeared serviceable
Type of combustion air supply: Intake duct
Condition of venting system: Appeared serviceable
Location of heat pump or air conditioning unit: Building exterior, Roof
Type: Split system
25) Safety, Repair/Maintain, Evaluate
The last service date of the gas or oil-fired forced air furnace appeared to be more than 1 year ago, or the inspector was unable to determine the last service date. Ask the property owner when it was last serviced. If unable to determine the last service date, or if this system was serviced more than 1 year ago, recommend that a qualified HVAC contractor inspect, clean, and service this system, and make repairs if necessary. For safety reasons, and because this system is fueled by gas or oil, this servicing should be performed annually in the future. Any needed repairs noted in this report should be brought to the attention of the HVAC contractor when it's serviced. For more information visit:http://www.reporthost.com/?ANFURINSP
26) Major Defect, Comment -
The estimated useful life for most forced air furnaces is 15-20 years. This furnace appeared to be beyond this age and/or its useful lifespan and may need replacing or significant repairs at any time. Recommend budgeting for a replacement in the near future.
Original to house. Furnace is 31 years old.
Recommend that home buyers replace or clean HVAC filters upon taking occupancy depending on the type of filters installed. Regardless of the type, recommend checking filters monthly in the future and replacing or cleaning them as necessary. How frequently they need replacing or cleaning depends on the type and quality of the filter, how the system is configured (e.g. always on vs. "Auto"), and on environmental factors (e.g. pets, smoking, frequency of house cleaning, number of occupants, the season).
28) Evaluate, Comment -
The furnace heating system was not fully evaluated because the pilot light was off. Recommend that a full evaluation be made by a qualified person when conditions have been corrected so the system is operable. Note that the inspector does not operate shut-off valves, pilot lights or circuit breakers, or any controls other than normal controls (thermostat).
The gas supply line into the furnace is missing a drip leg. This is a section of pipe that angles downward prior to shutoff valve. This helps prevent condensation to enter the appliance. Recommend evaluation/installation on gas line.
The damper from to the furnace needs to be closed/installed. Considerable amount of cold air was exiting form the furnace heat exchanger into the garage and out the return duct (reverse flow). Not only is this energy inefficient, the large moisture content in the swamp cooler air will damage the furnace components. recommend closing/installing damper.
Comparing both pictures, one can see the partially detached info sheet moving from the excessive air flow.
Comparing both pictures, one can see the partially detached info sheet moving from the excessive air flow.
Fireplaces, Stoves, Chimneys and Flues
Limitations: The following items are not included in this inspection: coal stoves, gas logs, chimney flues (except where visible). Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of drafting or sizing in fireplace and stove flues, and also does not determine if prefabricated or zero-clearance fireplaces are installed in accordance with the manufacturer's specifications. The inspector does not perform any evaluations that require a pilot light to be lit, and does not light fires. The inspector provides a basic visual examination of a chimney and any associated wood burning device. The National Fire Protection Association has stated that an in-depth Level 2 chimney inspection should be part of every sale or transfer of property with a wood-burning device. Such an inspection may reveal defects that are not apparent to the home inspector who is a generalist.
Condition of wood-burning fireplaces, stoves: Appeared serviceable
Wood-burning fireplace type: Metal pre-fab
Condition of chimneys and flues: Appeared serviceable
31) Safety, Repair/Maintain, Evaluate
One or more wood-burning fireplaces or stoves were found at the property. When such devices are used, they should be professionally inspected and cleaned annually to prevent creosote build-up and to determine if repairs are needed. The National Fire Protection Association states that a "Level 2" chimney inspection should be performed with every sale or transfer of property with a wood-burning device. Recommend consulting with the property owner about recent and past servicing and repairs to all wood-burning devices and chimneys or flues at this property. Recommend that a qualified specialist evaluate all wood-burning devices and chimneys, and clean and repair as necessary. Note that if a wood stove insert is installed, it may need to be removed for such an evaluation. For more information, search for "chimney inspection" at:http://www.reporthost.com/?CSIA
32) Repair/Replace -
The brick chimney was deteriorated. For example, loose or missing mortar, cracked, broken, loose or spalled bricks. Loose bricks can pose a safety hazard, and deteriorated masonry can allow water to infiltrate the chimney structure and cause further damage. Recommend that a qualified contractor repair as necessary.
One or more masonry chimney crowns were worn and/or deteriorated. Crowns are meant to keep water off of the chimney structure and prevent damage from freeze-thaw cycles. Chimney crowns are commonly constructed by mounding concrete or mortar on the top chimney surface, however this is substandard. A properly constructed chimney crown should:
- Be constructed using either precast concrete slabs, cast-in-place steel reinforced concrete, solid stone, or metal
- Be sloped down from the flue a minimum of 3 inches of fall per foot of run
- Extend a minimum of 2 1/2 inches beyond the face of the chimney on all sides
- Not directly contact the flue liner (if installed), with the gap filled with flexible caulk
- Have flashing installed between the bottom of the crown and the top of the brick chimney
Recommend that a qualified contractor repair or replace crowns as necessary, and per standard building practices.
Exposed gaps between flue and chimney noted. This can allow moisture to enter the air apace and cause damage inside the structure. Recommend repairs/resealing.
Limitations: The following items are not included in this inspection: household appliances such as stoves, ovens, cook tops, ranges, warming ovens, griddles, broilers, dishwashers, trash compactors, refrigerators, freezers, ice makers, hot water dispensers and water filters; appliance timers, clocks, cook functions, self and/or continuous cleaning operations, thermostat or temperature control accuracy, and lights. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of the remaining life of appliances, and does not determine the adequacy of operation of appliances. The inspector does not note appliance manufacturers, models or serial numbers and does not determine if appliances are subject to recalls. Areas and components behind and obscured by appliances are inaccessible and excluded from this inspection.
Condition of counters: Appeared serviceable
Condition of cabinets: Appeared serviceable
Condition of sinks and related plumbing: Not determined (water supply off, obscured by stored items, etc.), Obscured by stored items
Condition of under-sink food disposal: Not determined
Condition of dishwasher: Not determined
Condition of range, cooktop or oven: Appeared serviceable
Range, cooktop or oven type: Electric
Condition of refrigerator: Appeared serviceable
Bathrooms, Laundry and Sinks
Limitations: The following items are not included in this inspection: overflow drains for tubs and sinks; heated towel racks, saunas, steam generators, clothes washers, clothes dryers. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of washing machine drain lines, washing machine catch pan drain lines, or clothes dryer exhaust ducts. The inspector does not operate water supply or shut-off valves for sinks, toilets, bidets, clothes washers, etc. due to the possibility of valves leaking or breaking when operated. The inspector does not determine if shower pans or tub and shower enclosures are water tight, or determine the completeness or operability of any gas piping to laundry appliances.
Location #A: Full bath
Location #B: Full bath
Location #C: 3/4 bath
Condition of counters: Appeared serviceable
Condition of cabinets: Appeared serviceable
Condition of flooring: Required repairs, replacement and/or evaluation (see comments below)
Condition of sinks and related plumbing: Required repair, replacement and/or evaluation (see comments below)
Condition of toilets: Appeared serviceable
Condition of bathtubs and related plumbing: Appeared serviceable
Condition of shower(s) and related plumbing: Required repair, replacement and/or evaluation (see comments below)
Condition of ventilation systems: Appeared serviceable, Required repair, replacement and/or evaluation (see comments below)
Bathroom and laundry ventilation type: Spot exhaust fans
Gas supply for laundry equipment present: Not determined
240 volt receptacle for laundry equipment present: Not determined
35) Safety, Repair/Replace -
Carpeting found in one or more bathrooms. Although this installation adds to comfort, carpets in bathrooms can harbor bacteria and lead to mold. Evidence of this is present in master bathroom. Recommend remove carpet from all bathrooms.
36) Safety, Repair/Replace
No accessible gas shut-off valve was visible within 6 feet of the gas-fired clothes dryer. This is a potential safety hazard when the appliance needs to be shut down quickly. Recommend that a qualified contractor install a shut-off valve per standard building practices.
38) Safety, Maintain
Note that the dryer vent exhaust outside was full of lint. This is an indicator that the vent needs to be clean. Clogged dryer vents is one the leading causes of residential fires annually. Recommend thorough cleaning.
Water damage was found in shelving or cabinet components below one or more sinks at location(s) #A. Recommend that a qualified contractor repair as necessary after any plumbing leaks have been repaired. If moisture is present then concealed areas should be dried thoroughly.
40) Repair/Replace -
The shower enclosure at location(s) #B was deteriorated, damaged or substandard. Water can damage the wall structure as a result. Recommend that a qualified contractor repair or replace the surround as necessary.
One or more sink drains were leaking at location(s) #A. A qualified person should repair as necessary.
Second story loft bathroom.
43) Maintain, Comment
Rusting found around register. This is an indicator of too much moisture in the bathroom and around/from vent. Exhaust fans should used frequently and/or windows should be opened to help expel moisture from the bathroom. This can be remedied by occupant behavior. Recommend replacing register.
Interior, Doors and Windows
Limitations: The following items are not included in this inspection: security, intercom and sound systems; communications wiring; central vacuum systems; elevators and stair lifts; cosmetic deficiencies such as nail-pops, scuff marks, dents, dings, blemishes or issues due to normal wear and tear in wall, floor and ceiling surfaces and coverings, or in equipment; deficiencies relating to interior decorating; low voltage and gas lighting systems. Any comments made regarding these items are as a courtesy only. Note that the inspector does not evaluate any areas or items which require moving stored items, furnishings, debris, equipment, floor coverings, insulation or similar materials. The inspector does not test for asbestos, lead, radon, mold, hazardous waste, urea formaldehyde urethane, or any other toxic substance. Some items such as window, drawer, cabinet door or closet door operability are tested on a sampled basis. The client should be aware that paint may obscure wall and ceiling defects, floor coverings may obscure floor defects, and furnishings may obscure wall, floor and floor covering defects. If furnishings were present during the inspection, recommend a full evaluation of walls, floors and ceilings that were previously obscured when possible. Determining the cause and/or source of odors is not within the scope of this inspection.
Condition of exterior entry doors: Required repair, replacement and/or evaluation (see comments below)
Exterior door material: Wood
Condition of interior doors: Appeared serviceable
Condition of windows and skylights: Required repair, replacement and/or evaluation (see comments below)
Type(s) of windows: Metal, Multi-pane, Sliding
Condition of walls and ceilings: Appeared serviceable, Required repairs, replacement and/or evaluation (see comments below)
Wall type or covering: Drywall
Ceiling type or covering: Drywall
Condition of flooring: Required repairs, replacement and/or evaluation (see comments below)
Condition of concrete slab floor(s): Required repairs, replacement and/or evaluation (see comments below)
Flooring type or covering: Carpet, Tile
Condition of stairs, handrails and guardrails: Appeared serviceable
44) Safety, Repair/Maintain
Handrails at one or more flights of stairs were wobbly. This is a safety hazard. Recommend that a qualified person repair as necessary.
Recommend adding additional upright supports to strengthen.
46) Repair/Replace, Evaluate
One or more skylights appeared to have an active leak. A qualified contractor should evaluate and repair as necessary.
47) Repair/Replace, Evaluate -
Floors in one or more areas were not level. This can be caused by foundation settlement or movement of the foundation, posts and/or beams. Significant repairs may be needed to make floors level. Recommend that a qualified contractor and/or engineer evaluate further. Repairs should be performed by a qualified contractor.
This was noted in the area at the base o the stairs.
48) Repair/Replace, Evaluate
Floors in one or more areas were sagging or springy. This can be caused by over-spanned, undersized or too few joists or beams, too few support posts, or too much 'live load'.Recommend that a qualified contractor and/or engineer evaluate further. Repairs should be performed by a qualified contractor.
49) Repair/Replace, Evaluate
Squeaking or creaking noises occur when walking on one or more sections of flooring. This is usually caused by substandard construction practices where the sub-floor decking is not adequately fastened to the framing below. For example, not enough glue was used and/or nails were used rather than screws. In most cases, this is only an annoyance rather than a structural problem. Various solutions such as Squeeeeek No More and Counter Snap fasteners
exist to correct this. Repairs to eliminate the squeaks or creaks may be more or less difficult depending on the floor covering and the access to the underside of the sub-floor. Recommend that a qualified contractor evaluate and repair as necessary. For more information, visit:http://www.reporthost.com/?SQUEAK
51) Repair/Maintain -
Tile, stone and/or grout in the flooring in one or more areas was deteriorated (e.g. loose or cracked tiles, missing grout) or substandard. If in a wet area, water can damage the sub-floor. Recommend that a qualified contractor repair as necessary.
Both second story bathrooms around toilets.
52) Maintain, Comment
One or more exterior doors had minor damage and/or deterioration. Although serviceable, the client may wish to repair or replace such doors for appearances' sake. Exterior finish is failing due to weather and sun exposure
Tiled area with drain, pump, and water supply located in front entry area. Use is unknown, but it was noted that no additional ventilation was present for the additional moisture this would create in this area. If used, Recommend adding adequate ventilation to prevent moisture damage to walls/structure. Inspection was limited due to stored items.
Your default report footer here...