This report is the exclusive property of this inspection company and the client(s) listed in the report title. Use of this report by any unauthorized persons is prohibited.
2816 Charleston St NE
Albuquerque NM 87110-2702
Inspector: Henry Schichtel
Property Inspection Report
Santa Fe NM
||Thursday, April 07, 2016
This report published on Monday, May 09, 2016 9:15:03 PM MDT
How to Read this Report
This report is organized by the property's functional areas. Within each functional area, descriptive information is listed first and is shown in bold type. Items of concern follow descriptive information.
Concerns are shown and sorted according to these types:
|Safety||Poses a safety hazard|
|Major Defect||Correction likely involves a significant expense|
|Repair/Replace||Recommend repairing or replacing|
|Repair/Maintain||Recommend repair and/or maintenance|
|Maintain||Recommend ongoing maintenance|
|Evaluate||Recommend evaluation by a specialist|
|Monitor||Recommend monitoring in the future|
|Comment||For your information|
Click here for a glossary of building construction terms.Contact your inspector If there are terms that you do not understand, or visit the glossary of construction terms at http://www.reporthost.com/glossary.asp
Time started: 11:00
Time finished: 12:45
Present during inspection: Client, Realtor
Client present for discussion at end of inspection: No
Weather conditions during inspection: Dry (no rain)
Temperature during inspection: Warm, 60 degrees
Type of building: Single family, Det. Barn
Buildings inspected: One house
Number of residential units inspected: 1
Age of main building: 2007
Front of building faces: East
Main entrance faces: East
Occupied: Yes, Furniture or stored items were present
Limitations: Unless specifically included in the inspection, the following items and any related equipment, controls, electric systems and/or plumbing systems are excluded from this inspection: detached buildings or structures; fences and gates; retaining walls; underground drainage systems, catch basins or concealed sump pumps; swimming pools and related safety equipment, spas, hot tubs or saunas; whether deck, balcony and/or stair membranes are watertight; trees, landscaping, properties of soil, soil stability, erosion and erosion control; ponds, water features, irrigation or yard sprinkler systems; sport courts, playground, recreation or leisure equipment; areas below the exterior structures with less than 3 feet of vertical clearance; invisible fencing; sea walls, docks and boathouses; retractable awnings. Any comments made regarding these items are as a courtesy only.
Site profile: Minor slope
Condition of driveway: Appeared serviceable
Driveway material: Gravel
Condition of sidewalks and/or patios: Appeared serviceable
Sidewalk material: Poured in place concrete
Condition of deck, patio and/or porch covers: Appeared serviceable
Deck, patio, porch cover material and type: Covered (Refer to Roof section)
1) Monitor -
The driveway sloped down towards the garage or house. This can result in water accumulating in the garage, around building foundations or underneath buildings, and is a conducive condition for wood-destroying organisms. Monitor these areas in the future, especially during and after periods of rain. If significant amounts of water are found to accumulate, then recommend that a qualified contractor evaluate and repair as necessary. For example, by installing drain(s) or removing and installing new pavement.
No issues noted at time of inspection.
Exterior and Foundation
Limitations: The inspector performs a visual inspection of accessible components or systems at the exterior. Items excluded from this inspection include below-grade foundation walls and footings; foundations, exterior surfaces or components obscured by vegetation, stored items or debris; wall structures obscured by coverings such as siding or trim. Some items such as siding, trim, soffits, vents and windows are often high off the ground, and may be viewed using binoculars from the ground or from a ladder. This may limit a full evaluation. Regarding foundations, some amount of cracking is normal in concrete slabs and foundation walls due to shrinkage and drying. Note that the inspector does not determine the adequacy of seismic reinforcement.
Wall inspection method: Viewed from ground
Condition of wall exterior covering: Appeared serviceable
Apparent wall structure: Wood frame
Wall covering: Stucco
Condition of foundation and footings: Required repairs, replacement and/or evaluation (see comments below)
Apparent foundation type: Concrete slab on grade
2) Repair/Maintain, Maintain, Evaluate, Monitor
Cracks, deterioration and/or damage were found in one or more areas of the exterior stucco finish. Moisture can enter cracks or damaged areas and further deteriorate the stucco. Also the wall behind the stucco can become damaged from moisture. Note that areas behind the stucco are inaccessible and excluded from this inspection. Recommend that a qualified contractor repair or replace stucco as necessary.
Multiple cracks found around the exterior of the home. This might be from the settling (unknown if settling will continue and cause more problems in the future). At this time, it should be understood that the house should be monitored for further evidence of continuous settling issues. At this time, there were no problems resulting from this, but monitoring is advised.
Vegetation such as trees, shrubs and/or vines was in contact with or close to the building exterior. Vegetation can serve as a pathway for wood-destroying insects and can retain moisture against the exterior after it rains. This is a conducive condition for wood-destroying organisms. Recommend pruning, moving or removing vegetation as necessary to maintain at least 6 inches of space between it and the building exterior. A 1-foot clearance is better.
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; solar roofing components. Any comments made regarding these items are made as a courtesy only. Note that the inspector does not provide an estimate of remaining life on the roof surface material, nor guarantee that leaks have not occurred in the roof surface, skylights or roof penetrations in the past. Regarding roof leaks, only active leaks, visible evidence of possible sources of leaks, and evidence of past leaks observed during the inspection are reported on as part of this inspection. The inspector does not guarantee or warrant that leaks will not occur in the future. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high wind and rain, melting snow) would be needed to do so. Occupants should monitor the condition of roofing materials in the future. For older roofs, recommend that a professional inspect the roof surface, flashings, appurtenances, etc. annually and maintain/repair as might be required. If needed, the roofer should enter attic space(s). Regarding the roof drainage system, unless the inspection was conducted during and after prolonged periods of heavy rain, the inspector was unable to determine if gutters, downspouts and extensions perform adequately or are leak-free.
Roof inspection method: Traversed
Condition of roof surface material: Appeared serviceable, Required repair, replacement and/or evaluation (see comments below), 2007
Roof surface material: Rolled composition
Roof type: Flat or low slope
Condition of exposed flashings: Appeared serviceable
Condition of gutters, downspouts and extensions: Appeared serviceable
4) Major Defect, Evaluate -
The roof surface appeared to be near the end of its service life and will likely need replacing in the near future even if repairs are made now. Recommend discussing replacement options with a qualified contractor, and budgeting for a replacement roof surface in the near future. The client may also wish to consider having a qualified contractor attempt to issue a "5 year roof certificate."
Attic and Roof Structure
Condition of roof structure: Appeared serviceable
Roof structure type: Rafters
Ceiling structure: Ceiling beams
Condition of insulation in attic (ceiling, skylight chase, etc.): Appeared serviceable
Ceiling insulation material: Not determined (inaccessible or obscured), Not visible
Approximate attic insulation R value (may vary in areas): Not determined (inaccessible or obscured)
Vermiculite insulation present: Not determined, Not visible
Vapor retarder: Not determined (inaccessible or obscured), Not visible
Condition of roof ventilation: Required repair, replacement and/or evaluation (see comments below)
Roof ventilation type: Parapet vents
One or more attic or roof vent screens were clogged with caulking. This can reduce air flow through the roof structure or attic and result in reduced service life for the roof surface materials because of high temperatures. Moisture from condensation is also likely to accumulate in the roof structure. Recommend that a qualified person repair as necessary so air flows freely through all vents.
The reasoning behind this caulking is unknown and therefore the seller should be asked if there are any explanations.
Garage or Carport
Limitations: The inspector does not determine the adequacy of firewall ratings. Requirements for ventilation in garages vary between municipalities.
Condition of door between garage and house: Appeared serviceable
Type of door between garage and house: Metal
Condition of garage vehicle door(s): Appeared serviceable
Type of garage vehicle door: Sectional
Number of vehicle doors: 1
Condition of automatic opener(s): Appeared serviceable
Mechanical auto-reverse operable (reverses when meeting reasonable resistance during closing): Yes
Condition of garage floor: Appeared serviceable
Condition of garage interior: Appeared serviceable
Garage ventilation: Adequate
Limitations: The following items are not included in this inspection: generator systems, transfer switches, surge suppressors, inaccessible or concealed wiring; underground utilities and systems; low-voltage lighting or lighting on timers or sensors. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of grounding or bonding, if this system has an adequate capacity for the client's specific or anticipated needs, or if this system has any reserve capacity for additions or expansion. The inspector does not operate circuit breakers as part of the inspection, and does not install or change light bulbs. The inspector does not evaluate every wall switch or receptacle, but instead tests a representative number of them per various standards of practice. When furnishings, stored items or child-protective caps are present some receptacles are usually inaccessible and are not tested; these are excluded from this inspection. Receptacles that are not of standard 110 volt configuration, including 240-volt dryer receptacles, are not tested and are excluded. The functionality of, power source for and placement of smoke and carbon monoxide alarms is not determined as part of this inspection. Upon taking occupancy, proper operating and placement of smoke and carbon monoxide alarms should be verified and batteries should be changed. These devices have a limited lifespan and should be replaced every 10 years. The inspector attempts to locate and evaluate all main and sub-panels. However, panels are often concealed. If panels are found after the inspection, a qualified electrician should evaluate and repair if necessary. The inspector attempts to determine the overall electrical service size, but such estimates are not guaranteed because the overall capacity may be diminished by lesser-rated components in the system. Any repairs recommended should be made by a licensed electrician.
Electric service condition: Appeared serviceable
Primary service type: Underground
Service voltage (volts): 120-240
Estimated service amperage: 200
Primary service overload protection type: Circuit breakers
Service entrance conductor material: Stranded aluminum
Main disconnect rating (amps): 200
System ground: Not determined, not readily apparent, Not visible
Condition of main service panel: Appeared serviceable
Location of main service panel #A: Garage
Location of main disconnect: Breaker at top of main service panel
Condition of branch circuit wiring: Serviceable
Branch circuit wiring type: Non-metallic sheathed
Solid strand aluminum branch circuit wiring present: None visible
Arc fault circuit interrupter (AFCI) protection present: Yes
Smoke alarms installed: Yes, but not tested
Carbon monoxide alarms installed: No, recommend install
7) Safety, Repair/Replace, Evaluate
One or more electric receptacles at the kitchen and/or garage had no visible ground fault circuit interrupter (GFCI) protection, or the inspector was unable to determine if GFCI protection was present. If not GFCI-protected, receptacles in wet areas pose a shock hazard. Recommend that a qualified electrician evaluate and install GFCI protection if necessary and per standard building practices. General guidelines for GFCI-protected receptacles include the following locations:
- Outdoors (since 1973)
- Bathrooms (since 1975)
- Garages (since 1978)
- Kitchens (since 1987)
- Crawl spaces and unfinished basements (since 1990)
- Wet bar sinks (since 1993)
- Laundry and utility sinks (since 2005)
For more information, visit:http://www.reporthost.com/?GFCI
8) Safety, Repair/Replace
One or more plug ends were installed on non-metallic sheathed wiring. This type of wiring is only intended for permanent, immovable installations. Wiring may be damaged by repeated movement. This is a safety hazard for shock and/or fire. Recommend that a qualified electrician repair per standard building practices.
9) Safety, Repair/Replace
One or more electric receptacles had reverse-polarity wiring, where the hot and neutral wires were reversed. This is a shock hazard. Recommend that a qualified electrician repair as necessary. For more information, visit:http://www.reporthost.com/?RPR
10) Safety, Repair/Replace
One electric receptacle found on the exterior of the barn was incorrectly wired without an ground (open ground). Recommend that a qualified electrician repair as necessary.
Plumbing / Fuel Systems
Limitations: The following items are not included in this inspection: private/shared wells and related equipment; private sewage disposal systems; hot tubs or spas; main, side and lateral sewer lines; gray water systems; pressure boosting systems; trap primers; incinerating or composting toilets; fire suppression systems; water softeners, conditioners or filtering systems; plumbing components concealed within the foundation or building structure, or in inaccessible areas such as below tubs; underground utilities and systems; overflow drains for tubs and sinks; backflow prevention devices. Any comments made regarding these items are as a courtesy only. Note that the inspector does not operate water supply or shut-off valves due to the possibility of valves leaking or breaking when operated. The inspector does not test for lead in the water supply, the water pipes or solder, does not determine if plumbing and fuel lines are adequately sized, and does not determine the existence or condition of underground or above-ground fuel tanks.
Condition of service and main line: Appeared serviceable
Water service: Shared well
Location of main water shut-off: At well
Condition of supply lines: Appeared serviceable
Supply pipe material: PVC plastic
Condition of drain pipes: Appeared serviceable
Drain pipe material: Plastic
Condition of waste lines: Appeared serviceable
Waste pipe material: Plastic
Vent pipe condition: Appeared serviceable
Vent pipe material: Plastic
Visible fuel storage systems: None visible
One leak was found at a water supply valve in the barn. A qualified plumber should repair as necessary.
12) Maintain, Evaluate
Based on visible components or information provided to the inspector, this property appeared to have a private sewage disposal (septic) system. These are specialty systems and are excluded from this inspection. Comments in this report related to this system are made as a courtesy only and are not meant to be a substitute for a full evaluation by a qualified specialist. Generally, septic tanks should be pumped and inspected every 3 years. Depending on the type of system and municipal regulations, inspection and maintenance may be required more frequently, often annually. Recommend the following:
- Consult with the property owner about this system's maintenance and repair history
- Review any documentation available for this system
- Review inspection and maintenance requirements for this system
- That a qualified specialist evaluate, perform maintenance and make repairs if necessary
For more information, visit:http://www.reporthost.com/?SEPTIC
Based on information provided to the inspector, the water supply to this property is from a shared or community well. These are specialty systems and are excluded from this inspection. Comments in this report related to this system are made as a courtesy only and are not meant to be a substitute for a full evaluation by a qualified specialist. Recommend that the client review the recorded agreements regarding the well, the deeds of the property owners involved, and easements permitting access to, use of, and maintenance of the water system. If no shared well agreement exists, access to the well water supply will be uncertain. Also recommend the following:
- That a qualified well contractor fully evaluate the well, including a conducting a pump/flow test
- That the well water be tested per the client's concerns (e.g. coliforms, pH, contaminants)
- Research the well's history (e.g. how/when constructed, how/when maintained or repaired)
- If the well is not on the client's property, verify that the well's property owner does not harm the well water's quality through land use practices
- Document the current well capacity and water quality for future reference
Limitations: Evaluation of and determining the adequacy or completeness of the following items are not included in this inspection: water recirculation pumps; solar water heating systems; Energy Smart or energy saver controls; catch pan drains. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on water heaters, does not determine if water heaters are appropriately sized, or perform any evaluations that require a pilot light to be lit or a shut-off valve to be operated.
Condition of water heater: Appeared serviceable
Energy source: Electricity
Estimated age: 2007
Capacity (in gallons): 50
Temperature-pressure relief valve installed: Yes
Location of water heater: Utility room
Hot water temperature tested: No
Condition of burners: Appeared serviceable
Heating, Ventilation and Air Condition (HVAC)
Limitations: The following items are not included in this inspection: humidifiers, dehumidifiers, electronic air filters; solar, coal or wood-fired heat systems; thermostat or temperature control accuracy and timed functions; heating components concealed within the building structure or in inaccessible areas; underground utilities and systems; safety devices and controls (due to automatic operation). Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on heating or cooling system components, does not determine if heating or cooling systems are appropriately sized, does not test coolant pressure, or perform any evaluations that require a pilot light to be lit, a shut-off valve to be operated, a circuit breaker to be turned "on" or a serviceman's or oil emergency switch to be operated. It is beyond the scope of this inspection to determine if furnace heat exchangers are intact and free of leaks. Condensation pans and drain lines may clog or leak at any time and should be monitored while in operation in the future. Where buildings contain furnishings or stored items, the inspector may not be able to verify that a heat source is present in all "liveable" rooms (e.g. bedrooms, kitchens and living/dining rooms).
General heating system type(s): Electric heaters
General heating distribution type(s): None, individual heaters
Last service date of primary heat source: Unknown
Condition of electric heaters (not forced air): Appeared serviceable
Electric heater type (not forced air): Baseboard
Condition of controls: Appeared serviceable
Fireplaces, Stoves, Chimneys and Flues
Limitations: The following items are not included in this inspection: coal stoves, gas logs, chimney flues (except where visible). Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of drafting or sizing in fireplace and stove flues, and also does not determine if prefabricated or zero-clearance fireplaces are installed in accordance with the manufacturer's specifications. The inspector does not perform any evaluations that require a pilot light to be lit, and does not light fires. The inspector provides a basic visual examination of a chimney and any associated wood burning device. The National Fire Protection Association has stated that an in-depth Level 2 chimney inspection should be part of every sale or transfer of property with a wood-burning device. Such an inspection may reveal defects that are not apparent to the home inspector who is a generalist.
Condition of wood-burning fireplaces, stoves: Appeared serviceable, Dirty, needs cleaning
Wood-burning fireplace type: Masonry, L
Condition of chimneys and flues: Appeared serviceable
Wood-burning chimney type: Masonry, Teracota
14) Safety, Repair/Replace, Evaluate
A significant amount of creosote or burning by-products (ash, soot, etc.) was visible in one or more chimneys. This is a potential fire hazard and a sign that chimney system maintenance has been deferred. The client should be aware that the type and quality of wood burned, and the moisture content of the wood, will affect the rate at which burning by-products accumulate in the chimney. When wood-burning devices are used regularly, they should be cleaned annually at a minimum. A qualified contractor should evaluate, clean, and repair if necessary.
15) Safety, Repair/Maintain, Evaluate
One or more wood-burning fireplaces or stoves were found at the property. When such devices are used, they should be professionally inspected and cleaned annually to prevent creosote build-up and to determine if repairs are needed. The National Fire Protection Association states that a "Level 2" chimney inspection should be performed with every sale or transfer of property with a wood-burning device. Recommend consulting with the property owner about recent and past servicing and repairs to all wood-burning devices and chimneys or flues at this property. Recommend that a qualified specialist evaluate all wood-burning devices and chimneys, and clean and repair as necessary. Note that if a wood stove insert is installed, it may need to be removed for such an evaluation. For more information, search for "chimney inspection" at:http://www.reporthost.com/?CSIA
16) Monitor, Comment
Cracks on and surrounding the fireplace seem to be from the building settling possibly. No evidence was found to support that these cracks were from heat.
Limitations: The following items are not included in this inspection: household appliances such as stoves, ovens, cook tops, ranges, warming ovens, griddles, broilers, dishwashers, trash compactors, refrigerators, freezers, ice makers, hot water dispensers and water filters; appliance timers, clocks, cook functions, self and/or continuous cleaning operations, thermostat or temperature control accuracy, and lights. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of the remaining life of appliances, and does not determine the adequacy of operation of appliances. The inspector does not note appliance manufacturers, models or serial numbers and does not determine if appliances are subject to recalls. Areas and components behind and obscured by appliances are inaccessible and excluded from this inspection.
Condition of counters: Appeared serviceable
Condition of cabinets: Appeared serviceable
Condition of sinks and related plumbing: Appeared serviceable
Condition of under-sink food disposal: Appeared serviceable
Condition of dishwasher: Appeared serviceable
Condition of range, cooktop or oven: Appeared serviceable
Type of ventilation: Hood or built into microwave over range or cooktop
Condition of refrigerator: Appeared serviceable
Condition of built-in microwave oven: Appeared serviceable
Bathrooms, Laundry and Sinks
Limitations: The following items are not included in this inspection: overflow drains for tubs and sinks; heated towel racks, saunas, steam generators, clothes washers, clothes dryers. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of washing machine drain lines, washing machine catch pan drain lines, or clothes dryer exhaust ducts. The inspector does not operate water supply or shut-off valves for sinks, toilets, bidets, clothes washers, etc. due to the possibility of valves leaking or breaking when operated. The inspector does not determine if shower pans or tub and shower enclosures are water tight, or determine the completeness or operability of any gas piping to laundry appliances.
Location #A: Full bath, Master bath
Location #B: 3/4 bath
Condition of counters: Appeared serviceable
Condition of cabinets: Appeared serviceable
Condition of flooring: Appeared serviceable
Condition of sinks and related plumbing: Appeared serviceable
Condition of toilets: Appeared serviceable
Condition of bathtubs and related plumbing: Appeared serviceable
Condition of shower(s) and related plumbing: Appeared serviceable
Condition of ventilation systems: Appeared serviceable
Bathroom and laundry ventilation type: Spot exhaust fans
Gas supply for laundry equipment present: No
240 volt receptacle for laundry equipment present: Yes
Dryer vent looks to be in good condition currently. Be advised that dryer vents should be cleaned at least once an year. A clogged dry vent is one of the leading cause of residential fires.
Interior, Doors and Windows
Limitations: The following items are not included in this inspection: security, intercom and sound systems; communications wiring; central vacuum systems; elevators and stair lifts; cosmetic deficiencies such as nail-pops, scuff marks, dents, dings, blemishes or issues due to normal wear and tear in wall, floor and ceiling surfaces and coverings, or in equipment; deficiencies relating to interior decorating; low voltage and gas lighting systems. Any comments made regarding these items are as a courtesy only. Note that the inspector does not evaluate any areas or items which require moving stored items, furnishings, debris, equipment, floor coverings, insulation or similar materials. The inspector does not test for asbestos, lead, radon, mold, hazardous waste, urea formaldehyde urethane, or any other toxic substance. Some items such as window, drawer, cabinet door or closet door operability are tested on a sampled basis. The client should be aware that paint may obscure wall and ceiling defects, floor coverings may obscure floor defects, and furnishings may obscure wall, floor and floor covering defects. If furnishings were present during the inspection, recommend a full evaluation of walls, floors and ceilings that were previously obscured when possible. Determining the cause and/or source of odors is not within the scope of this inspection.
Condition of exterior entry doors: Appeared serviceable
Exterior door material: Wood, Metal
Condition of interior doors: Appeared serviceable
Condition of windows and skylights: Appeared serviceable
Type(s) of windows: Vinyl
Condition of walls and ceilings: Appeared serviceable
Wall type or covering: Drywall
Ceiling type or covering: Drywall
Condition of flooring: Appeared serviceable
Condition of concrete slab floor(s): Appeared serviceable
Flooring type or covering: Tile
18) Comment -
No window screens were installed. Windows may not provide ventilation during months when insects are active.
Your default report footer here...