Company email: Alloverhomeinspections@gmail.com
Inspector's email: Kriz57@aol.com
Phone: (321) 377-0523
2681 Windsor Heights St.
Deltona, Fl. 32738
Inspector: Keith Rizzo
This report published on Wednesday, November 10, 2010 7:18:31 PM EST
Home Inspection Report|
||560 Bernasek Dr
Debary, Fl. 32713
View summary page
This report is the exclusive property of All Over Home Inspections and the client(s) listed in the report title. Use of this report by any unauthorized persons is prohibited.
How to Read this Report
This report is organized by the property's functional areas. Within each functional area, descriptive information is listed first and is shown in bold type. Items of concern follow descriptive information.
Concerns are shown and sorted according to these types:
|Safety||Poses a risk of injury or death |
|Repair/Replace||Recommend repairing or replacing |
|Repair/Maintain||Recommend repair and/or maintenance |
|Evaluate||Recommend evaluation by a specialist |
|Comment||For your information |
Click here for a glossary of building construction terms. Contact your inspector if there are terms that you do not understand, or visit the glossary of construction terms at http://www.reporthost.com/glossary.asp
Structures inspected: Home
Type of building: Single family
Age of building: 25 Years
Present during inspection: Client(s), Realtor(s)
Weather conditions: Clear
Ground condition: Dry
Foundation type: Slab on grade
The following items are excluded from this inspection: Private sewage disposal system, Irrigation system, Swimming pool, Central vacuum system
Footing material: Poured in place concrete
Foundation material: Poured in place concrete
Apparent wall structure: Wood frame
Wall covering: Cedar Siding
Driveway material: Poured in place concrete
Vegetation such as trees, shrubs and/or vines are in contact with or less than one foot from the structure's exterior. Vegetation can serve as a conduit for wood destroying insects and may retain moisture against the exterior after it rains. Vegetation should be pruned and/or removed as necessary to maintain a one foot clearance between it and the structure's exterior. There is a large hole in the siding where the water line exits the rear of the home. this should be sealed to prevent insects and rodents from entering the home. Two plants have roots growing into the siding on the rear of the home. these roots should be removed to prevent the siding from splitting or being loosened.
vegetation growing against home.
Plant root growing into siding at rear of home.
Vegetation growing against home.
Hose bib at rear of the home needs siding sealed.
Plant root growing into siding below hose bib needs to be removed.
Small isolated areas of wood rot was observed on the siding. I recommend having the rotted areas replaced and the exterior of the home repainted.
Roof inspection method: Traversed
Wood rot on siding at garage door
Wood rot on siding
Roof type: Gable
Roof covering: Asphalt or fiberglass composition shingles
Roof ventilation: Adequate
Roofing nails in one or more areas have loosened or backed out. Leaks may occur as a result. A qualified roofing contractor should evaluate the entire roof and make repairs as necessary, such as reseating nails and applying sealant.
Nail pops on roof.
The overhead garage door does not have the auto reverse installed properly. As a result the door will continue to close even if something is in its path.
Inspection method: Traversed
Roof structure type: Trusses
Ceiling structure: Trusses
Insulation material: Fiberglass loose fill
The attic of this home is very large. Insulation is on average 6 inches deep. The ridge vent and soffit vents were found to be unobstructed.
Primary service type: Underground
Primary service overload protection type: Circuit breakers
Service amperage (amps): 200
Service voltage (volts): 120/240
Location of main service switch: Panel next to meter base.
Location of sub panels: Garage
Location of main disconnect: Breaker at top of main service panel
Service entrance conductor material: Aluminum
System ground: Ground rod(s) in soil
Main disconnect rating (amps): 200
Branch circuit wiring type: Non-metallic sheathed
All outlets were checked and found to be in working order. Some of the outlets in the home are missing covers. These outlets should have the covers replaced. No open grounds or reverse polarity was found.
Estimated age: new
Energy source: Electricity
Capacity (in gallons): 40
This is a new water heater and should have many years of useful life.
Primary heating system energy source: Electric
Primary heat system type: Forced air
Primary A/C energy source: Electric
Primary Air conditioning type: Heat pump
Distribution system: Sheet metal ducts, Flexible ducts
Manufacturer: American Standard
Filter location: At the base of the furnace
The AC and Furnace of this home appear to have been replaced. The AC was run and a differential of 15 degrees was found. These units should have many years of service left. However, regular maintenance should be preformed to maximize their life.
Water service: Public
Service pipe material: Galvanized steel
Supply pipe material: Copper
Vent pipe material: Plastic
Drain pipe material: Plastic
Waste pipe material: Plastic
Neither the clothes washer nor dryer were operated or evaluated. They are excluded from this inspection.
All sinks tubs and toilets were tested and found to be free of leaks. Water pressure throughout the home was good and drainage was adequate.
One or more kitchen appliances appear to be near, at, or beyond their intended service life of 10 to 15 years. Recommend budgeting for replacements as necessary.
The light in the hall bath needs new bulbs. All tubs, showers, sinks and toilets were operating at the time of the inspection. No leaks were found under the bathroom vanities.
The interior of the home is in very good condition for a home of this age. Only minor cosmetic damage was observed. some light bulbs in the home are burned out. Some of the light fixtures are missing globes. These bulbs and globes should be replaced.
All Over Home Inspections