3152 Big Ben South
Hernando, MS 38632
Inspector: Frank Magdefrau
TN License # 0056 Exp: 6/30/14
MS License # 0234 Exp: 1/30/14
Home Inspection Report for |
||Mr. & Mrs. Home Buyer
||123 Any Town USA
||Wednesday, May 20, 2009
This report published on Wednesday, May 01, 2013 8:52:31 PM CDT
View report summary
Real estate agents: Please ask permission from your client before giving this report to anyone else, or sending the web address and password of this on -line to anyone else.
Thank you for choosing De Soto Home Inspection Services. We've made every effort to provide you with the best possible home inspection. We hope the information in this report proves to be valuable in your consideration of this property. If for any reason you are unsatisfied with this report, or have questions after viewing it, please don't hesitate to call us. If you are satisfied, please tell your friends about us.
This inspection complies with the National Association of Certified Home Inspectors' (NACHI) "Standards of Practice" and " Codes of Ethics". These standards list items to be described in this report and items to be observed or evaluated during a home inspection. Cosmetic items such as damaged molding, trim, interior paint or carpet are generally excluded from this report.
Home inspection reports by nature focus on defects and may seem negative in tone. Some features of this property may be in excellent condition and of high quality but have been deemed "adequate" in the report. This is not met to downplay this property's assets, but to focus on alerting you to potentially expensive problems. Bear in mind that all homes, regardless of their age, have some number of defects.
How to Read this Report
This report is organized by the property's functional areas. Within each functional area, descriptive information is listed first and is shown in bold type. Items of concern follow descriptive information.
Concerns are shown and sorted according to these types:
|Safety||Poses a safety risk |
|Major Defect||Correction likely involves a significant expense |
|Repair/Replace||Recommend repairing or replacing |
|Repair/Maintain||Recommend repair and/or maintenance |
|Minor Defect||Correction likely involves only a minor expense |
|Evaluate||Recommend evaluation by a specialist |
|Monitor||Recommend monitoring in the future |
|Comment||For your information |
Click here for a glossary of building construction terms.Contact your inspector If there are terms that you do not understand, or visit the glossary of construction terms at http://www.reporthost.com/glossary.asp
Overview: This sample report was designed to help you understand common concerns found with most homes regardless of the homes age. All concerns noted are actual findings from daily performed home inspections.
Seller's name: Mr. & Mrs Home Seller
Report number: 02-0888
Time started: 9:00 am
Time finished: 11:45 am at property
Inspection Fee: $325.00
Present during inspection: Buyer, Realtor
Age of building: Any
Type of building: Single family
Weather conditions: Clear
Temperature: Warm 74 degree's
Ground condition: Damp
Main entrance faces: East
Foundation type: Slab on grade and crawl space areas
Driveway material: Poured in place concrete
Exterior Foundation and Grounds
Sidewalk material: Poured in place concrete
Apparent wall structure: Wood frame
Wall covering: Composition wood clapboard, Brick veneer
Footing material: Poured in place concrete
Foundation material: Poured in place concrete, Concrete block
Exterior door material: Solid core wood
Water pressure (psi): 98 psi
Exterior outlet(s) or switches were not waterproof. This can pose a safety concern due to the risk of fire and shock. Recommend installing waterproof covers where necessary.
Back exterior door wood frame (brick molding) was damaged and/or deteriorating at the bottom of the frame. Recommend having a qualified contractor evaluate and repair or replace brick molding as necessary.
The end cap on the clothes dryer exhaust duct was damaged. Their purpose is to prevent air from entering the house through the clothes dryer, save energy, and keep out birds, rodents and bugs. Birds' nests can block the opening and are flammable. Recommend installing a new vent cap.
Tree(s) and shrubs were in contact with structure. Recommend pruning or moving tree(s) and shrubs so there's at least a one foot gap between them and structure.
Downspout extensions were missing and/or ineffective. Recommend installing extensions such as splashblocks or a drain line where missing, or repairing where necessary so rain water is carried at least several feet away from the structure to soil that slopes down and away from the structure.
Recommend caulking and sealing were necessary.
Missing lintel over window. A steel lintel is recommend over window's to support the brick above. The mortar was coming loose and the bricks were not properly supported. Recommend removing bricks over window, install a steel lintel for support, and reset the bricks in mortar.
This mistake was overlooked by the builder, mason contractor, and city code inspector.
Flower bed mulch was piled over the weep holes in the brick veneer wall. Brick veneer walls absorb moisture. The wall is designed to discharge moisture with flashing and weep holes. When weep holes are obstructed they can create moisture problems to the structural of home. This condition leads to mold, mildew, termite infestation and deteriorating wood framing members. Recommend keeping all weep holes clear and un-obstructed from mulch and other debris.
Roof inspection method: Viewed from eaves on ladder, Viewed from ground
Roof type: Cross-hipped
Roof covering: Asphalt or fiberglass composition shingles
Estimated age of roof: Any
Gutter material: Aluminum
Downspout material: Aluminum
Roof ventilation: Adequate
Flashing was missing in some areas of roof. Whenever shingles meet brick or any other siding, metal flashing is recommended to help prevent water from penetrating these areas. Recommend installing flashing were necessary.
This mistake was overlooked by builder, roofing contractor, and city code inspector. The damage shown was caused in just a short time.
Shingles were missing and damaged in some areas of roof. Recommend repairing shingles were necessary.
Recommend cleaning gutters.
Trees were overhanging roof and were within 10 feet of roof vertically. Recommend pruning trees so they're at least 10 feet above roof, or don't overhang the roof.
The chimney is wider than 2' and no "cricket" (a small ridged roof section just above the chimney to shed water off to the sides) is installed above the chimney. Organic debris from trees may accumulate here and cause leaks. Recommend monitoring this area for accumulated debris and cleaning when necessary. Recommend installing a cricket when next roof is installed.
The chimney needs re-sealing around base. The tar is deteriorating and needs to be replaced.
Wire connections exposed due to no cover plates over one or more junction, switch or outlet boxes. Recommend installing cover plates where missing.
All safety features for the automatic garage door were checked and working properly at time of inspection.
Primary service type: Underground
Primary service overload protection type: Circuit breakers
Service voltage (volts): 3 phase 120-240
Location of main service panel: Garage
Location of sub panels: By condensing unit
Location of main disconnect: Breaker at top of main panel
Service conductor material: Copper
Main disconnect rating (amps): 200
Branch circuit wiring type: Non-metallic sheathed (Romex)
Solid strand aluminum branch circuit wiring present: No
Smoke detectors present: Yes
One or more circuit breakers were "double tapped", where 2 or more wires are clamped in a circuit breaker terminal and the circuit breaker was only designed for 1 wire. This is a safety hazard since wires may come loose and cause arcing, sparking and fires.
The photo on the right shows "tapping before the main" In other words, there's no over current protection provided for the circuit with the orange wires. This condition is much more of a safety issue than the double tap.
Recommend having a licensed electrician evaluate and repair.
Estimated age: Any
Energy source: Natural gas
Capacity (in gallons): 50
Brand & model: Any
The vent pipe from the hot water heater was in contact with the roof's sheeting. The sheeting is a combustible material. The vent flue does reach high temperatures and can ignite the sheeting. Recommend cutting sheeting from the flue so there is at least a 2 inch clearance from all combustible materials by a licensed contractor.
This mistake was overlooked by the builder, plumbing contractor, and city code inspector.
The vent pipe has come lose from the water heater. Carbon monoxide was venting into attic area. Recommend repairs by a licensed contractor.
Temperature-pressure relief valve was leaking. Recommend having a licensed plumber replace valve.
Heating system energy source: Natural gas
Heating and air conditioning
Heat system type: Forced air
A/C energy source: Electric
Air conditioning type: Split system
Distribution system: Sheet metal ducts
The insulation on the main line by the condensing unit was deteriorating and needs replacing. Recommend removing old insulation, cleaning lines and replacing with new insulation.
The drain line from the air handlers catch pan to the exterior was missing and/or never installed. Water can now overflow pan and cause water damage. Recommend installing a drain line to the exterior of home.
This mistake was overlooked by the builder, heating and air contractor, and city code inspector.
Water from the evaporating cooler was leaking into the furnace. Rusting has occurred in this unit. The drain line is most likely clogged. Recommend further evaluation and repairs by a licensed heating and air contractor.
Filter(s) were dirty, recommend replacing filter(s).
The condensing unit was not sitting level. The oil for the motor is more to one side and the motor is not being properly lubricated. This concern will lead to a short life cycle for the condensing unit. Recommend leveling this unit.
As most manufactures warn not to operate heating units when outside air is above 65 degree's, this unit was not tested. Recommend client verify the operation of this system when outside temperature allows.
Inspection method: Traversed
Roof structure type: Rafters
Ceiling structure: Ceiling beams
Insulation material: Fiberglass loose fill, Fiberglass roll or batt
Insulation estimated R value: R30
Wire connections exposed due to missing cover(s) over one or more junction boxes. Recommend installing covers over boxes where missing.
Exposed wiring due to splices not being contained in junction box. Some of the wires are also missing wire nuts as well. Recommend having a licensed electrician install wire nuts,and junction boxes with cover plates where needed to contain wiring splices.
No weatherstrip was installed around the attic access hatch. Recommend installing weatherstrip around hatch to prevent heated interior air from entering attic.
The roll insulation is installed back-wards. The paper side (vapor barrier) should face the living side of home. The paper vapor barrier is a moisture barrier to prevent condensation concerns. Recommend removing installation and re-installing it correctly.
This mistake was overlooked by the builder, insulation contractor, and the city code inspector.
Location of main water shut-off valve: Under downstairs hall bathroom's sink
Location of main water meter: By the street in front yard
Location of main fuel shut-off: Gas meter on the south side of home
Water service: Public
Supply pipe material: Polybutylene
Vent pipe material: Plastic
Drain pipe material: Plastic
Waste pipe material: Plastic
Leak found behind washing machine at the water hook up connections. This leak was most likely caused by the noted high water pressure. This leak has caused wall, floor and trim damage. Mold and mildew appears to have developed. Recommend repairs and further evaluation by licensed contractors.
The water pressure was greater than 80 psi. Recommend having a licensed plumber install a pressure reducing valve on the main service pipe to lower the pressure below 80 psi to avoid damage to appliances such as washing machines and hot water heaters.
Plumbing supply lines were made of Polybutylene. Polybutylene is a plastic material used extensively during the 1980s and 1990s that has proven itself to be more prone to leakage than other types of supply piping systems like copper. Recommend reviewing the seller's property disclosure statement for comments on Polybutylene plumbing supply lines in this house.
A class action lawsuit has been filed regarding this material that requires the manufacturers to cover piping systems installed between Jan. 1, 1978 through July 31, 1995. For more information on the class action lawsuit, visit http://www.pbpipe.com/index1.htm, or call the Plumbing Claims Group at (800) 356-3496 for more information.
Noted leak under hall bathroom during crawlspace inspection. Recommend repairing leak by a licensed plumber.
Fireplace type: Masonry
Fireplaces and solid fuel burning appliances
Chimney type: Masonry
Significant creosote buildup in fireplace chimney. Recommend having a chimney sweep clean chimney.
The damper was checked and working at the time of the inspection.
Inspection method: Traversed
Insulation material underneath floor above: Fiberglass roll or batt
Pier or support post material: Masonry
Beam material: Built up wood
Floor structure above: Solid wood joists
Vapor barrier present: No
Vapor barrier was missing. Recommend installing 6 mil polyethylene with seams overlapped at least 24" so no soil is exposed in the crawlspace.
Some insulation in the crawlspace has fallen down. Recommend reinstalling or replacing this insulation.
Wood scraps found in crawl space. Recommend removing to avoid attracting wood destroying insects.
One or more hot-neutral reversed outlets. Recommend having a licensed electrician evaluate and repair.
Water stains visible in ceiling. Ceiling material is wet, apparently from an active leak. Recommend repairing leak. Recommend removing wet wallboard or plaster and replacing with new after area has dried thoroughly.
Hardware for the front security door has pulled loose from the door frame. The door frame is damaged. Recommend repairing hardware and door frame.
Sink drains slowly. Recommend clearing drain.
Evidence of condensation in double pane window(s), apparently due to broken in seal(s). Recommend replacing glass.
Door binds in jamb and was difficult to operate. Recommend repairing door so it opens and closes easily.
Caulk below tub at floor is deteriorated. Recommend removing old caulk and applying new bead of tub-tile caulk.
Light in range hood inoperable. Recommend replacing light bulb or repairing as necessary.
Scope and Limitations of this Inspection
This inspection is limited to a visual observation of the exposed and readily accessible areas of the home. The concealed and inaccessible areas are not included. Observation includes operation of the systems or components by means of the normal user controls. Dismantling of equipment, and destructive testing is not included. Some specific items are also excluded, and these are listed in the following section. If you feel there is a need for evaluation of any of these items, then you will need to arrange for specific inspections.
The report(s) does not cover (unless specifically stated):
*underground utilities *playground equipment
*wells/spring *cosmetic items
*solar systems *security systems
*underground items *personal property
*septic tanks *appliances
*elevators *water treatment
*environmental hazards *code compliance
*sprinkler systems *chimney/flues
*central vacuum *fuel tanks
*detached structures *drain fields
*defects unobserved *fuel quality
*the suitability of the property for any specialized use
*the market value of the property or its marketability
*the methods, materials and costs of corrections
*any component or system which was not observed
*life expectancy of any component or system
*the advisability or inadvisability or purchase of the property
*items not permanently installed
*the causes of the need for a repair
*the presence or absence of pests such as wood damaging organisms, rodents, or insects.
As a part of our service, we sometimes provide approximate, cost of repair estimates for particular items. These estimates should be considered as background information only. It is beyond the scope of this inspection and report to supply you with accurate repair costs. Such estimates should be supplied by contractors who specialize in this type of work. Our estimates should be used only as guidelines. If you intend to negotiate the price of this property based on defects found during this inspection, we strongly suggest you obtain one or more written bids from a licensed contractor(s). It is a conflict of interest for De Soto Home Inspection Services to recommend any specific contractor.
Evaluations are made as to the present age and remaining economic life of any item, i.e. water heaters, roofs, plumbing, heating, etc. These evaluations are based on visual observation, industry averages and prior experience. THEY ARE NOT OFFERED AS A WARRANTY OR CERTIFICATION OF REMAINING LIFE.
In some cases we may recommend your consulting a specialist such as a structural engineer or licensed electrician. Hiring a specialist can be a prudent means of providing some protection of your financial investment in this property. WE DO NOT MAKE ANY TYPE OF WARRANTY OR GUARANTEE AS TO THE CONDITION OF THE PROPERTY. SOME THINGS MAY REMAIN HIDDEN OR BECOME DEFECTIVE AFTER THE INSPECTION. IT IS NOT POSSIBLE TO DETECT EVERY DEFECT WITHIN A BUILDING DURING THE COURSE OF A GENERAL INSPECTION. THIS REPORT SHOULD BE USED IN CONJUNCTION WITH, AND NOT A REPLACEMENT FOR, A PRE-CLOSING WALK-THROUGH BY THE CLIENT.
THIS INSPECTION IS NOT AN INSURANCE POLICY AGAINST HIDDEN DEFECTS, OR CONDITIONS THAT ARE NOT VISIBLE AND READILY APPARENT AT THE TIME OF INSPECTION.
THE COST OF THIS INSPECTION DOES NOT ENTITLE YOU TO ANY TYPE OF PROTECTION FROM HIDDEN FLAWS AND DEFECTS. THIS INSPECTION DOES NOT TRANSFER YOUR ULTIMATE RESPONSIBILITY TO DE SOTO HOME INSPECTION SERVICES.