Inspector's email: firstname.lastname@example.org
Phone: (315) 380-3294
Inspector's phone: (315) 380-3294
3462 Collins Rd
syracuse, ny, 13215
Inspector: Jay Rotella
|Property Inspection Report|
|Client(s):||Ann Informed Buyer|
|Property address:||123 your st.|
This report is the exclusive property of this inspection company and the client(s) listed in the report title. Use of this report by any unauthorized persons is prohibited.
Concerns are shown and sorted according to these types:
|Safety||Poses a risk of injury or death|
|Repair/Replace||Recommend repairing or replacing|
|Repair/Maintain||Recommend repair and/or maintenance|
|Minor Defect||Correction likely involves only a minor expense|
|Evaluate||Recommend evaluation by a specialist|
|Serviceable||Item or component is in servicable condition|
|Comment||For your information|
1) - This property has one or more fuel burning appliances, and no carbon monoxide alarms are visible. This is a safety hazard. Recommend installing one or more carbon monoxide alarms as necessary and as per the manufacturer's instructions. For more information, visit http://www.cpsc.gov/CPSCPUB/PREREL/prhtml05/05017.html
3) - One or more downspouts have no extensions, or have extensions that are ineffective. This can result in water accumulating around the structure's foundation, or in basements and crawl spaces if they exist. Accumulated water is a conducive condition to wood destroying insects and organisms, and may also cause the foundation to settle and possibly fail over time. Repairs should be made as necessary, such as installing or repositioning splash blocks, or installing and/or repairing tie-ins to underground drain lines, so rain water is carried at least several feet away from the structure to soil that slopes down and away from the structure.
4) - Gaps exist at one or more openings around the exterior, such as those where outside faucets, refrigerant lines, and/or gas supply pipes penetrate the exterior. Gaps should be sealed as necessary to prevent moisture intrusion and entry by vermin.
5) - One or more minor cracks (1/8 inch or less) were found in the foundation. These don't appear to be a structural concern, but recommend sealing them to prevent water infiltration and monitoring them in the future. Numerous products exist to seal such cracks including:
8) - The auto-reverse mechanism on the vehicle door opener is inoperable or requires too much force to activate. This is a safety hazard, especially for small children. A qualified contractor should evaluate and repair as necessary. For more information on garage door safety issues, visit: http://www.cpsc.gov/cpscpub/pubs/523.html or http://www.ohdstl.com/safety.html
Heating and cooling
10) - The air handler's filter(s) are damaged and/or deteriorated and should be replaced.
14) - Substandard wiring was found for the under-sink food disposal. Unprotected solid-strand, non-metallic sheathed (Romex) wiring is used. The insulation can be damaged by objects coming in contact with it and/or it being repeatedly moved. This is a safety hazard due to the risk of shock and fire. Armored (BX) cable, or a flexible appliance cord with a plug end and electric outlet should be used. A qualified electrician should evaluate and repair as necessary.
15) - The dishwasher drain line is not configured with a "high loop" or "air gap". A high loop is created by routing the drain line up to the bottom surface of the counter top above, and securely fastening it to that surface. It is meant to prevent water from siphoning out of the dishwasher, and to prevent water from the sink drain or food disposal from entering the dishwasher. Some dishwashers have a built-in high loop where one is not required to be configured in the drain line. The clients should try to determine if a high loop is required for this brand and model of dishwasher (review installation instructions, etc.). If one is required, or it cannot be determined if one is not required, then a qualified contractor should install a high loop as per standard building practices.
Also, no "air gap" is installed. Air gaps are another device meant to prevent water from the sink drain or food disposal from entering the dishwasher. These are required in some municipalities for new construction and when remodeling. The client(s) should consult with a qualified contractor to determine if an air gap should be installed.
16) - The under-sink food disposal is noisy. A qualified plumber or contractor should evaluate and repair or replace the food disposal as necessary.
17) - The sink sprayer at the kitchen sink is inoperable or defective. It should be replaced, and by a qualified plumber if necessary.
THERE IS A SLIGHT LEAK AT THE SPRAYER HOSE /HANDLE CONNECTION
18) - Water damage was found in the WINDOW TRIM above the sinks. A qualified contractor should evaluate and make repairs as necessary.
19) - One or more sinks are clogged or drain slowly. Drain(s) should be cleared as necessary, and by a qualified plumber if necessary.
20) - the tub spout in the bathroom needs to be sealed against the tub wall to prevent water damage to the lower floor ceilings
21) - One or more ceiling fans wobbles excessively during operation. This is a potential safety hazard and may be caused by one or more of the following:
Recommend having a qualified contractor evaluate and repair as necessary. For more information, visit: