This report is the exclusive property of this inspection company and the client(s) listed in the report title. Use of this report by any unauthorized persons is prohibited.
DK Home Inspections LLC
12408 Ridgedale Dr
Hudson FL 34669-2897
Inspector: Dale Krispin
||Wednesday, August 12, 2015
This report published on Tuesday, March 07, 2017 9:49:48 PM EST
Time started: 2:30
Time finished: 5:00
Present during inspection: Client, Property owner
Client present for discussion at end of inspection: Yes
Weather conditions during inspection: Rain, Sunny for first half then rain.
Temperature during inspection: Hot
Type of building: Single family
Buildings inspected: One house
Number of residential units inspected: 1
Age of main building: 10
Source for main building age: Property owner
Front of building faces: West
Main entrance faces: West
Some areas and items at this property were obscured by furniture, stored items and/or debris. This often includes but is not limited to walls, floors, windows, inside and under cabinets, under sinks, on counter tops, in closets, behind window coverings, under rugs or carpets, and under or behind furniture. Areas around the exterior, under the structure, in the garage and in the attic may also be obscured by stored items. The inspector in general does not move personal belongings, furnishings, carpets or appliances. When furnishings, stored items or debris are present, all areas or items that are obscured, concealed or not readily accessible are excluded from the inspection. The client should be aware that when furnishings, stored items or debris are eventually moved, damage or problems that were not noted during the inspection may be found.
Limitations: Unless specifically included in the inspection, the following items and any related equipment, controls, electric systems and/or plumbing systems are excluded from this inspection: detached buildings or structures; fences and gates; retaining walls; underground drainage systems, catch basins or concealed sump pumps; swimming pools and related safety equipment, spas, hot tubs or saunas; whether deck, balcony and/or stair membranes are watertight; trees, landscaping, properties of soil, soil stability, erosion and erosion control; ponds, water features, irrigation or yard sprinkler systems; sport courts, playground, recreation or leisure equipment; areas below the exterior structures with less than 3 feet of vertical clearance; invisible fencing; sea walls, docks and boathouses; retractable awnings. Any comments made regarding these items are as a courtesy only.
Site profile: Minor slope
Condition of driveway: Appeared serviceable
Condition of sidewalks and/or patios: Appeared serviceable
Sidewalk material: Poured in place concrete
Condition of deck, patio and/or porch covers: Appeared serviceable
Sprinkler valves were missing covers. This can be a safety hazard. These covers can be bought at most hardware stores.
Sprinkler valves need covers.
Sprinkler valve needs cover.
Minor deterioration (e.g. cracks, holes, settlement, heaving) was found in the driveway, but no trip hazards were found. The client may wish to have repairs made for cosmetic reasons.
Trenching was observed along the sides of the house where rain water falls from the roof. Having gutters installed and rainwater directed away from the home is recommended.
A trench is being made around the perimeter of the building due to water coming off the roof. Installation of gutters or hedge bushes would resolve this issue.
Exterior and Foundation
Limitations: The inspector performs a visual inspection of accessible components or systems at the exterior. Items excluded from this inspection include below-grade foundation walls and footings; foundations, exterior surfaces or components obscured by vegetation, stored items or debris; wall structures obscured by coverings such as siding or trim. Some items such as siding, trim, soffits, vents and windows are often high off the ground, and may be viewed using binoculars from the ground or from a ladder. This may limit a full evaluation. Regarding foundations, some amount of cracking is normal in concrete slabs and foundation walls due to shrinkage and drying. Note that the inspector does not determine the adequacy of seismic reinforcement.
Wall inspection method: Viewed from ground
Condition of wall exterior covering: Appeared serviceable
Apparent wall structure: Concrete block
Wall covering: Stucco
Condition of foundation and footings: Appeared serviceable
Apparent foundation type: Concrete slab on grade
Foundation/stem wall material: Concrete slab on grade
Footing material (under foundation stem wall): Poured in place concrete
One or more minor cracks (1/8 inch or less) were found in the foundation. This seems to be from normal settling. Monitor to be sure it does not expand much. You may also speak to the current owner as it has been painted to see how long the paint has been there. The paint that covers the crack has not separated.
Crack on the garage floor. Likely due to settling when the house was constructed. I would monitor to see if it changes.
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; solar roofing components. Any comments made regarding these items are made as a courtesy only. Note that the inspector does not provide an estimate of remaining life on the roof surface material, nor guarantee that leaks have not occurred in the roof surface, skylights or roof penetrations in the past. Regarding roof leaks, only active leaks, visible evidence of possible sources of leaks, and evidence of past leaks observed during the inspection are reported on as part of this inspection. The inspector does not guarantee or warrant that leaks will not occur in the future. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high wind and rain, melting snow) would be needed to do so. Occupants should monitor the condition of roofing materials in the future. For older roofs, recommend that a professional inspect the roof surface, flashings, appurtenances, etc. annually and maintain/repair as might be required. If needed, the roofer should enter attic space(s). Regarding the roof drainage system, unless the inspection was conducted during and after prolonged periods of heavy rain, the inspector was unable to determine if gutters, downspouts and extensions perform adequately or are leak-free.
Roof inspection method: Traversed
Condition of roof surface material: Appeared serviceable
Roof surface material: Asphalt or fiberglass composition shingles
Roof type: Hipped
Apparent number of layers of roof surface material: One
Condition of exposed flashings: Appeared serviceable
Condition of gutters, downspouts and extensions: Gutters not present. Instalation of gutters are suggested.
Gap between soffit and roof can allow wildlife to enter attic. Repair by a qualified roofer or handyman is recommended.
Soffit over the porch roof has an opening into the attic. This may cause wildlife intrusion.
A damaged shingle near the front porch. This is in the same area with excessive ware. Installing shingles over porch and covering this area with an approved sealant is recommended.
A small whole in the top shingle near the front entry was noted. This shingle is overlapping another shingle and also has underlayment under it. It does not appear to be leaking as viewed from the attic.
Soffits near large oak tree in the back are dirty. Trimming this tree and cleaning the soffits is recommended.
Soffits near large oak tree are dirty. Trimming this tree would cut down on moss and mold growth.
There is an area near front porch that has excessive ware. This is due to large amounts of rain water passing this section during rain. Having gutters installed in this area to prevent further premature ware is recommended.
The roof near the porch entry on the north side. A lot of the water runs off the main roof to this area. Gutters would prolong the life of this portion of the roof.
Fascia over front porch entrance does not reach roof. This may allow wildlife to enter attic. Repair by a qualified roofer or handyman is recommended.
Attic and Roof Structure
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; areas and components obscured by insulation. Any comments made regarding these items are made as a courtesy only. The inspector does not determine the adequacy of the attic ventilation system. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high/low temperatures, high/low humidity, high wind and rain, melting snow) would be needed to do so. The inspector is not a licensed engineer and does not determine the adequacy of roof structure components such as trusses, rafters or ceiling beams, or their spacing or sizing.
Attic inspection method: Traversed
Condition of roof structure: Appeared serviceable
Roof structure type: Trusses
Ceiling structure: Trusses
Condition of insulation in attic (ceiling, skylight chase, etc.): Appeared serviceable
Ceiling insulation material: Fiberglass loose fill
Approximate attic insulation R value (may vary in areas): R-30
Vermiculite insulation present: None visible
Vapor retarder: None
Condition of roof ventilation: Appeared serviceable
Roof ventilation type: Box vents (roof jacks), Open soffit vents
Garage or Carport
Limitations: The inspector does not determine the adequacy of firewall ratings. Requirements for ventilation in garages vary between municipalities.
Condition of door between garage and house: Appeared serviceable
Type of door between garage and house: Solid core
Condition of garage vehicle door(s): Appeared serviceable
Type of garage vehicle door: Sectional
Number of vehicle doors: 1
Condition of automatic opener(s): Appeared serviceable
Mechanical auto-reverse operable (reverses when meeting reasonable resistance during closing): No
Condition of garage floor: Appeared serviceable
Condition of garage interior: Appeared serviceable
Garage ventilation: None visible
Minor cracks were found in the concrete slab floor. These are common and appeared to be only a cosmetic issue.
Limitations: The following items are not included in this inspection: generator systems, transfer switches, surge suppressors, inaccessible or concealed wiring; underground utilities and systems; low-voltage lighting or lighting on timers or sensors. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of grounding or bonding, if this system has an adequate capacity for the client's specific or anticipated needs, or if this system has any reserve capacity for additions or expansion. The inspector does not operate circuit breakers as part of the inspection, and does not install or change light bulbs. The inspector does not evaluate every wall switch or receptacle, but instead tests a representative number of them per various standards of practice. When furnishings, stored items or child-protective caps are present some receptacles are usually inaccessible and are not tested; these are excluded from this inspection. Receptacles that are not of standard 110 volt configuration, including 240-volt dryer receptacles, are not tested and are excluded. The functionality of, power source for and placement of smoke and carbon monoxide alarms is not determined as part of this inspection. Upon taking occupancy, proper operating and placement of smoke and carbon monoxide alarms should be verified and batteries should be changed. These devices have a limited lifespan and should be replaced every 10 years. The inspector attempts to locate and evaluate all main and sub-panels. However, panels are often concealed. If panels are found after the inspection, a qualified electrician should evaluate and repair if necessary. The inspector attempts to determine the overall electrical service size, but such estimates are not guaranteed because the overall capacity may be diminished by lesser-rated components in the system. Any repairs recommended should be made by a licensed electrician.
Electric service condition: Appeared serviceable
Primary service type: Underground
Number of service conductors: 3
Service voltage (volts): 120-240
Estimated service amperage: 150
Primary service overload protection type: Circuit breakers
Service entrance conductor material: Stranded copper
Main disconnect rating (amps): 150
System ground: Concrete encased electrode
Condition of main service panel: Appeared serviceable
Location of main service panel #A: Garage
Location of main disconnect: Breaker at bottom of main service panel
Condition of branch circuit wiring: Serviceable
Branch circuit wiring type: Non-metallic sheathed
Ground fault circuit interrupter (GFCI) protection present: Yes
Arc fault circuit interrupter (AFCI) protection present: No
One or more light fixtures installed outside were not rated for exterior use. This is a potential shock and fire hazard. Recommend that a qualified electrician repair per standard building practices.
Fan in back porch is not exterior rated. The fan blades are drooping due to not being an exterior fan.
Bulbs in one or more light fixtures were missing or broken. These light fixtures couldn't be fully evaluated. If replacement bulbs are inoperable, then recommend that a qualified electrician evaluate and repair or replace light fixtures as necessary.
One in kitchen, Three in master bath, one in master bed room.
Plumbing / Fuel Systems
Limitations: The following items are not included in this inspection: private/shared wells and related equipment; private sewage disposal systems; hot tubs or spas; main, side and lateral sewer lines; gray water systems; pressure boosting systems; trap primers; incinerating or composting toilets; fire suppression systems; water softeners, conditioners or filtering systems; plumbing components concealed within the foundation or building structure, or in inaccessible areas such as below tubs; underground utilities and systems; overflow drains for tubs and sinks; backflow prevention devices. Any comments made regarding these items are as a courtesy only. Note that the inspector does not operate water supply or shut-off valves due to the possibility of valves leaking or breaking when operated. The inspector does not test for lead in the water supply, the water pipes or solder, does not determine if plumbing and fuel lines are adequately sized, and does not determine the existence or condition of underground or above-ground fuel tanks.
Condition of service and main line: Appeared serviceable
Water service: Public
Location of main water shut-off: Building exterior, Outside of garage
Condition of supply lines: Appeared serviceable
Supply pipe material: CPVC plastic
Condition of drain pipes: Appeared serviceable
Drain pipe material: Plastic
Waste pipe material: Plastic
Vent pipe condition: Appeared serviceable
Vent pipe material: Plastic
Sump pump installed: No
Sewage ejector pump installed: No
Type of irrigation system supply source: Public
One or more leaks were found in water supply valves. A qualified plumber should repair as necessary.
One water shut-off valve in master bath was inoperable. Recommend that a qualified plumber replace or repair as necessary.
The hot water valve in the master bath nearest to the tub is taped in the on position. This valve may be faulty and not stay in the on position on its own.
Based on visible equipment or information provided to the inspector, this property appeared to have a yard irrigation (sprinkler) system. These are specialty systems and are excluded from this inspection. Comments in this report related to this system are made as a courtesy only and are not meant to be a substitute for a full evaluation by a qualified specialist. When this system is operated, recommend verifying that water is not directed at building exteriors, or directed so water accumulates around building foundations. Sprinkler heads may need to be adjusted, replaced or disabled. Consider having a qualified plumber verify that a backflow prevention device is installed per standard building practices to prevent cross-contamination of potable water. Recommend that a qualified specialist evaluate the irrigation system for other defects (e.g. leaks, damaged or malfunctioning sprinkler heads) and repair if necessary.
Sprinkler system is leaking at atmospheric vacuum breaker (AVB). This will leak unless the system is shut off. Repair by a certified irrigation specialist is suggested.
Crack in (APB) where sprinkler system is leaking.
Limitations: Evaluation of and determining the adequacy or completeness of the following items are not included in this inspection: water recirculation pumps; solar water heating systems; Energy Smart or energy saver controls; catch pan drains. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on water heaters, does not determine if water heaters are appropriately sized, or perform any evaluations that require a pilot light to be lit or a shut-off valve to be operated.
Condition of water heater: Appeared serviceable
Energy source: Electricity
Estimated age: 10 years old
Capacity (in gallons): 50
Temperature-pressure relief valve installed: Yes
Location of water heater: Garage
The estimated useful life for most water heaters is 8-12 years. This water heater appeared to be near this age and/or its useful lifespan and may need replacing at any time. Recommend budgeting for a replacement in the near future, or considering replacement now before any leaks occur. The client should be aware that significant flooding can occur if the water heater fails. If not replaced now, consider having a qualified person install a catch pan and drain or a water alarm to help prevent damage if water does leak.
Heating, Ventilation and Air Condition (HVAC)
Limitations: The following items are not included in this inspection: humidifiers, dehumidifiers, electronic air filters; solar, coal or wood-fired heat systems; thermostat or temperature control accuracy and timed functions; heating components concealed within the building structure or in inaccessible areas; underground utilities and systems; safety devices and controls (due to automatic operation). Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on heating or cooling system components, does not determine if heating or cooling systems are appropriately sized, does not test coolant pressure, or perform any evaluations that require a pilot light to be lit, a shut-off valve to be operated, a circuit breaker to be turned "on" or a serviceman's or oil emergency switch to be operated. It is beyond the scope of this inspection to determine if furnace heat exchangers are intact and free of leaks. Condensation pans and drain lines may clog or leak at any time and should be monitored while in operation in the future. Where buildings contain furnishings or stored items, the inspector may not be able to verify that a heat source is present in all "liveable" rooms (e.g. bedrooms, kitchens and living/dining rooms).
General heating system type(s): Forced air
General heating distribution type(s): Ducts and registers
Last service date of primary heat source: 8/14
Source for last service date of primary heat source: Property owner
Condition of forced air heating/(cooling) system: Appeared serviceable
Forced air heating system fuel type: Electric
Estimated age of forced air furnace: 10
Location of forced air furnace: Garage
Vegetation such as trees, shrubs and/or vines were too close to the heat pump or air conditioning condensing unit. There should be at least 12 inches of clearance on all sides and at least 4-6 feet above. Inadequate clearance around and above can result in reduced efficiency, increased energy costs and/or damage to equipment. Recommend pruning and/or removing vegetation as necessary.
The outside air compressor needs 12" of clearance around the sides. Vegetation should be trimmed.
The last service date of the forced air heating/cooling system appeared to be within the last year based on information provided to the inspector or labeling on the equipment. If this is true, then routine servicing is not needed at this point. However a qualified HVAC contractor should inspect, clean, and service this system, and make repairs if necessary annually in the future.
Limitations: The following items are not included in this inspection: household appliances such as stoves, ovens, cook tops, ranges, warming ovens, griddles, broilers, dishwashers, trash compactors, refrigerators, freezers, ice makers, hot water dispensers and water filters; appliance timers, clocks, cook functions, self and/or continuous cleaning operations, thermostat or temperature control accuracy, and lights. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of the remaining life of appliances, and does not determine the adequacy of operation of appliances. The inspector does not note appliance manufacturers, models or serial numbers and does not determine if appliances are subject to recalls. Areas and components behind and obscured by appliances are inaccessible and excluded from this inspection.
Condition of counters: Appeared serviceable
Condition of sinks and related plumbing: Appeared serviceable
Condition of under-sink food disposal: Appeared serviceable
Condition of dishwasher: Appeared serviceable
Condition of range, cooktop or oven: Appeared serviceable
Range, cooktop or oven type: Electric
Condition of refrigerator: Appeared serviceable
Condition of built-in microwave oven: Appeared serviceable
The dishwasher was noisy or vibrated excessively. Recommend that a qualified specialist evaluate and repair or replace as necessary.
The under-sink food disposal was noisy or vibrated excessively. Recommend that a qualified contractor repair or replace as necessary.
The refrigerator was rusted near the water dispenser. This appears to only be cosmetic.
Some rust was noted on the refrigerator on the bottom of the water dispenser. This is only cosmetic.
Gaps, no caulk, or substandard caulking were found between countertops and backsplashes. Water may penetrate these areas and cause damage. Recommend that a qualified person repair as necessary. For example, by installing caulk.
Caulking around the kitchen sink is deteriorated and should be recaulked to prevent water damage.
The sink had minor wear, blemishes or deterioration.
Large chip in the pain of the kitchen sink. Sink also has many scratches inside. This is only cosmetic.
Bathrooms, Laundry and Sinks
Limitations: The following items are not included in this inspection: overflow drains for tubs and sinks; heated towel racks, saunas, steam generators, clothes washers, clothes dryers. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of washing machine drain lines, washing machine catch pan drain lines, or clothes dryer exhaust ducts. The inspector does not operate water supply or shut-off valves for sinks, toilets, bidets, clothes washers, etc. due to the possibility of valves leaking or breaking when operated. The inspector does not determine if shower pans or tub and shower enclosures are water tight, or determine the completeness or operability of any gas piping to laundry appliances.
Location #A: Full bath
Location #B: Master bath
Condition of counters: Appeared serviceable
Condition of cabinets: Appeared serviceable
Condition of flooring: Appeared serviceable
Condition of sinks and related plumbing: Appeared serviceable
Condition of toilets: Appeared serviceable
Condition of shower(s) and related plumbing: Appeared serviceable
Condition of ventilation systems: Appeared serviceable
Bathroom and laundry ventilation type: Windows, Central exhaust fan, with individual ducts
240 volt receptacle for laundry equipment present: Yes
The clothes dryer exhaust duct was kinked, crushed or damaged. Air flow will be restricted as a result and the clothes dryer may overheat. This is a safety hazard due to the risk of fire. Recommend that a qualified person replace or repair the duct as necessary. For more information, visit:http://www.reporthost.com/?DRYER
Dryer vent hose is kinked. This may pose a fire hazard. This vent hose should be replaced with a shorter vent hose to prevent kinking.
The toilet in main bathroom ran water continuously or didn't shut off after being flushed, and water leaked from the tank into the bowl. Significant amounts of water can be lost through such leaks. If this system uses a septic system, the septic system can be overloaded and cause significant and potentially expensive damage. A qualified person should repair or replace components as necessary.
The exhaust fan at location(s) # was noisy or vibrated excessively. Moisture may accumulate and result in mold, bacteria or fungal growth. Recommend that a qualified person clean, repair or replace fans as necessary.
Gaps, no caulk, or substandard caulking were found at location(s) #B. Water can penetrate these areas and cause damage. Recommend that a qualified person repair as necessary. For example, by installing or replacing caulk.
Caulking in master bath sink where the counter meets the backsplash is deteriorating. This should be replaced to prevent water damage to the counter.
The main bathroom faucet was not properly attached to wall. Having this repaired by a qualified person is recommended.
Bath faucet in main bathroom has a gap between the faucet and the wall. This may allow water to get into the wall by splashing water. A licensed plumber or handyman would be able to easily repair this issue.
Chip in main bathroom tub.
Interior, Doors and Windows
Limitations: The following items are not included in this inspection: security, intercom and sound systems; communications wiring; central vacuum systems; elevators and stair lifts; cosmetic deficiencies such as nail-pops, scuff marks, dents, dings, blemishes or issues due to normal wear and tear in wall, floor and ceiling surfaces and coverings, or in equipment; deficiencies relating to interior decorating; low voltage and gas lighting systems. Any comments made regarding these items are as a courtesy only. Note that the inspector does not evaluate any areas or items which require moving stored items, furnishings, debris, equipment, floor coverings, insulation or similar materials. The inspector does not test for asbestos, lead, radon, mold, hazardous waste, urea formaldehyde urethane, or any other toxic substance. Some items such as window, drawer, cabinet door or closet door operability are tested on a sampled basis. The client should be aware that paint may obscure wall and ceiling defects, floor coverings may obscure floor defects, and furnishings may obscure wall, floor and floor covering defects. If furnishings were present during the inspection, recommend a full evaluation of walls, floors and ceilings that were previously obscured when possible. Determining the cause and/or source of odors is not within the scope of this inspection.
Condition of exterior entry doors: Appeared serviceable
Exterior door material: Metal
Condition of windows and skylights: Appeared serviceable
Type(s) of windows: Vinyl
Condition of walls and ceilings: Appeared serviceable
Wall type or covering: Drywall
Ceiling type or covering: Drywall
Condition of flooring: Appeared serviceable
Condition of concrete slab floor(s): Appeared serviceable, Due to floor covering the concrete slab floor was not observed.
Flooring type or covering: Carpet, Wood or wood products, Tile
Screens were missing from 4 windows. These windows may not provide ventilation during months when insects are active.
Screens missing in dinning room, Master Bath, Main Bath and front family room
A few tile cracks were observed.
Crack in two consecutive tiles in kitchen. Several hollow tiles were also noted.
Crack in master bath tile.
DK Home Inspections (813)817-1421