This report is the exclusive property of this inspection company and the client(s) listed in the report title. Use of this report by any unauthorized persons is prohibited.
Bret's Home InspectionsWebsite: http://www.reporthost.com/bretshomeinspections
Phone: (714) 296-8321
PO Box 4228
Big Bear Lake CA 92315-4228
Inspector: Bret Rasmussen
Certification from Allied Business School and Licensed General Contractor
For 12 years. (License still active #852611 California)
Property Inspection Report
||9876 Pine, Big Bear
||Wednesday, November 22, 2017
This report published on Sunday, December 03, 2017 1:18:57 PM CST
Report number: 1745
Time started: 11:30
Present during inspection: Client
Weather conditions during inspection: Dry (no rain), Sunny
Temperature during inspection: Cool
Inspection fee: 225
Payment method: Cash
Type of building: Single family
Buildings inspected: One house
Number of residential units inspected: 1
Front of building faces: East
Main entrance faces: East
Occupied: Yes, Furniture or stored items were present
Limitations: Unless specifically included in the inspection, the following items and any related equipment, controls, electric systems and/or plumbing systems are excluded from this inspection: detached buildings or structures; fences and gates; retaining walls; underground drainage systems, catch basins or concealed sump pumps; swimming pools and related safety equipment, spas, hot tubs or saunas; whether deck, balcony and/or stair membranes are watertight; trees, landscaping, properties of soil, soil stability, erosion and erosion control; ponds, water features, irrigation or yard sprinkler systems; sport courts, playground, recreation or leisure equipment; areas below the exterior structures with less than 3 feet of vertical clearance; invisible fencing; sea walls, docks and boathouses; retractable awnings. Any comments made regarding these items are as a courtesy only.
Site profile: Level
Condition of driveway: Appeared serviceable
Driveway material: Poured in place concrete
Condition of sidewalks and/or patios: Appeared serviceable
Sidewalk material: Poured in place concrete
Condition of decks, porches and/or balconies: Appeared serviceable
Deck, porch and/or balcony material: Concrete
Condition of stairs, handrails and guardrails: None
Exterior and Foundation
Limitations: The inspector performs a visual inspection of accessible components or systems at the exterior. Items excluded from this inspection include below-grade foundation walls and footings; foundations, exterior surfaces or components obscured by vegetation, stored items or debris; wall structures obscured by coverings such as siding or trim. Some items such as siding, trim, soffits, vents and windows are often high off the ground, and may be viewed using binoculars from the ground or from a ladder. This may limit a full evaluation. Regarding foundations, some amount of cracking is normal in concrete slabs and foundation walls due to shrinkage and drying. Note that the inspector does not determine the adequacy of seismic reinforcement.
Wall inspection method: Viewed from ground
Condition of wall exterior covering: Appeared serviceable
Apparent wall structure: Wood frame
Wall covering: Wood/ T-111 Siding
Condition of foundation and footings: Appeared serviceable
Apparent foundation type: Concrete slab on grade
Foundation/stem wall material: Poured in place concrete, Concrete slab on grade
Footing material (under foundation stem wall): Poured in place concrete
Trees were in contact with or were close to the building at one or more locations. Damage to the building can occur, especially during high winds, or may have already occurred (see other comments in this report). Recommend that a qualified tree service contractor or certified arborist remove trees as necessary to prevent damage to the building exterior.
Branches getting close to home
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; solar roofing components. Any comments made regarding these items are made as a courtesy only. Note that the inspector does not provide an estimate of remaining life on the roof surface material, nor guarantee that leaks have not occurred in the roof surface, skylights or roof penetrations in the past. Regarding roof leaks, only active leaks, visible evidence of possible sources of leaks, and evidence of past leaks observed during the inspection are reported on as part of this inspection. The inspector does not guarantee or warrant that leaks will not occur in the future. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high wind and rain, melting snow) would be needed to do so. Regarding the roof drainage system, unless the inspection was conducted during and after prolonged periods of heavy rain, the inspector was unable to determine if gutters, downspouts and extensions performed adequately or were leak-free.
Roof inspection method: Traversed
Condition of roof surface material: Near, at or beyond service life
Roof surface material: Asphalt or fiberglass composition shingles
Roof type: Gable
Apparent number of layers of roof surface material: One
Condition of exposed flashings: Required repair, replacement and/or evaluation (see comments below)
Condition of gutters, downspouts and extensions: Required repair, replacement and/or evaluation (see comments below)
One or more roof flashings were missing. Leaks can occur as a result. This is a conducive condition for wood-destroying organisms. Recommend that a qualified person repair as necessary.
Perimeter drip flashing was missing in 3 sides of home
Missing drip flashing, should run full length of all roof line
Missing drip flashing, should run full length of all roof line
One or more gutters and/or downspouts were missing. Rainwater can come in contact with the building exterior or accumulate around the building foundation as a result. This is a conducive condition for wood-destroying organisms. Recommend that a qualified person repair as necessary.
There are No gutters or Down spouts on home
Attic and Roof Structure
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; areas and components obscured by insulation. Any comments made regarding these items are made as a courtesy only. The inspector does not determine the adequacy of the attic ventilation system. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high/low temperatures, high/low humidity, high wind and rain, melting snow) would be needed to do so. The inspector is not a licensed engineer and does not determine the adequacy of roof structure components such as trusses, rafters or ceiling beams, or their spacing or sizing.
Attic inspection method: Viewed from hatch(es)
Condition of roof structure: Appeared serviceable
Roof structure type: Trusses
Ceiling structure: Trusses
Condition of insulation in attic (ceiling, skylight chase, etc.): Appeared serviceable
Ceiling insulation material: Fiberglass roll or batt
Approximate attic insulation R value (may vary in areas): R-13, R-19
Vermiculite insulation present: None visible
Vapor retarder: None visible
Condition of roof ventilation: Appeared serviceable
Roof ventilation type: Gable end vents
Garage or Carport
Limitations: The inspector does not determine the adequacy of firewall ratings. Requirements for ventilation in garages vary between municipalities.
Limitations: The following items are not included in this inspection: generator systems, transfer switches, surge suppressors, inaccessible or concealed wiring; underground utilities and systems; low-voltage lighting or lighting on timers or sensors. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of grounding or bonding, if this system has an adequate capacity for the client's specific or anticipated needs, or if this system has any reserve capacity for additions or expansion. The inspector does not operate circuit breakers as part of the inspection, and does not install or change light bulbs. The inspector does not evaluate every wall switch or receptacle, but instead tests a representative number of them per various standards of practice. When furnishings, stored items or child-protective caps are present some receptacles are usually inaccessible and are not tested; these are excluded from this inspection. Receptacles that are not of standard 110 volt configuration, including 240-volt dryer receptacles, are not tested and are excluded. The functionality of, power source for and placement of smoke and carbon monoxide alarms is not determined as part of this inspection. Upon taking occupancy, proper operating and placement of smoke and carbon monoxide alarms should be verified and batteries should be changed. These devices have a limited lifespan and should be replaced every 10 years. The inspector attempts to locate and evaluate all main and sub-panels. However, panels are often concealed. If panels are found after the inspection, a qualified electrician should evaluate and repair if necessary. The inspector attempts to determine the overall electrical service size, but such estimates are not guaranteed because the overall capacity may be diminished by lesser-rated components in the system. Any repairs recommended should be made by a licensed electrician.
Electric service condition: Appeared serviceable
Primary service type: Overhead
Number of service conductors: 2
Service voltage (volts): 120-240
Estimated service amperage: 100
Primary service overload protection type: Circuit breakers
Service entrance conductor material: Stranded copper
Main disconnect rating (amps): 100
System ground: Not determined, not readily apparent
Condition of main service panel: Appeared serviceable
Location of main disconnect: Breaker at top of main service panel, At main disconnect panel outside
Condition of branch circuit wiring: Serviceable
Branch circuit wiring type: Non-metallic sheathed
Solid strand aluminum branch circuit wiring present: None visible
Ground fault circuit interrupter (GFCI) protection present: No,not at kitchen counter
Arc fault circuit interrupter (AFCI) protection present: No
Smoke alarms installed: Yes, but not tested
Main disconnect rating (amps): 200
Ground fault circuit interrupter (GFCI) protection present: No, Innate yes not at kitchen counter
One or more electric receptacles (outlets) at the kitchen had no visible ground fault circuit interrupter (GFCI) protection, or the inspector was unable to determine if GFCI protection was present. If not GFCI-protected, receptacles in wet areas pose a shock hazard. Recommend that a qualified electrician evaluate and install GFCI protection if necessary and per standard building practices. General guidelines for GFCI-protected receptacles include the following locations:
- Outdoors (since 1973)
- Bathrooms (since 1975)
- Garages (since 1978)
- Kitchens (since 1987)
- Crawl spaces and unfinished basements (since 1990)
- Wet bar sinks (since 1993)
- Laundry and utility sinks (since 2005)
For more information, visit:http://www.reporthost.com/?GFCI
Plug at kitchen sink should be GFCI protected
Exterior receptacles should be GFCI protected
Plumbing / Fuel Systems
Limitations: The following items are not included in this inspection: private/shared wells and related equipment; private sewage disposal systems; hot tubs or spas; main, side and lateral sewer lines; gray water systems; pressure boosting systems; trap primers; incinerating or composting toilets; fire suppression systems; water softeners, conditioners or filtering systems; plumbing components concealed within the foundation or building structure, or in inaccessible areas such as below tubs; underground utilities and systems; overflow drains for tubs and sinks; backflow prevention devices. Any comments made regarding these items are as a courtesy only. Note that the inspector does not operate water supply or shut-off valves due to the possibility of valves leaking or breaking when operated. The inspector does not test for lead in the water supply, the water pipes or solder, does not determine if plumbing and fuel lines are adequately sized, and does not determine the existence or condition of underground or above-ground fuel tanks.
Condition of service and main line: Appeared serviceable
Water service: Public
Water pressure (psi): Seemed Strong
Location of main water shut-off: Building exterior, Out front near steet behind trash enclosure
Condition of supply lines: Appeared serviceable
Supply pipe material: Copper
Condition of drain pipes: Appeared serviceable
Drain pipe material: Plastic
Condition of waste lines: Appeared serviceable
Waste pipe material: Plastic
Vent pipe condition: Appeared serviceable
Vent pipe material: Plastic
Sump pump installed: None visible
Sewage ejector pump installed: None visible
Visible fuel storage systems: None visible
Location of main fuel shut-off valve: At gas meter
Location of main water shut-off: Building exterior, Out front near steer behind trash enclosure
Limitations: Evaluation of and determining the adequacy or completeness of the following items are not included in this inspection: water recirculation pumps; solar water heating systems; Energy Smart or energy saver controls; catch pan drains. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on water heaters, does not determine if water heaters are appropriately sized, or perform any evaluations that require a pilot light to be lit or a shut-off valve to be operated.
Condition of water heater: Appeared serviceable
Energy source: Natural gas
Capacity (in gallons): 30
Temperature-pressure relief valve installed: Yes
Location of water heater: Utility room
Hot water temperature tested: Yes
Condition of burners: Appeared serviceable
Condition of venting system: Appeared serviceable
The insulated jacket was Missing and should be replaced.
Heating, Ventilation and Air Condition (HVAC)
Limitations: The following items are not included in this inspection: humidifiers, dehumidifiers, electronic air filters; solar, coal or wood-fired heat systems; thermostat or temperature control accuracy and timed functions; heating components concealed within the building structure or in inaccessible areas; underground utilities and systems; safety devices and controls (due to automatic operation). Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on heating or cooling system components, does not determine if heating or cooling systems are appropriately sized, does not test coolant pressure, or perform any evaluations that require a pilot light to be lit, a shut-off valve to be operated, a circuit breaker to be turned "on" or a serviceman's or oil emergency switch to be operated. It is beyond the scope of this inspection to determine if furnace heat exchangers are intact and free of leaks. Condensation pans and drain lines may clog or leak at any time and should be monitored while in operation in the future. Where buildings contain furnishings or stored items, the inspector may not be able to verify that a heat source is present in all "liveable" rooms (e.g. bedrooms, kitchens and living/dining rooms).
General heating system type(s): Forced air, Wood-burning fireplace or stove
General heating distribution type(s): Ducts and registers, Elements in floor or ceiling
Last service date of primary heat source: Undetermined
Condition of forced air heating/(cooling) system: Appeared serviceable
Forced air heating system fuel type: Natural gas
Location of forced air furnace: Attic
Condition of furnace filters: Required replacement
Location for forced air filter(s): Behind return air grill(s)
Condition of forced air ducts and registers: Required repair, replacement and/or evaluation (see comments below)
One or more heating or cooling ducts were Come loose from unit. This can result in reduced energy efficiency. Recommend that qualified HVAC contractor repair or replace ducts or components as necessary.
Fireplaces, Stoves, Chimneys and Flues
Limitations: The following items are not included in this inspection: coal stoves, gas logs, chimney flues (except where visible). Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of drafting or sizing in fireplace and stove flues, and also does not determine if prefabricated or zero-clearance fireplaces are installed in accordance with the manufacturer's specifications. The inspector does not perform any evaluations that require a pilot light to be lit, and does not light fires. The inspector provides a basic visual examination of a chimney and any associated wood burning device. The National Fire Protection Association has stated that an in-depth Level 2 chimney inspection should be part of every sale or transfer of property with a wood-burning device. Such an inspection may reveal defects that are not apparent to the home inspector who is a generalist.
Condition of wood-burning fireplaces, stoves: Appeared serviceable
Wood-burning fireplace type: Masonry
Wood-burning stove type: Insert
Condition of chimneys and flues: Appeared serviceable
Wood-burning chimney type: Metal
Limitations: The following items are not included in this inspection: household appliances such as stoves, ovens, cook tops, ranges, warming ovens, griddles, broilers, dishwashers, trash compactors, refrigerators, freezers, ice makers, hot water dispensers and water filters; appliance timers, clocks, cook functions, self and/or continuous cleaning operations, thermostat or temperature control accuracy, and lights. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of the remaining life of appliances, and does not determine the adequacy of operation of appliances. The inspector does not note appliance manufacturers, models or serial numbers and does not determine if appliances are subject to recalls. Areas and components behind and obscured by appliances are inaccessible and excluded from this inspection.
Condition of counters: Appeared serviceable
Condition of cabinets: Appeared serviceable
Condition of sinks and related plumbing: Appeared serviceable
Condition of under-sink food disposal: Appeared serviceable
Condition of dishwasher: N/A (none installed)
Condition of range, cooktop or oven: Appeared serviceable
Range, cooktop or oven type: Natural gas, Electronic ignition
Type of ventilation: Hood or built into microwave over range or cooktop
Condition of refrigerator: Appeared serviceable
Condition of built-in microwave oven: Appeared serviceable
Bathrooms, Laundry and Sinks
Limitations: The following items are not included in this inspection: overflow drains for tubs and sinks; heated towel racks, saunas, steam generators, clothes washers, clothes dryers. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of washing machine drain lines, washing machine catch pan drain lines, or clothes dryer exhaust ducts. The inspector does not operate water supply or shut-off valves for sinks, toilets, bidets, clothes washers, etc. due to the possibility of valves leaking or breaking when operated. The inspector does not determine if shower pans or tub and shower enclosures are water tight, or determine the completeness or operability of any gas piping to laundry appliances.
Location #A: Full bath
Condition of counters: Appeared serviceable
Condition of cabinets: Appeared serviceable
Condition of flooring: Appeared serviceable
Condition of sinks and related plumbing: Appeared serviceable
Condition of toilets: Appeared serviceable
Condition of bathtubs and related plumbing: Appeared serviceable
Condition of shower(s) and related plumbing: Appeared serviceable
Condition of ventilation systems: Appeared serviceable
Bathroom and laundry ventilation type: Windows
Gas supply for laundry equipment present: Yes
240 volt receptacle for laundry equipment present: Yes
The clothes dryer was equipped with a vinyl or mylar, accordion-type, flexible exhaust duct. The U.S. Consumer Product Safety Commission considers these types of ducts to be unsafe, and a fire hazard. They can trap lint and are susceptible to kinks or crushing, which can greatly reduce the air flow and cause overheating. Recommend that such ducts be replaced with a rigid or corrugated semi-rigid metal duct, and by a qualified contractor if necessary. For more information, visit:http://www.reporthost.com/?DRYER
The sink at location(s) #A drained slowly. Recommend clearing drain and/or having a qualified plumber repair if necessary.
Probably just slightly clogged
Supply lines to washer are rubber, which are prone to fail. Would suggest replacing with bradded lines.
Interior, Doors and Windows
Limitations: The following items are not included in this inspection: security, intercom and sound systems; communications wiring; central vacuum systems; elevators and stair lifts; cosmetic deficiencies such as nail-pops, scuff marks, dents, dings, blemishes or issues due to normal wear and tear in wall, floor and ceiling surfaces and coverings, or in equipment; deficiencies relating to interior decorating; low voltage and gas lighting systems. Any comments made regarding these items are as a courtesy only. Note that the inspector does not evaluate any areas or items which require moving stored items, furnishings, debris, equipment, floor coverings, insulation or similar materials. The inspector does not test for asbestos, lead, radon, mold, hazardous waste, urea formaldehyde urethane, or any other toxic substance. Some items such as window, drawer, cabinet door or closet door operability are tested on a sampled basis. The client should be aware that paint may obscure wall and ceiling defects, floor coverings may obscure floor defects, and furnishings may obscure wall, floor and floor covering defects. If furnishings were present during the inspection, recommend a full evaluation of walls, floors and ceilings that were previously obscured when possible. Determining the cause and/or source of odors is not within the scope of this inspection.
Condition of exterior entry doors: Appeared serviceable
Exterior door material: Wood
Condition of interior doors: Appeared serviceable
Condition of windows and skylights: Appeared serviceable
Type(s) of windows: Metal, Multi-pane, Sliding
Condition of walls and ceilings: Appeared serviceable
Wall type or covering: Drywall, Paneling
Ceiling type or covering: Drywall
Condition of flooring: Appeared serviceable
Condition of concrete slab floor(s): Appeared serviceable
Flooring type or covering: Carpet, Vinyl, linoleum or marmoleum
Condition of stairs, handrails and guardrails: None
The Parties Understood and Agreed as follows:
1. INSPECTOR GUARANTEES to perform a visual inspection of the home and to provide CLIENT with a written inspection report identifying the defects that INSPECTOR both observed and deemed material. INSPECTOR may offer comments as a courtesy, but these comments will not comprise the bargained-for report. The report is only supplementary to the sellers disclosure.
2. INSPECTOR agrees to perform the inspection in accordance to the current Standards of Practice of the National Association of Certified Home Inspectors posted at http://www.nachi.org/sop.htm.
3. CLIENT understands that the inspection will be performed in accordance to the aforementioned Standards, which contain certain limitations, exceptions, and exclusions.
4. The inspection and report are performed and prepared for the use of CLIENT, who gives INSPECTOR permission to discuss observations with real estate agents, owners, repair persons and other interested parties. INSPECTOR accepts no responsibility for use or misinterpretation by third parties.
5. INSPECTOR does not perform engineering, architectural, plumbing, or any other job function requiring an occupational license in the jurisdiction where the inspection is taking place, unless the inspector holds a valid occupational license, in which case he/she may inform the CLIENT that he/she is so licensed, and is therefore qualified to go beyond this basic home inspection, and for additional fee, perform additional inspections beyond those within the scope of the basic home inspection.
6. In the event of a claim against INSPECTOR, CLIENT agrees to supply INSPECTOR with the following: (1) Written notification of adverse conditions within 14 days of discovery, and (2) Access to the premises. Failure to comply with the above conditions will release INSPECTOR and its agents from any and all obligations.
7. HOLD HARMLESS AGREEMENT: CLIENT agrees to hold any and all real estate agents involved in the purchase of the property to be inspected harmless and keep them exonerated from all loss, damage, liability or expense occasioned or claimed by reasons of acts or neglects of the INSPECTOR or his employees or visitors or of independent contractors engaged or paid by INSPECTOR for the purpose of inspecting the subject home.
8. In the event that CLIENT fails to prove any adverse claims against INSPECTOR in a court of law, then the CLIENT will pay all legal costs, expenses and fees of INSPECTOR in defending said claims.
9. If any provision of this Agreement is declared invalid or unenforceable by any court, the remaining provisions will remain in effect. This agreement represents the entire agreement between the parties. No change or modification shall be enforceable against any party unless such change or modification is in writing and signed by the parties. This Agreement shall be binding upon and enforceable by the parties and their heirs, executors, administrators, successors and assigns. CLIENT shall have no cause of action against INSPECTOR after one year after from the date of the inspection.
10. Payment, by CLIENT or CLIENTs representative, is due in full at the inspection site, upon completion of the on-site inspection. The CLIENT will pay all legal and time expenses incurred in collecting due payments.
"A Home Inspection is a Non-Invasive Visual Examination of a Residential Dwelling. Components may include any combination of mechanical, structural, electrical, plumbing, or other essential systems or portions of the home, as identified and agreed to by the Client and Inspector, such as: Roof ~ Exterior ~ Basement / Foundation ~ Heating Cooling ~ Plumbing ~ Electrical ~ Fireplace ~ Attic & Insulation ~ Doors, Windows & Interior."
From NACHI Standards of Practice
"There are conditions that require the removal of some part of the building to observe, measure, or test otherwise concealed construction. Such intrusive inspections require some demolition and should be performed only with the permission of the owner and by experienced, qualified mechanics."
-From the U.S. Department of Housing and Urban Development's
Residential Rehabilitation Inspection Guide, 2000
- HOMES BEING INSPECTED DO NOT "PASS" OR "FAIL" -
A home inspector merely discloses his or her findings and reports those findings to the client. Everyone involved graduates to a state of higher learning, and the client can now make better informed decisions about the purchase of a home and its future needs of upkeep and repair.
Four key areas of most home/building inspections cover the exterior, the basement or crawlspace areas, the attic or crawlspace areas and the living areas. Inspectors typically will spend sufficient time in all of these areas to visually look for a host of red flags, tell-tale clues and signs or defects and deficiencies.
The inspected areas of a home/building will consist of all of the major visible and accessible electro-mechanical systems as well as the major visible and accessible structural systems and components of a building as they appeared and functioned at the time and date of the inspection.
Inspectors typically do not provide warranties or guaranties with their inspections and reports. Buyers should therefore not rely on the inspection as any form of insurance policy against any latent, hidden, concealed or future defects and deficiencies.
The following are also some key items that buyers should remember and consider when reviewing their inspection reports:
* Inspections are not code compliance evaluations.
* Inspection reports are not structural engineering reports.
* Systems and components that are off during the inspection are not tested or reactivated.
* Buyers should consult with and ask questions of owners and their representatives.
* Roof inspections and their components are typically done from eaves or street level with binoculars.
* Reports are confidential and are meant exclusively for buyers, and not brokers or owners.
* Inspectors typically will not find each and every defect in a building, hence buyers should anticipate future typical defects and deficiencies.
* Further evaluation by specialists is recommended for any areas showing defects/deficiencies.
* A final walk-through inspection should be carried out the day before closing by the new owners to double check the condition of the building.
I. An inspection is not technically exhaustive.
II. An inspection will not identify concealed or latent defects.
III. An inspection will not deal with aesthetic concerns or what could be deemed matters of taste, cosmetic, etc.
IV. An inspection will not determine the suitability of the property for any use.
V. An inspection does not determine the market value of the property or its marketability.
VI. An inspection does not determine the advisability or inadvisability of the purchase of the inspected property.
VII. An inspection does not determine the life expectancy of the property or any components or systems therein.
VIII. An inspection does not include items not permanently installed.
IX. These Standards of Practice apply only to homes with four or fewer dwelling units.
I. The inspectors are not required to determine:
A. Property boundary lines or encroachments.
B. The condition of any component or system that is not readily accessible.
C. The service life expectancy of any component or system.
D. The size, capacity, BTU, performance, or efficiency of any component or system.
E. The cause or reason of any condition.
F. The cause for the need of repair or replacement of any system or component.
G. Future conditions.
H. The compliance with codes or regulations.
I. The presence of evidence of rodents, animals or insects.
J. The presence of mold, mildew or fungus.
K. The presence of air-borne hazards.
L. The presence of birds.
M. The presence of other flora or fauna.
N. The air quality.
O. The existence of asbestos.
P. The existence of environmental hazards.
Q. The existence of electro-magnetic fields.
R. The presence of hazardous materials including, but not limited to, the presence of lead in paint.
S. Any hazardous waste conditions.
T. Any manufacturer recalls or conformance with manufacturer installation or any information included in the consumer protection bulletin.
U. Operating costs of systems.
V. Replacement or repair cost estimates.
W. The acoustical properties of any systems.
X. Estimates of how much it will cost to run any given system.
II. The inspectors are not required to operate:
A. Any system that is shut down.
B. Any system that does not function properly.
C. Or evaluate low voltage electrical systems such as, but not limited to:
1. Phone lines.
2. Cable lines.
5. Remote controls.
D. Any system that does not turn on with the use of normal operating controls.
E. Any shut off valve.
F. Any electrical disconnect or over current protection devices.
G. Any alarm systems.
H. Moisture meters, gas detectors or similar equipment.
III. The inspectors are not required to:
A. Move any personal items or other obstructions,
such as, but not limited to:
1. Throw rugs.
3. Floor or wall coverings.
4. Ceiling tiles
5. Window coverings.
B. Dismantle, open, or uncover any system or component.
C. Enter or access any area which may, in the opinion of the inspector, to be unsafe or risk personal safety.
D. Enter crawlspaces or other areas that are unsafe or not readily accessible.
E. Inspect underground items such as, but not limited to, underground storage tanks or other indications of their presence, whether abandoned or actively used.
F. Do anything which, in the inspector's opinion, is likely to be unsafe or dangerous to the inspector or others or damage property, such as, but not limited to, walking on roof surfaces, climbing ladders, entering attic spaces or negotiating with dogs.
G. Inspect decorative items.
H. Inspect common elements or areas in multi-unit housing.
I. Inspect intercoms, speaker systems, radio-controlled, security devices or lawn irrigation systems.
J. Offer guarantees or warranties.
K. Offer or perform any engineering services.
L. Offer or perform any trade or professional service other than home inspection.
M. Research the history of the property, report on its potential for alteration, modification, extendibility, or its suitability for a specific or proposed use for occupancy.
N. Determine the age of construction or installation of any system structure, or component of a building, or differentiate between original construction or subsequent additions, improvements, renovations or replacements thereto.
O. Determine the insurability of a property.