This report is the exclusive property of 231 home inspections llc and the client(s) listed in the report title. Use of this report by any unauthorized persons is prohibited.
231 Home Inspections llcWebsite: http://www.reporthost.com/231home
Inspector's email: email@example.com
Phone: (616) 881-3933
Inspector's phone: (616) 881-3933
1451 Canterbury Ave
Norton Shores MI 49444-3237
Inspector: Tom Breuker
Property Inspection Report
||1234 berg Rd
Wherever MI 49999
||Friday, October 10, 2014
This report published on Thursday, December 04, 2014 11:04:27 AM EST
Inspector accepts no responsibility for use or misrepresentation by third parties and release 231 home inspections llc from any liability whatsoever.
How to Read this Report
This report is organized by the property's functional areas. Within each functional area, descriptive information is listed first and is shown in bold type. Items of concern follow descriptive information.
Concerns are shown and sorted according to these types:
|Safety||Poses a safety hazard|
|Repair/Replace||Recommend repairing or replacing|
|Repair/Maintain||Recommend repair and/or maintenance|
|Maintain||Recommend ongoing maintenance|
|Evaluate||Recommend evaluation by a specialist|
|Monitor||Recommend monitoring in the future|
|Comment||For your information|
Click here for a glossary of building construction terms.Contact your inspector If there are terms that you do not understand, or visit the glossary of construction terms at http://www.reporthost.com/glossary.asp
1300Present during inspection:
ClientClient present for discussion at end of inspection:
YesWeather conditions during inspection:
Dry (no rain), SunnyTemperature during inspection:
CheckType of building:
single family homeBuildings inspected:
One houseNumber of residential units inspected:
1Age of main building:
54Source for main building age:
ClientFront of building faces:
Microbial growths were found at one or more locations in the crawl space. It is beyond the scope of this inspection to identify what substance or organism this staining is. However such staining is normally caused by excessively moist conditions, which in turn can be caused by plumbing or building envelope leaks and/or substandard ventilation. These conducive conditions should be corrected before making any attempts to remove or correct the staining. Normally affected materials such as drywall are removed, enclosed affected spaces are allowed to dry thoroughly, a mildewcide may be applied, and only then is drywall reinstalled. For evaluation and possible mitigation, consult with a qualified industrial hygienist or mold/moisture mitigation specialist. For more information, visit:http://www.reporthost.com/?MOLDCDChttp://www.reporthost.com/?MOLDEPA
possible mold or substance. referred to a contractor.
not sure but should be cleaned.
Unless specifically included in the inspection, the following items and any related equipment, controls, electric systems and/or plumbing systems are excluded from this inspection: detached buildings or structures; fences and gates; retaining walls; underground drainage systems, catch basins or concealed sump pumps; swimming pools and related safety equipment, spas, hot tubs or saunas; whether deck, balcony and/or stair membranes are watertight; trees, landscaping, properties of soil, soil stability, erosion and erosion control; ponds, water features, irrigation or yard sprinkler systems; sport courts, playground, recreation or leisure equipment; areas below the exterior structures with less than 3 feet of vertical clearance; invisible fencing; sea walls, docks and boathouses; retractable awnings. Any comments made regarding these items are as a courtesy only.Site profile:
Minor slopeCondition of driveway:
Appeared serviceableDriveway material:
GravelCondition of sidewalks and/or patios:
Required repairs, replacement and/or evaluation (see comments below)couple of cracks. fill in.Sidewalk material:
Poured in place concreteCondition of decks, porches and/or balconies:
Appeared serviceableDeck, porch and/or balcony material:
Exterior and Foundation
The inspector performs a visual inspection of accessible components or systems at the exterior. Items excluded from this inspection include below-grade foundation walls and footings; foundations, exterior surfaces or components obscured by vegetation, stored items or debris; wall structures obscured by coverings such as siding or trim. Some items such as siding, trim, soffits, vents and windows are often high off the ground, and may be viewed using binoculars from the ground or from a ladder. This may limit a full evaluation. Regarding foundations, some amount of cracking is normal in concrete slabs and foundation walls due to shrinkage and drying. Note that the inspector does not determine the adequacy of seismic reinforcement.Wall inspection method:
Viewed from groundCondition of wall exterior covering:
Required repairs, replacement and/or evaluation (see comments below)couple panels on left side of houseApparent wall structure:
Wood frameWall covering:
Wood fiberCondition of foundation and footings:
Required repairs, replacement and/or evaluation (see comments below)Apparent foundation type:
Crawl spaceFoundation/stem wall material:
Concrete blockFooting material (under foundation stem wall):
Poured in place concrete
Some sections of siding and/or trim were damaged. Recommend that a qualified person repair, replace or install siding or trim as necessary.
One or more exhaust duct end caps were damaged. Their purpose is to prevent unconditioned air from entering the building, and keep out birds, rodents and bugs. Blocked ducts can cause fan motors and/or clothes dryers to overheat and can pose a fire hazard. Recommend that a qualified person repair or replace caps as necessary.
This property was clad with composition wood-fiber siding. Various manufacturers (e.g. Louisiana Pacific, Weyerhaeuser and Masonite) have produced this type of siding, which is made from oriented strand board (OSB) or "hardboard." It is prone to deteriorate and/or fail prematurely due to moisture penetration, especially when the paint coating is substandard or has not been maintained. Failure is typically visible in the form of swelling, cracking, buckling, wafer pops, delamination and fungal growth.
Some areas of siding on this structure showed symptoms described above and need replacement and/or maintenance. Some manufacturers (e.g. Louisiana Pacific) recommend a repair process for this siding where affected areas are sealed with Permanizer Plus, a flexible primer made by Pittsburgh Paint, followed by two coats of 100% acrylic latex paint. This sealant must be applied to the bottom edges using a brush. The face of the siding can be sprayed. The Permanizer Plus sealer isn't required for edges that aren't swollen, cracked or deteriorated, but the acrylic latex should still be brushed on these edges.
Recommend that a qualified contractor evaluate and replace siding as necessary, and/or seal and repaint as necessary. Repairs should be made per the siding and/or sealant manufacturer's installation instructions, and per standard building practices.
For more information, visit:http://www.reporthost.com/?PERMPLUShttp://www.reporthost.com/?COMPSDNG
Soil was in contact with or less than 6 inches from siding, trim or structural wood. This is a conducive condition for wood-destroying organisms. Recommend grading or removing soil as necessary to maintain a 6-inch clearance. If not possible, then recommend replacing untreated wood with pressure-treated wood. Installation of borate-based products such as Impel rods can also reduce the likelihood of rot or infestation if soil cannot be removed. Note that damage from fungal rot and/or insects may be found when soil is removed, and repairs may be necessary.
vegetation close and no splash block. diverts water away from foundation.
crack in the wall. should be sealed up.
crawlspace vent should be replaced.
The paint or stain finish in some areas was failing (e.g. peeling, faded, worn, thinning). Siding and trim with a failing finish can be damaged by moisture.Recommend that a qualified contractor prep (e.g. clean, scrape, sand, prime, caulk) and repaint or restain the building exterior where necessary and per standard building practices. Any repairs needed to the siding or trim should be made prior to this.
peeling paint. just simple maintenance. crack
simple maintenance, painting threshold.
Structural components such as joists and beams, and other components such as piping, wiring and/or ducting that are obscured by under-floor insulation are excluded from this inspection. The inspector does not determine if support posts, columns, beams, joists, studs, trusses, etc. are of adequate size, spanning or spacing.
The inspector does not guarantee or warrant that water will not accumulate in the crawl spaces in the future. Complete access to all crawl space areas during all seasons and during prolonged periods of all types of weather conditions (e.g. heavy rain, melting snow) would be needed to do so.
The inspector attempts to locate all crawl space access points and areas. Access points may be obscured or otherwise hidden by furnishings or stored items. In such cases, the client should ask the property owner where all access points are that are not described in this inspection, and have those areas inspected. Note that crawl space areas should be checked at least annually for water intrusion, plumbing leaks and pest activity.Crawl space inspection method:
TraversedCondition of floor substructure above:
Required repairs, replacement and/or evaluation (see comments below)one beam needs attentionPier or support post material:
Bearing wallBeam material:
Solid woodFloor structure above:
Solid wood joistsCondition of insulation underneath floor above:
Not applicable, none installedInsulation material underneath floor above:
None visibleCondition of vapor barrier:
Required repairs, replacement and/or evaluation (see comments below)Vapor barrier present:
Evidence of prior water intrusion or accumulation was found in one or more sections of the crawl space. For example, sediment stains on the vapor barrier or foundation, and/or efflorescence on the foundation. Accumulated water is a conducive condition for wood-destroying organisms and should not be present in the crawl space. Recommend that the client review any disclosure statements available and ask the property owner about past accumulation of water in the crawl space. The crawl space should be monitored in the future for accumulated water, especially after heavy and/or prolonged periods of rain. If water is found to accumulate, then recommend that a qualified contractor who specializes in drainage issues evaluate and repair as necessary. Typical repairs for preventing water from accumulating in crawl spaces include:
- Repairing, installing or improving rain run-off systems (gutters, downspouts and extensions or drain lines)
- Improving perimeter grading
- Repairing, installing or improving underground footing and/or curtain drains
Ideally, water should not enter crawl spaces, but if water must be controlled after it enters the crawl space, then typical repairs include installing trenches, gravity drains and/or sump pump(s) in the crawl space.
effloresence. moisture intrusion.
Fungal rot was found at one or more joists, sections of floor sheathing. Recommend that a qualified contractor evaluate and repair as necessary. All rotten wood should be replaced.
contractor was recommended
sheathing on crawlspace ceiling. also no insulation
not sure but should be cleaned.
joist deteriorated. have looked at soon.
No insulation was installed under the floor above the crawl space. Recommend that a qualified person install insulation for better energy efficiency and per standard building practices. Typically this is R-19 rated fiberglass batt with the attached facing installed against the warm (floor) side.
One or more exhaust ducts (e.g. bathroom fan, clothes dryer) in the crawl space were not insulated. This can result in moisture forming inside the duct or "sweating" on the outside of the duct depending on the surrounding air temperature and the exhaust air temperature. Recommend that a qualified person install insulation on exhaust ducts per standard building practices (typically R-4 rating), or replace uninsulated ducts with insulated ducts.
The vapor barrier in some areas of the crawl space was deteriorated, damaged, loose or askew, missing. Soil was exposed as a result and will allow water from the soil to evaporate up into the structure. This is a conducive condition for wood-destroying organisms. A 6 mil black plastic sheet should be placed over all exposed soil with seams overlapped to 24 inches, and not in contact with any wood structural components. The sheeting should be held in place with bricks or stones, not wood. Recommend that a qualified person replace or repair the vapor barrier where necessary and per standard building practices.
vapor barrier incorrect in alot of areas. none in some areas.
The screens for one or more crawl space vents were damaged. Vermin or pets can enter the crawl space and nest, die and/or leave feces and urine. Vermin often damage under-floor insulation too. Recommend that a qualified person install or replace screens where necessary using 1/8-inch to 1/4-inch wire mesh.
crawlspace vent should be replaced.
One or more indoor crawl space access hatches or doors were not insulated, or had substandard insulation. Weatherstripping was also missing or substandard. Recommend installing weatherstripping and insulation per current standards at hatches or doors for better energy efficiency and to prevent dust or odor-laden air from the crawl space entering living spaces.
The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; solar roofing components. Any comments made regarding these items are made as a courtesy only. Note that the inspector does not provide an estimate of remaining life on the roof surface material, nor guarantee that leaks have not occurred in the roof surface, skylights or roof penetrations in the past. Regarding roof leaks, only active leaks, visible evidence of possible sources of leaks, and evidence of past leaks observed during the inspection are reported on as part of this inspection. The inspector does not guarantee or warrant that leaks will not occur in the future. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high wind and rain, melting snow) would be needed to do so. Regarding the roof drainage system, unless the inspection was conducted during and after prolonged periods of heavy rain, the inspector was unable to determine if gutters, downspouts and extensions performed adequately or were leak-free.Roof inspection method:
TraversedCondition of roof surface material:
Appeared serviceableRoof surface material:
Asphalt or fiberglass composition shinglesRoof type:
GableApparent number of layers of roof surface material:
OneCondition of gutters, downspouts and extensions:
Limited evaluation due to little or no rainfall during and prior to the inspection
Flashings at the base of one or more chimneys were substandard. Leaks can occur as a result. This is a conducive condition for wood-destroying organisms. Recommend that a qualified contractor evaluate and repair as necessary.
monitor for future problems or leaks
bad sealing job. monitor for future leaks or problems.
Significant amounts of debris have accumulated in one or more gutters or downspouts. Gutters can overflow and cause water to come in contact with the building exterior, or water can accumulate around the foundation. This is a conducive condition for wood-destroying organisms. Recommend cleaning gutters and downspouts now and as necessary in the future.
Attic and Roof Structure
The following items or areas are not included in this inspection: areas that could not be traversed or viewed clearly due to lack of access; areas and components obscured by insulation. Any comments made regarding these items are made as a courtesy only. The inspector does not determine the adequacy of the attic ventilation system. Complete access to all roof and attic spaces during all seasons and during prolonged periods of all types of weather conditions (e.g. high/low temperatures, high/low humidity, high wind and rain, melting snow) would be needed to do so. The inspector is not a licensed engineer and does not determine the adequacy of roof structure components such as trusses, rafters or ceiling beams, or their spacing or sizing.Attic inspection method:
TraversedCondition of roof structure:
Appeared serviceableRoof structure type:
Ceiling joistsCondition of insulation in attic (ceiling, skylight chase, etc.):
Appeared serviceableCeiling insulation material:
Fiberglass loose fillApproximate attic insulation R value (may vary in areas):
R-21Vermiculite insulation present:
None visibleVapor retarder:
None visibleCondition of roof ventilation:
Appeared serviceableRoof ventilation type:
One or more sections of the roof structure appeared to have substandard ventilation, soffit vents were missing, there were too few vents. This can result in high attic and roof surface temperatures, reduce the life of the roof covering materials, and/or increase cooling costs. High levels of moisture are also likely to accumulate in the roof structure or attic, and can be a conducive condition for wood-destroying organisms. Standard building practices require one free square foot of ventilation for every 150 square feet of attic space, and that vents be evenly distributed between the lowest points of the roof structure and the highest points to promote air circulation. Often this means that both soffit vents and ridge or gable end vents are installed. Recommend that a qualified contractor evaluate and repair per standard building practices.
no venting for the soffits.
The roof structure, or one or more sections of it, had no visible venting. This can result in high attic and roof surface temperatures, reduce the life of the roof covering materials, and/or increase cooling costs. High levels of moisture are also likely to accumulate in the roof structure or attic, and can be a conducive condition for wood-destroying organisms. Standard building practices require one free square foot of ventilation for every 150 square feet of attic space, and that vents be evenly distributed between the lowest points of the roof structure and the highest points to promote air circulation. Often this means that both soffit vents and ridge or gable end vents are installed. Recommend that a qualified contractor evaluate and install vents per standard building practices.
One or more outdoor attic access hatch covers or doors were missing, damaged and/or substandard. When located outdoors, vermin, rainwater and/or snow can enter the attic. A qualified person should replace, install or repair hatches or doors as necessary and per standard building practices. For more information, visit:http://www.reporthost.com/?ATTACC
Garage or Carport
The inspector does not determine the adequacy of firewall ratings. Requirements for ventilation in garages vary between municipalities.Type:
AttachedCondition of door between garage and house:
Appeared serviceableType of door between garage and house:
Hollow coreCondition of garage vehicle door(s):
Appeared serviceableType of garage vehicle door:
SectionalCondition of automatic opener(s):
Appeared serviceableMechanical auto-reverse operable (reverses when meeting reasonable resistance during closing):
YesCondition of garage floor:
Appeared serviceableCondition of garage interior:
Appeared serviceableGarage ventilation:
The door between the garage and the house did not appear to be fire resistant, or the inspector was unable to verify that it was via a label. This is a potential safety hazard. House to garage doors, to prevent fire and fumes from spreading from the garage into interior living space, should be constructed of fire-resistant materials. Doors, generally considered to be suitable for the purpose, are solid core wood, steel, honeycomb steel or a door that has been factory labeled as fire rated. Recommend that a qualified contractor replace or repair the door and, at that time, make any other corrections that might be required to provide suitable fire resistance between the garage and the dwelling per standard building practices. For more information, visit:http://www.reporthost.com/?AGFR
The following items are not included in this inspection: generator systems, transfer switches, surge suppressors, inaccessible or concealed wiring; underground utilities and systems; low-voltage lighting or lighting on timers or sensors. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of grounding or bonding, if this system has an adequate capacity for the client's specific or anticipated needs, or if this system has any reserve capacity for additions or expansion. The inspector does not operate circuit breakers as part of the inspection, and does not install or change light bulbs. The inspector does not evaluate every wall switch or receptacle, but instead tests a representative number of them per various standards of practice. When furnishings, stored items or child-protective caps are present some receptacles are usually inaccessible and are not tested; these are excluded from this inspection. Receptacles that are not of standard 110 volt configuration, including 240-volt dryer receptacles, are not tested and are excluded. The functionality of, power source for and placement of smoke and carbon monoxide alarms is not determined as part of this inspection. Upon taking occupancy, proper operating and placement of smoke and carbon monoxide alarms should be verified and batteries should be changed. These devices have a limited lifespan and should be replaced every 10 years. The inspector attempts to locate and evaluate all main and sub-panels. However, panels are often concealed. If panels are found after the inspection, a qualified electrician should evaluate and repair if necessary. The inspector attempts to determine the overall electrical service size, but such estimates are not guaranteed because the overall capacity may be diminished by lesser-rated components in the system. Any repairs recommended should be made by a licensed electrician.Electric service condition:
Appeared serviceablePrimary service type:
OverheadService voltage (volts):
120-240Estimated service amperage:
100Primary service overload protection type:
Circuit breakersMain disconnect rating (amps):
Ground rod(s) in soilCondition of main service panel:
Appeared serviceableLocation of main service panel #A:
Laundry roomLocation of main disconnect:
Breaker at top of main service panelCondition of branch circuit wiring:
ServiceableBranch circuit wiring type:
Non-metallic sheathedSolid strand aluminum branch circuit wiring present:
None visibleGround fault circuit interrupter (GFCI) protection present:
NoArc fault circuit interrupter (AFCI) protection present:
NoSmoke alarms installed:
Yes, but not tested
One or more electric receptacles (outlets) at the kitchen, laundry sink, garage had no visible ground fault circuit interrupter (GFCI) protection, or the inspector was unable to determine if GFCI protection was present. If not GFCI-protected, receptacles in wet areas pose a shock hazard. Recommend that a qualified electrician evaluate and install GFCI protection if necessary and per standard building practices. General guidelines for GFCI-protected receptacles include the following locations:
- Outdoors (since 1973)
- Bathrooms (since 1975)
- Garages (since 1978)
- Kitchens (since 1987)
- Crawl spaces and unfinished basements (since 1990)
- Wet bar sinks (since 1993)
- Laundry and utility sinks (since 2005)
For more information, visit:http://www.reporthost.com/?GFCI
One or more modern, 3-slot electric receptacles (outlets) were found with an open ground. Three-slot receptacles should have a hot, a neutral and a ground wire connected. Homeowners often install new 3-slot receptacles on older, 2-wire circuits that only have hot and neutral wires. This is a shock hazard when appliances that require a ground are used with these receptacles. Examples of such appliances include computers and related hardware, refrigerators, freezers, portable air conditioners, clothes washers, aquarium pumps, and electrically operated gardening tools. Where the electric system was installed prior to when grounded circuits were required (1960s), it is permissible to replace 3-slot receptacles with 2-slot receptacles to prevent appliances that require a ground from being plugged in to an ungrounded circuit. However, the client should be aware of this limitation when planning use for various rooms, such as an office. For newer electric systems, circuits should be repaired so grounded, 3-wire cables provide power to 3-slot receptacles. Recommend that a qualified electrician repair per standard building practices.
No carbon monoxide alarms were visible. This is a potential safety hazard. Some states and/or municipalities require CO alarms to be installed for new construction and/or for homes being sold. Recommend installing approved CO alarms outside of each separate sleeping area in the immediate vicinity of the bedrooms on each level and in accordance with the manufacturer's recommendations. For more information, visit:http://www.reporthost.com/?COALRM
Batteries in all the smoke alarms should be replaced after taking occupancy, and annually in the future. "Chirping" noises emitted from smoke alarms typically indicate that batteries need replacing. For more information, visit:http://www.reporthost.com/?SMKALRM
Few receptacles (outlets) were installed in one or more areas by modern standards. This can result in "octopus" wiring with extension cords, which is a fire hazard. Also, 2-slot receptacles (outlets) rather than 3-slot, grounded receptacles were installed in one or more areas. These do not have an equipment ground and are considered to be unsafe by today's standards. Appliances that require a ground should not be used with 2-slot receptacles. Examples of such appliances include computers and related hardware, refrigerators, freezers, portable air conditioners, clothes washers, aquarium pumps, and electrically operated gardening tools. The client should be aware of this limitation when planning use for various rooms, such as an office. Upgrading to grounded receptacles typically requires installing new wiring from the main service panel or sub-panel to the receptacle(s), in addition to replacing the receptacle(s). Consult with a qualified electrician about upgrading circuits with additional receptacles and 3-wire, grounded receptacles per standard building practices.
Plumbing / Fuel Systems
The following items are not included in this inspection: private/shared wells and related equipment; private sewage disposal systems; hot tubs or spas; main, side and lateral sewer lines; gray water systems; pressure boosting systems; trap primers; incinerating or composting toilets; fire suppression systems; water softeners, conditioners or filtering systems; plumbing components concealed within the foundation or building structure, or in inaccessible areas such as below tubs; underground utilities and systems; overflow drains for tubs and sinks; backflow prevention devices. Any comments made regarding these items are as a courtesy only. Note that the inspector does not operate water supply or shut-off valves due to the possibility of valves leaking or breaking when operated. The inspector does not test for lead in the water supply, the water pipes or solder, does not determine if plumbing and fuel lines are adequately sized, and does not determine the existence or condition of underground or above-ground fuel tanks.Condition of service and main line:
Appeared serviceableWater service:
Private wellCondition of supply lines:
Appeared serviceableSupply pipe material:
CopperCondition of drain pipes:
Appeared serviceableDrain pipe material:
Galvanized steelCondition of waste lines:
Appeared serviceableWaste pipe material:
Cast ironSump pump installed:
None visibleSewage ejector pump installed:
None visibleCondition of fuel system:
Appeared serviceableVisible fuel storage systems:
in yardLocation of main fuel shut-off valve:
Insulation for one or more water supply pipes in the crawl space was . Recommend replacing or installing insulation on pipes per standard building practices to prevent them from freezing during cold weather, and for better energy efficiency with hot water supply pipes.
A water softener system was installed on the premises. These are specialty systems and are excluded from this inspection. Comments in this report related to this system are made as a courtesy only and are not meant to be a substitute for a full evaluation by a qualified specialist. Water softeners typically work by removing unwanted minerals (e.g. calcium, magnesium) from the water supply. They prevent build-up of scale inside water supply pipes, improve lathering while washing, and prevent spots on dishes. Recommend consulting with the property owner about this system to determine its condition, required maintenance, age, expected remaining life, etc. For more information, visit:http://www.reporthost.com/?WTRSFThttp://www.reporthost.com/?HRDWTR
The inspector did not determine the location of the main water shut-off valve, or verify that a readily accessible shut-off valve in the building exists. Recommend consulting with the property owner to determine if a main shut-off valve exists, locating it yourself, or that a qualified plumber find it if necessary. If no readily accessible main shut-off valve is found in the building, then recommend that a qualified plumber install one so the water supply can be quickly turned off in the event of an emergency, such as when a supply pipe bursts.
Evaluation of and determining the adequacy or completeness of the following items are not included in this inspection: water recirculation pumps; solar water heating systems; Energy Smart or energy saver controls; catch pan drains. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on water heaters, does not determine if water heaters are appropriately sized, or perform any evaluations that require a pilot light to be lit or a shut-off valve to be operated.Condition of water heater:
TankCapacity (in gallons):
40Location of water heater:
Mechanical roomHot water temperature tested:
The estimated useful life for most water heaters is 8-12 years. The inspector was unable to determine the age of the water heater due to the manufacturer's label being obscured, no serial number being visible, or the serial number not clearly indicating the age. The client should be aware that this water heater may be near, at or beyond its useful life and may need replacing at any time. Recommend attempting to determine the water heater's age.
If found to be near, at or beyond its useful lifespan, recommend budgeting for a replacement in the near future, or considering replacement now before any leaks occur. The client should be aware that significant flooding can occur if the water heater does fail. If not replaced now, consider having a qualified person install a catch pan and drain or a water alarm to help prevent damage if water does leak.
Heating, Ventilation and Air Condition (HVAC)
The following items are not included in this inspection: humidifiers, dehumidifiers, electronic air filters; solar, coal or wood-fired heat systems; thermostat or temperature control accuracy and timed functions; heating components concealed within the building structure or in inaccessible areas; underground utilities and systems; safety devices and controls (due to automatic operation). Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of remaining life on heating or cooling system components, does not determine if heating or cooling systems are appropriately sized, does not test coolant pressure, or perform any evaluations that require a pilot light to be lit, a shut-off valve to be operated, a circuit breaker to be turned "on" or a serviceman's or oil emergency switch to be operated. It is beyond the scope of this inspection to determine if furnace heat exchangers are intact and free of leaks. Condensation pans and drain lines may clog or leak at any time and should be monitored while in operation in the future. Where buildings contain furnishings or stored items, the inspector may not be able to verify that a heat source is present in all "liveable" rooms (e.g. bedrooms, kitchens and living/dining rooms).General heating system type(s):
RadiantGeneral heating distribution type(s):
Ducts and registersLast service date of primary heat source:
n/aCondition of forced air ducts and registers:
Appeared serviceableCondition of burners:
Fireplaces, Stoves, Chimneys and Flues
The following items are not included in this inspection: coal stoves, gas logs, chimney flues (except where visible). Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of drafting or sizing in fireplace and stove flues, and also does not determine if prefabricated or zero-clearance fireplaces are installed in accordance with the manufacturer's specifications. The inspector does not perform any evaluations that require a pilot light to be lit, and does not light fires. The inspector provides a basic visual examination of a chimney and any associated wood burning device. The National Fire Protection Association has stated that an in-depth Level 2 chimney inspection should be part of every sale or transfer of property with a wood-burning device. Such an inspection may reveal defects that are not apparent to the home inspector who is a generalist.Condition of chimneys and flues:
Appeared serviceableWood-burning chimney type:
No spark screen or rain cap was installed at one or more chimney flue terminations. Spark screens reduce the chance of embers exiting the flue and causing fires. They also prevent wildlife (e.g. birds, rodents, raccoons) from entering flues. Rain caps prevent water from entering flues, mixing with combustion deposits and creating caustic chemicals which can corrode flues. They also prevent damage to masonry from freeze-thaw cycles and prevent metal components (e.g. dampers, metal firebox liners) from rusting. Recommend that a qualified person install rain caps with spark screens per standard building practices where missing.
The following items are not included in this inspection: household appliances such as stoves, ovens, cook tops, ranges, warming ovens, griddles, broilers, dishwashers, trash compactors, refrigerators, freezers, ice makers, hot water dispensers and water filters; appliance timers, clocks, cook functions, self and/or continuous cleaning operations, thermostat or temperature control accuracy, and lights. Any comments made regarding these items are as a courtesy only. Note that the inspector does not provide an estimate of the remaining life of appliances, and does not determine the adequacy of operation of appliances. The inspector does not note appliance manufacturers, models or serial numbers and does not determine if appliances are subject to recalls. Areas and components behind and obscured by appliances are inaccessible and excluded from this inspection.Condition of counters:
Appeared serviceableCondition of cabinets:
Appeared serviceableCondition of sinks and related plumbing:
Appeared serviceableCondition of dishwasher:
Appeared serviceableCondition of range, cooktop or oven:
Appeared serviceableRange, cooktop or oven type:
ElectricCondition of refrigerator:
Appeared serviceableCondition of built-in microwave oven:
Bathrooms, Laundry and Sinks
The following items are not included in this inspection: overflow drains for tubs and sinks; heated towel racks, saunas, steam generators, clothes washers, clothes dryers. Any comments made regarding these items are as a courtesy only. Note that the inspector does not determine the adequacy of washing machine drain lines, washing machine catch pan drain lines, or clothes dryer exhaust ducts. The inspector does not operate water supply or shut-off valves for sinks, toilets, bidets, clothes washers, etc. due to the possibility of valves leaking or breaking when operated. The inspector does not determine if shower pans or tub and shower enclosures are water tight, or determine the completeness or operability of any gas piping to laundry appliances.Location #A:
Full bathCondition of counters:
Appeared serviceableCondition of cabinets:
Appeared serviceableCondition of flooring:
Appeared serviceableCondition of sinks and related plumbing:
Appeared serviceableCondition of toilets:
Appeared serviceableCondition of bathtubs and related plumbing:
Appeared serviceableCondition of shower(s) and related plumbing:
Appeared serviceableCondition of ventilation systems:
Appeared serviceableBathroom and laundry ventilation type:
Spot exhaust fans
The clothes dryer was equipped with a vinyl or mylar, accordion-type, flexible exhaust duct. The U.S. Consumer Product Safety Commission considers these types of ducts to be unsafe, and a fire hazard. They can trap lint and are susceptible to kinks or crushing, which can greatly reduce the air flow and cause overheating. Recommend that such ducts be replaced with a rigid or corrugated semi-rigid metal duct, and by a qualified contractor if necessary. For more information, visit:http://www.reporthost.com/?DRYER
The clothes dryer exhaust duct was kinked, crushed or damaged. Air flow will be restricted as a result and the clothes dryer may overheat. This is a safety hazard due to the risk of fire. Recommend that a qualified person replace or repair the duct as necessary. For more information, visit:http://www.reporthost.com/?DRYER
Interior, Doors and Windows
The following items are not included in this inspection: security, intercom and sound systems; communications wiring; central vacuum systems; elevators and stair lifts; cosmetic deficiencies such as nail-pops, scuff marks, dents, dings, blemishes or issues due to normal wear and tear in wall, floor and ceiling surfaces and coverings, or in equipment; deficiencies relating to interior decorating; low voltage and gas lighting systems. Any comments made regarding these items are as a courtesy only. Note that the inspector does not evaluate any areas or items which require moving stored items, furnishings, debris, equipment, floor coverings, insulation or similar materials. The inspector does not test for asbestos, lead, radon, mold, hazardous waste, urea formaldehyde urethane, or any other toxic substance. Some items such as window, drawer, cabinet door or closet door operability are tested on a sampled basis. The client should be aware that paint may obscure wall and ceiling defects, floor coverings may obscure floor defects, and furnishings may obscure wall, floor and floor covering defects. If furnishings were present during the inspection, recommend a full evaluation of walls, floors and ceilings that were previously obscured when possible. Determining the cause and/or source of odors is not within the scope of this inspection.Condition of exterior entry doors:
Appeared serviceableExterior door material:
WoodCondition of interior doors:
Appeared serviceableCondition of windows and skylights:
Appeared serviceableType(s) of windows:
VinylCondition of walls and ceilings:
Appeared serviceableWall type or covering:
DrywallCeiling type or covering:
TilesCondition of flooring:
Appeared serviceableFlooring type or covering:
Wood Destroying Organism Findings
This report only includes findings from accessible and visible areas on the day of the inspection. In addition to the inaccessible areas documented in this report, examples of other inaccessible areas include: sub areas less than 18 inches in height; attic areas less than 5 feet in height, areas blocked by ducts, pipes or insulation; areas where locks or permanently attached covers prevent access; areas where insulation would be damaged if traversed; areas obscured by vegetation. All inaccessible areas are subject to infestation or damage from wood-destroying organisms. The inspector does not move furnishings, stored items, debris, floor or wall coverings, insulation, or other materials as part of the inspection, nor perform destructive testing. Wood-destroying organisms may infest, re-infest or become active at any time. No warranty is provided as part of this inspection.
Your default report footer here...