This report is the exclusive property of this inspection company and the client(s) listed in the report title. Use of this report by any unauthorized persons is prohibited.
AA Home InspectionsWebsite: http://aahomeinspectionstn.com
Phone: (865) 993-2554
Inspector: Duff Woodward
TN License #995
Property Inspection Report
||707 Main St.
Tazewell, TN. 37879
||Wednesday, July 26, 2017
This report published on Monday, September 18, 2017 1:34:47 PM EDT
Report number: sample20170726
Time started: 10:00 AM
Time finished: 2:00 PM
Present during inspection: Client
Client present for discussion at end of inspection: Yes
Weather conditions during inspection: Dry (no rain), Sunny
Temperature during inspection: Warm, 73
Inspection fee: $250.00
Payment method: Cash
Type of building: Single family
Buildings inspected: One house
Number of residential units inspected: 1
Age of main building: 53
Source for main building age: Municipal records or property listing
Front of building faces: Northeast
Occupied: Yes, Furniture or stored items were present
Some areas and items at this property were obscured by furniture. This often includes but is not limited to walls, floors, windows, inside and under cabinets, under sinks, on counter tops, in closets, behind window coverings, under rugs or carpets, and under or behind furniture. Areas around the exterior, under the structure, in the garage and in the attic may also be obscured by stored items. The inspector in general does not move personal belongings, furnishings, carpets or appliances. When furnishings, stored items or debris are present, all areas or items that are obscured, concealed or not readily accessible are excluded from the inspection. The client should be aware that when furnishings, stored items or debris are eventually moved, damage or problems that were not noted during the inspection may be found.
Limitations: Unless specifically included in the inspection, the following items and any related equipment, controls, electric systems and/or plumbing systems are excluded from this inspection: detached buildings or structures; fences and gates; retaining walls; underground drainage systems, catch basins or concealed sump pumps; swimming pools and related safety equipment, spas, hot tubs or saunas; whether deck, balcony and/or stair membranes are watertight; trees, landscaping, properties of soil, soil stability, erosion and erosion control; ponds, water features, irrigation or yard sprinkler systems; sport courts, playground, recreation or leisure equipment; areas below the exterior structures with less than 3 feet of vertical clearance; invisible fencing; sea walls, docks and boathouses; retractable awnings. Any comments made regarding these items are as a courtesy only.
Site profile: Moderate slope
Condition of driveway: Appeared serviceable
Driveway material: Asphalt
Condition of sidewalks and/or patios: Appeared serviceable
Sidewalk material: Poured in place concrete
Condition of deck, patio and/or porch covers: Appeared serviceable
Deck, patio, porch cover material and type: Open
Condition of decks, porches and/or balconies: Appeared serviceable
Deck, porch and/or balcony material: Wood
Condition of stairs, handrails and guardrails: Appeared serviceable
Exterior stair material: Wood
Ledger boards for one or more decks, balconies or porches appeared to be attached with nails and masonry screws only. This method of attachment is substandard and may result in such structures separating from the main building. This is a potential safety hazard. Modern standards call for ledger boards to be installed with 1/2 inch lag screws or bolts into solid backing, and brackets such as Simpson Strong Tie DTT2 brackets and threaded rod
, connecting interior and exterior joists. Recommend that a qualified contractor repair per standard building practices. For more information, visit:http://www.reporthost.com/?LBhttp://www.reporthost.com/?SD
Retaining wall is failing, needs repaired or replaced.
Soil was in contact with one or more wooden deck, porch or balcony support posts. This is a conducive condition for wood destroying organisms. Even if posts are made of treated wood, the cut ends below soil may not have been field treated. Recommend grading soil or repairing as necessary to prevent wood-soil contact.
Exterior and Foundation
Limitations: The inspector performs a visual inspection of accessible components or systems at the exterior. Items excluded from this inspection include below-grade foundation walls and footings; foundations, exterior surfaces or components obscured by vegetation, stored items or debris; wall structures obscured by coverings such as siding or trim. Some items such as siding, trim, soffits, vents and windows are often high off the ground, and may be viewed using binoculars from the ground or from a ladder. This may limit a full evaluation. Regarding foundations, some amount of cracking is normal in concrete slabs and foundation walls due to shrinkage and drying. Note that the inspector does not determine the adequacy of seismic reinforcement.
Wall inspection method: Viewed from ground
Condition of wall exterior covering: Appeared serviceable
Apparent wall structure: Wood frame
Wall covering: Vinyl, Brick veneer
Condition of foundation and footings: Appeared serviceable
Apparent foundation type: Crawl space
Foundation/stem wall material: Concrete block
Footing material (under foundation stem wall): Poured in place concrete
Limitations: Structural components such as joists and beams, and other components such as piping, wiring and/or ducting that are obscured by under-floor insulation are excluded from this inspection. The inspector does not determine if support posts, columns, beams, joists, studs, trusses, etc. are of adequate size, spanning or spacing.
The inspector does not guarantee or warrant that water will not accumulate in the crawl spaces in the future. Complete access to all crawl space areas during all seasons and during prolonged periods of all types of weather conditions (e.g. heavy rain, melting snow) would be needed to do so.
The inspector attempts to locate all crawl space access points and areas. Access points may be obscured or otherwise hidden by furnishings or stored items. In such cases, the client should ask the property owner where all access points are that are not described in this inspection, and have those areas inspected. Note that crawl space areas should be checked at least annually for water intrusion, plumbing leaks and pest activity.
Crawl space inspection method: Traversed
Condition of floor substructure above: Appeared serviceable
Pier or support post material: Concrete block
Floor structure above: Solid wood joists
Condition of vapor barrier: Required repairs, replacement and/or evaluation (see comments below)
Vapor barrier present: Partial
Condition of crawl space ventilation: Appeared serviceable
Ventilation type: with vents
Evidence of prior water intrusion or accumulation was found in one or more sections of the crawl space. For example, sediment stains on the vapor barrier or foundation, and/or efflorescence on the foundation. Accumulated water is a conducive condition for wood-destroying organisms and should not be present in the crawl space. The crawl space should be monitored in the future for accumulated water, especially after heavy and/or prolonged periods of rain. If water is found to accumulate, then recommend that a qualified contractor who specializes in drainage issues evaluate and repair as necessary. Typical repairs for preventing water from accumulating in crawl spaces include:
- Repairing, installing or improving rain run-off systems (gutters, downspouts and extensions or drain lines)
- Improving perimeter grading
- Repairing, installing or improving underground footing and/or curtain drains
Ideally, water should not enter crawl spaces, but if water must be controlled after it enters the crawl space, then typical repairs include installing trenches, gravity drains and/or sump pump(s) in the crawl space.
Fungal rot was found at one or more sill plates and/or joists. Recommend that a qualified contractor evaluate and repair as necessary. All rotten wood should be replaced.
Minor amounts of standing water were found at one or more locations in the crawl space. Some minor seasonal water accumulation can be normal. However significant amounts of Water may evaporate and enter the structure above causing high levels of moisture in the structure. This can be a conducive condition for wood-destroying organisms. Rain runoff is the most common cause of wet crawl spaces but water can come from other sources such as groundwater or underground springs. Recommend monitoring the crawl space in the future, especially after heavy and/or prolonged periods of rain. Correct any issues related to outside perimeter grading and/or roof drainage (see any other comments about this in this report). Also, review any disclosure statements available and ask the property owner about past accumulation of water in the crawl space.
If standing water persists or increases in amount, recommend that a qualified contractor who specializes in drainage issues evaluate and repair as necessary. Typically such repairs include:
- Repairing, installing or improving underground footing and/or curtain drains
- Applying waterproof coatings to foundation walls
- Digging trenches in the crawl space to collect or divert water
- Installing sump pumps
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; solar roofing components. Any comments made regarding these items are made as a courtesy only. Note that the inspector does not provide an estimate of remaining life on the roof surface material, nor guarantee that leaks have not occurred in the roof surface, skylights or roof penetrations in the past. Regarding roof leaks, only active leaks, visible evidence of possible sources of leaks, and evidence of past leaks observed during the inspection are reported on as part of this inspection. The inspector does not guarantee or warrant that leaks will not occur in the future. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high wind and rain, melting snow) would be needed to do so. Occupants should monitor the condition of roofing materials in the future. For older roofs, recommend that a professional inspect the roof surface, flashings, appurtenances, etc. annually and maintain/repair as might be required. If needed, the roofer should enter attic space(s). Regarding the roof drainage system, unless the inspection was conducted during and after prolonged periods of heavy rain, the inspector was unable to determine if gutters, downspouts and extensions perform adequately or are leak-free.
Roof inspection method: Viewed from ground with binoculars
Condition of roof surface material: Appeared serviceable
Roof surface material: Metal panel
Roof type: Hipped
Apparent number of layers of roof surface material: One
Condition of gutters, downspouts and extensions: Appeared serviceable
Electrical mast boot is missing. The mast has sealant around it instead of a boot. The sealant by itself could possibly fail and be prone to leaks.
Attic and Roof Structure
Limitations: The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; areas and components obscured by insulation. Any comments made regarding these items are made as a courtesy only. The inspector does not determine the adequacy of the attic ventilation system. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high/low temperatures, high/low humidity, high wind and rain, melting snow) would be needed to do so. The inspector is not a licensed engineer and does not determine the adequacy of roof structure components such as trusses, rafters or ceiling beams, or their spacing or sizing.
Attic inspection method: Viewed from hatch(es)
Condition of roof structure: Appeared serviceable
Roof structure type: Rafters
Ceiling structure: Ceiling joists
Condition of insulation in attic (ceiling, skylight chase, etc.): Appeared serviceable
Ceiling insulation material: Fiberglass roll or batt
Condition of roof ventilation: Appeared serviceable
Roof ventilation type: Ridge vent(s), Enclosed soffit vents
Roof sheathing has damage.
Limitations: The following items are not included in this inspection: generator systems, transfer switches, surge suppressors, inaccessible or concealed wiring; underground utilities and systems; low-voltage lighting or lighting on timers or sensors. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of grounding or bonding, if this system has an adequate capacity for the client's specific or anticipated needs, or if this system has any reserve capacity for additions or expansion. The inspector does not operate circuit breakers as part of the inspection, and does not install or change light bulbs. The inspector does not evaluate every wall switch or receptacle, but instead tests a representative number of them per various standards of practice. When furnishings, stored items or child-protective caps are present some receptacles are usually inaccessible and are not tested; these are excluded from this inspection. Receptacles that are not of standard 110 volt configuration, including 240-volt dryer receptacles, are not tested and are excluded. The functionality of, power source for and placement of smoke and carbon monoxide alarms is not determined as part of this inspection. Upon taking occupancy, proper operating and placement of smoke and carbon monoxide alarms should be verified and batteries should be changed. These devices have a limited lifespan and should be replaced every 10 years. The inspector attempts to locate and evaluate all main and sub-panels. However, panels are often concealed. If panels are found after the inspection, a qualified electrician should evaluate and repair if necessary. The inspector attempts to determine the overall electrical service size, but such estimates are not guaranteed because the overall capacity may be diminished by lesser-rated components in the system. Any repairs recommended should be made by a licensed electrician.
Electric service condition: Appeared serviceable
Primary service type: Overhead
Number of service conductors: 3
Estimated service amperage: 200
Primary service overload protection type: Circuit breakers
Main disconnect rating (amps): 200
Condition of main service panel: Appeared serviceable
Condition of sub-panel(s): Appeared serviceable
Location of main service panel #A: Bedroom
Condition of branch circuit wiring: Serviceable
Branch circuit wiring type: non-metallic sheathed
Ground fault circuit interrupter (GFCI) protection present: Yes
One or more electric receptacles at the bathroom(s) and/or full bath had no visible ground fault circuit interrupter (GFCI) protection, or the inspector was unable to determine if GFCI protection was present. If not GFCI-protected, receptacles in wet areas pose a shock hazard. Recommend that a qualified electrician evaluate and install GFCI protection if necessary and per standard building practices. General guidelines for GFCI-protected receptacles include the following locations:
- Outdoors (since 1973)
- Bathrooms (since 1975)
- Garages (since 1978)
- Kitchens (since 1987)
- Crawl spaces and unfinished basements (since 1990)
- Wet bar sinks (since 1993)
- Laundry and utility sinks (since 2005)
For more information, visit:http://www.reporthost.com/?GFCI
Also, the receptacle has an open ground.
Bare wire ends, or wires with a substandard termination, were found at one or more locations. This is a potential shock hazard. Recommend that a qualified electrician repair as necessary. For example, by cutting wires to length and terminating with wire nuts in a permanently mounted, covered junction box.
This wire is in the crawl space. It's located where the wires enter the floor going to the breaker box. It's live.
One or more modern, 3-slot electric receptacles were found with an open ground. Three-slot receptacles should have a hot, a neutral and a ground wire connected. Homeowners often install new 3-slot receptacles on older, 2-wire circuits that only have hot and neutral wires. This is a shock hazard when appliances that require a ground are used with these receptacles. Examples of such appliances include computers and related hardware, refrigerators, freezers, portable air conditioners, clothes washers, aquarium pumps, and electrically operated gardening tools. Where the electric system was installed prior to when grounded circuits were required (1960s), it is permissible to replace 3-slot receptacles with 2-slot receptacles to prevent appliances that require a ground from being plugged into an ungrounded circuit. However, the client should be aware of this limitation when planning use for various rooms, such as an office. For newer electric systems, circuits should be repaired so grounded, 3-wire cables provide power to 3-slot receptacles. Recommend that a qualified electrician repair per standard building practices.
The reason for having a drip loop on an electrical service is to allow any rain or moisture, that may make contact with the wires, a place to go away from the weather head and the electrical connection to the utility company's wires. Water or moisture running down the service pipe or running into electrical connection points would spell costly repairs for you in the future. A qualified electrician or the utility company should repair per standard building practices.
The inspector was unable to open and evaluate panel(s) #A because items were blocking access. The condition of these panel(s) is unknown and they are excluded from this inspection. Repairs may be needed. Recommend that a qualified person correct conditions, or that a qualified contractor make repairs if necessary so panels can be opened, and that a qualified person fully evaluate panel(s).
One or more globes or covers for light fixtures were missing or damaged. Recommend replacing as necessary to avoid exposed bulbs. With closet lighting or where flammable stored objects are near light fixtures, missing or broken covers can be a fire hazard.
Bulbs in one or more light fixtures were missing or broken. These light fixtures couldn't be fully evaluated. If replacement bulbs are inoperable, then recommend that a qualified electrician evaluate and repair or replace light fixtures as necessary.
Plumbing / Fuel Systems
Limitations: The following items are not included in this inspection: private/shared wells and related equipment; private sewage disposal systems; hot tubs or spas; main, side and lateral sewer lines; gray water systems; pressure boosting systems; trap primers; incinerating or composting toilets; fire suppression systems; water softeners, conditioners or filtering systems; plumbing components concealed within the foundation or building structure, or in inaccessible areas such as below tubs; underground utilities and systems; overflow drains for tubs and sinks; backflow prevention devices. Any comments made regarding these items are as a courtesy only. Note that the inspector does not operate water supply or shut-off valves due to the possibility of valves leaking or breaking when operated. The inspector does not test for lead in the water supply, the water pipes or solder, does not determine if plumbing and fuel lines are adequately sized, and does not determine the existence or condition of underground or above-ground fuel tanks.
Condition of service and main line: Appeared serviceable
Water service: Public
Location of main water shut-off: Crawl space
Condition of supply lines: Appeared serviceable, Required repair, replacement and/or evaluation (see comments below)
Supply pipe material: Copper, PEX plastic, CPVC plastic
Condition of drain pipes: Appeared serviceable
Drain pipe material: Plastic
Condition of waste lines: Appeared serviceable
Waste pipe material: Plastic
Vent pipe condition: Appeared serviceable
Vent pipe material: Plastic
One or more copper water supply pipes had substandard support or were loose. Leaks can occur as a result. Copper supply pipes should have approved hangers every 6-8 feet. If hangers are in contact with the copper pipe, they should be made of a material that doesn't cause the pipes or hangers to corrode due to contact of dissimilar metals. Recommend that a qualified person install hangers or secure pipes per standard building practices.
One or more plastic PEX water supply pipes had substandard support or were loose. Leaks can occur as a result. PEX supply pipes should have approved hangers every 32-36 inches when run horizontally. Special hangers that allow movement from expansion and that won't damage the soft plastic piping should be used. Recommend that a qualified person install hangers or secure pipes per standard building practices.
The hose bib is loose, needs to be secured to the wall.
What appeared to be the main water shut-off valve was located in the crawl space. This is an inconvenient location at best, and may prevent the water from being turned off in a timely manner in the event of a plumbing emergency. Consider having a qualified plumber relocate the shut-off valve to a more convenient location, such as in a closet or a cabinet under a sink.
Water supply pressure OK.
Limitations: Evaluation of and determining the adequacy or completeness of the following items are not included in this inspection: water recirculation pumps; solar water heating systems; Energy Smart or energy saver controls; catch pan drains. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on water heaters, does not determine if water heaters are appropriately sized, or perform any evaluations that require a pilot light to be lit or a shut-off valve to be operated.
Condition of water heater: Appeared serviceable
Energy source: Electricity
Capacity (in gallons): 50
Temperature-pressure relief valve installed: Yes
Location of water heater: Laundry room
The estimated useful life for most water heaters is 8-12 years. This water heater appeared to be at this age and/or its useful lifespan and may need replacing at any time. Recommend budgeting for a replacement in the near future, or considering replacement now before any leaks occur. The client should be aware that significant flooding can occur if the water heater fails. If not replaced now, consider having a qualified person install a catch pan and drain or a water alarm to help prevent damage if water does leak.
Manufactured in 2007
Heating, Ventilation and Air Condition (HVAC)
Limitations: The following items are not included in this inspection: humidifiers, dehumidifiers, electronic air filters; solar, coal or wood-fired heat systems; thermostat or temperature control accuracy and timed functions; heating components concealed within the building structure or in inaccessible areas; underground utilities and systems; safety devices and controls (due to automatic operation). Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on heating or cooling system components, does not determine if heating or cooling systems are appropriately sized, does not test coolant pressure, or perform any evaluations that require a pilot light to be lit, a shut-off valve to be operated, a circuit breaker to be turned "on" or a serviceman's or oil emergency switch to be operated. It is beyond the scope of this inspection to determine if furnace heat exchangers are intact and free of leaks. Condensation pans and drain lines may clog or leak at any time and should be monitored while in operation in the future. Where buildings contain furnishings or stored items, the inspector may not be able to verify that a heat source is present in all "liveable" rooms (e.g. bedrooms, kitchens and living/dining rooms).
General heating system type(s): Heat pump
General heating distribution type(s): Ducts and registers
Condition of forced air ducts and registers: Appeared serviceable
Condition of cooling system and/or heat pump: Appeared serviceable
Cooling system and/or heat pump fuel type: Electric
Type: Split system, Heat pump
Condition of controls: Appeared serviceable
One or more heating or cooling ducts in an unconditioned space (e.g. crawl space, attic or basement) were not insulated, or the insulation was damaged or deteriorated. This can result in reduced energy efficiency, moisture inside heating ducts, and/or "sweating" on cooling ducts. Recommend that a qualified person repair per standard building practices. For example, by wrapping ducts in insulation with an R-value of R-8.
The outdoor air temperature was above 65 degrees Fahrenheit during the inspection. Heating systems can be damaged if operated at such high temperatures. Because of this, the inspector was unable to operate and fully evaluate the heating system.
Manufactured in 2014
Limitations: The following items are not included in this inspection: household appliances such as stoves, ovens, cook tops, ranges, warming ovens, griddles, broilers, dishwashers, trash compactors, refrigerators, freezers, ice makers, hot water dispensers and water filters; appliance timers, clocks, cook functions, self and/or continuous cleaning operations, thermostat or temperature control accuracy, and lights. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of the remaining life of appliances, and does not determine the adequacy of operation of appliances. The inspector does not note appliance manufacturers, models or serial numbers and does not determine if appliances are subject to recalls. Areas and components behind and obscured by appliances are inaccessible and excluded from this inspection.
Condition of counters: Appeared serviceable
Condition of cabinets: Appeared serviceable
Condition of sinks and related plumbing: Appeared serviceable
Type of ventilation: Hood or built into microwave over range or cooktop
The range could tip forward. An anti-tip bracket may not be installed. This is a potential safety hazard since the range can tip forward when weight is applied to the open door, such as when a small child climbs on it or if heavy objects are dropped on it. Anti-tip brackets have been sold with all free-standing ranges since 1985. Recommend installing an anti-tip bracket to eliminate this safety hazard. For more information, visit:http://www.reporthost.com/?ATB
Bathrooms, Laundry and Sinks
Limitations: The following items are not included in this inspection: overflow drains for tubs and sinks; heated towel racks, saunas, steam generators, clothes washers, clothes dryers. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of washing machine drain lines, washing machine catch pan drain lines, or clothes dryer exhaust ducts. The inspector does not operate water supply or shut-off valves for sinks, toilets, bidets, clothes washers, etc. due to the possibility of valves leaking or breaking when operated. The inspector does not determine if shower pans or tub and shower enclosures are water tight, or determine the completeness or operability of any gas piping to laundry appliances.
Location #A: Full bath, first floor
Location #B: Full bath, first floor
Condition of counters: Appeared serviceable
Condition of cabinets: Appeared serviceable
Condition of flooring: Appeared serviceable
Condition of sinks and related plumbing: Appeared serviceable
Condition of toilets: Appeared serviceable
Condition of bathtubs and related plumbing: Appeared serviceable
Condition of shower(s) and related plumbing: Appeared serviceable
Condition of ventilation systems: Appeared serviceable
240 volt receptacle for laundry equipment present: Yes
Interior, Doors and Windows
Limitations: The following items are not included in this inspection: security, intercom and sound systems; communications wiring; central vacuum systems; elevators and stair lifts; cosmetic deficiencies such as nail-pops, scuff marks, dents, dings, blemishes or issues due to normal wear and tear in wall, floor and ceiling surfaces and coverings, or in equipment; deficiencies relating to interior decorating; low voltage and gas lighting systems. Any comments made regarding these items are as a courtesy only. Note that the inspector does not evaluate any areas or items which require moving stored items, furnishings, debris, equipment, floor coverings, insulation or similar materials. The inspector does not test for asbestos, lead, radon, mold, hazardous waste, urea formaldehyde urethane, or any other toxic substance. Some items such as window, drawer, cabinet door or closet door operability are tested on a sampled basis. The client should be aware that paint may obscure wall and ceiling defects, floor coverings may obscure floor defects, and furnishings may obscure wall, floor and floor covering defects. If furnishings were present during the inspection, recommend a full evaluation of walls, floors and ceilings that were previously obscured when possible. Carpeting and flooring, when installed over concrete slabs, may conceal moisture. If dampness wicks through a slab and is hidden by floor coverings that moisture can result in unhygienic conditions, odors or problems that will only be discovered when/if the flooring is removed. Determining the cause and/or source of odors is not within the scope of this inspection.
Condition of exterior entry doors: Appeared serviceable
Exterior door material: Metal
Condition of interior doors: Appeared serviceable
Type(s) of windows: Vinyl, Double-hung, Fixed
Condition of walls and ceilings: Appeared serviceable
Wall type or covering: Drywall
Ceiling type or covering: Drywall
Condition of flooring: Appeared serviceable
Flooring type or covering: Vinyl, linoleum or marmoleum, Laminate, Tile
Floors in one or more areas were not level. This can be caused by foundation settlement or movement of the foundation, posts and/or beams. Significant repairs may be needed to make floors level. Recommend that a qualified contractor and/or engineer evaluate further. Repairs should be performed by a qualified contractor.
One or more window screens were damaged or deteriorated. These window(s) may not provide ventilation during months when insects are active. Recommend replacing window screens as necessary.
Kick board is rotted. Should be repaired or replaced by a qualified contractor.
Minor cracks, nail pops and/or blemishes were found in walls and/or ceilings in one or more areas. Cracks and nail pops are common, are often caused by lumber shrinkage or minor settlement, and can be more or less noticeable depending on changes in humidity. They did not appear to be a structural concern, but the client may wish to repair these for aesthetic reasons. For recurring cracks, consider using an elastic crack covering product:http://www.reporthost.com/?ECC
Door jamb damage.
Home appliance estimated design life:
1. Gas furnace: 15-20 years
2. Gas boiler: 17-24 years
3. Oil furnace: 18-25 years
4. Electric furnace: 18-25 years
5. Heat pump: 15 years
6. Central air conditioning: 15 years
7. Water heater (tank): 8-12 years
8. Water heater (tankless): 20+ years
9. Range and oven: 18-20 years
10. Refrigerator/Freezer: 18-20 years
11. Dishwasher: 9-11 years
12. Microwave oven: 10 years
13. Range hood and fan: 14 years
14. Food disposal: 10-12 years
15. Garage door opener: 10 years
16. Laundry washing machine: 14 years
17. Laundry dryer: 14 years
18. Bathtub/Sink: 10-30 years
19. Smoke or CO detector: 8-10 years
20. Exhaust fans: 10 years
Home Maintenance Check List
1. Clean any removable dishwasher filters.
2. Purge food disposal by filling the kitchen sink with clean water, then turn on the device until the water drains through.
3. Wash refrigerator/freezer interior walls and door gaskets with a solution of one quart of warm water to two tablespoons of baking soda and wipe dry.
4. Vacuum and clean "return" air ducts/grills.
5. Inspect lighting fixtures and replace any burned-out bulbs.
6. Clean clothes dryer lint trap and/or duct for better energy efficiency and to decrease the risk of fire.
1. Inspect and service doors by cleaning and lubricating latches, hinges or replacing weather strippings as might be required.
2. Inspect and repair, if necessary, exterior caulking and finish around windows, doors, and siding.
3. Replace/clean, at least quarterly, furnace, heating, and cooling system filters.
4. Re-tighten knobs and pulls on cabinets. Clean and lubricate drawer tracks and guides.
1. Inspect and test smoke and carbon monoxide alarms. Replace backup batteries as might be required.
2. Test (GFCI) ground fault circuit interrupters and (AFCI) arc fault breakers.
3. Inspect and maintain/clean gutters and downspouts. Runoff water must be directed away from the home.
4. Inspect attics and substructure areas for rodent droppings or other signs of pests or leaks/standing water, etc.
5. Prior to the beginning of the rainy season, test sump pumps for adequacy and function.
6. Look for moisture or decay, outside and inside the house, where flat surface decks and landings attach to the home. This is especially important if the landings do not have proper flashings.
7. Clean range hood fan grills and housings.
8. Use a vacuum cleaner to remove dust on coils behind the refrigerator/freezer.
1. Licensed contractor to inspect and service heating and air conditioning systems.
2. Professional contractor to inspect and service wood burning appliances and chimneys.
3. Seal any foundation cracks.
4. Inspect, clean and lubricate garage vehicle door tracks and test auto-reverse functions.
5. Clean and lubricate sliding glass door and window tracks.
6. Inspect exterior paint for cracking and wear. Repaint, caulk, and seal as needed.
7. Reseal, as required, wood decks and landings.
8. Inspect, for water damage, pests or rot, any substructure and attic areas.
9. Inspect roof flashings, chimney caps, shingles.
10. Inspect outside electrical service lines for damage, exposed wires or proximity to tree limbs.
11. Inspect all supply hoses at sinks, toilets and washing machines.
12. Clean and repair caulking or grout in bathrooms or kitchens.
13. Clean bathroom exhaust fan blades and grills.
14. Inspect all electric cords and replace as needed.
15. Change water filters and have fresh water systems professionally serviced.
Tips for keeping drains clear:
1. Pour a pot of hot water down the drain once a week to help clear away fat or grease that may have built-up in the drain line or the P-trap.
2. If a drain is clogged, try pouring 1/2 cup of baking soda and 1/2 cup of white vinegar down the drain. Cover the drain and let the mixture sit for a few minutes. Then pour a pot of water down the drain.
General safety tips:
Ensure that you know where the following items are located:
1. Emergency contact telephone numbers.
2. Fire extinguishers and water hose pipes.
3. Heating gas/fuel main shutoff valve.
4. Main electrical disconnect circuit breaker(breaker box/service panel).
5. Main drain line clean-out.
6. Main water shut-off valve.
7. All window and door exits.